Description Function and application The DIM PICO sensor controls brightness at the workplace and in offices to increase comfort and save energy. DIM PICO The sensor is integrated in individual lamps and is connected directly to ECGs with a 1...10 V interface. Function The sensor measures the brightness in the area requiring control for the purpose of keeping the brightness value constant at an adjustable setpoint by adding artificial light to daylight when necessary. As the amount of daylight increases, artificial lighting is reduced. Construction A B The sensor is made up of the following components: • Bulb clip (A) • Light sensor (B) • Cover (C) C 1…10 V Light sensor Fitting instructions Mounting Safety instructions The sensor must only be installed and put into operation by a qualified electrician. The applicable safety regulations and German accident prevention regulations must be observed. WARNING! Exposed, live cables or damaged housing. Danger of electric shock! • Only work on the sensor when it is deenergized. CAUTION! Destruction of the sensor and other devices through incorrect mounting! • Only use ECGs with a 1...10 V interface. • Take note of leakage and creepage distances when laying cables. Connecting the sensor E On/off switch PE N L G White cable (+) E F Striped cable (-) F D ~ ~ - 1...10V DIMM EVG G Electronic ballast (ECG): connect max. 10 ECG. + DIM PICO G Attaching the sensor H HT8 lamp: min. 50 mm T5 lamp: max. 10 mm, use stamped side! II 2009 DIM_PICO_ma0902en_we1.01.indd OSRAM GmbH Kunden Service Center Customer-Service-Center (CSC) Steinerne Furt 62 86167 Augsburg Germany Tel : +49 (0) 1803 677 - 200 (kostenpflichtig / charges apply) Fax.: +49 (0) 1803 677 - 202 www.osram.com www.osram.de 40503005544572 4050300554457 Continued on the back page! Adjusting the setpoint for the brightness Fitting (cont.) Note: • Make the setting while there is a low level of daylight. • Do not cover the sensor during adjustment. • During a function check, ensure that there is a sufficient distance to avoid incorrect luminance measurements. Connect the sensor. In screw terminals, replace the soldered ends with wire end sleeves. Close the cover. Operate the lamp for approx. 30 minutes until the luminous flux has stabilised. Open the cover until dimming begins. Turn the cover back slightly. Transfer the setting to other sensors, if necessary, with the aid of the housing markings. Selecting the installation location I Surveillance cone: not on window surfaces. K Avoid exposure to direct light 50° 50° I K Appendix Technical data 31 mm Load capacity of signal output Max. 6 mA or 10 OSRAM EVG Cable length (2 x 0.5 mm2) 700 mm Light sensor detection area Conical, opening angle approx. 50° Protection class II Protection type IP 20 Weight Approx. 21 g Material Makrolon/polycarbonate Dimensions (L x W x H) 21 x 21 x 31 mm Operating temperature +5 °C … +55 °C ∅ 22 mm 21 mm Conformity with the relevant EU directives is confirmed by the CE symbol.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project