Sequencer module for automatically running a predefined sequence Type D Assembly/installation: •The DALI SQM must not be connected to the mains. It is supplied directly via the DALI signal line. •The function switch is connected directly to the DALI SQM (potential free contact) and must not be connected to the mains. •DALI signals are not SELV. Therefore the same procedures should be applied as working with mains voltage. This is also valid to the function switch and the cord. •5-year guarantee AS E Function: The DALI SQM constantly sends DALI signals with the set “step time”. These are broadcast-addressed scene calls. DALI scenes 0 to 15 can be called up. The end scene, after which scene 0 is called up again, can be programmed and set to DALI scene 7 on delivery. This means that a sequence of eight scenes is called up. O U T DALI SQM DALI SQM Article number 86458211 Power supply from the DALI line Current input 9 mA Inputs rotary switch, 1 s – 30 min. function switch: max. cable length 100 m OutputDALI Permissible ambient temperature L N 0 °C – 50 °C PH DALI PS PCA EXCEL one4all PCA EXCEL one4all DALI DALI SQM DALI USB Data sheet 08/13-CO057-0 We reserve the right to make technical changes without prior notice. Glow-wire test according to EN 60598-1 passed. DALI standard The DALI SQM is deisgned to control control gear with DALI standard IEC 60929 (DALI V0). Sequencer module for automatically running a predefined sequence do not connect Save DALI SQM 86458211 Reset Step Times 1s 3s 30 min. 10 s 10 min. 1 min. Step times: The “Step Times” rotary switch is used to set the step time. There is a choice of eight time (1 s, 3 s, 10 s, 30 s, 1 min., 3 min., 10 min. and 30 min.). The step time is the time for which a particular scene is active before the next scene is activated. Factory setting: 1 second Step Time 30 s DALI U 3 min. function key The end scene must be accessed by pressing the switch briefly. Pressing the switch for more than 5 seconds stores this as the end scene. The saving of the final scenes is indicated by fast stepping through all the scenes used, followed by an OFF signal. T luxCONTROL Scene 1 Scene 2 Scene 3 O Scene 0 Example: For a step time of 30 seconds the module sends a new scene command every 30 seconds. DALI Function switch AS E Function switch closed The sequencer module is active Setting the fade time Based on the normal DALI specification, the changes from one scene to the next in a sequence would be extremely abrupt. The colours for the individual scenes would come on instantly (within 0.7 s). To ensure that the transition is smooth and gentle you can change the fade time in the ballasts. The time during which the colour is changing can be set between 0.7 s and 90.5 s with the aid of configTOOL software and a DALI USB (article no. 24138923). D Function switch Function switch open The sequencer module is not active Function switch is opened The installation switches off because of the broadcast command “off” is sent. Module switch Up/Save switch ↑ This switch is only active if the sequencer module is not activated (Function switch is open). PH Up ↑ Pressing the switch briefly calls up the next scene. Save ↑ Holding down the switch (for about 5 seconds) defines the current scene as the last scene in the sequence. This setting is retained even after power-off. Down/Reset switch ↓ This switch is only active if the sequencer module is not activated (Function switch is open). Down ↓ Pressing the switch briefly calls up the previous scene. Reset ↓ Holding down the switch (for about 5 seconds) calls the broadcast command “OFF”. Data sheet 08/13-CO057-0 We reserve the right to make technical changes without prior notice. Scene 0 Step Time Scene 1 Scene 2 Scene 3 Fade Time Note: If the step time is less than the fade time the next scene will be selected even if the fade time has not been completed.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project