Wall-Mounted Cooler With Filter MODEL WM8A-WF-Q This water cooler is certified to NSF/ANSI 61. INLET STRAINER Easily cleaned in-line strainer screen traps particles of 140 microns or larger before they enter the waterway. GENERAL Self-contained, electric refrigerated, wall-mounted water cooler with lead filter designed to be easily accessible to able-bodied individuals. Unit is certified to NSF/ANSI 61 and meets requirements of the Safe Drinking Water Act. Unit provides 50° F water at 80° F inlet water and 90° F ambient. TEMPERATURE CONTROL Positive sensing thermostat for controlling temperature of storage tank water. Factory set at 50° F Adjustable ±5° F. STORAGE TANK Non-pressurized stainless steel evaporator/storage tank for long life. Waterways are certified to NSF/ANSI 61, far exceeding the requirements of the Safe Drinking Water Act. LEAD REDUCTION FILTER Halsey Taylor Water Cooler With Filter is equipped with the Water Sentry HWF 172 lead reduction system which is designed to remove cysts, such as cryptrosporidium and giardia, lead particles and chlorine. Also reduces odors and discoloration from incoming water. The filter has been tested to the following NSF International standards: NSF/ANSI Standards 42 Chlorine, Particulate, and Taste and Odor. NSF/ANSI Standard 53 for Reduction of Lead and Cyst. Features include Quick-Disconnect 1/4 turn installation. Has automatic inlet shut-off valve that closes when filter is removed. Filter should be replaced every 1,500 gallons (5678 liters) or approximately one (1) year after installation. Use part number 55897C when ordering replacement filter. REFRIGERATION SYSTEM Hermetically sealed, positive start compressor with lifetime lubrication and built-in overload protection, efficient capillary sizing, large capacity dryer-strainer, and self-lubricated fan cools copper/aluminum condenser. System uses R134A refrigerant. Protected by Halsey Taylor’s Limited 5 Year Warranty. VENTILATION Insure proper ventilation by maintaining 6" (152mm) minimum clearance from cabinet louvers to wall. SUGGESTED SPECIFICATIONS Shall deliver 8.0 GPH of 50° F water at 90° F ambient and 80° F inlet water. Shall have lead reduction filter and stainless steel basin with removable drain strainer. Bubbler shall be two stream, mound-building type. Separate valve and automatic stream regulator shall be mounted within cabinet. Refrigeration system shall employ high efficiency, positive start compressor using R134A non-pressurized tank with totally encapsulated insulation and be controlled by positive sensing thermostat. The manufacturer shall certify the unit to meet the requirements of NSF/ANSI 61, and the Safe Drinking Water Act. Unit complies with ARI Standard 1010. CABINET Heavy-gauge vinyl clad steel. Resistant to wear, moisture, perspiration, heat and sunlight. Optional Stainless Steel is available. COOLER TOP Non-corrosive stainless steel cooler top, number 300 series with satin finish resists stains and corrosion and is easy to maintain. Anti-splash ridge reduces splatter. Contoured to insure proper drainage. BUBBLER Exclusive one-piece, chrome-plated two-stream mound-building bubbler with non-removable anti-squirt feature and integral hood insures a satisfying drink of water. NOTE: Continued product improvement makes specifications subject to change without notice. See Halsey Taylor website for most current spec sheet. PUSHBUTTON ACTUATION MECHANISM Self closing, vandal-resistant pushbutton does not require grasping or twisting. Standard finish is Platinum Vinyl Optional Finish (extra cost) ■ All Stainless Steel Optional Accessories (extra cost) ■ Glass Filler ■ Vandal-Resistant Kit ■ Easy-Flex™ Bubbler Trap and service stop not included. JOB NAME: ENGINEER/CONTRACTOR NAME: AUTOMATIC STREAM HEIGHT REGULATOR Self-closing assembly is located inside unit to prevent tampering. Unit resists corrosion and liming. A constant stream height is automatically maintained under line pressures that vary from 20 to 105 psi. APPROVAL: DATE: WM WATER COOLER WITH FILTER Model No. WM8A-WF-Q 70°F 9.2 GPH Capacity Cooled to 50° F* Ambient Air Temp 80°F 90°F † 8.4 7.6 100°F 6.8 Base Rate Cap. F.L. Amps Shipping Weight lb. Rated Watt Usage 7.6 4.0 72 370 * With projector service and tap water at 80° F † UL listed and complies with ARI Standard 1010 halseytaylor.com HALSEY TAYLOR, 2222 CAMDEN COURT, OAK BROOK, ILLINOIS 60523 C2 / 8-2007 WM8A-WF-Q Wall-Mounted Cooler With Filter (CONTINUED) MOUNTING HEIGHT Adult mounting height recommended 40" from basin to floor. May be mounted at any desired height. MOUNTING INSTRUCTIONS Mount trap and install service stop to building supply line. Anchor hanger bracket securely to wall on all sides. To insure proper engaging of waste line into trap, centerline of trap must be 6 1/ 4" from wall face. Remove slip nut and gasket from trap and install on waste line tube. Hang cooler on bracket and engage waste line tube into trap inlet. Centerline height of waste outlet is 22 1/ 2" from floor line for conventional adult installation. PLUMBING CONNECTIONS Enter directly into cabinet. Waste 1 1/ 4" O.D. slip connection. Supply 3/ 8" tubing. OPERATING PRESSURES: Supply water-105 psi maximum ELECTRICAL DATA Furnished with plug-in, 3-wire grounding type service cord. Standard 120 volt, 60 Hz, single phase. Install 120 volt receptacle, rated at 15-amp minimum, to receive 3-wire parallel blade grounding type male plug. Trap and service stop not included. FRONT VIEW / WALL LAYOUT SIDE VIEW NOTE: Optional holes may be added to back panel to secure bottom of cooler to wall. Minimum wall clearance for air flow is 4 inches (102mm) on either side. NOTE: A service supply stop must be installed at the cooler inlet line. Printed in the U.S.A.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project