1 Inspection 2 Placement Remove the UPS from its packaging and inspect it for damage that may have occurred during shipping. If any damage is discovered, repack the unit and return it to the place of purchase. Modem/Phoneline Connection Plug incoming internet line into the “In” socket at the back of the UPS. Use one more Internet line cable and plug one end of the Internet line cable to the “Out” socket at the back of the UPS. Plug the other end to the modem input socket as shown. 3).When in battery mode, it will display as below. And the mark will flicker every 1second. Note: If I/P-V<40V，input voltage will display “000” Install the UPS unit in any protected environment that provides adequate airflow around the unit, and is free from excessive dust, corrosive fumes and conductive contaminants. Do not operate your UPS in an environment where the ambient temperature or humidity is high. On the other hand, place the UPS unit away from monitor at least 20cm to avoid interference. 3 5 4).When in off charging mode, it will display as below. 6 Turn On/Off To turn on the UPS unit, press the power switch lightly. To turn off the UPS unit, press the power switch again (When Swith ON，The LED lighting.). Charging This unit is shipped from the factory with its internal battery fully charged. however, some energy may be lost during shipping so the battery should be recharged before using it. Plug the unit into an appropriate power supply and allow the UPS to charge fully by leaving it plugged in for 8 hours. Note: the output voltage always is displayed as “000” in off charging mode. 5).When in fault mode, it will display as below. “FAULT” character and the reason of fault only. Note: the fault code will be showed in fault mode. 6).Load level definition: 7 Load LEVEL LCD Display Specification Load bar Indication 0%~25% The LED will always turns on when UPS works, including in off charging mode and fault mode. 25%~50% When LCD start to work, it will display all information for 3s 4 50%~75% 75%~100% Computer Connection 7).Battery capacity definition: Connect one computer-related device into each of the power receptacles supplied on the back of the UPS (maximum of three devices). Battery voltage ≤11V 1).When in normal mode, it will display as below. 11V≤Battery voltage ≤11.5V 11.5V≤Battery voltage≤12.5V Battery voltage ≥12.5V 2).When in AVR mode, it will display as below. And the mark will flicker every 1second. will flicker every 8).When over load, the mark 1second. 9).When battery low, the mark 1second. will flicker every UPS System Description Front Panel— Back Panel— 1. LCD Back-Light 1. USB Port 1 2. Power “ON/OFF” Switch 2. Modem/Phone Line Surge Protection 1 2 3. Battery Backup Outlets 2 4. Surge protected outlets OUT IN 5 6 5. AC input 6. Circuit breakerz * LONG 202-719-4978 IEC×3 for 220/230/240V 3 4 2. Choose the operation system you need and follow the instruction described on the website to download the software. 3. When downloading all required files from the internet, enter the serial No: 511C1-01220-0100-478DF2A to install the software. When your computer restarts, the WinPower software will appear as a green plug icon located in the system tray, near the clock. This UPS utilizes voltages that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user serviceable parts. Only factory service personnel may perform repairs. Internal battery voltage is 12Vdc. Sealed, lead-acid, 6 cells battery. Connection to any other type of receptacle other than a two-pole, three-wire grounding receptacle may result in s shock hazard as well as violate local electrical codes. In the event of an emergency, turn the power switch to the “off” position and disconnect the power cord form the AC power supply to Use the table below to solve minor UPS installation or operation problems. If any abnormal situations occur that are not listed above,please call service people immediately. Symptom the unit. This unit intended for installation in a controlled environment (temperature controlled, indoor area free of conductive contaminants). Do not attach a power strip or surge suppressor to the UPS. Do not attach non-computer-related items, such as medical equipment, life-support equipment, microwave ovens, or vacuum cleaners to UPS. To reduce the risk of overheating the UPS, do not cover the UPS’ cooling vents and avoid exposing the unit to direct sunlight or installing the unit near heat emitting appliances such as space heaters or furnaces. Unplug the UPS prior to cleaning and do not use liquid or spray detergent. Do not dispose of battery or batteries in a fire. The battery may explode. Do not open or mutilate the battery or batteries. Released electrolyte is harmful to the skin and eyes. It may be toxic. A battery can present a risk of electrical shock and high short circuit current. The following precautions should be observed when working on batteries : 1) Remove watches, rings, or other metal objects from the hand. 2) Use tools with insulated handles. 3) Wear rubber gloves and boots. 4) Do not lay tools or metal parts on the top of batteries. 5) Disconnect charging source prior to connecting or disconnecting batteries terminal. Servicing of batteries should be performed or supervised by personnel knowledgeable of batteries and the required precautions. Keep unauthorized personnel away from batteries. When replacing batteries, replace with the same number of the sealed lead-acid batteries. 1. Charge battery up to 8 hours. 2. Replace with the same type of battery. 3. Press the power switch again or elecerity the Input cord 3.When the Input cord isn’t electvified and Power switch is not pressed. Overload of the UPS. Do not allow any liquids or any foreign object to enter the UPS. Do not place beverages or any other liquid-containing vessels on or near Do not plug the UPS input into its own output. Remedy No LED display on 1. Missing battery. the front panel. 2. Battery defect. properly disable the UPS Avoid installing the UPS in locations where there is standing or running water, or excessive humidity. Possible Cause Alarm buzzer Verify that the load matches beeps continuously the UPS capability specified in when AC supply is the specs. normal. When power 1. Overload of the UPS. 1. Remove some noncritical failure, back-up load. time is shorten. 2. Battery voltage is too 2. Charge battery 8 hours or low. more. 3. Battery defect due to 3. Replace with the same type high temperature of battery. operation environment, or improper operation to battery. Communication 1. Software is not 1. Check the setting of the lost between UPS installed well. software . and computer. 2. Cable is not properly 2. Make sure both ends of the USB cable is connected connected. and recheck settings. Mains normal but 1. Circuit breaker is LCD display broken. Battery mode. 2. Power cord is loose. 1. Reset the circuit breaker.. 2. Reconnect the power cord properly. This pluggable type A equipment with battery already installed by the supplier is operator installable and may be operated by laymen. During the installation of this equipment it should be assured that the sum of the leakage currents of the UPS and the connected loads does not exceed 3.5mA. The mains socket outlet that supplies the UPS shall be installed near the UPS and shall be easily accessible. MODEL CAPACITY INPUT Software Installation VA/W PRO-400A LCD PRO-600A LCD PRO-800A LCD 400/240 600/360 800/480 Voltage Range 89-145VAC/162~290VAC Frequency 50Hz/60Hz (Auto-Sensing) Voltage 110/120/220/230/240VAC Voltage Regulation -- WinPower -- OUTPUT WinPower is a brand new UPS monitoring software, which provides BATTERY Frequency Regulation +/-1 Hz(Battery Mode) 12V/4.5Ah 12/7Ah 12V/9Ah Back up Time Up to 12 mins Up to 22 mins Up to 30 mins TRANSFER TIME Typical INDICATOR Modified Sine-wave Battery Type Recharge Time power failure. With this software, users can monitor and control any UPS on the same LAN no matter how far from the UPS 50Hz / 60Hz Output Waveform user-friendly interface to monitor and control your UPS. This unique software provides safely auto shutdown for multi-computer systems while +/- 10%(Battery Mode) Frequency LCD Display Models Backup Mode 8 Hours to 90% after complete discharge 2-6ms typical, 10 ms max The LCD will always turn on when UPS work, Including in off charging mode and fault mode Sounding every 10 seconds Battery Low AUDIBLE ALARM Overload Battery replace Sounding every 1 second Sounding every 0.5 seconds Sounding every 2 seconds Fault Buck/boost with >70% SPS load PROTECTION Full Protection PHYSICAL Dimension (DxWxH) WEIGHT ENVIRONMENT Installation procedure: 1. Go to the website: http://www.ups-software-download.com/winpower.htm INTERFACE Net Weight Continuous sounding Sounding every 0.5sec. after 25min. And fault after 30 mins Discharge,Overcharge short circuit and Overload Protection 330 x 100 x 140mm/12.9 x 3.9 x5.5 inch 4.4Kg/9.7lb 5.4Kg/11.9lb 6.1Kg/13.4lb Operating Environment 0- 40°C, 0-90 % Relative Humidity (non-condensing) Noise Level Less than 40dB USB (Software included) For Windows Family, Mac, Linux Family, and Unix Based Famillies All trade names are registered trademarks of respective manufacturers listed. Specifications may change without notification.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project