Power source Reader is powered by external power supply (or from controller) Proximity Readers PR 103 and PR 04 User manual PR 103 PR 04 7.5 – 15 V DC 7.5 – 15 V DC (Note 1) (Note 1) 5.5 V DC 5.5 V DC (Note 2) (Note 2) Consumption 40 mA max. 70 mA max. Notes: 1. Maximum permitted voltage oscillation (double amplitude) is 250 mV. 2. Maximum permitted voltage oscillation (double amplitude) is 20 mV. 3. Supply voltage measured directly on reader’s pins. Voltage (Note 3) Card read distance Card reading distance from 30 to 85 mm (depending on card or badge type) when card is in parallel with reader case. Application and Card Types. Actec proximity card reader can be used both with Wiegand 26 and Touch Memory systems. Any type of proximity cards of 125 KHz frequency is applicable. Technical Specifications. Case PR 103 PR 04 Material Plastic ABS Stainless steel Dimensions 150 x 46 x 22 mm 114 x 80 x 15 mm Environmental characteristics PR 103 Temperature -20 . . +55 ° C Humidity 0 . . . 99 % PR 04 -40 . . +55 ° C Cables Reader has 8-wire colored cable which connects it to access control system. Wires are specified below in Table 1. Table 1. Shielded multi wire signal cable with 0.22 mm2 wires is recommended for reader and controller Color Name Function Red +V Power supply Black GND Common wire Green W0 “0” data / Touch Memory White W1 “1” data / Touch Memory Orange Led-G Green LED on Brown Led-R Red LED on Yellow BEEP Buzzer on Blue N/C Reserved – do not connect connection. It provides up to 150 m distance between reader and controller. Part # 7101335 Output signals There are two modes (formats) supported by the Reader: • Wiegand 26 Bits mode is set by Green and White wires connection to the appropriate controller inputs. • Touch Memory mode is set when Green and White wires are connected together. It simulates Dallas Semiconductor DS1990A Touch Memory keys and can be used with controllers compatible with this identification devices. In Wiegand 26 mode pulse and pause durations are 50 ms and 2 ms, respectively (standard values for HID readers.) In a stand-by mode (when no card presented), connected to internal +5 volts through 4,7 kOhm resistors reader outputs logic “1” level. It is strongly recommended to use pull-up resistors (680…470 Ohm) at controller side of communication line for maximum distance between reader and controller. Installation Reader should be installed on the wall near the door on the lock side and at similar height. A small cavity or a big diameter hole should be available under reader case to provide for cable connection. Caution! It is not recommended to install reader on metal surface, as this reduces the read distance. In case more than one reader is used they should be installed at 50 sm minimum distance between any two of them. Reader installation For PR 103: Drill two 6 mm diameter, 35 mm deep vertical holes for plastic nailing plugs. Distance between hole centers shall be 132 mm. For PR 04: Drill four 6 mm diameter, 35 mm deep holes for plastic nailing plugs. Distance between hole centers shall be 46 mm horizontal and 83 mm vertical. Connect reader and controller with the prepared cable and secure reader case with two (four) screws. Reader performance and indications. As the card positioned with in the reading range, reader checks the card code and transfers it to controller. Power-on self-test On powering on the reader it will perform a self-test for 1 sec. maximum. In case the test passed successfully it will produce a sound signal together with a green LED and will switch to a stand-by mode. Reader indication While reading card code the reader produces a short sound signal and switches green LED for a short time (approximately 0,1 s). This confirms that the card code has been read successfully, but it is not related to the rights of the card within the system. (E.g. right to enter). External indication (of the controller). Green or Red LED and a buzzer are used by controller to indicate the decision made by the system with respect to the presented card. Active level for LED and buzzer activation is logical “0”. Warranty Manufacturer guarantees trouble proof operation of the device during 12 months from the date of sale. Warranty is not applicable to devices used with violation of operating rules and modes, as well as to devices having mechanical damage. Warranty is not effective without a note about a date of sale or documents verifying the fact of sale. Please, consult you Vendor on after-sale service.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project