T ok iLum TOKISTAR TOKISTAR LIGHTING TokiLum™ T okiLum uses high-output LEDs to provide an indirect wash of light on building facades, underneath step-nosings and from within very shallow ceiling coves. In exposed applications, the LEDs create distinct points of vibrant light. TokiLum LED modules are tightly sealed within an all-environment package and approved for use in wet-location settings. The system operates efficiently at 6 VDC. This lower voltage produces very little heat, adding to TokiLum’s reliability. How to Specify LUM - 50 - IW TokiLum is available in LED module spacings of 2" and 4". LEDs can be specified 3000K, 6500K or Blue. LED Spacing Code 50 100 LED Spacing 2" (50 mm) 4" (100 mm) Code IW WH BL Kelvin 3000K 6500K Blue 0.71" (18 mm) Watts/Volts 0.48 W / 6 VDC 0.48 W / 6 VDC 0.48 W / 6 VDC 1.14" (29 mm) 0.32" (8.2 mm) Specifications All plastic components are resistant to Ultraviolet Light in accordance with standard UL 746C. Flexible Conductors are #18 AWG Light Sources are 0.48 Watt/6 VDC LEDs Wet-Location Listed This product is protected under U.S. and Foreign Patents. LED Modules are permanently sealed to cable Insulation is flexible PVC with flammability rating UL 94V-0 2 | TOKISTAR LIGHTING System Layout Circuit Design TokiLum fixtures have two independent Class 2 circuits. Each circuit is fed by one of the two outputs from the LED Driver. + Input 100~240 VAC Circuit 1 Circuit 1 + 6 VDC + Fixture Length To minimize voltage drop and keep conductors safely within their ratings, do not exceed the maximum lengths shown for each independent fixture. + Maximum Run Lengths LED Spacing Length 2" (50 mm) 4" (100 mm) Secondary Lead Wires The LED Driver may be located at a remote location. Distance from the fixture to the Driver, and the spacing of the LED modules on the fixture, determine the proper size of the secondary wire. This chart indicates recommended wire size based on these two variables. Circuit 2 Circuit 2 20' (6 M) 40' (12 M) Wire Size 2” O.C. LED Spacing Wire Length 4” O.C. LED Spacing Wire Length #16 AWG #14 AWG #12 AWG #10 AWG 24' (7.3 M) 36' (11 M) 48' (14.6 M) 72' (22 M) 12' (3.6 M) 18' (5.5 M) 24' (7.3 M) 36' (11 M) Mounting Options TokiLum can be surface mounted to structures using our mounting track, panel fasteners or clamps. Mounting Track Part #: TRI-MT LED modules snap into a semi-rigid track. The track is fastened with screws, hi-bond adhesive tape or construction adhesive. 0.40" (10.5 mm) 0.80" (20.4 mm) Panel Fasteners Part #: TRI-PF TokiLum is easily incorporated into display panels and signs with our panel fasteners. The LED module is inserted from behind, concealing all wiring. 0.20" (5.2 mm) 0.71" Ø (18 mm) Clear Fastener Panel Thickness .047"~.079" (1.2 mm~2.0 mm) Mounting Clamps Part #: TRI-MC For maximum flexibility, TokiLum can be attached with clamps. Each clamp is fastened with a screw concealed behind the fixture. TOKISTAR LIGHTING | 3 LED Driver Specifications TokiLum is Wet-Location Listed when operated from our LED Drivers. Input Range: 100~240 VAC Frequency Range: 50/60 Hz Output: 6 VDC (Adjustable +40% / -5%) Max. Output Current: 5.0A x 2 channels Max. Output Power: 30W x 2 channels Protection: Overload, Overcurrent, Short Circuit Operating Temperature: -30ºC to +60ºC Tokistar’s LDR6-60 is a 60 Watt UL Recognized Class 2 LED Driver used to convert an AC input into a 6 VDC output. It may be operated from a wide range of input voltages. The enclosure is suitable for wet locations. Mechanical Specifications Dimensions: 3.6" x 11" x 2.25" Weight: 4 lbs Enclosure Rating: Nema 3/IP65 Mounting: Flange Mount Connection: Knockouts for 1/2" Conduit Compliance/Safety 11" (280 mm) UL 1310 Class 2 CAN/CSA 22.2#9 EN60950 3.6" (92 mm) 2.25" (57 mm) TokiLum Capacity Part #: LDR6-60 0.48 Watt LEDs: 124 pieces LED Dimmers DMX Dimming System Part #: LC-1CH-MULTI Max. Load: 30 Watts @ 6 VDC Environmental Rating: Dry Location/IP20 Dimensions: 3/4" x 1-3/4" x 3-1/2" Weight: 50g / 0.11 lbs Listing: ETL Listed/CE Certified Operating Temperature: 0~+50ºC Tokistar’s LC-1CH-MULTI Dimmer Pack is compatible with industry-standard dimmers working on DMX or 0/1-10 VDC protocol. DMX Mode - Each unit is independently addressable. Up to 36 dimmer packs may be connected in series. For applications exceeding 36 dimmer packs, an additional feed from the DMX dimmer is required. The additional feed(s) can be sent directly from the dimmer, or you may specify DMX Splitters. Consult factory on details of DMX Splitters. Analog Modes - For operation from devices using 0/1-10VDC protocol, up to 10 dimmer packs may be connected in series. For applications exceeding 10 dimmer packs, an additional feed from the analog dimming device is required. Manual Mode - You may select a light intensity at which the fixtures will operate. In this case, no external dimming device is required. Dimmer DMX or 0/1-10VDC Fixture 0-6VDC 0-6VDC Dimmer Pack LED Driver 6VDC 6VDC Data Data LC Dimming System Dimmer Pack Data Part #: LC-DMR The remote wall dimmer has a rotary dial and on/off switch. Power to the wall dimmer is provided from the LED Driver powering the first Dimmer Pack. A 50 foot CAT5 cable is provided with each unit. LC-DMR Fixture Signal Out Part #: LC-1CH-DP Signal Out 0-6VDC 0-6VDC Each dimmer pack receives one of the two 6 VDC outputs from an LDR6-60 LED Driver. A CAT5 cable is provided with each unit. Size: 1-1/2" x 3-1/2" x 4-1/16”" Dimmer Pack 6VDC 6VDC Dimmer Pack LED Driver TOKISTAR ® LIGHTING INC. 1015 E, Discovery Lane • Anaheim, CA 92801 Tel: 714.772.7005 • Fax: 714.772.7014 • Toll free in U.S.A.: 877.340.7633 E-mail: email@example.com • Web site: www.tokistar.com © 2012 TOKISTAR LIGHTING INC. / V1.2 This proprietary Dimming System provides full-range dimming of TokiLum LEDs. The system components connect with CAT5 cable. Up to 25 dimmer packs may be connected in series if the total length of all CAT5 cable does not exceed 165 feet from the wall dimmer to the last dimmer pack. CAT5 cables are included with units.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project