IL05003006E.pdf 1.6 Installation 1.3 Panel Function Explanation PANEL COMPONENT Alarm Indication LED (RED) ELC-GP04 GRAPHIC PANEL SERIES Instruction Sheet EXPLANATION Status 1: When power is on, the LED will flash three times slowly. Status 2: When there is an abnormal situation, the LED will flash quickly along with an alarm sound. RS-232 Indication LED (Yellow) It will be flashing when transmitting program and communicating by using RS-232. RS-485/RS-422 Indication LED (Green) It will be flashing when communicating by using RS-485/RS-422. LCD Display Area Liquid Crystal Module display area used to display current program state. Escape/Exit Used to cancel an incorrect input, or to Exit a programming step. Mounting ELC-GP04 into the opening is done by carefully fitting the unit into the opening and pressing firmly on all four corners. You could fix it by using the fixed support packaged with ELC-GP04. Warning: If you turn the screw exceeds torque: 4-5(kg-cm), ELC-GP04 may be damaged. (Note the flat surface shoud be a Type 4 “Indoor Use Only” enclosure or equivalent.) Please leave sufficient space (more than 50mm) around the unit for heat dissipation. ： Thickness: 0.5~9.0mm Mounting dimension (unit: mm [inch]) WARNING Please carefully read this instruction before using the ELC-GP04. DANGER! DC input power must be disconnected before any maintenance. Do not connect or 50mm disconnect wires and connectors while power is applied to the circuit. Maintenance must be performed by qualified technicians. The ELC-GP04 display panel is waterproof. But please prevent grease, corrosive liquids and sharp objects from contacting the ELC-GP04. DANGER! The ELC-GP04 requires 24VDC input power. The 24VDC input power should not be connected to the RS-485 communication port. The unit may be destroyed or can’t be repaired if the input power is improperly applied. Please always check the correctly input power wiring before apply power. 85 [3.35] UP/Pg Up: Used to increase the value or move up one page. Pg Dn/DOWN: Used to decrease the value or move down one page. Arrow Keys Left: Left direction key. (move curser to left) Right: Right direction key. (move cursor to right) 135~136.5[5.31~5.37] Thickness Range 0.5~9mm Shift Key Used to select keys F5, F6, F7, F8, F9. Enter Key Used to input a value or accept a programming command. F0/F5: They are used to be constant 0 (F0) and 5 (Shift+F0) when they are in system F1/F6: They are used to be constant 1 (F1) and 6 (Shift+F1) when they are in system has been removed. Do not conduct any wiring or investigation on the ELC-GP04 until 1 minute after power has been removed. Do NOT touch terminals when power on. SPECIFICATION 2.1 Electrical Specification ITEM menu and user can define the functions separately when they are in user page. F2/F7: They are used to be constant 2 (F2) and 7 (Shift+F2) when they are in system Function Keys menu and user can define the functions separately when they are in user page. Function Key/Digital Key menu and user can define the functions separately when they are in user page. F4/F9: They are used to be constant 4 (F4) and 9 (Shift+F4) when they are in system adjusted too tight. menu and user can define the functions separately when they are in user page. 1.4 Back Panel Memory Capacity 256K Byte CPU Hitachi HD64F3064F RAM of System Environment Condition BATTERY SWITCH OR RS-485/422 Division 2. Storage Temperature for Hardware 5-PIN terminals: Wire gauge: 12-24 AWG Torque: 4.5 lb.-inch WARNING – Explosion Hazard – Do not disconnect equipment unless power has been switched off or the area is known to be Non – Hazardous. 32K Byte COM1: RS232; COM2: RS485/RS422(See Section 6) 1.5 Dimension INTRODUCTION Front panel (unit: mm [inch]) 1.1 Model Explanation Right side diagram (unit: mm [inch]) CISPR22, Class A Electrostatic Discharge Immunity EN61000-4-2/1995 Radiated Immunity EN61000-4-31995 Electrical Fast Transient EN61000-4-4/1995 Weight/Dimension Temperature Code 85.00 [3.35] ℃, relative humidity 20-90% RH (non-condensing) -20~60℃ Radiated Emission Cooling Method 97.00 [3.82] 0~50 10G, 11ms, from X, Y, Z three directions and three times for each direction Impact methods, Article 501-4 (b) of the National Electrical Code, NEPA 70,or as specified in Section 18-152 of the Canadian Electrical Code for units installed within Canada, and in accordance with that location’s authority. IP65/NEMA4/UL Type 4 (indoor use) 0.5mm displacement, 10-55Hz, X, Y, Z three directions and two hours for each direction Vibration Power, input and output (I/O) wiring must all be in accordance with Class I, Division 2 wiring Possess extension slot for ELC-GPXFERMOD to copy settings and programs rapidly and save download time. Built-in variety objects to meet your requirement. 24VDC (-15%~20%) 3.5W MAX. Waterproof Class of Front Panel WARNING – Explosion Hazard – Substitution of components may impair suitability for class I, Thank you for choosing Eaton Logic Controller (ELC) GP Series. The features of ELC-GP04 are: resolution is 128*64, display 8*4 Chinese characters (max.) and multi-language support. It is built-in two communication ports (RS-232 and RS-485/RS-422, can be used simultaneously), and Built-in RTC and communication/alarm indication LED. F0~F4, ESC, SHIFT, ENTER and ARROW keys External Input Power Communication Interface This equipment is suitable for use in Class I, Division 2, Groups A, B, C, D or Non-Hazardous Locations only. 1 ELC-GP04 F3/F8: They are used to be constant 3 (F3) and 8 (Shift+F3) when they are in system CAUTION! ELC-GP04 may be damaged if the fixed support (shipped with the pack) is Battery replacement: please use UL component type: CR2032 lithium battery (NOTE: RTC should be reset after changing battery). 2 menu and user can define the functions separately when they are in user page. DANGER! An electrical charge will remain on the DC-link capacitors for 1 minute after power CAUTION! Always ground the ELC-GP04 by using the grounding terminal. Not only this acts as a safety, but also filter out electrical noise. The ground method must comply with the laws of the country where the unit is to be installed. 50mm Hazardous Location rating 0.24kg/147×97×35.5mm (Width × Height × Deep) Natural Air Cooling T6 Class I, Division 2, Group A, B, C, and D 2.2 Function Specification ITEM 1.2 Outline 147.00 [5.79] Vertical view (Unit: mm) Display Screen Screen Color Backlight Resolution Display Range Contrast Adjustment ELC-GP04 STN-LCD Monochromatic The back-light automatic turn off time is 1~99 minutes (0 = do not turn off) (back-light life is about 50 thousand hours at 25 ) ℃ 128X64 Points 72mm (W) X 40mm (H); 3.00” (diagonal preferred) 10-step contrast adjustment IL05003006E.pdf F1/F6: scrolls in a loop as follows 1 6 G H I J K 1 ASCII: characters Other: user define Font F2/F7: scrolls in a loop as follows 2 7 L M N O P 2 5X 8: 25 words X 8 rows COMMUNICATION CONNECTION ■ ELC-GP04 may connect to a PC by using cable ELC-CBPCGP3 F3/F8: scrolls in a loop as follows 3 8 Q R S T U V 3 8X8: 16 words X 8 rows Maximum Words x Rows, for Each Font Size 6 ELC-CBPCGP3 F4/F9: scrolls in a loop as follows 4 9 W X Y Z 4 8X12: 16 words X 5 rows ON PC (R S-232) 8X16: 16 words X 4 rows Font Size ASCII: 5X8, 8X8, 8X12, 8X16 The steps to Startup the ELC-GP04: It will be flashing when transmitting program and communicating by using RS-232. 2. Enter into the startup display, RS-485/RS-422 Indication LED (green) It will be flashing when communicating by using RS-485/RS-422. Program Memory 256KB flash memory RS-232 Data length: 7 or 8 bits, Stop bits: 1or 2 bits Parity: None/Odd/Even, Transmission speed: 9600bps~115200bps RS-232: 9 PIN D-SUB male Serial Communication Port RS-232 (COM1) External Interface HARDWARE OPERATION 1. Power on indication (Flash three times) 2. Flash for communication error or other alarm 3. Special Indication by user programming Alarm Indication LED (RED) RS-232 Indication LED (Yellow) 5 5 1 6 6 1 5 9 9 PIN D-SUB 9 PIN D-SUB 1. Apply 24V DC power, PC COM Port 3. Enter the user-designed program, 9 PIN D-SUB female 4. Press Esc key and hold on for 5 seconds to return to system menu. There are five selections in the system menu and are described below. SELECTIONS ON ELC-GP02/04 9 9 PIN D-SUB female Rx 2 3 Tx GND 5 5 GND EXPLANATION ■ ELC-GP04 may connect to a ELC by using cable ELC-CBPCELC3 Use the connection cable (ELC-CBPCGP3) to connect the serial communication port RS-232 Download Program of ELC-GP04 to a PC. Then use the ELCSoftGP software to download an application program to the ELC-GP04. RS-485/RS-422 Data length: 7 or 8 bits, Stop bits: 1 or 2 bits Parity: None/Odd/Even Transmission speed: 9600bps~115200bps RS-422: 9 PIN D-SUB male RS-485: 5-Pin removal terminal Extension Communication Port RS-422/RS-485 (COM2) Extension Slot 1. Update program version 2.The slot for program copy card Battery Cover DC 3V battery for HMI 5-Pin Removal Terminal There are DC 24V input and RS-485 input Use the connection cable (ELC-CBPCGP3) to connect the serial communication port RS-232 Upload Program of ELC-GP04 to a PC. Then use the ELCSoftGP software to upload an application program from the ELC-GP04. PC/HMI COM Port 9 PIN D-SUB female Transfer a program between two ELC-GP04 units. Rx 2 GND 7 8 1: transmit programs 1 4 6 2: receive programs Copy Program When transmitting programs and data between two ELC-GP04 units. Set one ELC-GP04 to ELC COM1 Port 8 PIN MINI DIN 2 Rx 4 1,2 GND 5V 5 4 8 7 1 3 6 “Receive Program” mode and the other ELC-GP04 to “Transmit Program” mode. Please use 3 TRANSFER MODULE twisted pair wires to connect the two units via the RS-485 ports. There are 8 items that used to modify ELC-GP04 system settings: The function of transfer module that ELC-GP04 provides to copy user program, system function and passwords is different from the copy program. It is used to copy the whole HMI environment settings and application programs to another HMI rapidly. It can save much time and manpower. The operation is in the following. 1 Turn the switch on the XMOD to GPXMOD Turn the switch on the XMOD to XMODGP 2 Insert the XMOD into the extension slot of GP Insert the XMOD into the extension slot of GP 3 Input the power to GP Input the power to GP 4 It will display “remove XMOD” on the screen and It will display “remove XMOD” on the screen and power on again power on again RS-232 9 PIN D-SUB male the communication string for either RS-232 or RS-485. 2. Contrast: Adjust the contrast of LCD screen. 3. Back-light: adjust the automatic turn off time of LCD. Setting range is 00~99 seconds. If 3 Tx 5 GND set to 00, the LCD Back-light will not turn off. XMODGP GPXMOD RS-232: 1. Communication protocol: Setting the address of ELC-GP04, the control port of ELC, and Definition: Transfer module (ELC-GPXFERMOD) = XMOD, GP Series = GP Step ■ The Pin definition of 9 PIN D-SUB 4. Date and Time: It is used to set the ELC-GP04 built-in RTC including year, month, day, RS-422: hour, minute, second and week. Also the internal battery capacity display is shown here. ELC-GP04 Settings RS-422 9 PIN D-SUB male 5. Buzzer: Used to set the buzzer sound, normal mode or quiet mode. 6 6. Language Setting: Used to set the displayed language. English, Traditional Chinese, 8 9 simplified Chinese or user defined language. Rx + Tx + Tx - 7. Password setting: Used to set, enable, and disable the password function. If the password function is enabled, it will require the user to input a password before entering any system HMI display message ■ Switch between RS-422 / RS-485 (by using 8-PIN DIP switch) menu. The factory password is 1234. Copy HMI program to XMOD (GPXMOD) 8. Startup display: Used to select the ELC-GP04 startup display. User can select “user Copy XMOD program to HMI (XMODGP) If the model type of GP does not correspond with the If there is no program in XMOD, GP will display “The model type of program of XMOD, GP will display “GP XMOD is Empty. XMODGP series is illegal”. defined” to use the file that designed by ELCSoftGP and download to ELC-GP04. 9. Comm. Indicator : Used to select the communication Indicator enable or disable. series and XMOD is different. Press Enter to Confirm There are three methods to connect to ELC: 8-PIN DIP switch RS-485 RS-422 SW1~SW4 On Off SW5~SW8 Off On 7 BATTERY LIFE AND PRECISION OF CALENDAR TIMER GP seriesXMOD. Press Esc to Exit”. Using serial communication port (COM1) RS-232 of ELC-GP04: set 8-pin DIP switch to GP will display “GP XMOD series Please wait!” during GP will display “XMOD GP series Please wait!” transmission. during transmission. GP will display “Please Remove the XMOD and GP will display “Please Remove the XMOD and Reboot !” when completing transmitting. Reboot !” when completing transmitting. RS-485 mode and connect the cable (ELC-CBPCELC3) to program communication I/O RS-232C of ELC. ELC Connection 1. 2. Using extension communication port (COM2): set 8-pin DIP switch to RS-422 mode and If the password is forgotten, the password may be cleared using the following code: 8888. This connect four pins (6, 7, 8, 9) of 9 PIN D-SUB male to RS-422 of ELC with 4-wire cable. universal code will clear the password and all internal programs of ELC-GP04. The ELC-GP04 will be re-set to the factory settings. Execute the internal program that download from ELCSoftGP or transmitted from other F0~F4 to input the password characters. F0/F5: scrolls in a loop as follows 0 5 A B C D E F 0 -20 0 20 60 Life (year) 1.972 2.466 2.712 2.835 connect 5-pin removal terminal of extension communication port to RS-485 of ELC with PASSWORD FUNCTION Users may use 0~9 and A~Z as characters for the password. Users must use the function keys ° Temperature ( C) Using extension communication port (COM2): set 8-pin DIP switch to RS-485 mode and twisted pair. 4 ■ Battery life Execution ELC-GP04 units. When entering execution program, you can return to system menu by pressing Escape/Exit (Esc) key for 5 seconds. ■ Precision of calendar timer(sec) ° ° At 0 C/32 F, less than –117 seconds error per month. ° ° At 55°C/131°F, less than –132 seconds error per month. At 25 C/77 F, less than 52 seconds error per month.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project