GB.TBLZ481.160408 Installation equipment cabinet for smoke funct. TBLZ-1-48-1 GOLD/COMPACT 1. General Equipment cubicle for smoke function consists of a control unit installed in a box with transparent cover. There are necessary terminals for external connection. The equipment cubicle is equipped with knockout grommets. 2. Range of Application The equipment cubicle is used together with smoke detectors TBLZ-2-49-a. In the event of an error indication the unit is designed to control dampers and stop the unit and give an alarm. Connected damper actuators must be suitable for a 230 V supply. 3. Function control unit smoke The control unit is designed to meet the requirements set to provide reliable fire protection together with our smoke detectors. Equipped with relay contactors for controlling dampers and fans. Besides smoke alarms, the control unit is equipped with a service alarm and error alarm relays. In the event of a smoke alarm, a red LED lights and the alarm relays trip at the same time. In the event of a service alarm on the smoke detector, the LED for the service alarm flashes quickly for 1 minute. Then the service alarm relay is active and the LED lights continuously. If the service alarm on the detector resets, the relay trips and the LED starts to flash slowly: Alarm memory. Short-circuits and open-circuits cause fault relays and alarm relays to activate at the same time as the respective LED lights (open-circuit, approx. 10 seconds delay). If a short-circuit or open-circuit recurs, the relays trip and the respective LED starts to flash slowly: Alarm memory. Exercising the relays: keep the reset button depressed for 5 seconds. 4. Installation Use the four screws to mount the equipment cabinet on the wall, unit or similar. 5. Technical Data Supply voltage 230VAC, 50-60Hz Power consumption (control unit) 1.8VA Degree of protection IP 65 Ambient temperature 0-50°C Dimensions (WxHxD) 175 x 125 x 100mm Weight 740g Specifications are subject to alteration without notice. www.swegon.com 1 GB.TBLZ481.160408 6. Electrical Connections The electrical connections are to be wired by a qualified electrician in accordance with local electrical safety regulations. GOLD RX/PC/CX/SD version E/F, GOLD LP, COMPACT SMOKE FUNCTION GOLD RX/PX/CX/SD Terminals on the control unit and in electrical equipment cubicle SMOKE DETECTOR CONTROL UNIT Wiring terminal 101 102 6 Ext. fire alarm 7 Ext. alarm 2 12 13 GOLD LP/COMPACT Wiring terminals inside electrical equip201 ment cubicle 202 Wiring terminals 5 on the control *6 unit Terminal block 7 ** 8 *Should be selected for ext. fire alarm in the micro terminal. **Should be selected for ext. alarm in the micro terminal. Function: In the event that the smoke detector B7 in the duct trips, the alarm is forwarded to GOLD/COMPACT, external fire alarm. Damper actuator MG7 is controlled via control unit B6. When the smoke detectors become dirty, a service alarm is initiated in control unit B6 and is forwarded to GOLD/COMPACT via the external alarm 2. Alarms can be reset on control unit B6 and in the air handling unit’s hand-held micro terminal. 2 www.swegon.com 2,2 MG7: MG7: Damper actuator Damper actuator If additional smoke damper actuators are installed, they must be connected in parallel in the terminal block. B7: Smoke detector B7: Smoke detector If additional smoke detectors are installed, they must be connected in series (install the termination resistor on the last smoke detector only). Specifications are subject to alteration without notice.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project