Gas Stoves C34-10 Direct Vent Gas Stove Model C34-NG10 Fuel Type C34-LP10 Natural Gas Propane Minimum Supply Pressure 5.0” W.C. (1.25 kPa) 12.0” W.C. (3.00 kPa) Manifold Pressure - High 3.8” W.C. (0.95 kPa) 11” W.C. (2.74 kPa) Manifold Pressure - Low 1.1” W.C. (0.27 kPa) 2.9” W.C. (0.72 kPa) Orifice Size Minimum Input Maximum Input Vent Sizing #36 #52 16,000 BTU/h 16,000 BTU/h 32,000 BTU/h 32,000 BTU/h 4” Inner / 6-5/8” Outer 4” Inner / 6-5/8” Outer Approved Venting Systems FPI AstroCap™ Flex Vent Simpson Direct Vent Pro® American Metal Products® Amerivent Direct Security Secure Vent® Selkirk Direct-Temp™ Metal-Fab® Sure Seal Back wall B C A A Side wall Rigid Pipe Vent Systems: Side wall Flex Vent Systems: D Side wall E F E Back wall F C34 Clearances to Combustibles Dimension Description C34 A Side Wall to Unit 10” (250mm) B Back Wall to Unit 6” (150mm) C Back wall to Vent Center line 13” (559mm) D Side wall to Vent Center line 22” (330mm) Dimension Description E Side wall to unit 1.5” (38mm) F Side wall to Vent Center line 14” (356mm) Corner Clearances C34 Minimum ceiling height is 36" (914mm) from top of unit. Minimum clearance to vent is 1-1/4” (32mm). The above listed clearances are minimum distances to combustible materials. When installing on carpet or vinyl flooring the bottom pedestal cover plate must be installed. Gas Stoves C34-10 Gas Stove Regency Direct Vent System Snorkel Terminations These venting systems, in combination with the C34 Direct Vent Gas Fireplace, have been tested and listed as a direct vent heater system by Warnock Hersey. The location of the termination cap must conform to the requirements in the Vent Terminal Locations diagram. Snorkel Terminations: For installations requiring a vertical rise on the exterior of the building, 14-inch and 36-inch tall Snorkel Terminations and the Riser Vent are available. Follow the same installation procedures as used for standard Horizontal Termination. NEVER install the snorkel upside down. Horizontal Terminations Only FPI Direct Vent (Flex) System Termination Kits include all the parts needed to install the C34 using a flexible vent. Contains: #946-116 2 Feet 1. 6-5/8” Rigid Pipe Section (Kit length) 2. 4” flexible liner (Kit length) 3. spring spacers (4) 4. 90° Elbow 5. Adjustable pipe section 13-1/2” to 24” 6. thimble cover (1) 7. thimble (1) 8.adapter 9. AstroCap termination cap (1) 10. trim collar (2) 11. tube of Mill Pac (1) 12. S.S. screws #8 x 1-1/2”, self-tap, (12) 13. Blk. screws #8 x 1-1/2”, self-tap, (14) 14. Blk. screws #8 x 1-1/2” drill point, (4) 15. S.S. screws #8 x 1-1/2” drill point, (4) 16. Wood screws #8 x 1” (8) #946-216 4 Feet Dura-Vent Snorkel Min. 12"* (305mm) Notes: 1. Liner sections should be continuous without VNT-SNR1.EPS any joints or seams. 2. Only Flex pipe purchased from Regency may be used for Flex installations. 3. Horizontal sections must be supported every 3 feet. Dura-Vent Snorkel Dura-Vent Snorkel Dura-Vent Snorkel Min. 12"* (305mm) Min. 12"* (305mm) Dura-Vent Snorkel Dura-Vent Snorkel Window Well VNT-SNR1.EPS VNT-SNR1.EPS Adequate drainage Min. 12"* (305mm) Min. 12"* (305mm) Length Min. 12"* (305mm) FPI Kit # Window Well Window Well Adequate drainage Adequate drainage Gravel Gravel VNT-SNR2.EPS VNT-SNR2.EPS Gravel Below Grade Snorkel Installation If the Snorkel Termination must be installed below grade, i.e. basement application, proper drainage must be provided to prevent water from VNT-SNR2.EPS entering the Snorkel Termination. Refer to Rigid Pipe Installation Riser Vent instructions for details. Do not attempt to enclose the Snorkel within the Termination Riser Vent Termination wall, or any other type of enclosure. Riser Vent Termination Min. 6-1/4"* (159mm) Min. 6-1/4"* (159mm) Min. 6-1/4"* (159mm) VNT-SNR3.EPS VNT-SNR3.EPS Alternate Horizontal Termination Caps VNT-SNR3.EPS Alternate: Horizontal Riser Vent Terminal Part# 640-530/P Gas Stoves Vent Restrictor Position Vent restriction is required for certain venting installations, see the diagrams in "Venting Arrangement" section to determine if they are required for your installation. The vent restrictor has three settings: "C" Center (factory setting), "L" Left, and "R" Right. Simply loosen the screws and push the vent restrictor plate to the correct position. Tighten the screws. Rigid Pipe Venting Systems Horizontal or Vertical Terminations Vertical Termination Cap Storm Collar Vinyl Siding Standoff (Optional) Flashing Horizontal Termination Cap # 946-523/P Ceiling Firestop Wall Thimble Pipe Length Adj.Pipe Length 11" - 14-5/8" o 90 Elbow 24" Pipe Length Gas Stoves C34-10 Gas Stove Venting Arrangements - Vertical Terminations Rigid Pipe System (Propane & Natural Gas) The C34 is approved for a maximum 30 ft. straight vertical, with Rigid Pipe vent systems for Propane and Natural Gas. The shaded area in the diagram (right) shows allowable venting configurations with a maximum of two 45° elbows allowed. Terminations falling in the shaded area must have the Vent Restrictor Position set to “R” Right. • • • • • Vent must be supported at offsets. Horizontal sections must be supported every 3 feet Firestops are required at each floor level and whenever passing through a wall. Maintain clearances to combustible materials. Minimum of 1’ pipe section between elbows. VENTING ARRANGEMENTS VERTICAL TERMINATION SYSTEMS FOR RESIDENTIAL MANUFACTURED AND MOBILE HOMES The shaded area in the diagram below shows all allowable combinations of straight vertical and offset to vertical runs with vertical terminations. Maximum two 45o elbows. All vertical and offset to vertical vent installations require Vent Restrictor Position "R" (Right). If the vent is ENCLOSED in a chase (min. size 9" x 9") maintain a 1-1/4" clearance to combustibles. May be installed in Manufactured (Mobile) Homes after first sale. Vertical Venting with Two (2. 90° Elbows Two 45° elbows = One 90° elbow Option V H V+ V1 A) 1’ Min. 4’ Max. 2’ Min. B) 2’ Min. 5’ Max. 3’ Min. C) 3’ Min. 6’ Max. 4’ Min. D) 4’ Min. 7’ Max. 5’ Min. E) 5’ Min. 8’ Max. 6’ Min. Maximum total pipe length, of all sections, must not exceed 30 feet. Total horizontal sections must not exceed 8 feet. Minimum of 1 foot between 90° elbows is required. Vent Restrictor in position “C” (Center), Straight Vertical and Offset to Vertical Terminations use Vent Restrictor Position "R" (Right) Gas Stoves VENTING ARRANGEMENTS HORIZONTAL TERMINATIONS FOR ALL VENTING SYSTEMS The shaded areas in the diagram below show all allowable combinations of vertical runs with horizontal term-inations. Maximum one 90O elbow (two 45o elbows equal one 90o elbow). Propane and Natural Gas: Residential, Manufactured and Mobile Homes Installations The venting arrangements diagrammed below, have a min. of 75% (flue loss) efficiency with Fan Off, as required for manufactured homes. (Actual efficiency may be as high as 85%) May be installed in Manufactured (Mobile) Homes after first sale. C34-10 Gas Stove Horizontal Venting with Two (2. 90° Elbows Two 45° elbows = One 90° elbow Option V H + H1 A) 4’ Min. 6’ Max. B) 5’ Min. 7’ Max. C) 6’ Min. 8’ Max. Maximum total pipe length, of all sections, must not exceed 30 feet. Total horizontal sections must not exceed 8 feet. Minimum of 1 foot between 90° elbows is required. Vent Restrictor in position “C” (Center).