DATA SHEET LS Programmable Logic Controller Analog Output Option Board Safety Precautions ► Safety Precautions is for using the product safely and correctly in order to prevent the accidents and danger, so please go by them. ► The precautions explained here only apply to this module. For safety precautions on the PLC system, refer to User‟s manual. ► The precautions are divided into 2 sections, „Warning‟ and „Caution‟. Each of the meanings is represented as follows. If you violate instructions, it can cause death, fatal injury or a XGB Warning considerable loss of property XBO-DA02A Caution If you violate instructions, it can cause a slight injury or a slight loss of products ► The symbols which are indicated in the PLC and User‟s Manual mean as follows. This symbol means paying attention because of danger of injury, fire, or malfunction ► This symbol means paying attention because of danger of electric shock. Store this datasheet in a safe place so that you can take it out and read it whenever necessary. Always forward it to the end user Related Manual Read this data sheet carefully prior to any operation, mounting, installation or start-up of the product. Name Code XGB analog 10310000920 XGK/XGB Instruction & Programming 10310000754 XG5000 10310000512 XGB Hardware 10310000926 Revision History Date 2011.01 2011.05 Version V1.0 V1.1 Updated Information First Edition CI changed Applicable version For system configuration, the following version is necessary. Segment XGB E type XGB S type XGB SU type XG5000 Version V1.1 or above V1.1 or above V1.0 or above V3.61 or above Handling Precautions ► Don‟t drop or make impact. ► Don‟t detach PCB from case. It may cause problem. ► When wiring, let no foreign material go into the module. If it goes into the module, remove it. ► Don‟t detach the module from slot while power is on - When using LSIS equipment, thoroughly read this datasheet and associated manuals introduced in this datasheet. Also pay careful attention to safety and handle the module properly. - Store this datasheet in a safe place so that you can take it out and read it whenever necessary. Warning 2. Performance Specifications Following presents performance specification of analog input option board. Item Number of channel Type Performance specification 2 channels Current DC 4 ~ 20㎃ DC 0 ~ 10V DC 0 ~ 20㎃ Analog (load resistance: (load resistance: output 2㏀ or above) Range 450Ω) Output range can be set at user program or I/O parameter per each channel-Note1) Form 12 bit binary data Unsigned 0 ~ 4000 Digital Signed -2000 ~ 2000 Input Range Precise 0 ~ 1000 (DC 0 ~10V) 400~2000 (DC 4~20㎃) 0 ~ 2000 (DC 0~20㎃) value Percentile 0 ~ 1000 1/4000 (DC 4~20㎃: 1/3200) Max. resolution 5㎂ (DC 0~20㎃) 2.5mV (DC 0 ~10V) 6.25㎂ (DC 4~20㎃) Precision ±1.0% or less Max. conversion speed 1ms/channel + scan time CH output status setting Additional function (select among former, min, middle, max value) Gain adjustment function Non-insulation between analog output channels Insulation method Non-insulation between output terminal and PLC basic unit Input terminal 5-point terminal block I/O occupation point Fixed type: 64 point Max. installation count Supply power Consumption current Weight ► Do not contact the terminals while the power is applied. Risk of electric shock and malfunction. ► Protect the product from being gone into by foreign metallic matter. Risk of fire, electric shock and malfunction. Voltage 1EA (when using XBC-DR10E/DR14E “E” type) 2EA (when using XBC-DR20E/DR30E “E” type) 2EA (when using XBC-DxxxS/SU “S” type) Internal DC5V 150㎃ 20g Remarks Note1) Offset/gain value on the analog output range can be adjusted at XG5000- I/O parameter ► Risk of fire, electric shock and malfunction. Risk of injury and fire by explosion and ignition. 1. General Specifications HEAD OFFICE LS Tower, 127, LS-ro, Dongan-gu, Anyang-si,Gyeonggi-do, 431-848, Korea Tel: 82-2-2034-4870 Fax: (82-2)2034-4648 e-mail: email@example.com Caution ► Be sure to check the rated voltage and terminal arrangement for the module before wiring work. Risk of electric shock, fire and malfunction. LSIS(ME) FZE _ Dubai, U.A.E. Tel: 971-4-886-5360 Fax: 971-4-886-5361 e-mail: firstname.lastname@example.org ► Tighten the screw of terminal block with the specified torque range. If the terminal screw is loose, it can cause fire and electric shock. LSIS Tokyo Office _ Tokyo, Japan Tel: 81-3-3582-9128 Fax: 81-3-3582-2667 . e-mail: email@example.com LSIS Shanghai Office _ Shanghai, China Tel: 86-21-5237-9977(609) Fax: 89-21-5237-7189 ► Use the PLC in an environment that meets the general specifications contained in this datasheet. Risk of electrical shock, fire, erroneous operation and deterioration of the PLC. e-mail: firstname.lastname@example.org LSIS Beijing Office _ Beijing, China Tel: 86-10-5825-6027(666) Fax: 86-10-5825-6028 ► Be sure that external load does not exceed the rating of output module. Risk of fire and erroneous operation. e-mail: email@example.com ► Do not use the PLC in the environment of direct vibration Risk of electrical shock, fire and erroneous operation. LSIS Guangzhou Office _ Guangzhou, China Tel: 86-20-8328-6754 Fax: 86-20-8326-6287 e-mail: firstname.lastname@example.org LSIS Chengdu Office _ Chengdu, China Tel: 86-20-8328-6754 Fax: 86-20-8326-6287 ► Do not disassemble, repair or modify the PLC. Risk of electrical shock, fire and erroneous operation No Item 2 4 5 Vibration resistance 6 Shocks resistance e-mail: email@example.com LSIS Europe B.V., Netherlands Tel: +31 (0)20 654 1420 Fax: +31(0)20 654 1429 e-mail: firstname.lastname@example.org Precautions for use ► Do not Install other places except PLC controlled place. ► Make sure that the FG terminal is grounded with class 3 grounding which is dedicated to the PLC. Otherwise, it can cause disorder or malfunction of PLC PLC Others PLC Others PLC Noise resistance 7 LS constantly endeavors to improve our products so that information in this datasheet is subject to change without notice. The date of issue: 2011. 5 10310001188 Ver 1.1 3. Parts Name and Descriptions 35.0mm ► ► ► ► ► ① Hook for fixation ② Terminal block ③ Cover ⑤ Connector for option board ⑥ Input connector ⑤ ⑥ C) Bad Connect expansion connector correctly when expansion module is needed. Do not detach PCB from the case of the module and do not modify the module. Turn off power when attaching or detaching module. Cellular phone or walkie-talkie should be farther than 30cm from the PLC. Input signal and communication line should be farther than10cm from a hightension and a power line in order not to be affected by noise and magnetic field. (1) Precautions for wiring (a) Don‟t let AC power line near to analog output option board‟s external output signal line. With an enough distance kept away between, it will be free from surge or inductive noise. (b) Cable shall be selected in due consideration of ambient temperature and allowable current. More than AWG22 (0.3㎟) is recommended. (c) Don‟t let the cable too close to hot device and material or in direct contact with oil for long, which will cause damage or abnormal operation due to short-circuit. (d) Check the polarity when wiring the terminal. (e) Wiring with high-voltage line or power line may produce inductive hindrance causing abnormal operation or defect. (f) Enable the channel that you want to use Wiring example ④ Hook for fixation ③ B) Good 4. Wiring 49.0mm ② - 5 ~ 95%RH, non-condensing - 5 ~ 95%RH, non-condensing - For discontinuous vibration Acceleration Frequency Amplitude times 10≤f∠57 Hz 0.075 mm 10 times in 57 ≤f≤150 Hz 9.8㎨ (1G) each For continuous vibration direction Acceleration Frequency Amplitude for 10≤f∠57 Hz 0.035 mm X, Y, Z 57≤f≤150 Hz 4.9㎨(0.5G) Max. impact acceleration : 147 ㎨ (15G) Authorized time : 11㎳ Pulse wave : Sign half-wave pulse (Each 3 times in X,Y,Z directions) Square wave AC: ±1,500V impulse noise DC: ±900V Electrostatic Voltage: 4kV (Contact discharge) discharge - Radiated electromagnetic field noise Name Description Hook for fixation ▶ Hook for fixing the option board to basic unit ▶ Wiring terminal block to connect with external Term nal block device(Analog output) Cover ▶ Option board cover Connector for ▶ Connection connector for connecting the option option board board to the basic unit ▶ Wiring connector for connecting with the external Input connector device Ambient conditions Operating height Pollution degree Cooling type 8 9 10 11 Power supply module 2 kV IEC61131-2 IEC61131-2 LSIS standard IEC61131-2 IEC61000-4-2 IEC61131-2 IEC61000-4-3 80 ~ 1,000 MHz, 10 V/m Voltage A) Best No. ①④ - -25 ~ 70℃ Fast transient Segment /burst noise Others Homepage: http://eng.lsis.biz 10.3mm Standard 0 ~ 55℃ Operating humidity Storage humidity 3 ► When disposing of PLC and battery, treat it as industrial waste. Risk of poisonous pollution or explosion. LSIS Qingdao Office _ Qingdao, China Tel: 86-532-8501-6068 Fax: 86-532-8501-6057 e-mail: email@example.com Specification Operating temperature Storage temperature 1 Digital/analog input/output communication interface 1 kV IEC61131-2 IEC61000-4-4 No corrosive gas or dust - 2000m or less - 2 or less - Natural air cooling - 5. Internal memory 7. Dimension (㎜) Internal memory area for analog output option board (1) Analog/digital conversion data I/O area type Device _0x_ERR _0x_RDY _0x_DA0_ACT _0x_DA1_ACT _0x_DA0_ERR _0x_DA1_ERR Variable BIT BIT BIT BIT BIT BIT U0x.00.0 U0x.00.F U0x.01.2 U0x.01.3 U0x.01.A U0x.01.B _0x_DA0_OUTEN BIT U0x.06.0 _0x_DA1_OUTEN BIT U0x.06.1 WORD WORD U0x.07 U0x.08 _0x_DA0 DATA _0x_DA1_DATA Comment Module Error Module Ready CH0 active CH1 active CH0 error CH1 error CH0 output state setting CH1 output state setting CH0 input value CH1 input value Read/ Write Signal direction Read Option→ CPU Write Option↔ CPU a) Current Output Load Remarks How to express U device U0x.00.0 450 Ω or less b) Voltage Output Load 2kΩ or above Slot Bit no. Word no. Ex1) CH0 input value of the module at slot 9 -> U09.07 Ex2) CH0 error of the module at slot 9 -> U09.01.A (2) Analog/digital operation parameter setting area Memory address Description Hex Dec 0H 1H 2H 8H BH CH DH 0 1 2 8 11 12 13 Enable CH Output range setting Input data type setting CH output state setting Output CH0 gain weighting Output CH1 gain weighting Setting error information output area Read/Write Instruction Read/Write PUT GET Read GET 6. Error code (1) It saves error code detected when setting (in case of setting by program) (2) Setting error is canceled when setting goes in the normal range by re-setting (3) When U0X.01.8~ U0X.01.9 (setting error flag) is on, check this area and fix the corresponding setting to cancel the error (4) When using GET instruction, setting error information address is as follows. Error Type Description Priority Remark code 50# Output CH range setting error 2 60# Output CH data type setting error 3 Setting # means CH No. 70# Output CH count average setting error 4 error Output ch0,1 80# Output CH gain weighting setting error 5 90# Output CH input value out of range error 1 (5) When more than one error occurs, it saves error code having higher priority. 8. Warranty (1) Warranty period LSIS provides an 18-month-warranty from the date of the production. (2) Warranty conditions For troubles within the warranty period, LSIS will replace the entire PLC or repair the troubled parts free of charge except the following cases. (a) The troubles caused by improper condition, environment or treatment except the instructions of LSIS. (b) The troubles caused by external devices. (c) The troubles caused by remodeling or repairing based on the user‟s own discretion. (d) The troubles caused by improper usage of the product. (e) The troubles caused by the reason which exceeded the expectation from science and technology level when LSIS manufactured the product. (f) The troubles caused by natural disaster. (3) This warranty is limited to the PLC itself only. It is not valid for the whole system which the PLC is attached to.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project