ECO3B OE9955 Visit www.NSF.org for the claims associated with products that are NSF listed Cleaner thinking. Greener solutions. • On installation allow room around the clamp ring to grip and rotate • Minimum 30mm vertical clearance below base of housing for cartridge change • On replacing cartridge in sump, align arrow on cartridge top metal plate with arrow on sump - insert and rotate clockwise as per "IN" arrow to stop • To reconnect to head, align arrows on head and sump, push sump into head and rotate clamp ring counter-clockwise • Apply new change date label over existing main product label Operation Tips • Change cartridge every 6 months • Change cartridges when capacity is reached or when pressure falls below 10 psi • Flush for 2 litres following initial installation and cartridge change Warranty eco3 systems (excluding replacement cartridges) are covered by a limited warranty against defects in material and workmanship for a period of 5 years after date of purchase. Replacement cartridges are covered by a limited warranty against defects in materials and workmanship for a period of 1 year after date of purchase. Warning Do not use with water that is micro-biologically unsafe or of unknown quality without adequate disinfection before or after the system. Install in cold water applications only. The contaminants removed by this water filter are not necessarily present in all water. Systems certified for cyst reduction may be used on disinfected water that may contain filterable cysts. We recommend regular replacement of the filter cartridges - change the cartridge at least every 6 months. Do not install if water pressure exceeds 120 psi. If your water pressure exceeds 80 psi, you must install a pressure limiting valve. Do not install where water hammer conditions may occur. If water hammer conditions exist you must install a water hammer arrester. Contact a plumbing professional if you are uncertain how to check for these conditions. Installation and use must comply with all state and local plumbing laws and regulations. Improper installation may result in property damage due to water leakage.