Single Pole (One location) or 3-Way (Multi-location) Scene Capable Incandescent/Magnetic Low Voltage or Fluorescent Dimmer Cat. No. DZMX1, 1000VA, 1000W, 450W LED/CFL (Lighted) 120VAC, 60Hz INSTALLATION INSTRUCTIONS WARNINGS AND CAUTIONS: • TO AVOID FIRE, SHOCK, OR DEATH; TURN OFF POWER at circuit breaker or fuse and test that power is off before wiring! • TO AVOID FIRE, SHOCK, OR DEATH; DO NOT install to control a receptacle, a motor or a transfer operated appliance. • To be installed and/or used in accordance with electrical codes and regulations. • If you are unsure about any part of these instructions, consult an electrician. • Use ONLY with the appropriate Advance Transformer 120V Mark 10™ Powerline or Lutron Tu-Wire® electronic ballasts for controlling the speciﬁc ﬂuorescent lamps in Fluorescent Mode. • Use with LED, CFL, incandescent, magnetic low voltage, ﬂuorescent, or 120V halogen ﬁxtures only. Use a Leviton electronic low voltage dimmer to control electronic (solid state) low voltage transformers. • When retroﬁtting Mark 10™ Powerline dimming ballasts into ﬁxtures that originally had Instant Start ballasts, the sockets MUST be replaced with Rapid Start sockets to allow proper dimmer operation and prevent damage to the dimmer ballast. Refer to the instructions provided with the ballast. • Decora® Z-Wave® control dimmers are not compatible with standard 3-way or 4-way switches. They must be used with compatible Vizia +® matching or coordinating remotes for multi-location dimming. • Maximum wire length from dimmer to all installed remotes cannot exceed 300 ft. • Dimmer may feel warm to the touch during normal operation. Leviton’s Decora® Z-Wave® control components are designed to communicate with each other via Radio Frequency (RF) to provide remote control of your lighting. In a Z-Wave® network, each device is designed to act as a router. These routers will re-transmit the RF signal from one device to another until the intended device is reached. This ensures that the signal is received by its intended device by routing the signal around obstacles and radio dead spots. This dimmer is compatible with any Z-Wave® enabled network, regardless of the manufacturer and can also be used with other devices displaying the Z-Wave® logo. WARNING: TO AVOID FIRE, PERSONAL INJURY OR DEATH DO NOT USE the remote for the control of high power heating appliances such as portable heaters. Remember to exercise good common sense when using the Timer features of your remote, especially when scheduling unattended devices. There can be some unexpected consequences if not used with care. For example, an empty coffee pot can be remotely turned on. If that should happen, your coffee pot could be damaged from overheating. If an electric heater is turned on by remote control while clothing is draped over it, a ﬁre could result. DO NOT USE the remote for the control of high power heating appliances such as portable heaters. This device will not control lighting that is used with electronic low-voltage and high frequency power supply transformers, nor high pressure discharge lamps (HID lighting). This includes mercury-vapor, sodium vapor and metal halide lamps. MULTI-DEVICE APPLICATION Lutron Tu-Wire®: In multi-dimmer installations, the reduction of the dimmer’s capacity is required. Refer to the chart for maximum load per dimmer. To determine total ballast load, add the line current found on the ballast label for all ballasts in the circuit. This will indicate the total load for the control. Remove all inner side sections NOTE: Use check boxes • • • • • • • Soft fade ON/OFF Scene capable ON/OFF LED and Brightness level LED Two way communication RF reliability Ease of installation – No new wiring Compatible with other Z-Wave® enabled devices MAXIMUM LOAD PER DIMMER FOR MULTI-DEVICE Load Single Two Devices More than 2 Devices Incand 1000W 800W 650W Mag LV 1000VA 800VA /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. /&& /. Pliers Ruler Your device may include color options. To change color of the face proceed as follows: Line up tabs and press in sides one at a time to attach INSTALLING DIMMER BY ITSELF OR WITH OTHER DEVICES If installing Dimmer in a single device application, proceed with the INSTALLING YOUR DIMMER section. If installing Dimmer in a multi-device application, proceed as follows: Black White 2 Rating Single Two Gang More than 2 Gang 1000VA 800W 640W 520W Advance Mark 10TM Powerline Part No. Lamp White REZ-2Q18-M2-LD REZ-1T32 REZ-2Q26 REZ-1T32 REZ-1T42 REZ-1Q18-M2-BS REZ-1Q18-M2-LD REZ-2Q18-M2-BS REZ-1T32 REZ-1T42-M2-BS REZ-1T42-M2-LD REZ-2Q26 REZ-2Q26-M2-BS REZ-2Q26-M2-LD REZ-1Q18-M2-BS REZ-1Q18-M2-LD REZ-2Q18-M2-BS REZ-2Q18-M2-LD REZ-1T42-M2-BS REZ-1T42-M2-LD REZ-2Q26-M2-BS REZ-2Q26-M2-LD REZ-1T42-M2-BS REZ-1T42-M2-LD REZ-2T42-M3-BS CFM18W/GX24Q CFM26W/GX24Q CFM26W/GX24Q CFM32W/GX24Q CFM42W/GX24Q CFQ18W/G24Q CFQ18W/G24Q CFQ18W/G24Q CFQ26W/G24Q CFQ26W/G24Q CFQ26W/G24Q CFQ26W/G24Q CFQ26W/G24Q CFQ26W/G24Q CFTR18W/GX24Q CFTR18W/GX24Q CFTR18W/GX24Q CFTR18W/GX24Q CFTR26W/GX24Q CFTR26W/GX24Q CFTR26W/GX24Q CFTR26W/GX24Q CFTR32W/GX24Q CFTR32W/GX24Q CFTR32W/GX24Q Single Gang Two Ganged More than 2 Gang 23 32 17 26 20 46 46 23 32 32 32 17 17 17 46 46 23 23 32 32 17 17 26 26 13 18 25 13 20 16 37 37 18 25 25 25 13 13 13 37 37 18 18 25 25 13 13 20 20 10 15 20 11 16 13 30 30 15 20 20 20 11 11 11 30 30 15 15 20 20 11 11 16 16 8 1 Coordinating Remote (no LEDs) Black (PRIMARY SIDE OF MAGNETIC LOW-VOLTAGE TRANSFORMER) 3 Yellow/Red Red Black Black White 3-Way 1. Line or Load (see important instruction) 2. Neutral 3. Ground 4. First Traveler – note color 5. Second Traveler – note color IMPORTANT: For 3-Way applications, note that one of the screw terminals from the old switch being removed will usually be a different color (Black) or labeled Common. Tag that wire with electrical tape and identify as the common (Line or Load) in both the dimmer wall box and remote wall box. Step 3 Preparing and connecting wires: Pull off pre-cut insulation from dimmer leads. Make sure that the ends of the wires from the wall box are straight (cut if necessary). Remove insulation from each wire in the wall box as shown: 5/8" (1.6 cm) Strip Gage (measure bare wire here) • Pull off pre-cut insulation from dimmer leads. • Make sure that the ends of the wires from the wall box are straight (cut if necessary). • Remove insulation from each wire in the wall box as shown. • For Single-Pole Application, go to Step 4a. • For 3-Way Coordinating Remote (no LEDs) Application, go to Step 4b. Insulating Label Green Ground BK (unused) Red Dimmer RD YL/RD Black Hot (Black) White Green Ground (unused) Yellow/ Red Line 120VAC, 60Hz Green Ground Neutral (White) Hot (Black) White Yellow/Red Single Pole 1. Line (Hot) 2. Neutral 3. Ground 4. Load WH Green 2 3 4 5 Cut (if necessary) 5 2 (PRIMARY SIDE OF BALLAST) Max. # Ballasts/Dimmer for Multi-gang 3 Yellow/ Red 1 Dimmer 3 4 4 Green 5 Terminal Screw marked Yellow/Red (YL/RD) Insulating label: This wire is used in 3-way installations only. For single pole installations, do not remove this insulating label. 2 RD YL/RD Black NOTE: If the wiring in your wall box does not resemble any of these conﬁgurations, consult an electrician. 1 Red 4 Step 4a Single Pole Wiring Application: Step 2 Identifying your wiring application (most common): Low-voltage dimmers are rated in Volt-Amps (VA). The maximum bulb wattage is determined by the efﬁciency of the transformer in the low-voltage lighting system. Transformer efﬁciencies will vary from different manufacturers; consider 80% efﬁcient as average. Use the chart to determine maximum bulb wattage for typical transformer efﬁciency ratings. 2 1 4 MAXIMUM BULB WATTAGE 1 BK 3 650VA Mark 10™ Powerline dimmers are rated in Volt-Amps (VA). The maximum bulb wattage is determined by the efﬁciency of the Mark 10™ Powerline ballast. The following table shows the maximum number of ballasts that can be connected to a single dimmer for different Mark 10™ Powerline ballasts. Also note that the table shows maximum ballasts for multi-gang installations. Changing the color of your Dimmer: Push in side at tab to release /. MAXIMUM BULB WATTAGE TOOLS NEEDED TO INSTALL YOUR DIMMER Electrical Tape Cutters /&& Terminal Screw marked White (WH) Red Cat. No. DZMX1, 120V, For use with Advance Transformer 120V Mark 10TM Powerline Electronic Ballasts Slotted/Phillips Screwdriver Pencil OFF POWER at circuit breaker or fuse and test that power is off before wiring! Dimmer Coordinating Remote 1 - #12 w/ 1 to 3 #14, #16 or #18 2 - #12 w/ 1 or 2 #16 or #18 1 - #14 w/ 1 to 4 #16 or #18 2 - #14 w/ 1 to 3 #16 or #18 when Steps are completed. 3-Way Wiring with VP00R-10Z Coordinating Remote (no LEDs) Application: Step 4b WIRE CONNECTOR / # OF COND. COMBINATION CHART WARNING: TO AVOID FIRE SHOCK OR DEATH; TURN Step 1 Do not remove outer side sections Bend back and forth to remove side section For non-standard wiring applications, refer to Wire Nut and Connector Size Chart INSTALLING YOUR DIMMER MAXIMUM BULB WATTAGE AT 75% EFFICIENCY FEATURES DI-000-DZMX1-02A Line 120 VAC, 60Hz White Neutral (White) WIRING DIMMER: Connect wires per WIRING DIAGRAM as follows: WARNING: CONNECT A MAGNETIC LOW-VOLTAGE DIMMER ONLY TO THE PRIMARY (HIGH-VOLTAGE) SIDE OF A MAGNETIC LOW-VOLTAGE TRANSFORMER. • Green or bare copper wire in wall box to Green dimmer lead. • Line Hot wall box wire to Black dimmer lead. • Load wall box wire to Red dimmer lead. • Line Neutral wall box wire to White dimmer lead. • Yellow/Red dimmer lead should have Red insulation label afﬁxed. NOTE: If insulating label is not afﬁxed to Yellow/Red dimmer lead, use electrical tape to cover. • Proceed to Step 5. WIRING DIMMER: Connect wires per WIRING DIAGRAM as follows: WARNING: FOR MAGNETIC LOW-VOLTAGE APPLICATIONS, CONNECT DIMMER ONLY TO THE PRIMARY (HIGH-VOLTAGE) SIDE OF A MAGNETIC LOW-VOLTAGE TRANSFORMER. NOTE: When using the coordinating remote without LEDs, the dimmer can be installed on either the Line or Load side of the 3-way circuit. NOTE: Maximum wire length from dimmer to all installed remotes cannot exceed 300 ft (90 m). • Green or bare copper wire in wall box to Green dimmer lead. • Line Hot (common) wall box wire identiﬁed (tagged) when removing old switch to Black dimmer lead. • First Traveler wall box wire to Red dimmer lead (note wire color). • Remove Red insulating label from Yellow/Red dimmer lead. • Second Traveler wall box wire to Yellow/Red dimmer lead (note wire color). This traveler from the dimmer must go to the terminal screw on the remote marked "YL/RD". • Line Neutral wall box wire to White dimmer lead. WIRING COORDINATING REMOTE: Connect wires per WIRING DIAGRAM as follows: WEB VERSION INTRODUCTION WARNINGS AND CAUTIONS: • When magnetic low voltage circuits are operated at a dim level, with all lamps inoperative, excess current may ﬂow through the transformer. To avoid possible transformer failure due to overcurrent, use a transformer that incorporates thermal protection or a fuse at the primary windings. • Recommended minimum wall box depth is 2-1/2". • Use this device WITH COPPER OR COPPER CLAD WIRE ONLY. • Use with compatible dimmable LED, CFL bulbs, incandescent or 120V halogen ﬁxtures only. For a list of compatible LED and CFL bulbs refer to www.leviton.com. • When multiple bulbs are used with one dimmer DO NOT mix bulb types. All bulbs shall be either LED; CFL or incandescent. Using the same make/model of each bulb will enhance dimmer performance. • Not for use with Vizia RF® lighting systems. NOTE: "BK" and "RD" terminals on coordinating remote are unused. Tighten both screws. NOTE: Maximum wire length from dimmer to last remote is 300 ft (90 m). • Green or bare copper wire in wall box to Green terminal screw. • Load wall box wire identiﬁed (tagged) when removing old switch to First Traveler (note color as above). • Second Traveler wall box wire (note color as above) to terminal screw marked "YL/RD". This traveler from the remote must go to the Yellow/Red dimmer lead. • Remove White insulating label from terminal screw marked "WH". • Line Neutral wall box wire to terminal screw marked "WH". • Proceed to Step 5. Dimmer Matching Remote Additional Neutral Wire Black 2 4 Red 3 RD 1 Green 5 Yellow/ Red Matching Remote (with LEDs) Hot (Black) Installation may now be completed by tightening mounting screws into wall box. Attach wallplate. White 1 YL/RD 4 2 BK WH 3 Step 7 Restore Power: 5 Restore power at circuit breaker or fuse. Installation is complete. Dimmer NOTE: To include your dimmer into a network, contact Leviton’s Techline at 1-800-824-3005 or visit Leviton’s website at www.leviton.com. Black BK Green Ground Line 120VAC, 60Hz YL/RD Green Ground Yellow/ Red Red Ballast Black Primary Side White White Neutral (White) NOTE: The dimmer must be installed in a wall box that has a Load connection. The matching remote must be installed in a wall box with a Line Hot connection and a Neutral connection. A Neutral wire to the matching remote needs to be added as shown. If you are unsure about any part of these instructions, consult an electrician. NOTE: Maximum wire length from dimmer to all installed remotes cannot exceed 300 ft (90 m). WIRING MATCHING REMOTE (wall box with line hot connection): Connect wires per WIRING DIAGRAM as follows: • Green or bare copper wire in wall box to Green terminal screw. • Line Hot (common) wall box wire identiﬁed (tagged) when removing old switch and First Traveler to Remote terminal marked BK. • Second Traveler wall box wire from dimmer to remote terminal screw marked "YL/RD" (note wire color). This traveler from the remote must go to Yellow/Red dimmer lead. • Line Neutral wall box to remote terminal screw marked "WH". WIRING DIMMER (wall box with load connection): Connect wires per WIRING DIAGRAM as follows: • Green or bare copper wire in wall box to Green dimmer lead. • Load wall box wire identiﬁed (tagged) when removing old switch to Red dimmer lead. • First Traveler Line Hot to Black dimmer lead. • Remove Red insulating label from Yellow/Red dimmer lead. • Second Traveler wall box wire (note color as above) to Yellow/Red dimmer lead. This traveler from the dimmer must go to the terminal screw on the remote marked "YL/RD". • Line neutral wall box wire to White dimmer lead. • Proceed to Step 5. Step 5 Testing your Dimmer prior to mounting in wall box: NOTE: If using in a dimmable ﬂuorescent application see Advanced Programming Feature B-4 prior to testing the device. • Position all wires to provide room in outlet wall box for device. • Ensure that the word “TOP” is facing up on device strap. • Partially screw in mounting screws in wall box mounting holes. NOTE: Dress wires with a bend as shown in diagram in order to relieve stress when mounting device. • Restore power at circuit breaker or fuse. • Press pad until locator light is OFF. Lights should turn ON. If lights do not turn ON, press the right half of the DIM/BRIGHT Bar until the lights brighten. If lights still do not turn ON, refer to the TROUBLESHOOTING section. Chart B ADVANCED PROGRAMMING FEATURES TURN OFF POWER AT CIRCUIT BREAKER OR FUSE. FACTORY DEFAULT If your dimmer is not responding, or you are unable to control it after you have tried to Include/Exclude it multiple times, it may be necessary to reset the dimmer to its original factory settings. To accomplish this, proceed as follows: • On the dimmer, engage the air-gap switch (refer to Operation section) and wait 5 seconds. Press the push pad back into the frame and hold push pad until the locator LED turns Amber and then turns Red. The dimmer is now reset. Once the dimmer is reset, it will be necessary to Re-Include it to a network before it can be used. CAUTION: SETTING A DEVICE TO A FACTORY DEFAULT DOES NOT EXCLUDE THAT DEVICE FROM A NETWORK. THE EXCLUSION PROCEDURE MUST STILL BE FOLLOWED TO REMOVE THE DEVICE FROM THE PRIMARY CONTROLLER’S INFORMATION TABLE. FAILURE TO DO SO MAY RESULT IN SYSTEM THAT IS SLOW TO RESPOND, OR MAY FAIL TO RESPOND TO SOME DEVICES. Deﬁnition of A Modes A-1) Energy Save: Sets the maximum brightness level for energy savings. A-2) Minimum Brightness Level: Sets the minimum dimming level. A-3) Preset ON Level: Sets the turn on brightness level regardless of the previous set light level (formerly Dim Lock). Deﬁnition of B Modes B-1) ON Fade Rate: Sets the amount of time in seconds it takes the lights to turn ON to maximum brightness. B-2) OFF Fade Rate: Sets the amount of time in seconds it takes the lights to turn OFF from maximum brightness. B-3) LED Options: Sets the time period in seconds the Locator LED and Brightness display will stay on before extinguishing. B-4) Fluorescent Mode: Allows dimmer to control Mark 10 Powerline dimming ballasts. Deﬁnition of LEDs Leftmost LED = LED 1 Rightmost LED = LED 7 NOTES: • The device will exit programming mode after 3 minutes of inactivity. • Pressing the push pad at any time during programming will advance the device to the next programming mode. push pad Air-Gap Switch: On the dimmer only, engage the air-gap switch by gently pressing the top of the push pad until the bottom lifts completely out of the frame and a click is heard (refer to Figure). LED's will turn OFF. This will stop power to the ﬁxture to replace the bulb. After servicing is complete, press the push pad back into place for normal operation. Cleaning: Clean with a damp cloth. DO NOT use chemical cleaners. FADE ON TROUBLESHOOTING FADE OFF LED 1 0 seconds (instant) 0 seconds (instant) LED 2 (Default) 0.5 seconds 0.5 seconds LED 3 1.5 seconds 1.5 seconds LED 4 3.0 seconds 3.0 seconds LED 5 6.0 seconds 6.0 seconds LED 6 10 seconds 10 seconds LED 7 25 seconds 25 seconds B-3) The Locator LED will blink 3 times per second to indicate Program Mode B-3, LED Options. To change the LED Options settings, use the DIM/BRIGHT Bar to move the LED to the desired preset setting according to the Chart B-3. By tapping the Push Pad this setting will automatically be saved and the device will advance to the next Programming Mode B-4. Chart B-3 1 2 3 4 5 6 7 LED Brightness Display Program Mode A To enter Program Mode A: Press and hold the Push Pad and then the right half of the DIM/BRIGHT Bar (^) for 5 seconds until the Locator LED and leftmost LED (LED 1) begin to blink. A-1) Upon releasing the Push Pad and the right half of the DIM/BRIGHT Bar (^), the Locator LED will continue to blink once per second and the rightmost LED will illuminate to display the device is in Program Mode A-1, Energy Save. The default energy save mode is 100% i.e. full bright. To change the Energy Save level, use the LED Brightness DIM/BRIGHT Bar to move the corresponding LED to the desired OPERATION Display discrete preset level according to Chart A. By tapping the Push Pad NOTE: The locator light will illuminate when the load this setting will automatically be saved and the device will advance DIM/BRIGHT is in the OFF position to facilitate access in the dark. to the next programming mode, A-2. Bar NOTE: If using the dimmer in a 3-wayapplication, the Chart A lights will turn ON at brightness set on dimmer’s Energy consumption When indicator DIM/BRIGHT bar. The lighting can be controlled Light output is at savings amounts to light is at LED # from either the dimmer or the remote location. Push Pad (Default settings) 0% 7 100% 5% 6 97% Turn ON from OFF position: 8% 5 95% Tap – Lights turn ON to preset level. Press and Hold – Lights turn ON to full bright. 4 90% 16% 3 85% 24% Turn OFF from ON position: 2 80% Tap – Lights turn OFF. 29% 75% 1 34% DIM/BRIGHT Bar Push Locator BRIGHTEN: Pad Light Press the right half of the DIM/BRIGHT Bar – Lights brighten to desired level. DIM: Press the left half of the DIM/BRIGHT Bar – Lights dim to desired level. If you continue to hold, the lights will DIM to minimum level and then turn OFF. NOTE: When lights are OFF you can change the light level that the lights will turn ON to using the DIM/BRIGHT Bar. If there is a power outage, when the power is restored, the lights will return to the last setting Gently press top of before the power interruption. LED LED LOCATOR LED TIMEOUT LED BRIGHTNESS DISPLAY OPTIONS LED 1 Active Active LED 2 Active Turns off 5 sec. after use • Lights Flickering - Lamp has a bad connection. - Wires not secured ﬁrmly with wire connectors of dimmer or terminal screws of remote. - If using in a dimmable ﬂuorescent application see Advanced Programming Feature B-4. • Light does not turn ON and Locator LED does not turn ON - Circuit breaker or fuse has tripped. - Lamp is burned out. - Neutral not wired to Dimmer (White wire). - Conﬁrm that the device is being supplied from a 120V, 60 Hz AC source ONLY. - Conﬁrm that unit is programmed properly. Repeat "TO INSTALL" section to verify that it has been included in the Z-Wave® network. • Intermittent dimmer operation - Conﬁrm that the Load being controlled does not exceed the 1000VA dimmer limit. • Remote does not operate lights - Ensure that total wire length does not exceed 300 ft. - Ensure wiring is correct. • LED bulb is illuminated even when off - Replace the bulb with a different brand or a higher wattage rating. LED 3 Turns off 5 sec. after use Active LED 4 Turns off 5 sec. after use Turns off 5 sec. after use LED 5 Active LED Bar active LED 6 Active LED Bar turns off 5 sec. after use For additional information, contact Leviton’s Techline at 1-800-824-3005 or visit Leviton’s website at www.leviton.com LED 7 Turns off 5 sec. after use LED Bar turns off 5 sec. after use B-4) The Locator LED will blink 4 times per second to indicate Program Mode B-4, Fluorescent Mode. Default operation mode is incandescent/magnetic low voltage mode. To change from normal to ﬂuorescent mode, use the DIM/BRIGHT Bar. Press and hold the right half of the DIM/BRIGHT Bar (^) until LED is lit (default setting is LED OFF). By tapping the Push Pad this setting will automatically be saved and device will exit Programming Mode B. A-2) The Locator LED will blink 2 times per second to indicate the device is in Program Mode A-2, Minimum Brightness Level. The default Minimum Brightness Level is LED 1. To change the Minimum Brightness Level from 1-50%, use the DIM/BRIGHT Bar. The light output will reﬂect the minimum brightness level selected. By tapping the Push Pad this setting will automatically be saved and the device will advance to the next programming mode, A-3. A-3) The Locator LED will blink 3 times per second to indicate Program Mode A-3, Preset ON Level. To change the current Preset ON Level from 1-100%, use the DIM/BRIGHT Bar. If this feature is not desired, press and hold the left half of the DIM/BRIGHT Bar (v) until no LED is lit (default setting). By tapping the Push Pad this setting will automatically be saved and the device will exit Programming Mode A. Program Mode B To enter Program Mode B: Press and hold the Push Pad and then the left half of the DIM/BRIGHT Bar (v) for 5 seconds until the Locator LED and rightmost LED (LED 7) begin to blink. B-1) Upon releasing the Push Pad and the left half of the DIM/BRIGHT Bar (v), the Locator LED will continue to blink once per second indicating the dimmer is in Program Mode B-1, ON Fade Rate. To change the ON Fade Rate, use the DIM/BRIGHT Bar to move the LED to the desired preset level according to Chart B. By tapping the Push Pad this setting will automatically be saved and the device will advance to the next programming mode, B-2. B-2) The Locator LED will blink 2 times per second to indicate Program Mode B-2, OFF Fade Rate. To change the OFF Fade Rate, use the DIM/BRIGHT Bar to move the LED to the desired preset level according to Chart B. By tapping the Push Pad this setting will automatically be saved and the device will advance to the next programming mode, B-3. Covered by U.S. Pat. Nos.: 7,756,556; 7,985,937; 8,003,904; D609,650 and corresponding foreign equivalents. Licensed under U.S. Pat. Nos. 5,905,442, and 5,982,103 FCC COMPLIANCE STATEMENT This device complies with Part 15 of the FCC Rules. Operation is subject to following two conditions: (1) this device may not cause harmful interference, and (2) this device must accept any interference received, including interference that may cause undesired operation of the device. This equipment has been tested and found to comply with the limits for a Class B Digital Device, pursuant to Part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference in a residential installation. This equipment generates, uses, and can radiate radio frequency energy and, if not installed and used in accordance with the instructions, may cause harmful interference to radio communications. However, there is no guarantee that interference will not occur in a particular installation. If this equipment does cause harmful interference to radio or television reception, which can be determined by turning the equipment OFF and ON, the user is encouraged to try to correct the interference by one or more of the following measures: • Reorient or relocate the receiving Antenna. • Increase the separation between the equipment and the receiver. • Connect the equipment into an outlet on a circuit different from that to which the receiver is connected. • Consult the dealer or an experienced radio/tv technician for help. FCC CAUTION Any changes or modiﬁcations not expressly approved by Leviton Manufacturing Co., Inc., could void the user's authority to operate the equipment. Copyright and Trademark Information This document and all its contents herein are subject to and protected by international copyright and other intellectual property rights and are the property of Leviton Manufacturing Co., Inc, its subsidiaries, afﬁliates and/or licensors. Use herein of third party trademarks, service marks, trade names, brand names and/or product names are for informational purposes only, are/may be the trademarks of their respective owners; such use is not meant to imply afﬁliation, sponsorship, or endorsement. No part of this document may be reproduced, transmitted or transcribed without the express written permission of Leviton Manufacturing Co., Inc. FOR CANADA ONLY For warranty information and/or product returns, residents of Canada should contact Leviton in writing at Leviton Manufacturing of Canada Ltd to the attention of the Quality Assurance Department, 165 Hymus Blvd, Pointe-Claire (Quebec), Canada H9R 1E9 or by telephone at 1-800-405-5320. Z-Wave is a registered trademark of Sigma Designs Inc. and/or its subsidiaries © 2014 Leviton Mfg. Co., Inc. LIMITED 5 YEAR WARRANTY AND EXCLUSIONS Leviton warrants to the original consumer purchaser and not for the beneﬁt of anyone else that this product at the time of its sale by Leviton is free of defects in materials and workmanship under normal and proper use for ﬁve years from the purchase date. Leviton’s only obligation is leviton.com or call 1-800-824-3005. This warranty excludes and there is disclaimed liability for labor for removal of this product or reinstallation. This warranty is void if this product is installed improperly or in an improper environment, overloaded, misused, opened, abused, or accordance with any labels or instructions. There are no other or implied warranties of any kind, including merchantability and ﬁtness for a particular purpose, but if any implied warranty is required by the applicable jurisdiction, the duration of any such implied warranty, Leviton is not liable for incidental, indirect, special, or consequential damages, including without limitation, damage to, or loss of use of, any equipment, lost sales or proﬁts or delay or failure to perform this warranty obligation. The remedies provided herein are the WEB VERSION Step 6 Dimmer Mounting: Step 4c 3-Way Wiring with VP00R-1LZ Matching Remote (with LEDs) Application: DI-000-DZMX1-02A to correct such defects by repair or replacement, at its option. For details visit www. altered in any manner, or is not used under normal operating conditions or not in including merchantability and ﬁtness for a particular purpose, is limited to ﬁve years. exclusive remedies under this warranty, whether based on contract, tort or otherwise.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project