Type: Project/Location: Contractor: PHANTOM™ Series CLOSED FEATURES Supply and install Lumacell® Phantom™ Series. The unit shall be designed to be concealed in walls or ceilings with a cavity, including T-bar suspended ceilings. Bar hanger brackets shall be provided with the self-powered unit. The unit equipment shall come standard with a metal back box containing the batteries, the lamp assembly and a charging circuitry. The back box shall be constructed of heavy-duty galvanized steel. The unit components: battery assembly, charger circuitry and lamp assembly shall have a modular design and come standard with quick connect plugs for easy installation in the back box. The unit equipment shall be completely concealed in the wall or ceiling during normal power conditions. Upon a power failure the unit will expose the emergency heads by rotating its door 180° and then power the lamps. At the restoration of the AC power or at the end of the battery discharge, the lamps will turn off and the unit will retract the heads in the wall (ceiling) by rotating the door by 180°. Under normal conditions, the only visible parts of the unit shall be the flat door and trim plate, coated with a high-quality off-white finish that can be customized on site with paint or other suitable wall covering. The light source shall be 12V MR16 halogen lamps of specified wattage and light output. The unit shall supply the rated load for a minimum of 30 minutes or until the battery is discharged to 87 ½% of its nominal voltage (whichever duration is longer). The charger circuitry shall utilize a micro-controller IC that samples the battery in relation to the ambient temperature, state of charge, and input voltage fluctuations. The charger shall be current limited, temperature compensated, short-circuit proof, and reverse-polarity protected. The circuit will charge in accordance with the CSA C22.2 – 141 requirements. The unit shall be furnished with a recessed, illuminated push button serving as test switch and status indicator light. When specified, the unit shall come complete with the Lumacell® of auto-test microcontroller circuitry that will ensure the equipment readiness and reliability by continuously monitoring every critical function of the unit. If a problem occurs, the pilot light located on the front of the unit, will change color from green to red and will flash indicating a fault. A detailed diagnostic legend shall be available on the door back side and shall provide fault identification (battery, charger circuitry, lamps) for the maintenance personnel. The auto-test shall simulate a power loss for one minute monthly, 10 minutes every sixth months, and a full 30-minute test every 12 months. . The equipment shall be Lumacell® model: and closes or upon power back-on at the end of battery discharge •Input: Standard AC input 120/347VAC, 0.25/0.09 As; optional 120/277VAC •Battery: maintenance-free, sealed Lead-Acid battery, with a 10-year design life •Charger: micro-controller driven, temperature compensated, high-precision, fast recharge •Back-box (self-powered unit): made of heavy-duty, galvanized steel •Remote fixture: version available in 12VDC or 24VDC; no back box, no AC wires are required •Certification: CSA C22.2 No.141 DIMENSIONS Dimensions are approximate and subject to change. 91/8” [23.2 cm] 77/8” [20.0 cm] 237/8” [60.6 cm] 7” [17.8 cm] 33/8” [8.6 cm] REPLACEMENT LAMPS: MR16 TYPE POWER CONSUMPTION PH75 120/347 0.25/0.09 VAC A PH150 Model No.: TYPICAL SPECIFICATIONS •Fully automatic operation: the unit door opens upon loss of AC power AC ASPECS Date: 100% Recessed Emergency Lighting OPENED MODEL Prepared By: WATTAGE CAPACITY 30MIN 2H00 4H00 75 1H00 1H30 40 30 24 15 150 80 60 48 30 IN THE SAME FAMILY: - Phantom™ Series Remote Fixtures p. 128 MODEL VOLTAGE/WATTAGE 580.0080-L 12V-12W 580.0064-L 12V-20W 580.0083-L 12V-35W 580.0076-L 12V-50W 580.0068-L 12V-20W H* 580.0090-L 12V-35W H* 580.0089-L 12V-50W H* 580.0093-L 12V-4W LED 580.0104-L 12V-5W LED 580.0106-L 12V-6W LED *High-lumen output. See the complete list p. 144 to 146 ORDERING INFORMATION SERIES UNIT CAPACITY PH 75= 12V-75W, lead-acid 150= 12V-150W, lead-acid EXAMPLE: PH15012WAT 94 www.lumacell.com LAMP WATTAGE LD7= MR16 LED, 2x 4W LD9= MR16 LED, 2x 5W LD10= MR16 LED, 2x 6W 12W= MR16 halogen, 2x 12W 20W= MR16 halogen, 2x 20W 35W= MR16 halogen, 2x 35W 50W= MR16 halogen, 2x 50W 20WH=MR16-IR, 2x 20W high output 35WH= M R16-IR, 2x 35W, high output 50WH= M R16-IR, 2x 50W, high output VOLTAGE OPTIONS Blank= 120/347VAC ZC= 120/277VAC AT= auto-test* ATN= auto-test, non-audible* T3= time delay (15 minutes) * Minimum lamp load required: 20% of unit capacity.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project