ATTENTION ATTENTION: before installing Elios4you, remove the label (see picture below) with USER code. Keep the label in a safe place for future other device configuration and/or for logging in the website www.4-cloud.org. ID CODE: 00000 Register on: www.4-cloud.org and associate your device with USER: XXXXXXXX ATTENZIONE: if you are setting a connection through a Router/AP, data will be visible on the website after approximately 1 hour from configuration. ELIOS4YOU 1. After device installation and after having it powered on, download the free App Elios4you on your own device (smartphone or tablet) from Playstore (Android) or App Store (iOS) 2. Open the App and start the wizard, following the steps visible on your smartphone/tablet (read the Elios4you APP Quick Guide for further information) Guide 4. Check that collected data are correct: - Press “Home” button to to go the “Energy performance” page - Check that energy “Generation” value has similar value as you can read from the inverter - Check that the energy “Consumption” value is the same of the real time consumption you have in the home Elios4you: a wireless device for the monitoring of single-phase photovoltic installations via App. Maximum monitored power 6 kW. It measures the energy generated of the pv plant, exchanged with the grid, the household consumption and the self-consumption. ATTENTION: when Elios4you is configured for internet access through Router/AP, all data are collected even on 4-cloud website. Go to http://www.4-cloud.org and follow on line instructions for registering. Match your account with the device filling with the USER code on the label of your Elios4you. TROUBLE SHOOTING Installation - Power reading Problem Elios4you Solutions 1. I can’t see my PV system energy generation in the App’s home Page a. Change current clamp (CT) versus (white label) by inverting the green dot or the inside current clamp arrow position. b. Check that inside the current clamp you have only the PV Line cable (not also the Neutral). c. Check that the current clamp core is not broken or cracked inside. 2. The energy generation visible on the App is definitely less than the value read from the inverter a. Be sure that the Elios4you is powered from the same line of the 2 current clamps. b. Check that the current clamp (white label) is perfectly closed: any strong pressure should be need to clamp the cable properly 3. Consumption graph has the same shape of production graph line a. Be sure that the mains CT (yellow label) clamps all lines coming from the Mains Meter: if not it is possible that the meter is measuring only the consumption. b. Be sure that the Neutral cable is not clamped within the CT (yellow and white label). c. Check that both current clamps are not broken or cracked inside. 4. It seems that consumption values are shown in the “grid” icon a. Be sure that the mains CT (yellow label) clamps all lines coming from the Mains Meter: if not it is possible that the meter is measuring only the consumption. 5. I can never see purchased energy in my system a. Be sure that the mains CT (yellow label) clamps all lines coming from the Mains Meter: if not it is possible that the meter is measuring only the consumption. 6. During the night the consumption is zero, while during the day is always more than normal value expected a. Reverse CT (yellow label) current clamp position, by inverting green dot/inside arrow position. 7. In the App I can see high consumption levels, while the real time consumption is very low. a. Reverse CT (yellow label) current clamp position, by inverting green dot/inside arrow position. b. Be sure that the mains CT (yellow label) clamps all lines coming from the Mains Meter: if not it is possible that the meter is measuring only the consumption. ID CODE:YYYYY 123456789XXXXX Via Per Sacile, 158 - Francenigo di Gaiarine (TV) - Italy Tel. (+39) 0434 768462 - Fax (+39) 0438 694617 - email@example.com - www.4-noks.com ENG Quick 3. Set correct parameters for your PV system and your energy provider using the App menu: - Press “Menu” button - Select “Parameter Settings” - Select “Energy Management” and set values - Press OK when finished to save new values ID Code Label Current Transformers +05T408021R1.1_E4U Quick Guide_EN_20.10.2014 ! INSTALLATION INSTALLATION SCHEME PHOTOVOLTAIC PLANT INTO THE MAIN CIRCUIT BREAKER Generation meter N N Mains meter L L K L L Green point and the direction of the arrow K L towards the main circuit braker Mains CT (yellow label) N L K N L K L L Green point and the direction of the arrow K L towards the main circuit braker Mains CT (yellow label) Generation CT (white label) Main Circuit Breaker Do not wire L Do not wire Do not wire Alarm 1 -NO Alarm 1 -NO Load 13 14 15 16 17 18 19 20 21 22 23 24 Relay Normally Open 13 14 15 16 17 18 19 20 21 22 23 24 GND Ctrl +10 V 1A GND Ctrl +10 V Hole for CONFIG button Hole for CONFIG button ID Code Label ID CODE:YYYYY 123456789XXXXX SIG + Generation CT - Red color Shield = optional Generation CT SIG - Generation CT - Black color ID Code Label SIG - Mains CT - Black color Shield = optional Mains CT SIG + Mains CT - Red color ID CODE:YYYYY 123456789XXXXX SIG + Generation CT - Red color Shield = optional Generation CT SIG - Generation CT - Black color Do not wire Do not wire ! Elios4you Front panel icons Blink frequency proportional to the amount of generated energy of the pv plant (red) Power supply (green) Blink frequency proportional to the amount of exchanged energy with the grid (red) Wi-Fi on (green) If on: energy purchased from the grid (red) General alarm or failed attempt to get connected to the tablet or smartphone (green) SIG - Mains CT - Black color Shield = optional Mains CT SIG + Mains CT - Red color N L 3 4 5 6 7 8 9 10 11 12 N L 3 4 5 6 7 8 9 10 11 12 If on: energy sold to the grid N Alarm 2 -NO Common Relay Load Relay Normally Open Generation CT (white label) N Alarm 2 -NO Common Relay K Main Circuit Breaker L Do not wire Generation meter The two L phases are clamped into the mains CT 1A Mains meter PHOTOVOLTAIC PLANT DIRECTLY WIRED INTO THE MAINS METER Not used (red) (green) WARNING WARNING: if the generation energy LED does not blink when the pv instalaltion is producing energy, it is necessary to invert the Generation CT orientation by inverting the connection of the wires of Elios4you (terminals 7 and 9). WARNING: if the exchanged LEDs and detect the wrong energy flow (“sold” energy when it should report a situation of “purchased” energy or viceversa), it is necessary to invert the mains CT (yellow label) by inverting the connection of the wires of Elios4you (terminals 10 and 12). ! WARNING WARNING: make sure that between the 2 CTs and the meters there are any other electrical appliances connected. Otherwise, the resulting measurements would not be reliable. WARNING: possible alterations of CTs wires lenght will cause an increase in the marginal error during the measurements detection. We do not recommend such alterations of the device. ATTENTION ATTENTION: installation must be done by qualified personnel only.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project