CONNECTING COMPETENCE. W DATA SHEET: EHTD420VA REMOTE DIMMER 420 VA, ACTUATED VIA EXTERNAL PUSH-BUTTONS W FUNCTION Remote dimmer for controlling the light intensity of all standard type of illuminations, such as e.g. incandescent lamps, high-voltage and low-voltage halogen lamps with electric or conventional transformers. The control unit is operated via standard push-buttons by impulses from the 230 VAC operating voltage. Inputs for the following functions are available: • Memory On/Off/Dimming • Memory On (direct start with memory setting) • Central On (100% lighting intensity) and • Central Off (0% lighting intensity) For these resistive-inductive loads or resistive-capacitive loads the dimmer can work in a normal or reverse phase control mode. If the operating mode has been set incorrectly, or in the event of a short-circuit, it will automatically disconnect the load. In addition, the EHTD420VAis equipped with thermal overload protection, electronic short-circuit cut-out, overvoltage protection and a soft-start function. The device is also provided with electronic half-wave balancing and idle monitoring. This ensures the prevention of magnetic bias when conventional mains transformers are connected and of overvoltages when idling. SCHRACK TECHNIK GMBH Seybelgasse 13, A - 1230 Vienna, PHONE +43 1/866 85-0 E-MAIL email@example.com, INTERNET www.schrack.com PAGE 1/4 DATA SHEET: EHTD420VA-E / 04-2010 Errors and omissions excepted. CONNECTING COMPETENCE. W FEATURES • • • • • Acutation via standard push-buttons Dimming capacity: 10 VA – 420 VA 2 module widths only Phase control and reverse phase control dimmer Central On and Off function, memory function W MOUNTING METHOD • Snap-on fastening on DIN-rail to EN 50022 (2 modules) possible in all standard distribution panels • Any mounting position possible W NOTE The function is not guaranteed to dim compact fluorescent lamps (energy savings lamps). This remote dimmer is not compatible with NAK 16/3. W APPLICATIONS • Lighting control in - Private houses - Banks - Hospitals - Restaurants - etc. SCHRACK TECHNIK GMBH Seybelgasse 13, A - 1230 Vienna, PHONE +43 1/866 85-0 E-MAIL firstname.lastname@example.org, INTERNET www.schrack.com PAGE 2/4 DATA SHEET: EHTD420VA-E / 04-2010 Errors and omissions excepted. CONNECTING COMPETENCE. W TECHNICAL DATA Operating mode Control Dimmer Output Semiconductor output Rated voltage 230 V ± 10 % Frequency range 50 Hz Own consumption 4.5 W Overload protection, thermal Load disconnected when exceeding limit temperature (auto¬matic reconnection upon falling below temperature) Overload protection, short-circuit Load disconnection resulting from internal fault detection (fault reset by means of mains power disconnection for at least 2s) Load type adjustable via rotary switch Phase angle control (R,L) AC modulation control (R,C) Yes a) Yes, (observe manufacturer´s specification of min. load) Incandescent lamps 420 VA High-voltage halogen lamps 420 VA Low-voltage halogen lamps b) with conventional transformer 420 W Low-voltage halogen lamps b) with electronic ballast 420 W Min. dimming capacity 10 VA Max. dimming capacity c) d) 420 VA Dimmable energy-saving lamps No Fluorescent lamps No Mercury vapour lamps No Parallel compensation No Switch-on delay approx. 1 s, of 0% to 100% (soft start) Switch-off delay approx. 1 s, of 0% to 100% (soft stop) Switching cycles > 100000 Housing Material Installation Connection type Torque Contact area Distribution installation housing to DIN 43880 polycarbonate PC rail-mounting to DIN EN 50022 Strain relief clamps 0.6 Nm 0.4 - 2.5 mm² 1.1 L in 1.2 A1 Memory On 1.3 A4 Central On (max. 100%) 1.5 L out 1.6 A2 Memory On/Off/dimming 1.7 A3 Central OFF 2.1 N (neutral) 2.5 Ambient temperature Atm. humidity N (neutral) - 10° C up to + 45° C max. 85% (exposure to dew not permissible) Encl. protection type IP 40 after installation in distribution board Design requirements IEC 669 / DIN EN 60669 Dimensions (W x H x D in mm) / 2 modules Weight SCHRACK TECHNIK GMBH Seybelgasse 13, A - 1230 Vienna, PHONE +43 1/866 85-0 E-MAIL email@example.com, INTERNET www.schrack.com 36 x 85 x 58 0,146 kg PAGE 3/4 DATA SHEET: EHTD420VA-E / 04-2010 Errors and omissions excepted. CONNECTING COMPETENCE. W TECHNICAL DATA – Continued Conventional transformers for LV halogen lamps should be loaded least 20%. Too high an inductivity will result in the dimmer´being switched off (idle detection). It is imperative tu use only trasformers ap¬proved by the manufacturer für phase angle control (i. e. dimmer control at on). a) In the case of LV halogen lamps the transformer´s own power consumption has to be added to the lamp´s wattage when determining the total dissipated energy. With a matched transformer this may be assumed to be approx 10% of the lamp´s wattage. b) The dimming capacity is dependent upon the ambient temperature and applies to the specified range. Always allow for sufficient ventilation in the distribution board. If serveral dimmers are mounted next to each other in the distribution board and also subject to high loads, a ventilation space of approx 10 mm is recommended. c) d) Observe the manufacturer´s specifications. DESCRIPTION ORDER NUMBER Remote Dimmer 420 VA EHTD420VA SCHRACK TECHNIK GMBH Seybelgasse 13, A - 1230 Vienna, PHONE +43 1/866 85-0 E-MAIL firstname.lastname@example.org, INTERNET www.schrack.com PAGE 4/4 DATA SHEET: EHTD420VA-E / 04-2010 Errors and omissions excepted.