C8ES300 & C8SE300 Series Bilingual Extruded Aluminum Sign • Universal, field-selectable chevrons (knockout) • E nergy efficient – consumes less than 7W in AC or DC mode • Normal AC and emergency DC operation 120, 277 or 347V AC input; 6 to 24V DC input • Available in single or double face • Custom wording available on request • Indirect refractive technology provides bright, even illumination • Long-life ALINGAP technology, energy-efficient LED light source • CSA certified, meets or exceeds CSA 22.2 No. 141 requirements Prepared by: The Exit Sign in a Self-Powered configuration shall be equipped with a Nickel-Cadmium battery and shall stay illuminated during emergency operation for at least two hours upon AC failure. POwer consumption The Exit Sign shall be CSA-C860 approved and meets CSA 22.2 No.141 AC Specs The equipment shall be Emergi-Lite® Model: DC Specs AC/DC standard, red 120/347VAC Less than 2W 6 to 48VDC Less than 3W AC/ special DC, red 120/277/347VAC Less than 2W 36 or 48 or 120VDC Less than 6W 120VAC Less than 6W 120VDC Less than 6W 120 or 347VAC Less than 7W Nickel-Cadmium battery Min. 2 hours Self-Powered, red Date: Supply and install the Emergi-Lite® C8ES300 Series LED Exit Sign. The equipment shall operate with universal AC input voltage of 120, 277 or 347VAC at less than 1.5W and universal two-wire DC input voltage from 6VDC to 24VDC at less than 2.5W for single and double face signs. The Exit Sign shall consist of a two-piece white extruded aluminum combined body/faceplate with a maximum depth of 1 1/4”. The exit shall also include extruded aluminum end caps with white gaskets in order to provide protection to the internal components and eliminate any possible light leaks. The exit fixture shall be either single or double-faced as shown on the drawings. The faceplate shall be of a stencil design and will have 6” high letters with a 3/4” stroke indicating both EXIT and SORTIE side by side. The canopy shall fasten to the exit body for ease of installation in either ceiling or wall mount. The fixture shall contain a light source, which shall be LED with a long life and shall consist of separate AC and DC LED sources in the case of AC/DC-remote equipment. Red LED technology shall be ALINGAP. • P re-specified mounting 120VAC/DC two wires, red Contractor: Typical specifications Features • Thin profile, 2-piece extruded aluminum housing simply slides together Model Project/Location: . Wire guards 460.0059-E Wall Mount 460.0092-E Ceiling Mount Dimensions Dimensions are approximate and subject to change. 55/8” [14.2 cm] 55/8” [14.2 cm] 303/8” [77.1 cm] 95/8” [24.3 cm] 87/8” [22.5 cm] 47/8” [12.5 cm] 13/8” [3.4 cm] 303/8” [77.1 cm] ordering information Series Faces C8ES30= exit sortie C8SE30= sortie exit 2= single face 3= double face colour W= polar white B= black TA= textured aluminum BA= brushed aluminum mounting -CM= ceiling mount -WM= wall mount EXEMPLE: C8ES302W-CM-UTP 32 voltage -U= 120/277/347VAC, 6 to 24Vdc -U36= 120/277/347Vac-36Vdc -U48= 120/277/347/Vac-48Vdc -U120= 120/277/347/VAC-120Vdc -I= 120Vac, Self-Powered -3I= 347Vac, Self-Powered -EM120-2W= 120Vac-120Vdc-2 wires options -TP= tamper-proof screws 990.0119-E= tamper-proof bit* *One bit needed per order.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project