www.rohlhome.com UNIVERSAL 1/2” THERMOSTATIC ROUGH VALVE WITH INTEGRATED THREE OUTLET DIVERTER ROHL Spa Shower R1050BD FEATURES COLOR/FINISH WARRANTY • Temperature control with integrated three outlet diverter; factory setting at 100ºF •Top handle diverts the water three ways •Diverter outlets are 100% full flow. There is no volume control. •Bottom control sets temperature •Service stops included •Primary screens at the cartridge. Remove flow control valve to flush system. • Cast brass construction • Bottom outlet for tub filler only. A separate flow control valve and/or trim required for this application. •Back of valve to finished wall 3 1/2” min., 5 1/2” max. • Flow rate 6.7 GPM at 60 PSI • 1/2” male inlets, 3 x 1/2” male outlets • Complete with mud guard for installation • If PEX is utilized, oversize the supply line to 3/4” for full flow capacity • If only two outlets are being utilized, caps are included to close “dead” outlets ON • Extension kit included, may be cut to length (10:30) required • Authentically Crafted in the USA • Must order trim to complete • Rough only • Limited Lifetime TYP. 1/2''-14 NPT 5 3/8” 4 1/2” 7 3/4” 3 5/8” 3 3/8” 3 1/2” MIN. 5 1/2” MAX. OFF (12:00) ON (1:30) OFF OFF (3:30) (8:30) The R1050BD valve is Calgreen compatible • The operation is dedicated and only one outlet will operate at a time • There are 3 on positions and 3 off positions • It is suggested the 12 O’clock position be the off position; installer will need to set: - The on positions will then be 10:30, 6:00 and 1:30 - The off positions will be 8:30, 3:30 and 12:00 ON (6:00) H C 80º 120º • Turn counterclockwise for HOT • Turn clockwise for COLD 100º Consult your local ROHL showroom for additional information and specifications. For complete warranty details and a list of showrooms, go to www.rohlhome.com. www.rohlhome.com INSTALLATION INSTRUCTIONS INSTALLATION INSTRUCTIONS FOR 1/2” Thermostatic Valve w/ Diverter PART# R1050BD GENERAL CHARACTERISTICS WE RECOMMEND THAT ALL PLUMBING PRODUCTS BE INSTALLED BY A LICENSED PROFESSIONAL IMPORTANT: Thoroughly read instructions before installation. The valve without diverter is designed with two outlets for ease of installation, but are not intended to be used concurrently with each other. Using both outlets will reduce the performance of the valve. WARNING: IF THIS VALVE IS INSTALLED UPSIDE-DOWN A REVERSE CARTRIDGE IS NOT AVAILABLE. CONSEQUENTLY, VALVE MUST BE REMOVED AND REINSTALLED RIGHT-SIDE UP. 20 POINT BROACH EXTENSION PERRIN & ROWE ADAPTER COUNTRY ADAPTER M24X1.0 EXTENSION TEMPERATURE STOP HOT SUPPLY CONNECTION ADAPTOR SLEEVE VALVE SPECIFICATIONS MALE 1/2” NPT inlets and outlets Factory temperature setting = 100°F (38°C) Temperature range = 52° to 118°F (11°-48°C) Temperature hot supply = 149° to 180°F (65°-82°C) Temperature cold supply = 50° to 72°F (10°-22°C) Temperature stability = ±32°F (0°C) COLD SUPPLY CONNECTION VALVE MOUNTING TABS (X2) Recommended supply pressure = 20 to 80 PSI (1,38-5,52 bar) Recommended hot water supply temperature = 120° to 140°F (48°-60°C) Operating pressures between hot and cold supplies should vary no more than 30 PSI (2,07 bar). If water pressure exceeds 70 PSI (4,83 bar), install a pressure reducing valve. Ensure the mixing valve is in compliance with local plumbing codes when setting the temperature on the water heater. It is the installer’s responsibility to verify correct temperature setting to prevent any risk of scalding prior to consumer use. Consult your local ROHL showroom for additional information and specifications. For complete warranty details and a list of showrooms, go to www.rohlhome.com. www.rohlhome.com INSTALLATION INSTRUCTIONS ROUGH IN VALVE TO FRAME Once the desired location has been determined, install a cross support beam to wall studs. Ensure to level the valve and secure to the cross support. The valve should be level horizontally, vertically, and parallel to finished wall. Placement of valve and cross support within the wall shall be determined by the MIN/MAX limits shown on MUDGUARD. For complete detailed valve dimensions see ROUGH-IN DIMENSIONS. • R1050BD is shown OUTLETS (1) (2) (3) USE PLUMBERS TAPE TO MAKE THE CONNECTION TO VALVE DO NOT HEAT THE ROUGH BODY CROSS SUPPORT 4” M VERTICAL STUD HOT SUPPLY (see MOUNT SCREWS [6X] (not provided) IN. atten tion) COLD SUPPLY WATER CONNECTIONS Attach OUTLET (1) to the showerhead and outlets (2) and (3) to any optional devices, such as handshower or body sprays. Any outlet not being used must be capped. Pre-assemble fittings before attaching to valve. Attach the “COLD” INLET to COLD SUPPLY and “HOT” INLET to HOT SUPPLY. IMPORTANT: Thoroughly flush supply lines to remove any debris prior to installation to prevent damage and malfunction of thermostatic cartridge. ATTENTION: Use plumbers tape or thread sealant to all threaded port joints and attach to valve. All soldering/brazing of fittings shall be performed a minimum of 4” away from valve. WARNING: DO NOT APPLY HEAT DIRECTLY TO THE VALVE AS THIS MAY DAMAGE RUBBER & PLASTIC SEALS AND WILL VOID WARRANTY. Turn on water supplies to valve and check for leaks. Consult your local ROHL showroom for additional information and specifications. For complete warranty details and a list of showrooms, go to www.rohlhome.com. www.rohlhome.com INSTALLATION INSTRUCTIONS ROUGH IN DIMENSIONS (All dimensions shown are to the nearest 1/16”) 1 5 2 " MAX. 1 3 2 " MIN. 2-1/2” OPENING FOR FINISHED WALL USE PLUMBERS TAPE TO MAKE THE CONNECTION TO VALVE DO NOT HEAT THE MAINTENANCE THERMOSTATIC CARTRIDGE Carefully remove the trim and plate and place in a safe location for the time being. Use a flat head screwdriver to shut off the water supply to the cartridge by turning the temporary shutoff screws clockwise until screw stops. Ensure to close both the hot and cold sides of the water supplies. Remove extensions to gain access to the cartridge nut. Unscrew the cartridge nut using an 11/16” plumbers wrench or adjustable wrench, if possible. Gently pull the cartridge out of the housing body (rotating cartridge while pulling may assist in removing). Clean the cartridge by rinsing it under running water to remove any possible debris. Wipe cartridge and housing seat clean and apply a thin film of NON-PETROLEUM GREASE to o-rings. NOTE: Do NOT use oil based lubricants as this may cause the o-rings to dry out over time and crack. Carefully install the cartridge back into the housing body and tighten nut to 10 ft-lbs (13,56 nm). OPENING ON FINISHED WALL ATTENTION: Ensure the INDICATOR NOTCH on cartridge and GREEN LINE on stem are orientated at the 12 O’Clock position. The Temperature stop must be in the 6 O’Clock position. TOP VIEW INDICATOR 12 O’Clock Position THERMOSTATIC CARTRIDGE FRONT VIEW Fully open temporary shutoff screws and check for leaks. 6 O’Clock Position Check operation of flow. If improved, proceed to reinstall extensions, trim & plate; otherwise, CHECK VALVES. Consult your local ROHL showroom for additional information and specifications. For complete warranty details and a list of showrooms, go to www.rohlhome.com. www.rohlhome.com INSTALLATION INSTRUCTIONS MAINTENANCE (continued) CHECK VALVES Shut off water supply at main or upstream from valve body. Remove check valve with a 5/8” (16mm) socket wrench from the body. Clean check valve by rinsing it under running water to remove any possible debris. Wipe check valve and housing seat clean and apply a thin film of NON-PETROLEUM GREASE to o-rings. NOTE: Do NOT use oil based lubricants as this may cause o-rings to dry out over time and crack. Tighten check valves to 10 ft-lbs (13,56 nm). Reinstate water supply from upstream and check for leaks. Check operation of flow. If improved, proceed to reinstall extensions, trim, & plate; otherwise, see PARTS BREAKOUT for any replacement parts needed. CHECK VALVE (2X) OPENING ON FINISHED WALL PART# R1050BD ITEM NO. PART NO. DESCRIPTION QTY. 1 10333 C-WASHER STABILIZER 1 2 10334 M24X1.0 EXTENSION 1 3 10349 NUT CAP FOR 3WAY DIVERTER 1 4 10350 CARTRIDGE, DIV. MOTION C33, 1/3 TURN W/ SHUTOFF FLUHS 1 5 10625 CARTRIDGE VALVE, 1/2" THERMO 1 6 11197 CHECK VALVE, 1/2" THERMO 2 7 11318 RETAINER NUT FOR 1/2" THERM CARTRIDGE 1 8 11319 CARTRIDGE RETAINER SLEEVE, 1/2" THERM 1 9 11320 SAFETY AND MECHANICAL STOP, 1/2" THERM 1 10 2-130 SHUTOFF NUT, 1/2" THERMO 2 11 2-132 BRAZED 1/2" THERMO W/ DIVERTER VALVE 1 12 3-056 EXTENSION KIT, M24 - 20PT - STABILIZER 1 12.1 10332 20 POINT BROACH EXTENSION 1 12.2 10334 M24X1.0 EXTENSION 1 12.3 10333 C-WASHER STABILIZER 1 13 9.15402 STEM ADAPTOR FOR PERRIN & ROWE 2 14 30232 EXTENSION SLEEVE, M24 INT./EXT. 1/2" THERM W/ DIVERTER 1 15 30233 20 POINT BROACH EXTENSION 1 16 R30083 COUNTRY ADAPTOR 2 17 30238 CAP TO CLOSE UNUSED OUTLETS 2 11 4 15 1 13 16 3 14 5 8 2 9 7 6 12.2 10 12.1 17 12.3 13 16 Consult your local ROHL showroom for additional information and specifications. For complete warranty details and a list of showrooms, go to www.rohlhome.com.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project