DETECTION AND CONTROL EQUIPMENT DATA SHEET ® One Stanton Street Marinette, WI 54143 FCM-1 CONTROL MODULE either manually or through panel programming, on a select (zone or area of coverage) basis. FlashScan (patent pending) is a new communication protocol that greatly enhances the speed of communication between analog intelligent devices. Intelligent devices communicate in a grouped fashion. If one of the devices within the group has new information, the panel CPU stops the group poll and concentrates on single points. The net effect is response speed greater than five times that of other designs. Part No. 428101 CB500 004749 Features • Built-in type identification automatically identifies these devices to the control unit • Internal circuitry and relay powered directly by two-wire SLC loop; requires power (for horns, strobes, etc.), audio (for speakers), or a telephone riser (for handsets) • Integral LED blinks green each time a communication is received from the control unit and turns on in steady red when activated • LED blink may be deselected globally (affects all devices) • High noise immunity (EMF/RFI) • Switch between 24-volt NAC power, audio (up to 70.7 VRMS) or telephone • Wide viewing angle of LED • SEMS screws with clamping plates for wiring ease • Direct-dial entry of address (01-159)* • Speaker, audible/visual, and telephone applications may be wired for Class B or A (Style Y or Z) • Face plate is made of off-white Noryl® • Configured for a single Class B (Style Y) or Class A (Style Z) Notification Appliance Circuit • FlashScan™ (patent pending) communication protocol Applications The FCM-1 Addressable Control Module provides the PCR-400 control unit a circuit for Notification Appliances (horns, strobes, speakers, etc.) or monitors a telephone circuit. Addressability allows the FCM-1 to be activated, Description Each FCM-1 Control Module uses one of 159* possible module addresses on a SLC loop. It responds to regular polls from the control unit and reports its type and status, including the open/normal/short status of its Notification Appliance Circuit (NAC). The LED blinks with each poll received. On command, it activates its internal relay. The FCM-1 supervises Class B (Style Y) or Class A (Style Z) notification or control circuits. The FCM-1 can be used to replace the CMX-2 module, Part No. 417479, in existing systems. Upon code command from the unit, the FCM-1 will disconnect the supervision and connect the external power supply in the proper polarity across the load device. The disconnection of the supervision provides a positive indication to the panel that the control relay actually turned ON. The external power supply is always relay isolated from the communication loop so that a trouble condition on the external power supply will never interfere with the rest of the system. Rotary switches set a unique address for each module. The address may be set before or after mounting. The built-in TYPE CODE (not settable) will identify the module to the control panel, so as to differentiate between a module and a sensor address. The FCM-1 is used to switch 24 VDC audible/visual power, high-level audio (speakers), or control telephone devices. Technical Information Normal Operating Voltage: . . . . . . . . . . . 15 to 32 VDC Maximum Current Draw: . . . . . . . . . . 5.1 mA (LED on) Average Operating Current: . . . . 390 µA (LED flashing) External Supply Voltage . . . max 80 volts (RMS or DC) between T3 and T4: Drain on External. 2 µA max. (using internal EOL relay) Supply: EOL Resistance: . . . . . . . . . . . . . . . . . . . . . 47 K ohms Temperature Range: . . 32 °F to 120 °F ( 0 °C to 49 °C) Humidity Range: . . . . . . . 10% to 93% non-condensing NAC RATINGS Load Description Resistive Resistive Resistive Resistive Inductive ) (L/R = 5 ms Inductive (L/R = 2 ms) Inductive (PF = 0.35 ) Listings and Approvals* UL . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . S3705 ULC. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . CS669 Factory Mutual Research Corporation . . . . . . Approved (FMRC) California State Fire Marshal (CSFM) . . 7300-0028:202 MEA. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 457-99-E Maryland State Fire Marshal . . . . . . . . . Permit # 2020 Application Non-Coded Coded Non-Coded Non-Coded Coded Maximum Voltage 30 VDC 30 VDC 110 VDC 125 VAC 30 VDC Current Rating 3.0 A 2.0 A 0.9 A 0.9 A 0.5 A Coded 30 VDC 1.0 A Ordering Information 0.5 A Part No. Non-Coded 125 VAC NOTE: The CB500 barrier is required by U.L. for separating power-limited and non-power limited wiring in the same junction box. * Listings and Approvals are under NOTIFIER Division of Pittway Corporation Shipping Weight lb. (kg) Description 428101 FCM-1 Intelligent Control Module 1 (0.45) FlashScan is a trademark of Notifier. Noryl is a registered trademark of GE Plastics, a subsidiary of General Electric Company. * 01-99 with PCR-400 TYPICAL WIRING FOR SPEAKER SUPERVISION AND SWITCHING, NFPA STYLE Y • • • • CONNECT MODULES TO CONTROL UNITS ALL WIRING SHOWN IS SUPERVISED WIRES MUST BE SUPERVISED PER NFPA MODULE POLARITIES ARE SHOWN IN ALARM TO NEXT DEVICE COMMUNICATION LINE – 32 VDC MAXIMUM. TWISTED-PAIR RECOMMENDED FROM CONTROL UNIT OR PREVIOUS DEVICE AUDIO BRANCH CIRCUIT – DO NOT LOOP WIRE ON TERMINALS 3 & 4. BREAK WIRE TO ENSURE SUPERVISION OF CONNECTIONS. 47K EOL RESISTOR ELR-47K AUDIO AMPLIFIER 70.7 VRMS MAX. Use only models AA-30, AA-100, or AA-120. Amplifier must provide wiring Supervision per NFPA. SPEAKER SWITCHING CIRCUIT: NFPA STYLE W SPEAKERS MUST BE LISTED FOR FIRE PROTECTION. REFER TO THE RELAY CONTACT RATING TABLE FOR MAXIMUM LOAD. TO NEXT CONTROL MODULE – LAST MODULE MUST RETURN WIRES FOR SUPERVISION 004750a SUPERVISION TYPICAL FAULT-TOLERANT WIRING FOR SPEAKER SUPERVISION AND SWITCHING, NFPA STYLE Z • • • • CONNECT MODULES TO CONTROL UNITS ALL WIRING SHOWN IS SUPERVISED WIRES MUST BE SUPERVISED PER NFPA MODULE POLARITIES ARE SHOWN IN ALARM TO NEXT DEVICE COMMUNICATION LINE – 32 VDC MAXIMUM. TWISTED-PAIR RECOMMENDED FROM CONTROL UNIT OR PREVIOUS DEVICE EOL RESISTOR IS INTERNAL AT TERMINALS 8 & 9. BYPASS CAPACITORS: A2143-20, 100 µF, 16 V, NON-POLARIZED, < 10 µA LEAKAGE. AUDIO BRANCH CIRCUIT – DO NOT LOOP WIRE ON TERMINALS 3 & 4. BREAK WIRE TO ENSURE SUPERVISION OF CONNECTIONS. AUDIO AMPLIFIER 70.7 VRMS MAX. Use only models AA-30, AA-100, or AA-120. Amplifier must provide wiring Supervision per NFPA. SPEAKER SWITCHING CIRCUIT: NFPA STYLE X SPEAKERS MUST BE LISTED FOR FIRE PROTECTION. REFER TO THE RELAY CONTACT RATING TABLE FOR MAXIMUM LOAD. TO NEXT CONTROL MODULE – LAST MODULE MUST RETURN WIRES FOR SUPERVISION 004750b SUPERVISION NOTES: 1. Audio circuit wiring must be twisted-pair as a minimum. See Pyro-Chem installation manual for detailed information. 2. When a 70.7 V audio amplifier is used, terminals 1 and 2 are power limited, while terminals 3 through 9 are non-power limited. In this case, the CB500 barrier is required. Otherwise, all terminal wiring is power limited. The CB500 includes a label indicating which terminals are non-power limited. This label MUST BE PLACED adjacent to the nameplate label, which is on the module housing.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project