1 OF 2 Installation Instructions IL4RAIC / IL6RAIC / IL6SRAIC IC Air-Tight LED Dedicated Remodel Housing IS-R1005R2 IMPORTANT SAFETY INSTRUCTIONS –– Read all installation instructions before installing. It is important to save these instructions. –– Observe and follow all label information and instructions regarding dry, damp and wet location listings, proper Intense LED module, warnings of installation near combustible materials and/ or insulation. –– Turn off power at circuit breaker before attempting to install or perform maintenance on the fixtures. –– Be sure to connect ground wire to prevent electric shock or other potential hazards. –– The product must be installed in a manner consistent with the intended use and in compliance with the national electrical codes and local codes. –– Do not block the trim aperture as this may cause unsafe operating conditions. –– WARNING: RISK OF FIRE. IC fixture can be installed with direct contact with insulation. Minimum of 90°C supply conductors. Consult a qualified electrician before installation. WARNING: Use only Intense Lighting trims listed for use with this fixture. Use of trims other than those listed by Intense Lighting is a violation of N.E.C 110-3(B) and voids all warranties. INSTALLATION INSTRUCTIONS 1. Cut appropriate ceiling cut out, 4 5/16” cut out for 4” fixtures and 6 3/8” cut out for 6” fixtures. 2. Run your supply wire from the ceiling through the ceiling opening. 3. Remove junction box cover plate. Remove desired knockout, the junction box will accept metal conduit or non-metallic cable. 4. Connect black wire from fixture to black (HOT) supply wire, white wire from fixture to white (NEUTRAL) supply wire and connect the ground from fixture to green (GROUND) supply wire. Use UL listed connectors or wire nuts to make the connections (not included) (Fig. 1). 5. Make connections in junction box and replace cover plate. 6. Push tension springs up into housing and insert housing through ceiling cut out until the housing is flush against the ceiling (Fig. 2). 7. Using flat head screwdriver push tension springs to secure on the ceiling (Fig. 3). 8. Connect male connector on trim into the female connector inside the housing firmly (Fig. 4). 9. Push wires into housing and then trim push trim into the housing, ensuring the trim is flush to the ceiling. 10.Once all fixtures have been installed, power at the breaker can be restored. Fig. 1 Non Metallic Cable Fig. 2 Electrical Supply Wire Fig. 3 Knockouts Fig. 4 Housing Ceiling Remodel Hole Cutout Ceiling Housing Female Housing Connector Reflector Housing Reflector Metal Conduit Knockouts INSTRUCTIONS L/M-04132016 P-5 Intense Lighting 3340 E La Palma Ave, Anaheim, CA 92806 | tel 714 630-9877 | fax 714 630-9883 ©2016 Intense Lighting, LLC. All rights reserved. Subject to change without notice. Male Trim Connector 2 OF 2 INTENSE LIGHTING WARRANTY INTERIOR LED PRODUCTS: 10-YEAR LIMITED WARRANTY Intense Lighting warrants the LED electronics and components of its properly installed INTERIOR LED products listed below, to be free of defects in material and workmanship in normal use, for a period of 10 years from the date of our shipment or 50,000 hours of operation, whichever occurs first. Intense Lighting will repair or replace, at its option, any warranted product returned to it that it determines to be defective. Usage documentation may be requested to validate hours. This limited warranty does not include installation or removal, nor does it extend to the LED drivers which are warranted for five years. For the first year after the date of shipment, Intense Lighting will provide personnel to make field repairs for defective recessed fixtures only. Track fixtures must be sent back to factory for testing and evaluation. In addition to complete failure, defects include lumen depreciation to levels below 70% of initial lumen output within warranty period and/or color shift beyond that which is set forth in the Energy Star Program Requirements for SSL – Version 1.1 within warranty period. Defects do not include improper installation or operation, alterations, power surges or overheating due to external conditions. To receive credit for defective merchandise, product must undergo quality inspection prior to the processing of credit. If the product is found defective, you will be issued a credit. Product in good working condition will not receive a credit. Please inform your accounting department not to short pay or issue any debits to our company regarding a return. Testing and evaluation can take approximately 1-2 weeks based on quantity. At that time you will be notified if credit is granted for your warranty return. THE ABOVE EXPRESS WARRANTY STATES THE FULL AND COMPLETE OBLIGATION OF INTENSE LIGHTING. ALL IMPLIED WARRANTIES OF MERCHANTABILITY OR FITNESS FOR A PARTICULAR PURPOSE ARE LIMITED IN DURATION TO THE TERM OF THE EXPRESS WARRANTY. UNDER NO CIRCUMSTANCES WILL INTENSE LIGHTING ACCEPT LIABILITY FOR ANY CONSEQUENTIAL SPECIAL OR INDIRECT DAMAGES WHETHER ARISING OUT OF CONTRACT, TORT, OR STRICT LIABILITY. INSTRUCTIONS L/M-04132016 P-24 Intense Lighting 3340 E La Palma Ave, Anaheim, CA 92806 | tel 714 630-9877 | fax 714 630-9883 ©2016 Intense Lighting, LLC. All rights reserved. Subject to change without notice.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project