AC Power Systems For Business-Critical Continuity™ Liebert MicroPOD™ Wrap-Around Maintenance Bypass With Output Distribution When a computer system cannot be without power — even for maintenance — Key Benefits: a Liebert MicroPOD ensures continuous uptime. The Liebert MicroPOD Higher Availability provides maintenance bypass capability and power output distribution for ■ Provides utility power to attached equipment when switched to maintenance bypass mode. ■ Allows UPS maintenance or replacement of the UPS without discontinuing power to critical equipment. ™ Liebert GXT and Liebert PSI UPS models 3 kVA and below, as well as other brands of UPS systems. It allows removal of the UPS without powering down the connected equipment. The Liebert MicroPOD maintenance bypass and power output distribution switch allows you to manually transfer the connected Flexibility equipment to utility power via a maintenance bypass switch, ■ Easily installed — the UPS and utility power are both connected to the MicroPOD with the supplied cords. ■ Allows scheduled UPS maintenance to ensure continuous uptime without having to shut down protected equipment. ■ Rotary switch with indicators make the unit simple to operate. ■ Plug-and-play connectability for both input and output. ■ Compatible with any brand of UPS system. permitting scheduled maintenance or UPS replacement without discontinuing power to the critical load. Transferring back to UPS power is just as easy — simply turn the switch to the indicated position and the load is protected by the UPS. Available in plug-andplay or hardwired options at 120V or 208V rating, units include brackets for rack mounting in any direction. Lowest Total Cost Of Ownership UL c UL ® ® ■ Assures system uptime during maintenance activities. ■ Extreme affordability. ■ Two-year, no-hassle replacement warranty eliminates the cost of replacement during the warranty period. Liebert Corporation MicroPOD™ Specifications Part Number MP2-115A MP2-120C MP2-130C MP2-130E MP2-130P MP2-115HW MP2-120HW MP2-130HW Receptacle to UPS Input Plug to Utility Plug to UPS Output MicroPOD Output Receptacles 120V UL Listed MicroPODs 5-15R 5-15P 5-20R 5-20P L5-30R L5-30P L5-30R L5-30P 5-15P 5-20P L5-30P L5-30P L5-30P Hardwired Hardwired Hardwired L5-30R 5-15R 5-20R 5-30R (8)5-15R (8)5-20R (T-Slot) (8)5-20R (T-Slot) (2)5-15R, (4) 5-20R (T-Slot) (1) L5-30R (4) 5-15R, (2) L5-20R Hardwired Hardwired Hardwired L5-30P 5-15P 5-20P 5-30P 1050 Dearborn Drive P.O. Box 29186 Columbus, Ohio 43229 800 877 9222 Phone (U.S. & Canada Only) 614 888 0246 Phone (Outside U.S.) 614 841 6022 FAX Via Leonardo Da Vinci 8 Zona Industriale Tognana 35028 Piove Di Sacco (PD) Italy 39 049 9719 111 Phone 39 049 5841 257 FAX 208V UL Listed MicroPOD MP2-220N MP2-210K MP2-220L L6-20P OR Hardwire Connection (plug is removable for hardwire applications) L6-20R (2) L6-20R, (2) L6-15R, OR Hardwire Connections (receptacles are removable for hardwire applications) L6-20P 230V CE Marked MicroPODs EN60320/C13 EN60320/C14 EN60320/C19 EN60320/C20 EN60320/C14 EN60320/C20 (4) EN60320/C13 (4) EN60320/C13, (1)EN60320/C19 Emerson Network Power Asia Pacific 7/F., Dah Sing Financial Centre 108 Gloucester Rd, Wanchai Hong Kong 852 25722201 Phone 852 28029250 FAX liebert.com 24 x 7 Tech Support 800 222 5877 Phone 614 841 6755 (outside U.S.) Protected Devices Configuration The MicroPOD plugs into the utility and UPS, and the UPS is plugged into the MicroPOD. All protected devices are connected to the MicroPOD, allowing maintenance bypass for the UPS. While every precaution has been taken to ensure accuracy and completeness in this literature, Liebert Corporation assumes no responsibility, and disclaims all liability for damages resulting from use of this information or for any errors or omissions. © 2007 Liebert Corporation. All rights reserved throughout the world. Specifications subject to change without notice. All names referred to are trademarks or registered trademarks of their respective owners. ® Liebert and the Liebert logo are registered trademarks of the Liebert Corporation. SL-23800 (R02/07) 15 A M P PUSH TO RESET UPS UPS AVAILABLE UPS MAINTENANCE BYPASS AVAILABLE UTILITY 15 A M P PUSH TO RESET UTILITY OUTPUT OUTPUT CAUTION IF UTILITY LAMP IS ILLUMINATED MAINTENANCE BYPASS POSITION MAY BE SELECTED SWITCH TO UPS POSITION ONLY WHEN UPS LAMP IS ILLUMINATED Emerson Network Power. The global leader in enabling Business-Critical Continuity™. CONNECT UPS LINE CORD HERE From Utility MicroPOD plugs into UPS outlet Printed in USA UPS plugs into MicroPOD AC Power Connectivity DC Power Embedded Computing Embedded Power Monitoring Outside Plant Power Switching & Controls Precision Cooling Racks & Integrated Cabinets Services Surge Protection Emerson Network Power.com Business-Critical Continuity, Emerson Network Power and the Emerson Network Power logo are trademarks and service marks of Emerson Electric Co. ©2007 Emerson Electric Co.