In no event shall Mircom be liable for any direct, indirect or consequential damages, loss of anticipated profits, loss of time or any other losses incurred by the buyer in connection with the purchase, installation or operation or failure of this product. Important! Mircom recommends that the entire system be completely tested on a regular basis. However, despite frequent testing and due to but not limited to, criminal tampering or electrical disruption, it is possible for this product to fail to perform as expected. INSTALLATION INSTRUCTIONS RM-2200-4 Relay Expander for FX-2200 Fire Alarm Control Panel The RM-2200-4 is a four relay expander, connected via ribbon cable to a FX-2200 Main Board. This module occupies one spot of the three available mounting locations within the FX-2200 cabinet. The RM-2200-4 provides four additional programable function relays. Parts List • • • Qty 1 ... RM-2200-4 module Qty 4 ... No. 4 screws Qty 1 ... Ribbon Cable (short) Installing the RM-2200-4 The RM-2200-4 mounts inside the FX-2200 cabinet to the back plate in one of the three expander locations. 1. Position the RM-2200-4 in the upper most empty expander module locations. 2. Secure the relay expander to the back plate with the No. 4 screws and lock washers (provided). 3. Connect the ribbon cable from the panel or previous expansion module to CON1 on the Relay Expander. NOTE: This component must be included in the control panel battery calculation. Refer to the Battery Calculation Sheet included with the control panel. Relay Circuits are non-supervised. Relays must be connected to a power limited source that is listed Fire Protective Signaling. LT-2027MIR Canada 25 Interchange Way Vaughan, ON, L4K 5W3 Tel: (905) 660-4655 Fax: (905) 660-4113 www.mircom.com Rev. 0 USA 60 Industrial Parkway PMB 278 Cheektowaga, NY, 14227 Tel: (888) 660-4655 Fax: (888)660-4113 RM-2200-4 Relay Expander FX-2200 Panel Layout FRONT PANEL CON1 IN BACK PANEL DACT BD OR CITY BD Normally Off Equipment #1- NO #1 - C DISPLAY HARNESS MAIN BD DISPLAY BD NAC BD OR RELAY BD CON4 #1 - NC Normally Off Equipment #2- NO #2 - C Normally On Equipment #2 - NC Normally Off Equipment #3- NO Relays* User Equipment NAC BD OR RELAY BD Normally On Equipment #3 - C Normally On Equipment #3 - NC Normally Off Equipment #4- NO #4 - C Normally On Equipment NAC BD OR RELAY BD CON2 OUT LED DISPLAY XFORMER XFORMER (optional) T/B RECTIFIER BATTERY BATTERY (optional) Figure 1. RM-2200-4 Relay Expander Installation #4 - NC * Relays shown in de-energized state.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project