Installation guide RADIO TYBOX Warnings Presentation • Carefully read these instructions prior to installation. Wireless programmable thermostat • The unit must be installed in compliance with currently applicable standards. 1-zone pack or 2-zone pack • Always switch off the mains before installing or servicing the unit. Location The 1-zone pack features a RADIO TYBOX transmitter associated with an RF 640 receiver (1 zone). The 2-zone pack features two RADIO TYBOX transmitters associated with an RF 650 receiver (2 zones). Antenna Zone 1 LED Antenna LED Zone 2 LED 1 Button 2 Buttons • The receiver power supply cable must only be replaced by the manufacturer or an approved agent. • Check that the fastenings are suited to the surface that the unit will be attached to (plasterboard, brick, etc.). • The diagrams provided are simplified for greater clarity. The protective units and other accessories required by the standards are not illustrated. Standard UTE NF C15-100 and good practice must be complied with. Connected or nearby equipment must not generate excessive interference (directive 2004/108/CE). receiver Mounting RF 640 RF 650 Electric cable Electric cable The RF 640 and RF 640 can be connected either to a boiler or to contact switches to control electric heating. The elements of your system (receiver and transmitter(s)) are already associated when delivered. For the 2-zone pack, each transmitter is identified by a label (EMET 1, EMET 2). Connecting the receiver Screw-mounting Inverting the relay contact position Mounted on a wall using the screws and pegs supplied. During an On command: the relay closes. During an Off command: the relay opens. You can invert the operation of the relay by pressing the relevant button on the receiver for about 10 seconds. Contact Inverted contact ON ON OFF OFF OFF ON Command sent DELTA DORE - Bonnemain 35270 COMBOURG - FRANCE E-mail: [email protected] *2702000_rev1* Mounting by double-sided adhesive tape Device compliant with the requirements of directives: R&TTE 1999/5/CE If you fit the receiver using adhesive tape, you must strictly follow the installation recommendations (see “location” section). Ensure that the surface on which the tape is applied is thoroughly clean before attaching the tape. Connecting a boiler with thermostat input Connect the black and grey wires of the receiver to both terminals of the boiler thermostat input. N Connecting the receiver Blue Black Brown Grey black wire grey wire brown wire blue wire Mains N 230V L Boiler thermostat input Location / Mounting To control electrical convectors, you MUST use a power contact switch that is suitable for the total power to be controlled. N L 3A RF 650 3A Blue Black Brown Grey brown wire L 5 A max. RF 640 Because of changes in standards and equipment, the characteristics given in the text and the illustrations in this document are not binding unless confirmed by Delta Dore. For easier use, the RADIO TYBOX can be installed: - mounted on the wall with screws and pegs at an approximate height of 1.5 m, - on a support placed on an item of furniture or a shelf. If necessary, remove the shunt (electric wire) connecting the two thermostat input terminals. Example of a boiler terminal box Remove the shunt If the boiler has a clock input, do not mistake it for the thermostat input. do not mistake it for the clock input (on some boiler models) Connecting a boiler without thermostat input wires to be connected to the receiver N RF 640 If the boiler does not have a thermostat input, you can directly control the circulator located next to the boiler. L 5 A max. Blue Black Brown Grey brown wire blue wire black wire grey wire Mains N 230V L Circulator The contact output of the RF 640 receiver is not powered (dry contact). Configuration Fitting to the base Position the unit on its base and lock it. 1 Position the thermostat on its base. 2 Lock the thermostat Turn the knob to to access the configuration menus, then press the i button for 5 seconds. Separate the unit from its base by unlocking the casing. 5 sec. black wire grey wire blue wire L 230V N N N Power supply of the contact switch coil To avoid interference with the radio transmission, the antenna must be free from any metallic elements (cables, metallic covers, etc.). • Do not attempt to repair the unit yourself; an after-sales service is available. RADIO TYBOX mains L supply 230V/50Hz N The receiver must be placed near the heating control (burner or thermostat input for a boiler, electrical switchboard when used with a contact switch). The unit will propose 4 configurations to choose from: Starting up Turn the knob to The days flash. convector(s) Screw-mounting Zone 1 Mount the base with screws and pegs suited to the support or on a flush-mounted box, then close and lock the unit. Zone 2 The contact outputs of the RF 650 receiver are powered (phase). Basic configurations (Menu 1) When you turn the unit on for the first time, you will need to set the time. contact switches (not supplied) fitted in the electrical switchboard convector(s) Unit version Time setting Remove the batteries’ protective tabs. . Press + or - to change the day, then press OK to confirm and continue on to the next setting. Days Minutes Advanced configurations (Menu 2) (1 :Monday ... 7 : Sunday) Configurations of the consumption indication function (Menu 3) Radio association Hours Unit version Configuration mode Repeat the operations to set the hours and minutes. Menu 3 can only be accessed when the RADIO TYBOX is associated with a RADIO TYWATT. To leave the “time setting” mode, turn the knob. Basic configurations (menu 1) Advanced configurations (menu 2) With thermostatic valve electric heating or hot water heaters, the Comfort temperature can be provided by adjusting the thermostat of each radiator. In this case, only Economy and Frost Protection temperatures are set by the RADIO TYBOX. Press button 1, Press button 2. If there is a difference between the temperature noted (thermometer) and the temperature measured and displayed by the unit, function 2-02 modifies the way the probe takes measurements so as to compensate for this difference. Correction of the measured temperature. Comfort temperature set by the RADIO TYBOX (by default) To change the various settings, press the + or buttons, then press OK to confirm the change and go to the next setting. Temperature control Comfort Daily 1-hour increments (by default) Choice of programming increments 30-minute increments 15-minute increments Circulator anti-seizing Anti-seizing enabled (circulator operates for 1 minute every 24 hours). Modification authorization for the user Program and temperature settings (from 5 to 30°C) modification authorized Program and set-point setting modification unauthorized (Comfort: 16 to 22°C, Economy: 13 to 19°C Frost Protection: 5 to 11°C) Correction possible from -5°C to +5°C in increments of 0.1°C. Press the + or - buttons to make changes, and confirm with the OK button. E.g. If the temperature displayed by the unit is 19°C and the temperature measured is 20°C, add 1°C to the display and confirm by pressing OK. To change the various settings, press the + or buttons, then press OK to confirm the change and go to the next setting. Anti-seizing off (by default) Weekly (by default) Choice of programming Comfort temperature set on each radiator or convector. In this option the screen displays ConF. Advanced configurations (menu 2) Automatic mode temperature display option Continuous set-point temperature display (by default).. With this option, press i to display the room temperature. Continuous room temperature display. With this option, press i to display the set-point temperature. Radio association (menu R) This menu lets you associate all the installation’s wireless products (transmitters and receivers) with the RADIO TYBOX. Go to the radio association menu Pas de fonctions domotiques Fonctions domotiques sur l'installation Fonctions domotiques associées au RADIO TYBOX Press + or - to make your choice. Press OK to confirm and go to the next mode. “Consumption indication” feature Home automation features on the installation Up to 8 home automation products can be associated with the RADIO TYBOX. To associate a consumption indicator with the RADIO TYBOX (e.g. RADIO TYWATT). Radio association No consumption indication Consumption indication function Press i on the RADIO TYBOX. The screen displays “1”. The receiver is associated with the RADIO TYBOX Consumption indicator to associate The features are the following: - operation with door/window magnetic contacts, Press + or - to display “1” flashing. - operation with a TYXAL alarm central control unit, Confirm on the RADIO TYWATT. - operation with TYXAL or TYDOM remote controls (Delta Dore), Check on the RADIO TYBOX that “1” is no longer flashing. - operation with a home automation transmitter (e.g. TYDOM 310). The RADIO TYBOX and the RADIO TYWATT are associated. Radio association (menu R) Transmitter Association 1 2 3 4 5 6 7 8 9 0 # Remote control of the installation TYXAL control unit Transmitter Monitoring alarm on: Heating in Economy mode Monitoring alarm off: Heating in Comfort mode Association Press the domain button until until the remote control emits a beep and the symbol Enter the first 4 numbers of the access code (1234 by default), then press the ( ) button for 5 seconds. Simultaneously press and hold the ON and OFF buttons of the unit’s control device for 5 seconds to switch to maintenance mode. Each newly associated transmitter is displayed on the screen. Number of associated transmitters Transmitter Association Door/window Press the button. Open Window: heating in frost protection mode TYXIA remote control Simultaneously press and hold the buttons Comfort or Economy overrides. for 5 seconds, le LED comes on, goes off, and then comes back on, release the buttons. and The menus 3-12 to 3-18 are only accessible if the RADIO TYBOX is associated with a RADIO TYWATT. Configurations 3-13 to 3-18 let you modify costs according to your subscription. To access the display of consumption, heating, DHW and other uses, you must declare the number of CTs (current transformers, ref. 6330004) associated with the RADIO TYWATT option. Subscription option No consumption indication (by default) Press one of the tactile buttons Overrides Comfort / Economy or On / Off . Number of CTs Associate the buttons Press one of the tactile buttons or . To exit the association mode, press another domain button (e.g. ). Indication of the outdoor temperature tempo EJP Base OP OP blue day Normal hours - PH PH blue day Peak hours - white day OP - - - white day PH - 2 CTs (Heating + DHW) - - red day OP - - - red day PH - Not used The price displayed is the price per kWh (excl. subscription) expressed in euros including taxes (price including municipal and regional taxes and VAT (average of 30%)). For further information, contact your electricity provider. We advise you to round to the nearest cent. Once the radio associations are made, press the OK button to confirm and go on to the next mode. Double tariff - 3-13 to 3-18 Cost per Kwh (incl. tax) Open the sensor’s casing. Press the association button, the red LED will switch on then off. Close the sensor unit. Base 1 CT (Heating) and Outdoor probe Open the cover of the control unit and press the “test” button. Close the control unit. flashes. Associate the buttons or Set the control unit to maintenance mode before switching the RADIO TYBOX to radio association (menu rAd). The association operation is carried out channel by channel on the RF 650 receiver. On the transmitter, confirm the association as indicated in the table or refer to its user guide. Option configuration (menu 3) Home automation remote control Telephone transmitter 2nd step: associating the home automation products. From the menu rAd. 1st step: the receiver is delivered already associated with the transmitter. The display indicates “rAd” as well as the number of associated products (1 receiver). You can go straight on to the 2nd step, associating home automation products To associate a wireless receiver again, you must first remove all associations (see Removing radio associations section), then, on the receiver: for three seconds, press and hold the button of the channel you wish to associate. The corresponding LED flashes. PH: Peak Hours, OP: Off-peak Hours IMPORTANT: The consumption value that you can read on the digital screen is a non-contractual indication and cannot be substituted with the consumption value mentioned on your electricity bill. After menu 3 has been configured, the unit returns to the choice of menus. To exit the configuration, turn the knob to the right. E.g. 0.1085 euros gives 0.11 euros. 0.11 euros (incl. tax) Removing radio associations To cancel all radio associations, turn the knob to , then hold the i button down for 5 seconds. To associate the receiver with the transmitter again, refer to the “radio association” section. Return to the factory configuration Returning to the factory configuration is possible for each of the menus. Turn the knob to , then press and hold the i button for 5 seconds. Press the button of the menu you wish to reset, and hold the button for 5 seconds (this example uses menu 1). Press and hold the R button for 5 seconds. Radio test Summary table of configurations Turn the knob to , then hold the 2nd button (from the top) down for 5 seconds until tESt appears. 5 sec. The LED on the receiver should flash for each reception (approximately every 6 seconds). 1-01 Type of programming 0 = weekly 1-02 No programming 0 = 1 hour 1 = 30 minutes 1-08 Controlling the Comfort temperature 0 = controlled by the RADIO TYBOX 1 = by each radiator or convector. 1-09 Circulator anti-seizing 0 = off 1 = on 2-01 Modification authorization 0 = Program and settings may be changed 1 = Program not modifiable and set-point temperature settings limited (Comfort: 16 to 22°C, Economy: 13 to 19°C, Frost Protection: 5 to 11°C) 2-02 Correction of the measured temperature from -5°C to +5°C in increments of 0.1°C. 2-04 Automatic mode temperature display option 0 = Set-point temperature display 1 = Room temperature display If this happens, radio transmission is occurring correctly. If this does not occur, move your transmitter. Then press the OK button to confirm the reset. NOTE: You can manually reset the receiver by pressing the button of the channel to associate for 30 seconds until the LED flashes rapidly. Summary table of configurations Radio association (menu R) r-01 Home automation features 0 = No 1 = Yes r-02 Consumption indication 0 = No 1 = Yes rAd Radio association zone rAd 1 Reserved menu With a RADIO TYWATT 3-12 Number of CTs 0 = No RADIO TYWATT 1 = 1 CT (Heating) 2 = 2 CTs (Heating + DHW) 3 = 3 CTs (Three-phase) 3-13 à 3-18 Cost per kWh according to subscription Then press the OK button to confirm the reset. Turn the knob or press the OK button to exit the tESt mode. 1 = daily 2 = 15 minutes Follow the same steps for the other menus. To exit this mode, turn the knob to the right. Technical characteristics Technical characteristics RADIO TYBOX transmitter RF 640 / RF 650 receivers • Power supplied by two LR03 or AAA-type 1.5 V alkaline batteries (supplied), autonomy of 2 years for normal use • Class III insulation • Clock back-up in the event of battery change: 30 seconds • Radio range 100 to 300 metres outside, variable depending on the associated equipment (the range can be altered depending on the installation conditions and the electromagnetic environment) • Radio frequency 868 MHz, class I (standard EN 300 220) • Wireless remote control device • Dimensions: LxHxD = 80 x 103 x 16 mm • Protection index: IP 30 • Storage temperature: -10°C to +70°C • Operating temperature: 0°C to +40°C • Installation in an environment with normal pollution levels • Mounting with screws or on a support • 230 V, 50 Hz power supply, ±10% • Class II insulation • Power consumption: 0.5 VA • 1 dry contact output, 5 A max. (RF 640) • Two 3 A powered contact outputs, 230 V Cos ϕ = 1 (RF 650) • Radio frequency 868 MHz (standard EN 300 220) • Radio range 100 to 300 metres outside, variable depending on the associated equipment (the range can be altered depending on the installation conditions and the electromagnetic environment) • Type 1.C automatic action (brownout) • Operating temperature: -5°C to +55°C • Storage temperature: -10°C to +70°C • Dimensions: LxHxD = 102 x 54 x 20 mm • Protection index: IP 44 • Installation in an environment with normal pollution levels Troubleshooting Nothing is displayed on the room unit screen. There is no power supply. Check the batteries. The receiver does not accept orders from the transmitter. • Check the transmission by performing a radio test. • Move your transmitter if necessary. • Repeat the radio-controlled association of the receiver with the RADIO TYBOX. The indication is displayed. The batteries are low. Change the batteries, making sure they are the right way round. The unit displays: dEF 6 There is a communication fault between the RADIO TYBOX and the RF 640 or RF 650 receivers. Check the installation. You wish to associate a home automation feature and the screen displays ---- . You have reached the maximum number of functions to associate. During the radio association, then device displays: Zone rAd 1. This menu is reserved. Associate the receiver again from the rAd menu.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project