1 FLEXTEL 200 VV-K FLEXTEL 200 VV-K Flexible 0,6/1kV control cable. IEC 60502-1 / UNE 21123-1 DESIGN 2 1. Conductor Electrolytic copper, class 5 (flexible), based on EN 60228 and IEC 60228. 2. Insulation Flexible PVC. The standard identification of insulated conductors is the following: 1x Natural 2x Brown + Blue 3G Brown + Blue + Green/yellow 3x Brown + Black +Blue 3 x + 1 Brown + Black + Black + Blue (reduced cross section) 4G Brown + Black + Blue + Green/yellow 4x Brown + Black + Black + Blue 5G Brown + Black + Black + Blue + Green/yellow 6 or more conductors Black numbered+ Green/yellow 3 Other identifications are possible on request. 3. Outer sheath Flexible PVC outer sheath, black colour. Other colours available on request. APPLICATIONS Flextel VV-K cable is suitable for fixed installations with complex layouts where flexible cables are required. It is also ideal for connecting motors or frequency converters. The characteristics of the outer sheath material make this cable extremely versatile as it provides a high level of protection in all types of environments. This cable render is an example from this product range and does not neccesarily match the selected core size or number of cores. 46 47 FLEXTEL 200 VV-K CHARACTERISTICS Electrical performance LOW VOLTAGE 0,6/1kV Standard IEC 60502-1 / UNE 21123-1 Chemical performance Chemical & Oil resistance: Good. UV Resistant: UNE 211605. Water performance Water resistance: AD5 Jets. Approvals CE RoHS Other Meter by meter marking. Installation conditions Thermal performance Maximum service temperature: 70ºC (HD) / 90ºC (UL). Maximum short-circuit temperature: 160ºC (max. 5 s). Minimum service temperature: -40ºC (fixed and protected installations) Fire performance Flame non-propagation based on UNE-EN 60332-1 and IEC 60332-1. Reduced emission of halogens. Chlorine <15%. Mechanical performance Minimum bending radius: x5 cable diameter. Impact resistance: AG2 Medium severity. Open Air. Buried. In conduit. Applications Industrial use.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project