No.586 RELAY CONVERSION KIT The model 586 Relay Conversion Kit is an accessory for the Products-of-Combustion Using the No. 586 Relay Accessory with the No. 5800 Detector Detector, Model 580D. provides an interface to a residential control panel, a home fire warning system, or any other external device requiring a set of switch contacts for actuation. A short time delay (approximately 4 to 7 seconds) after alarm initiation permits testing the detector without activating any connected external device. Reference Figure Relay Contacts; CAUTION: Contact F I. Form C (SPOT) Break Before make. Rating: 6-30 VAC or DC,. ImA to I Amp. max. RED BROWN ORANGE t FIGURE To insta . I I the 1 relay accessory, detector cover to Figure and then 2 and do the remove the following: I. Take off 2. Plug the relay accessory onto two snap posts as shown in Figure 2. PI ease note that the snap posts will guide the four pins into the pin sockets. When relay accessory is installed properly, a snap will be heard (this is the snap posts locking ‘into position). NOTE: the refer battery. The 586 Relay Module is a limited energy circuit. NFPA 74 requires the use of listed cable suitable for power limited circuits per article 760 of the National Electric Code. The cable is available from your security dealer or distributor. 3. Attach appropriate 4. Reconnect 5. Test both the horn alarm and the relay operation using the test switch. Please note that the 5 second delay in relay operation will occur after the horn begins sounding. TO test the detector only, depress the test switch and hold in until the horn sounds a continuous, loud alarm. Release the test switch after 2-3 seconds of alarm. To test the detector and relay, depress the test switch, as above, but hold it in for 8 seconds. This will insure.operation of the relay. the battery wires to cable and replace using the 29 www.PDF-Zoo.com wire detector nuts. cover.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project