POWER PATROL Revenue Grade Power Meter The Setra Power Patrol is every electrical contractor’s dream. The Revenue Grade networked 3-phase power meter works with Rogowski Coils and has a small enough form factor to be mounted inside or outside of the panel using either mounting tabs or the DINrail clip making it the easiest installation in the industry. Rogowski and CT Compatible The Power Patrol works with either Rogowski Coil “flex” CT’s or conventional split-core CT’s. The ability to have interchangeable CT’s gives added flexibility for last minute changes at the job site. The Power Patrol is embedded with the necessary amplifier/integrator circuity for the Rogowski coil CT’s, eliminating the need to provide external power. n n Easy USB Configuration Power and configure the meter through your computer’s USB port using the Power Patrol HeadStart software. While other meter’s require configuration in a live enclosure, the Power Patrol can be easily configured outside of the panel, eliminating the risk of arc flash. HeadStart can save meter settings, allowing the installer to clone meter profiles quickly and easily. Field Selectable Communication (4-in-1) Each Power Patrol comes with field selectable Modbus and BACnet communication. Communications interface to the Power Patrol is through either an RS-485 serial connection (BACnet MS/TP / Modbus) or over Ethernet (BACnet IP / Modbus TCP). Line Powered From 80-600V The Power Patrol series instruments are line-powered and do not require external power. Its power supply can accommodate service voltage ranging from 80-600V (phase-to-phase). The Power Patrol has 3 LED indicators (Red/Green) which confirm proper CT-to-phase installation. n Configure & Power Through USB Field Selectable BACnet/Modbus (4-in-1) 5 Year Warranty Power Patrol Features: • Revenue Grade Approved by NRTL • Configure & Power Through USB • Eliminate Setup Within Live Enclosure • UL 610 Rated & BTL Certified • Phase-Check LED’s Confirm Wiring • Rogowski Coil & Split-Core CT Compatible • Field Selectable BACnet/Modbus (4-in-1) • Broadband Power Supply (80-600V) • Optional Display For Setup and Monitoring • ANSI C12.20-2010 Class 0.2 • Bidirectional • DINrail Mount • Digital Pulse Output Applications: • Measurement & Verification • Demand Response • Energy Cost Allocation • Equipment Efficiency Tracking • Preventative Maintenance Phone: 800-257-3872 • Fax: 978-264-0292 • setra.com © Setra Systems, Inc. All rights reserved. The Setra Systems name and logo are registered trademarks of Setra Systems, Inc. Power Patrol Revenue Grade Power Meter ACCESSORIES ORDERING INFORMATION S P P Model Communication Port SPP= Setra Power Patrol Display E Ethernet & Serial D Display S Serial Only (RS-485) N No Display MODBUS REGISTER/BACNET OBJECT DESCRIPTION LIST System True Energy (kWh) Individual Phase to Phase Voltages Instantaneous Total True Power (kW) Line Frequency (Hz) Peak Demand (Adjustable Window) (kW) Individual Phases True Energy (kWh) Maximum Instantaneous Power (kW) Individual Phases True Power (kW) System Reactive Energy (kVARh) Individual Phases Reactive Energy (kVARh) System Apparent Energy (kVAh) Individual Phases Reactive Power (kVAR) System Apparent Power (kVA) Individual Phases Apparent Energy (kVAh) System Displacement Power Factor (dPF) Individual Phases Apparent Power (kVA) System Apparent Power Factor (aPF) Individual Phases Apparent Power Factor (aPF) Average Current (Amps) Individual Phases Displacement Power Factor (dPF) Average Line to Line Voltage (Volts) Individual Phases Current (Amps) Average Line to Neutral Voltage (Volts) Individual Phases Line to Neutral Voltages (Volts) Multiple Meters External Data Synchronization Individual Phases Line to Line Voltages (Volts) Refer to Operating Manual For Complete List 900900-G USB Communication Cable, Type A to B, Power Patrol 900901-G USB Flash Drive, HeadStart Software, Power Patrol SPP-ACC-ENC1 Enclosure Kit SPP-ACC-LEADS-208 Voltage Leads 208 VAC SPP-ACC-LEADS-480 Voltage Leads 480 VAC SPP-ACC-FUSE-208 Fuse Leads 208 VAC SPP-ACC-FUSE-480 Fuse Leads 480 VAc GENERAL SPECIFICATIONS Technical Communications Service Type Single Phase, Three Phase-Four Wire (WYE), Three Phase-Three Wire (Delta) Direct BACnet IP, BACnet MS/TP, Modbus TCP, Modbus RTU Power From L1 Phase to L2 Phase. 80-600VAC CAT III 50/60Hz, 70 mA Max. Non-user replaceable 0.5 Amp internal fuse protection Max Distance 1200 meters with data rate of 100K bits/second of less Voltage Channels 80-346 Volts AC Line-to-Neutral, 600V Phase-to-Phase, CAT III Baud Rate Modbus: 9600 (default), 19200, 38400, 57600, 76800 & 115200. BACnet: 9600, 19200, 38400 & 76800 (default). Current Channels 3 Channels, 0.67 VAC max, 333 mV CT’s, 0-4,700 Amps depending on CT Data Bits 8 Maximum Current Input 200% of current transducer rating (mV CTs) Parity Measure up to 5000A with Patrol Flex None, Even, Odd Measurement Type True RMS using high-speed digital signal processing (DSP) Stop Bit 2, 1 Line Frequency 50/60 Data Formats Modbus or BACnet Waveform Sampling 12 kHz Mechanical Parameter Update Rate .5 seconds Operating -7o to 60o C (-20o to 140o F) Temperature Measurements Volts, Amps, kW, kWh, kVAR, kVARh, kVA, aPF, dPF (Partial List) Humidity 5% to 95% non-condensing Accuracy 0.2% (<0.1% typical) ANSI C12.20-2010 Class 0.2 Enclosure ABS Plastic, 94-VO flammability rating Resolution 0.01 Amp, 0.1 Volt, 0.01 watt, 0.01 VAR, 0.01 VA, 0.01 Power Factor depending on scalar setting Weight 340 g (12 ounces, exclusive of CT’s) LED Indicators Bi-color LEDs (red and green): 1 LED to indicate communication, 2 LEDs for correct CT-to-phrase installation (per meter element), 1 LED for pulse Dimensions 23.0 x 9.0 x 4.0 cm, (9.0” x 3.5” 1.5”) Pulse Output Open Collector, 5mA max current, 30V max open voltage Safety Power Patrol UL Listed and CE Mark, Conforms Serial and to UL Std 61010-1 Ethernet SSP-SPP Rev A 05/15 Phone: 800-257-3872 • Fax: 978-264-0292 • setra.com © Setra Systems, Inc. All rights reserved. The Setra Systems name and logo are registered trademarks of Setra Systems, Inc.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project