A P U B L I C AT I O N O F T H E I N T E R N AT I O N A L S O C I E T Y O F A U T O M AT I O N Wired versus wireless trade-offs How to choose for new installations By Moazzam Shamsi Figure 5. Steam trap monitoring with Rosemount 708 wireless acoustic/temperature transmitters allows accurate detection of issues before they escalate. F ieldbus technology has been available for more than 20 years. Initially, FOUNDATION Fieldbus and other digital fieldbus technologies were developed in the 1990s as a replacement for the 4–20 mA standard. Today, virtually every manufacturer of flowmeters, pressure transmitters, and similar instrumentation offers FOUNDATION Fieldbus and other popular fieldbus interfaces, and every major automation system vendor supports one or more fieldbus standards. More recently, ISA-100 and WirelessHART were also developed. The International Electrotechnical Commission (IEC) approved WirelessHART in March 2010 as IEC 62591, and ISA100 was approved in September 2014 as IEC 62734. For the purposes of this Roseure of SYSTEM INTEGRATION Fieldbus details Figure 1. Many process plants have both wired fieldbus and wireless infrastructure in place, allowing the use of either for new installations and projects. Interface card Device coupler Fieldbus power supply Spur 120 m Trunk 1900 m Terminator Figure 2. FOUNDATION Fieldbus diagram. Multiple FOUNDATION Fieldbus instruments can be connected to each instrument through the device coupler and then networked back to the host control system. article, wireless refers only to wireless sensor systems, and not to other wireless technologies such as 802.11 Wi-Fi. Today, automation professionals in a process plant have a choice to make for new installations: wired or wireless? For plants with existing wired and wireless infrastructure, the choice hinges on a straight comparison of the two technologies and the application of the solution that makes sense. For plants without an existing wireless infrastructure, the cost of installing one must be considered (figure 1). Compared to traditional 4–20 mA wiring, fieldbus technologies save wiring costs, simplify expansion, and are easier to make redundant because they allow multiple instruments to use a single cable called a trunk or segment. A trunk or segment begins at an interface device at the automation system. On a FOUNDATION Fieldbus system, the interface is called an H1 card. The DC power needed for instruments on a FOUNDATION Fieldbus segment is provided by a power supply rated up to 500 mA, enough to theoretically power more than 32 instruments. In practice, however, 12 to 16 instruments are typically installed on a segment. Some instruments require more than 20 mA; available power diminishes over long cable lengths; and engineers like to allow capacity for adding instruments. Typically, up to 12 devices can be installed on a fieldbus segment up to 120 m long. If the process unit has more than 12 instruments, a second or third segment can be installed. If a problem occurs in any instrument on the segment—such as a short circuit—it can disable the entire segment. Therefore, many plants install a segment protector or device coupler, allowing multiple instruments to connect at one location. The device coupler is installed in an enclosure near the process unit. Connections to the individual instruments are called spurs. A typical segment includes an interface card, a fieldbus power supply, a device coupler, and individual spur cables from the coupler to the instruments (figure 2). With FOUNDATION Fieldbus, the H1 card communicates to the plant’s distributed control system (DCS) via a high-speed Ethernet (HSE) connection. Other fieldbus This article shows the advantages of each technology, recognizing that almost every plant will end up with a mix of wired and wireless. To simplify comparisons, FOUNDATION Fieldbus and WirelessHART will be used as leading examples of fieldbus and wireless FAST FORWARD technologies. Each has • Automation professionals working in process significant competiplants can choose between wired fieldbus or wireless for many new projects. tors, but comparison • Some visionaries predict all-wireless plants are of competing techcoming, but this is not possible yet. nologies in each area • Wireless will gain in popularity because is outside the scope of it can monitor anything, anywhere. this discussion. SYSTEM INTEGRATION Figure 3. These two Rosemount 3051S multivariable transmitters are each sensing temperature and pressure, and transmitting this and other information back to the host control system via FOUNDATION Fieldbus. technologies use similar architectures. For critical process units, a redundant segment can be installed, using duplicate segment cables and power supplies. In hazardous areas, intrinsic safety barriers provide protection. Where do you use Fieldbus? The ideal application for wired fieldbus is a process unit containing many flow, pressure, temperature, level, multivariable, and other instruments, all within a reasonable distance of each other. The more instruments in a relatively small area, particularly complex multivariable units, the more fieldbus makes sense (figure 3). By using device couplers and marshalling cabinets strategically located around the unit, wiring from instruments to device couplers can be minimized. Most fieldbus instrument suppliers offer automated design tools, making it easy to design a segment, calculate maximum distances, and determine the wire types. When instruments on a segment are far apart, repeaters allow segment distances up to 300 m. Instrumenting such an application is fairly easy, because multiple vendors make components with various fieldbus interfaces. If a plant wants to modernize its legacy control system and install fieldbusbased instrumentation, HART can use existing 4–20 mA wiring from older instruments to carry digital response speed of a wired system— information to the device couplers. from the spur to the segment to the The device couplers can be installed H1 to HSE to the DCS and back again in the old marshalling cabinet, saving to a control component, such as a a considerable amount in wiring and control valve—can be significantly labor costs. Although HART does not faster than a wireless system. have performance levels comparable to newer fieldbus technologies, Because of the cost of the hardware it is the least costly wired digital (H1 interface, power supply, cable, option, and often sufficient from an etc.), wired fieldbus is not suitable for a operational standpoint. few devices located far away from other Valve and pump controls are also instrumentation. Such applications are available with fieldbus, so it is possible better handled by wireless transmitters, to set up local control loops within the along with other scenarios such as fieldbus array operating independently adding instruments to existing plants from the DCS. This is accomplished without installed extra capacity in the with function blocks allowing, for wired infrastructure. example, local proportional, integral, derivative (PID) control of a digital Wireless details valve controller based on signals from WirelessHART is a self-organizing mesh a nearby level transmitter. If the DCS or technology in which field devices form the HSE go down, the control loop will robust wireless networks to dynamically continue to operate. mitigate obstacles in the process environment (figure 4). Other wireless Shanghai Wujing Chemical, an acetic technologies employ similar strategies, acid plant in Shanghai, China, upgraded with varying degrees of effectiveness. its controls and instrumentation to Wireless technologies do not require increase its capacity from 300,000 tons/ communication wiring and related yr to 530,000 tons/yr. The new system infrastructure. Some wireless devices included an Emerson DeltaV DCS and require power wiring, but the vast FOUNDATION Fieldbus instrumentation. majority of deployments use battery Shanghai Wujing used local control for power and thus operate completely 114 PID loops. This saved 74 percent without wires. Wireless networks of the DCS controller process time. communicate data back to host FOUNDATION Fieldbus diagnostics and systems securely and reliably, and communications are now used during can be applied to both control and calibration of control valves, saving 80 monitoring applications. percent of the time previously needed A WirelessHART installation requires, for maintenance and operations. first of all, a wireless instrument Typically, wired fieldbus devices transmitting data according to the and segments have more power available than wireless transmitters. This makes wired fieldbus suitable when working with loop-powered devices such as twowire level transmitters with continuous wave modulation, eight-channel process temperature transmitters, tank gauging multispot temperature transmitters, intelligent on/off valves, and field indicators. Wired fieldbus is also Figure 4. Modern wireless networks can be used to communicate with many types of devices spread suitable for real-time over widely dispersed areas. process control. The SYSTEM INTEGRATION IEC 62591 WirelessHART standard. If a transmitter does not have WirelessHART, a wireless adapter can be installed on most existing two- or four-wire devices. With WirelessHART, each wireless device transmits to a gateway managing a specific wireless field network. Typically, the gateway is assigned to a process unit. Each gateway manages its own wireless field network and can have an assigned HART tag like any HART device. Each wireless field network in a plant has a unique network ID to prevent devices from attempting to join the wrong network. WirelessHART devices can communicate through each other to send messages to the gateway, forming a self-organizing “mesh.” The mesh extends the range of a device beyond that of its own radio. For example, a wireless device may be several hundred feet away from the gateway with obstacles between, but power-efficient “hops” through neighboring devices closer to the gateway ensure a reliable, extended range. The gateway connects to the DCS via a wired or wireless highspeed link, typically Ethernet. Where do you use wireless? The chief advantage of wireless systems is that they can be installed virtually anywhere in an efficient, timely, and cost-effective manner. Batterypowered transmitters require no wired infrastructure or local power supply, so they can be far away from a process unit’s wired fieldbus and power wiring. They can also be installed in locations where supplying power and cabling would be too expensive or hazardous. This flexibility means that there are benefits to using wireless in both greenfield capital projects and existing brownfield facilities. Greenfield capital projects typically want to make 10 to 20 percent of traditionally wired signals wireless. Engineering, procurement, and construction contractors and plant owners see strategically incorporating wireless as beneficial in terms of reducing physical fixed infrastructure. They also use wireless technology to manage schedule risk and cost escalation/containment and to reduce space requirements and weight. Wireless can reduce schedule and cost impacts because there is always the potential for scope creep and additional I/O as projects progress. The later in the project a change comes, the greater the risk of jeopardizing the project schedule and budget. Wireless can usually accommodate these changes better than fieldbus. Quite often, additional measurements are eliminated from the design of a new or retrofit project because those signals are deemed too costly to implement during the capital expenditure phase of a project. If those measurements are needed later, adding wired instrumentation can be much more costly than wireless solutions. On these types of brownfield projects, wireless solutions are a good way of supporting operational excellence programs to improve plant productivity and reliability and compliance to emerging environmental and safety legislation. A plantwide wireless network can be installed with minimal disruption to fixed infrastructure such as wiring, conduits, and cable trays. Adding wiring to these existing assets can be costly, and interfering with aging assets can cause unforeseen issues such as disrupting signal transmission. For example, a major chemical company in Europe implemented a plantwide wireless infrastructure to enable operational expenditure programs. The first application was an energy project to monitor steam traps. The company installed wireless acoustic transmitters to listen for acoustic signatures and monitor temperature—both vital signs related to steam trap operation (figure 5). The steam trap monitors took only two days to install, and they generated a complete return on investment (ROI) in six weeks through detection and remediation of previously unknown losses. In another application, a global contractor reported that adopting wireless solutions cut commissioning time by 50 percent. It also streamlined the design and engineering process, saving 10 hours per measurement point. Using wireless helped them maintain the project schedule and improved their ability to manage change on the project. A third leading wireless application is fixed asset inspections per IEC 60079 Part 17, which requires plants to continuously monitor electrical equipment in hazardous areas. This directive obliges maintenance personnel to manually check instrument cable glands, cables, terminal field junction boxes, safety barriers, trunking, ducting, pipes, and conduit for leaks, corrosion, tightness, and similar problems. Wireless transmitters do not require wired infrastructure, thus eliminating this costly maintenance task. The low-power nature of WirelessHART devices allows them to operate for several years without replacing the battery. Configurable update rates conserve battery life by choosing the most appropriate rate for a particular application, typically within a range of 1 second to 1 hour. Most applications today are “monitoring” and therefore only need infrequent updates. WirelessHART transmitters can in certain circumstances be used in real-time control applications, but this requires higher update rates, in some cases necessitating wired power. Many projects have a very attractive ROI when using wireless that they do not have with wired fieldbus due to its added installation and maintenance Table 1. Advantages of Fieldbus Widespread support among instrument suppliers l Supported by almost every automation system supplier l Familiar to maintenance personnel l Excellent for control l Decades of operating experience l Best for multivariable instruments and multipoint devices l Digital data shows raw measured signals l Extensive diagnostics l Less wiring than 4–20 mA l SYSTEM INTEGRATION Table 2. Advantages of wireless Significant reduction in installation complexity l Inexpensive l Reduces space, weight, and power requirements l Easy to expand to accommodate changes and additions l Excellent for monitoring applications l Can be used for control in some circumstances l Best for hard-to-reach locations l No need to modify existing wired infrastructure l Can reduce the need for fixed asset inspections, reference to IEC60079 Part 17 l Allows measurements to be made where fieldbus is not practical or feasible l costs. In these situations, wireless can quickly deliver an investment payback, with ongoing benefits. Using fieldbus and wireless together Some visionaries predict all-wireless plants are coming, but this is not possible yet. Instead, modern automation platforms and connectivity standards are making it easier to use fieldbus and wireless together. Those designing new automation projects should consider using both as complementary technologies in a tactical way to efficiently manage projects and to enable operational excellence programs. Fieldbus and wireless can be used together to manage project risks, such as I/O scope creep, and engineered to meet power, space, and weight design constraints. Ideally, a basis for design should be established early in the project so engineers clearly understand which technology to use in each situation. Wired fieldbus will continue to be used, because it can perform real-time process control with a DCS and with control-in-field function blocks and provide signals and power to control devices. Wireless control is possible with WirelessHART using PIDPlus algorithms, but it will take time for industry to gain the confidence and experience to apply this technology for real-time control. Wireless will become more popular because it can monitor anything, anywhere. Also, it is more economical than wired fieldbus and can be easily installed in both new and old plants. Industry-leading process plants will install both wired and wireless infrastructure and use whichever is most efficient and effective in each situation. n ABOUT THE AUTHOR Moazzam Shamsi, M.Sc., B.Eng., C.Eng., MinstMC, has been an automation professional for 25 years, and his career spans a broad range of industries and roles from technical leader to project management. He presently works for Emerson Process Management where he globally directs Emerson’s wireless consulting and execution solutions on large capital projects. Shamsi specializes in working with clients and contractors to implement technology solutions for capital and operational efficiency projects. RESOURCES “Big changes ahead for Fieldbus Foundation on the eve of twentieth anniversary” www.isa.org/standards-publications/isapublications/intech-magazine/2013/december/ big-changes-ahead-for-fieldbus-foundation-on-theeve-of-twentieth-anniversary “Projects commissioning with Fieldbus Foundation” www.isa.org/standards-publications/isa-publications/intech-magazine/2013/april/web-exclusive-projects-commissioning-with-fieldbus/ “Industrial wireless sensor networks” www.isa.org/standards-publications/isa-publications/intech-magazine/2012/october/webexclusive-industrial-wireless-sensor-networks Eprinted and posted with permission to Emerson Process Management from InTech January/February © 2015 ISA Services, Inc.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project