HSM2HOST 2-Way Wireless Transceiver V1.2 Installation Manual WARNING: This manual contains information on limitations regarding product use and function and information on the limitations as to liability of the manufacturer. The entire manual should be carefully read. Table of Contents Specifications and Features Compatible Wireless Devices Safety Instructions Introduction Installation Process Overview Controls and Indicators Tamper Setup and Wiring Mounting Connect the HSM2HOST Enroll The HSM2HOST Delete the HSM2HOST Permanently Mount Other Options Wireless Device Setup and Programming  Enroll Wireless Devices - Wireless Device Configuration  RF Jam Detect  Wireless Supervision Window  Wireless Option 1  Motion Cameras - Delete Wireless Devices - Replace Wireless Devices [001 – 005] Show All Devices  Reset to Factory Defaults  Placement Testing Wireless Devices Programming Worksheets Label Programming  Wireless Programming  Wireless Device Enrollment – Zones  Wireless Device Enrollment – Wireless Keys  Wireless Device Enrollment – Wireless Sirens  Wireless Device Enrollment – Wireless Keypads  Wireless Device Enrollment – Wireless Repeaters - Configure Wireless Zones 1-128 (copy as needed) - Configure Wireless Sirens 1-16 (copy as needed) Toggle Options Toggle Options - Configure Wireless Keys (copy as needed) - Wireless Key 1-32 -- Wireless Keypad Programming (copy as needed)  Jam Detect  Supervisory Window  Wireless Options FCC Compliance Statement 3 4 5 6 6 6 7 8 8 8 8 9 9 9 10 10 10 10 11 11 12 12 12 13 13 13 15 15 17 18 19 19 20 20 21 22 22 23 23 24 24 26 26 26 30 HSM2HOST Installation Manual Specifications and Features Current Draw: 60mA Voltage: Draws current from the PowerSeries Neo alarm controller (10.8VDC to 12.5VDC) - (Limited Power Supply) UL) l Frequency: 433MHz (HSM2HOST4), 868MHz (HSM2HOST8), 912-919MHz (HSM2HOST9 l Zones - can receive signals from up to 128 wireless zones, plus 16 wireless keypads. Also supports up to 32 wireless keys or 32 panic pendants and 16 sirens l Supervisory - programmable supervisory window l Can be wired up to 1000 ft. / 230 m from the main panel with 22 AWG wire l Connects to Corbus l Compatibility: The HSM2HOST is used with PowerSeries Neo alarm panels l Operating temperature: NA= 0°C – +49°C (32-122°F); EU= -10°C – +55°C l Relative humidity: 93% non-condensing l Separate, built-in wall and case tampers Note: For Commercial BURG (UL) the Supervisory window shall be set to 4 hours. For Residential Fire (UL/ULC) the Supervisory window shall be set to 200 seconds. For Residential BURG (UL/ULC) the supervisory window shall be set to 24 hours. For UL Home Healthcare applications the supervisory window shall be set to 24 hours Only models operating in the band 912-919 MHz are UL/ULC listed where indicated. Only UL approved devices are to be used with UL/ULC listed systems. l l 3 Compatible Wireless Devices Compatible Wireless Devices The HSM2HOSTx (x= 4/8/9) can receive signals from the devices listed in the following chart. Please refer to the individual device instruction sheet. Throughout this document, x in the model number represents the operating frequency of the device as follows: 9 (912-919 MHz), 8 (868MHz), 4 (433MHz). Alarm Controllers PowerSeries Neo alarm controllers HS2128/HS2128 E/HS2064/ HS2064 E/HS2032/ HS2016 Modules Wireless keypads HS2LCDWFx HS2LCDWFPx HS2LCDWFPVx Wireless Devices Wireless PG smoke detector PGx926UL Wireless PG smoke and heat detector PGx916UL Wireless PG CO detector PGx913 Wireless PG PIR motion detector PGx904(P)UL Wireless PG PIR + camera motion detector PGx934(P)UL Wireless Outdoor PG PIR + camera motion detector PGx944 Wireless PG curtain motion detector PGx924UL Wireless PG dual tech motion detector PGx984(P) Wireless PG mirror motion detector PGx974(P)UL Wireless PG outdoor motion detector PGx994UL Wireless PG glass break detector PGx912, PGx922 Wireless PG shock detector PGx935UL Wireless PG flood detector PGx985UL Wireless PG temperature detector (indoor use) PGx905UL Wireless PG key PGx939UL Wireless PG key PGx929UL Wireless PG panic key PGx938UL Wireless PG 2-button key PGx949UL Wireless PG indoor siren PGx901UL Wireless PG outdoor siren PGx911UL Wireless PG repeater PGx920UL Wireless PG door/window contact PGx975UL Wireless PG door/window contact w/ AUX PGx945UL 4 HSM2HOST Installation Manual Safety Instructions l l l l This equipment must be installed by Service Persons only (a service person is defined as a person having the appropriate technical training and experience necessary to be aware of hazards to which that person may be exposed in performing a task and of measures to minimize the risks to that person or other persons). It must be installed and used within a non-hazardous, indoor environment only (pollution degree max 2, over voltages category II). The installer is responsible for instructing the system user in regards to electrical safety precautions when using a system which includes this equipment and also in regards to each of the following: l Do not attempt to service this product. There are no user serviceable parts inside. If servicing is required, it shall be referred to service persons only. Using adequate mounting means (e.g., plastic/metal anchors), secure the transceiver to the building structure before applying power. Internal wiring must be routed in a manner that prevents: l Excessive strain on wire and on terminal connections; l Loosening of terminal; connections; l Damage to conductor insulation. Only UL/ULC listed devices can be used in UL/ULC listed installations. HSM2HOST9 is listed for UL Commercial Burglary, Residential Fire, Residential Burglary and Home Health Care, ULC Residential Fire and Residential Burglary: UL1610 Central-Station Burglar Alarm Units UL1023 Household Burglar-Alarm System Units UL985 Household Fire Warning System Units UL1637 Home Health Care Signaling Equipment ULC-S545-02 Residential Fire Warning System Control Units ORD-C1023-1974 Household Burglar-Alarm System Units UL 609 Local Burglar Alarm Units and Systems UL365 Police Station Connected Burglar Alarm Units and Systems 5 Introduction Introduction The HSM2HOSTx two-way wireless transceiver adds wireless capability to PowerSeries Neo alarm controllers, model HS2128 E, HS2064 E, HS2032 or HS2016. The HSM2HOST receives signals from wireless zones and wireless keys, and provides information to the alarm controller it is connected to. This manual describes how to install, program and maintain the HSM2HOST. Note that only one HSM2HOST or one RFK keypad can be enrolled on the alarm system. Before installing: 1. Plan the placement and wiring of the security system (see system installation manual). 2. Install the control panel and optional modules. 3. Temporarily mount all wireless devices in the intended location. Installation Process Overview To install and set up the HSM2HOST and wireless devices: 1. Temporarily mount and wire the HSM2HOST module ("Mounting" on page 8). 2. Enroll the HSM2HOST and first wireless keypad ("Enroll The HSM2HOST" on page 8). 3. Check the location for RF interference levels (" RF Jam Detect" on page 10). 4. Enroll wireless devices (" Enroll Wireless Devices" on page 10). 5. Complete zone and other programming on the system ("Wireless Device Setup and Programming" on page 10). 6. Test the placement of all the wireless devices (" Placement Testing Wireless Devices" on page 13). 7. Permanently mount the HSM2HOST and wireless devices ("Permanently Mount" on page 9). Controls and Indicators Status LEDs The LEDs on the front of the HSM2HOST provide feedback regarding the installation, operation and troubleshooting of the unit. The LEDs function as follows: Red LED Operation Module Power Up: On steady during module power-up sequence then off. Firmware Update: Slow flashing = update in progress Rapid flashing = update failed Trouble Condition: l l l l l No trouble: 1 rapid flash every 10 seconds. If troubles are present, a series of flashes occur every 2 seconds. Each series of flashes indicate troubles as follows: 1 flash: Module not enrolled 2 flashes: Loss of contact with module for over 60 seconds 3 flashes: Corbus low voltage 8 flashes: RF interference (jam condition) Module Confirmation: Flashes rapidly during module confirmation process. Placement Test: On steady when location is bad. Off when location is good. Green LED Placement Test: Operation On steady when location is suitable. Off when location is unsuitable. Note: For UL/ULC listed systems, signal must be “Strong”. See Wireless Device Status Indications on page 10 for details. 6 HSM2HOST Installation Manual Tamper The HSM2HOST has separate built-in wall and case tampers. The case tamper is disabled by default on the NA version (enabled on EU version). Section  option 3 enables or disables the case tamper. Enable or disable the wall tamper by fastening the breakaway wall tamper bracket securely to the wall using one of the supplied screws. The case tamper activates when the case is opened and restores when the case is closed. The wall tamper on the back of the unit is depressed by the mounting surface when properly installed. If the unit is removed, the tamper activates. Ensure the mounting surface is smooth and free of obstructions that block access to the rear of the unit. Electrical wires should not run over or under the module when it is mounted. Note: The built in wall and case tamper must be installed and enabled for UL/ULC listed Commercial/ Residential Burglary applications. 7 Setup and Wiring Setup and Wiring This section describes how to set up and wire the HSM2HOST module. Mounting Note: Permanently mount the HSM2HOST receiver and wireless devices AFTER placement testing each device ("  Placement Testing Wireless Devices" on page 13). Find a place that is: l dry, l within operating temperature range, l central to the proposed placement of all wireless devices, l as high as possible. The range is reduced if mounted below ground level, l far from sources of interference, including: electrical noise (computers, televisions, electric motors, appliances, heating and air conditioning units), large metal objects like heating ducts and plumbing which may shield the electro-magnetic waves, l smooth and free of obstructions that block access to the rear of the unit. Connect the HSM2HOST Caution: Remove all power (AC, DC, telephone lines) from the system while connecting modules to the Corbus. To connect the HSM2HOST: 1. With the alarm panel powered down, connect the HSM2HOST to the four-wire Corbus of the alarm panel according to Figure 1. 2. Once the wiring is complete, power up the security system. Figure: 1 Wiring Diagram Enroll The HSM2HOST The HSM2HOST must be enrolled onto the alarm panel before any wireless devices can be enrolled. When the alarm system is powered up for the first time, the first keypad or the HSM2HOST (if using a wireless keypad as the first keypad) can be enrolled. To do this: 1. Once the HSM2HOST is wired to the alarm panel and power has been applied, power up a wireless keypad. 2. Press any button on the keypad to enroll it on the HSM2HOST. The HSM2HOST is then automatically enrolled on the alarm panel. Alternately, enroll the HSM2HOST on the system at any time using the following procedure: 1. Enter Installer Programming section  (Auto Enroll All Modules). Modules are automatically detected in the following order: 1– Keypads 2 – Zone Expander 8 HSM2HOST Installation Manual 3 – Output Module 4 – HSM2HOSTx 5 – Audio Verification Module 6 – Power Supply 1A 2. When prompted, press [*] to enroll. Or another Alternate method, 1. Enter Installer Programming section  (Enroll Modules). 2. When prompted, key in the serial number found on the back of the module. The module is enrolled. Delete the HSM2HOST To remove the HSM2HOST from the system: 1. Enter Installer Programming section  (Delete HSM2HOSTx). 2. Press [*] to delete. Permanently Mount Once a suitable location is found, mount the HSM2HOST as follows: 1. Pull the Corbus wires through the holes at the back of the cabinet. 2. Mount the cabinet securely to the wall using the three screws supplied. 3. To enable the wall tamper, fasten the breakaway wall tamper bracket securely to the wall using the supplied screw. Figure: 2 Mounting the HSM2HOST Other Options The following actions may be performed on the HSM2HOST: Section Action  Delete the HSM2HOST from the alarm system.  Confirm that the HSM2HOST is enrolled.  Add a label to appear on LCD keypads.  View HSM2HOST model information. 9 Wireless Device Setup and Programming Wireless Device Setup and Programming This section describes how to enroll and program wireless devices such as contacts, motion sensors and sirens on the alarm panel.  Enroll Wireless Devices Once the HSM2HOST is installed and enrolled on the alarm panel, wireless devices can be enrolled using the following method: 1. Enter Installer Programming section . 2. When prompted, either activate the device (see device installation sheet) to enroll immediately or enter a device ID number. Do the latter to pre-enroll devices then enroll them later at the customer site. The alarm panel determines the type of device being enrolled and presents the appropriate programming options. Wireless Device Options Device Type Programming Options 3. 4. 5. 6. 7. Zone (01) Zone type (02) Partition assignment (03) Zone label Wireless Key (01) Partition assignment (02) User label Siren (01) Partition assignment (02) Siren label Repeater (01) Repeater label Use the scroll keys or type in the corresponding number to select an option. Scroll through the available selections, key in a number or enter text as appropriate. Press [*] to accept and move to the next option. Once all options are configured, the system prompts to enroll the next device. Repeat the process described above until all wireless devices are enrolled. Note: The configuration options listed above can be modified using  Modify Device. - Wireless Device Configuration To configure wireless devices: 1. Enter Installer Programming section  then select one of the following sub-sections: l 001-128 – Configure Wireless Zones l 551-566 – Configure Wireless Sirens l 601-632 – Configure Wireless Keys l 701-716 – Configure Wireless Keypads 2. Select a device to configure using the scroll keys or go directly to a specific device by entering a hotkey. 3. Use the scroll buttons or enter a hotkey to select a configuration option for the device. See device sheets for details. 4. Press [*] to accept and move to the next option. 5. Once all options are configured, the system returns to the base configuration menu. 6. Repeat the process described above to configure other wireless devices.  RF Jam Detect RF jam detection (continuous interfering transmissions on the radio network) can be turned on or off. When on, RF jamming is logged and reported. To configure RF jamming: 10 HSM2HOST Installation Manual 1. Enter Installer Programming section  then select one of the following options: 00 Disabled Jamming detection and reporting is enabled/disabled Note: Must be Enabled for UL/ULC listed installations. 01 UL 20/20-USA Continuous RF jamming for 20 seconds 02 EN 30/60Europe 30 seconds of accumulated jamming within 60 seconds 03 Class 6 30/60British As EN (30/60) but reported only if the jamming duration exceeds 5 minutes 2. Press [*] to accept the selection. 3. Press [#] to exit the section.  Wireless Supervision Window This option is used to program the length of time a wireless device can be absent from the system before a fault is generated. For EN installations, 1 hour or 2 hours must be selected. When option 06 is used, which configures the system to generate fault conditions after a device has been detected as absent for 24 hours, smoke detectors generate a fault condition after a maximum of 18 hours when the 200s supervision toggle option is disabled. To program the Wireless Supervisory Window: 1. Enter Installer Programming section . 2. Select one of the following options by scrolling or entering the hotkey: l 00 – Disabled l 01 – After 1 Hour l 02 – After 2 Hour l 03 – After 4 Hour l 04 – After 8 Hours l 05 – After 12 Hours l 06 – After 24 Hours 3. Press [*] to accept the selection. 4. Press [#] to exit the section. Note: For UL Residential Burglary (UL1023), Home Health Care (UL1637), ULC Residential Burglary (ULC/ORD-C1023) installations, the maximum Supervision window shall be set to 24 hours. For UL Residential Fire (UL985) installations, the maximum supervision window is set to 200s. For UL Commercial Burglary (UL1610/UL365) and ULC Residential Fire (ULC-S545), the maximum supervision window shall be set to 4 hours.  Wireless Option 1 To program wireless options: 1. Enter Installer Programming section . 2. Select one of the following options by scrolling or entering the hotkey: 11  Motion Cameras 01 RF Delinquency On: the system cannot be armed if a wireless supervisory trouble exists. An RF delinquency trouble is generated. Off: wireless supervisory troubles do not prevent arming. 02 Wireless Supervisory/ RF Jam Alarm On: if a supervisory or jamming trouble occurs during Away arming, the siren activates and the event is logged and reported. Off: supervisory or RF jam troubles during Away arming do not activate the siren or get logged and reported. 03 Wireless Tamper On: module tampers are logged and reported. Off: module tampers are not logged or reported. 04 Fire Supervision On: fire devices are supervised every 200 seconds. If the device fails to report within this window, a supervision trouble is generated. Off: fire devices follow the supervision window programmed in section 802, up to a maximum of 18 hours. The supervisory window can be programmed with a higher value, but detectors still go into fault after 18 hours. 3. Press [*] to accept the selection and [#] to exit.  Motion Cameras To program motion cameras: 1. Enter Installer Programming section . 2. Select one of the following options by scrolling or entering the hotkey:  Visual Verification On: Alarms trigger image capture from PIR Cameras Off: Alarms do not trigger image capture from PIR Cameras  View Time Window 01 Alarm + 5 Minutes 02 Alarm + 15 minutes 03 Alarm + 1 Hour  View Other Alarms 01 02 03 04 Fire key enabled/disabled Duress enabled/disabled Medical key enabled/disabled Panic key enabled/disabled - Delete Wireless Devices To delete wireless devices: 1. Enter Installer Programming section  then select one of the following sub-sections:  – Delete wireless zone devices  – Delete wireless key  – Delete sirens  – Delete repeaters  – Delete keypads 2. Select a device to delete using the scroll keys or go directly to a specific device by entering a hotkey. 3. Press [*] to delete or [#] to exit. - Replace Wireless Devices Use this option to replace a faulty device enrolled on the system with another device of the same type while maintaining the configuration of the original. The faulty device does not need to be deleted. To replace a wireless device: 12 HSM2HOST Installation Manual 1. Enter Installer Programming section  then select one of the following sub-sections:  – Replace wireless zone devices  – Replace wireless key  – Replace sirens  – Replace repeaters  – Replace keypads 2. Press [*] to select a sub-section. The first available device is displayed. 3. Select a device to replace using the scroll keys or go to a specific device by entering a hotkey. 4. Press [*]. When prompted, activate the device (full enrollment) or enter the device ID (pre-enrollment). A message is displayed confirming enrollment. [001 – 005] Show All Devices Use this section to review wireless devices enrolled on the system and to view serial numbers associated with each device. To review wireless device information: 1. Enter Installer Programming section  then select one of the following sub-sections: l  – All zones l  – Repeaters l  – Sirens l  – Wireless keys l  – keypads 2. Press [*] to select a wireless device type. The first available device is displayed. 3. Use the scroll keys to view the enrolled devices. Note: This option is not fully supported by LED and ICON keypads.  Reset to Factory Defaults Selecting this option resets HSM2HOST programming to factory default settings.  Placement Testing Wireless Devices This test is used to determine RF signal status for wireless devices and can be performed at a system keypad or at the individual device. These instructions pertain to testing at the keypad. For instructions on placement testing at the device, refer to the installation sheet provided with the wireless equipment. The following test modes are available: - Test wireless zones Test wireless devices individually by zone. Zones with vanishing contacts must be activated to placement test. - Test all repeaters Test each enrolled wireless repeater. 521-528 for repeaters 1-8 - Test all sirens Test each enrolled wireless siren. 551-566 for sirens 116 - Test all wireless keys Test individual wireless keys. Once in this section, press a button on the wireless key to begin the test. 601-632 for wireless keys 1-32. - Test all keypads Test each enrolled keypad. 701-716 for keypads 1-16 Two test results are provided: l 24-hour: Average results of signal strength testing over a 24-hour period. l Now: Signal status results of the current test. A flashing Trouble LED indicates RF interference. The following status indicators may be displayed: 13  Placement Testing Wireless Devices LCD Icon* LED+ Status Strong 1 9 Strong signal strength Good 2 10 Good signal strength Poor 3 11 Poor signal strength Not Test 5 13 Displayed as the Now result if no test was performed Not Test 5 13 Always displayed as the 24-hour result when testing wireless keys *For Icon keypads, digit 1 indicates 24-hour test results; digit 2 indicates Now test results. +For LED keypads, the first digit indicates 24-hour results; the second digit indicates Now test results. Note: For EN/UL/ULC installations, only STRONG signal levels are acceptable. 14 HSM2HOST Installation Manual Programming Worksheets Use these pages for recording custom programming options (Installers Programming: [*]).  Enroll Module 000 - Auto Enroll 001 - Enroll Modules 002 - Module Slot Assignment (LED/ICON) 003 - Module Slot Assignment (LED only) Delete Module 101 - Delete Keypads 102 - Delete Zone Expander 103 - Delete Output Expander 106 - Delete HSM2HOST 108 - Delete Audio Verification 109 - Delete Power Supply  Confirm Module 001 - Confirm Keypad 002 - Confirm Zone Expander 003 - Confirm Output Expander 006 - Confirm HSM2HOST 008 - Confirm Audio Verification 009 - Confirm Power Supply Label Programming  Module Lables  Keypad Label (1 x 14 Characters) 001: 009: 002: 010: 003: 011: 004: 012: 005: 013: 006: 014: 007: 015: 008: 016: 15 Label Programming  Zone Expander Label (1 x 14 Characters)  001: 009: 002: 010: 003: 011: 004: 012: 005: 013: 006: 014: 007: 015: 008: 016: Output Expander Label (1 x 14 Characters)  001: 009: 002: 010: 003: 011: 004: 012: 005: 013: 006: 014: 007: 015: 008: 016: HSM2HOST Label (1 x 14 Characters) 01:  HSM2300 Power Supply Label (1 x 14 Characters) 01: 02: 03: 04:  HSM2204 High-Current Output Label (1 x 14 Characters) 01: 02: 03: 04: 16 HSM2HOST Installation Manual  Siren Labels (1 x 14 Characters) 01: 02: 03: 04: 05: 06: 07: 08:  Repeater Labels (1 x 14 Characters) 01: 02: 03: 04: 05: 06: 07: 08:  Wireless Programming  Enroll Wireless Device Zone Wireless Key Siren Keypad Repeater 17  Wireless Device Enrollment – Zones  Wireless Device Enrollment – Zones Zone Zone Definition Label 18 Zone Type Partition HSM2HOST Installation Manual  Wireless Device Enrollment – Wireless Keys Key# Partition# User Label Key# Partition# 1 17 2 18 3 19 4 20 5 21 6 22 7 23 8 24 9 25 10 26 11 27 12 28 13 29 14 30 15 31 16 32 User Label  Wireless Device Enrollment – Wireless Sirens WLS Siren# Partition# WLS Partition# Siren# Siren Label 1 9 2 10 3 11 4 12 5 13 6 14 7 15 8 16 19 Siren Label  Wireless Device Enrollment – Wireless Keypads  Wireless Device Enrollment – Wireless Keypads WLS Keypad Keypad# Assignment WLS Keypad Keypad# Assignment Keypad Label 1 9 2 10 3 11 4 12 5 13 6 14 7 15 8 16 Keypad Label  Wireless Device Enrollment – Wireless Repeaters Repeater# Repeater Label 1 2 3 4 5 6 7 8 20 HSM2HOST Installation Manual - Configure Wireless Zones 1-128 (copy as needed) Zone#: Toggle Options  Device Options  High Traffic Shutdown ✓ 01 – Alarm LED ✓ 02 – Reed Switch 02 – Yes - No Delay 03 – External Input On 03 – Yes - 5s Delay 04 – Supervision 04 – Yes - 15s Delay 05 – Not Used 05 – Yes - 30s Delay 06 – Not Used 06 – Yes - 1m Delay 07 – Not Used 07 – Yes - 10m Delay 08 – Not Used 08 – Yes - 20m Delay 09 – Shock Accumulator 09 – Yes - 15s Delay 10 – Not Used 10 – Yes - 60m Delay 11 – 24hr/Night  Image Brightness 12 – Piezo Siren 01 – Image Bright -3 13 – Not Used 02 – Image Bright -2 14 – Fire Alarm 03 – Image Bright -1 ✓ ✓ ✓ 15 – Not Used ✓ ✓ 01 – Not Active ✓ 04 – Image Bright 0 16 – Not Used 05 – Image Bright +1  Zone EOL 06 – Image Bright +2 00 – Disable 07 – Image Bright +3 01 – Single EOL 02 – Normally Open 03 – Normally Closed 04 – Double EOL 21 - Configure Wireless Sirens 1-16 (copy as needed) ✓ ✓  Image Contrast  Event Counter 01 – Image Contrast -3 001-002 (Default: 002) 02 – Image Contrast -2  Camera Toggles 03 – Image Contrast -1 ✓ 01 – Color 04 – Image Contrast 0 ✓ 02 – High Res. 05 – Image Contrast +1 03 – Low Quality 06 – Image Contrast +2 04 – Microphone 07 – Image Contrast +3 09 – AC Power  Detection Range  Shock Sensitivity 01 – Low Sensitivity 001-019 (Default: 008) 02 – Mid Sensitivity  High Temp. Warning 03 – High Sensitivity +/- 000-999 (Default:999c)  Detection Sensitivity  High Temp. Alarm 01 – Low Sensitivity +/- 000-999 (Default:999c) 02 – Mid Sensitivity  LowTemp. Warning 03 – High Sensitivity +/- 000-999 (Default:999c) 03 – UL Standard  Low Temp. Alarm +/- 000-999 (Default:999c) - Configure Wireless Sirens 1-16 (copy as needed) Zone# Toggle Options  Partition Assignment 12345678  Device Toggles  Strobe Alarm  Squawk 01 – Disabled 01 – Disabled ✓ 01 – Fire Alarm ✓ 02 – Gas/CO Alarm ✓ 02 – Timer Limited ✓ 02 – Sounder Only ✓ 03 – Burglary Alarm 03 – Until Disarmed 03 – Strobe Only ✓ 04 – Flood Alarm  Exit Entry Beeps 04 – Sounder/Strobe 05 – Not Used ✓ 01 – Disabled 06 – Auto Temp Alarm 02 – Enabled 07 – Activity LED 03 – Disabled Stay 08 – Not Used  Sounder Volume 01 – Low ✓ 02 – Medium 03 – High 09 – AC Power ✓ 10 – Buzzer Notification ✓ 11 – Door Chime ✓ 12 – Trouble Beep 22 HSM2HOST Installation Manual Zone# Toggle Options  Partition Assignment 12345678  Device Toggles  Strobe Alarm  Squawk 01 – Disabled 01 – Disabled ✓ 01 – Fire Alarm ✓ 02 – Gas/CO Alarm ✓ 02 – Timer Limited ✓ 02 – Sounder Only ✓ 03 – Burglary Alarm 03 – Until Disarmed 03 – Strobe Only ✓ 04 – Flood Alarm  Exit Entry Beeps 04 – Sounder/Strobe 05 – Not Used ✓ 01 – Disabled 06 – Auto Temp Alarm 02 – Enabled 07 – Activity LED 03 – Disabled Stay  Sounder Volume 01 – Low ✓ 02 – Medium 08 – Not Used 03 – High 09 – AC Power ✓ 10 – Buzzer Notification ✓ 11 – Door Chime ✓ 12 – Trouble Beep - Configure Wireless Keys (copy as needed)  Wireless Key Partition Assignment (Default: 01) - Wireless Key Button Programming (Defaults: Key 1: 04, Key 2: 03, Key 3: 01, Key 4: 52, Key 5: 21)  Wireless Key Device Toggles (Default: 01)  Wireless Key User Assignment (Default: 00 – Not Assigned) Available programming options: 00- Disabled (Null) 01- Disarm 02- Instant Stay Arm 03- Stay Arm 04- Away Arm 05- [*] No Entry 06- Chime On/Off 07- System Test 09- Night Arm 12- Global Stay Arm 13- Global Away Arm 14- Global Disarm 16- Quick Exit 17- Arm Interior 21- Comm. Output 22- Comm. Output 23- Comm. Output 24- Comm. Output 23 1 2 3 4 29- Bypass Group Recall 33- Bypass Recall 51- [M] Key Alarm 52- [P] Key Alarm - Wireless Key 1-32 - Wireless Key 1-32 Wireless Key# Wireless Key# Wireless Key# Wireless Key# Wireless Key# Partition Button 12345678 1: 2: 3: 4: 5 Partition Button 12345678 1: 2: 3: 4: 5 Partition Button 12345678 1: 2: 3: 4: 5 Partition Button 12345678 1: 2: 3: 4: 5 Partition Button 12345678 1: 2: 3: 4: 5 Supervision Yes No User Number ✓ Supervision Yes No User Number ✓ Supervision Yes No User Number ✓ Supervision Yes No User Number ✓ Supervision Yes No User Number ✓ -- Wireless Keypad Programming (copy as needed) Keypad#  00 – Global 03 – Partition 3 03 – Partition 3 ✓ 01 – Partition 1 04 – Partition 4 04 – Partition 4 02 – Partition 2 05 – Partition 5 05 – Partition 5 Partition Assignment Function Key Programming Options: 24 HSM2HOST Installation Manual 00 02 03 04 05 06 07 09 11 12 - Null Key - Instant Stay Arm – Stay Arm - Away Arm - [*]No Entry Arm - Chime On/Off - System Test - Night Arm - Away Arm no Entry - Global Stay Arm Function Key: 13 14 16 17 21 22 23 24 29 30 - Global Away Arm - Global Disarming - Quick Exit - Arm Interior - Command Output 1 - Command Output 2 - Command Output 3 - Command Output 4 - Bypass Group Recall - Quick Bypass 31 - Local PGM Active 32 - Bypass Mode 33 - Bypass Recall 34 - User Programming 35 - User Functions 36 - Reactivate Stay/Away/Night zones 37 - Time/Date Programming 39 - Trouble Display 40 - Alarm Memory 61 62 63 64 65 66 67 68 - Partition - Partition - Partition - Partition - Partition - Partition - Partition - Partition  – Key 1: (Default: 03)  – Key 3: (Default: 06)  – Key 5: (Default: 16)  – Key 2: (Default: 04)  – Key 4: (Default: 22)  Keypad I/O (Zone number or output number; 3-digit decimal; Default: 000)  Local PGM Output Timer:  Keypad Option 1 Pulse Time (Default:00 minutes): Pulse Time (Default:05 minutes): ✓ 01 – [F] Key Enabled ✓ 02 – [M] Key Enabled ✓ 03 – [P] Key Enabled ✓ 04 – Display Code or X's  Keypad Option 1 ✓ 01 – Local Clock Display 02 – Local Clock 24-Hour ✓ 03 – Auto Alarm Scroll ✓ 05 – Power LED ✓ 06 – Power LED AC Present ✓ 07 – Alarms Displayed if Armed ✓ 08 – Auto Scroll Open Zones  Keypad Option 3 01 – Armed LED Power Save ✓ 02 – Keypad Status Shows Arm Mode 03 – 5th Terminal is PGM Output/Zone Input 07 – Local Display of Temperature 08 – Low Temperature Warning  LCD Message:  Downloaded LCD Message Duration (3-digit decimal; 000-255; Default: 000):  Indoor Temperature Zone Entry (3-digit decimal; 000-128; Default: 000):  Outdoor Temperature Zone Entry (3-digit decimal; 000-128; Default: 000): 25 Select Select Select Select Select Select Select Select 1 2 3 4 5 6 7 8  Jam Detect - Door Chime Beeps: 00 – Disabled ✓ 01 – 6 beeps 02 – Bing Bong 03 – Ding Dong 04 – Alarm Tone 05 – Zone Name Door Chime Zone Assignment: 1 ____ 2 ____ 3 ____ 4 ____ 5 ____ 6 ____ 7 ____ 8 ____ 9 ____ 10 ____ 11 ____ 12 ____ 13 ____ 14 ____ 15 ____ 16 ____ 17 ____ 18 ____ 19 ____ 20 ____ 21 ____ 22 ____ 23 ____ 24 ____ 25 ____ 26 ____ 27 ____ 28 ____ 29 ____ 30 ____ 31 ____ 32 ____ 33 ____ 34 ____ 35 ____ 36 ____ 37 ____ 38 ____ 39 ____ 40 ____ 41 ____ 42 ____ 43 ____ 44 ____ 45 ____ 46 ____ 47 ____ 48 ____ 49 ____ 50 ____ 51 ____ 52 ____ 53 ____ 54 ____ 55 ____ 56 ____ 57 ____ 58 ____ 59 ____ 60 ____ 61 ____ 62 ____ 63 ____ 64 ____ 65 ____ 66 ____ 67 ____ 68 ____ 69 ____ 70 ____ 71 ____ 72 ____ 73 ____ 74 ____ 75 ____ 76 ____ 77 ____ 78 ____ 79 ____ 80 ____ 81 ____ 82 ____ 83 ____ 84 ____ 85 ____ 86 ____ 87 ____ 88 ____ 89 ____ 90 ____ 91 ____ 92 ____ 93 ____ 94 ____ 95 ____ 96 ____ 97 ____ 98 ____ 99 ____ 100 ___ 101 ___ 102 ___ 103 ___ 104 ___ 105 ___ 106 ___ 107 ___ 108 ___ 109 ___ 110 ___ 111 ___ 112 ___ 113 ___ 114 ___ 115 ___ 116 ___ 117 ___ 118 ___ 119 ___ 120 ___ 121 ___ 122 ___ 123 ___ 124 ___ 125 ___ 126 ___ 127 ___ 128 ___  Jam Detect  Supervisory Window  Wireless Options UL EN UL UL EN EN Disabled After 1 Hour UL – UL 20/20 ✓ ✓ Disabled ✓ After 2 Hours 1 – RF Delinquency Tamper ✓ 2 – Missing/Jam Alarm EN 30/60 After 4 Hours 3 – Wireless Tamper Class 6 (30/60) After 8 Hours 4 – 200s Fire Supervision After 12 Hours ✓ After 24 Hours 26 HSM2HOST Installation Manual  Motion Cameras 001 Visual Verification 01 – Disabled ✓ 02 – Enabled 03 – Enabled 002 View Time Window ✓ 01 – Alarm + 5 Minutes 02 – Alarm + 15 Minutes 03 – Alarm + 1 Hour 003 View Other Alarms ✓ 01 – Fire Alarm ✓ 02 – Duress Alarm ✓ 03 – Medical Alarm ✓ 04 – Panic Alarm - Delete Wireless Devices  Delete Zones  Delete Wireless Keys  Delete Sirens  Delete Repeaters  Delete Keypads - Replace Wireless Devices  Replace Zones  Replace Wireless Keys  Replace Sirens  Replace Repeaters  Replace Keypads  Show All Devices  Show All Zones  Show All Repeaters  Sirens  Wireless Keys  Keypads 27 LIMITED WARRANTY Digital Security Controls warrants the original purchaser that for a period of twelve months from the date of purchase, the product shall be free of defects in materials and workmanship under normal use. During the warranty period, Digital Security Controls shall, at its option, repair or replace any defective product upon return of the product to its factory, at no charge for labour and materials. Any replacement and/or repaired parts are warranted for the remainder of the original warranty or ninety (90) days, whichever is longer. The original purchaser must promptly notify Digital Security Controls in writing that there is defect in material or workmanship, such written notice to be received in all events prior to expiration of the warranty period. There is absolutely no warranty on software and all software products are sold as a user license under the terms of the software license agreement included with the product. The Customer assumes all responsibility for the proper selection, installation, operation and maintenance of any products purchased from DSC. Custom products are only warranted to the extent that they do not function upon delivery. In such cases, DSC can replace or credit at its option. International Warranty is important that a security system be reviewed periodically to ensure that its features remain effective and that it be updated or replaced if it is found that it does not provide the protection expected. Access by Intruders Intruders may enter through an unprotected access point, circumvent a sensing device, evade detection by moving through an area of insufficient coverage, disconnect a warning device, or interfere with or prevent the proper operation of the system. Power Failure Control units, intrusion detectors, smoke detectors and many other security devices require an adequate power supply for proper operation. If a device operates from batteries, it is possible for the batteries to fail. Even if the batteries have not failed, they must be charged, in good condition and installed correctly. If a device operates only by AC power, any interruption, however brief, will render that device inoperative while it does not have power. Power interruptions of any length are often accompanied by voltage fluctuations which may damage electronic equipment such as a security system. After a power interruption has occurred, immediately conduct a complete system test to ensure that the system operates as intended. Failure of Replaceable Batteries The warranty for international customers is the same as for any customer within Canada and the United States, with the exception that Digital Security Controls shall not be responsible for any customs fees, taxes, or This system’s wireless transmitters have been designed to provide several years of battery life under normal conditions. The expected battery life is a function of the device environment, usage and type. Ambient conVAT that may be due. ditions such as high humidity, high or low temperatures, or large temperature fluctuations may reduce the Warranty Procedure To obtain service under this warranty, please return the item(s) in question to the point of purchase. All author- expected battery life. While each transmitting device has a low battery monitor which identifies when the batteries need to be replaced, this monitor may fail to operate as expected. Regular testing and maintenance will ized distributors and dealers have a warranty program. Anyone returning goods to Digital Security Controls keep the system in good operating condition. must first obtain an authorization number. Digital Security Controls will not accept any shipment whatsoever Compromise of Radio Frequency (Wireless) Devices for which prior authorization has not been obtained. Signals may not reach the receiver under all circumstances which could include metal objects placed on or Conditions to Void Warranty near the radio path or deliberate jamming or other inadvertent radio signal interference. This warranty applies only to defects in parts and workmanship relating to normal use. It does not cover: System Users l damage incurredinshippingor handling l damage causedbydisaster suchasfire,flood,wind,earthquake or lightning; A user may not be able to operate a panic or emergency switch possibly due to permanent or temporary physl damage due tocausesbeyondthe controlof DigitalSecurityControlssuchasexcessive voltage,mech- ical disability, inability to reach the device in time, or unfamiliarity with the correct operation. It is important anicalshock,water damage; that all system users be trained in the correct operation of the alarm system and that they know how to respond l damage causedbyunauthorizedattachment,alterations,modificationsor foreignobjects; when the system indicates an alarm. l damage causedbyperipherals(unlesssuchperipheralswere suppliedbyDigitalSecurityControls Smoke Detectors Ltd.); Smoke detectors that are a part of this system may not properly alert occupants of a fire for a number of reasl defectscausedbyfailure toprovide a suitable installationenvironmentfor the products; ons, some of which follow. The smoke detectors may have been improperly installed or positioned. Smoke l damage causedbyuse of the productsfor purposesother thanthose for whichitwasdesigned; may not be able to reach the smoke detectors, such as when the fire is in a chimney, walls or roofs, or on the l damage from improper maintenance; l damage arisingoutof anyother abuse,mishandlingor improper applicationof the products. other side of closed doors. Smoke detectors may not detect smoke from fires on another level of the residence or building. Items Not Covered by Warranty Every fire is different in the amount of smoke produced and the rate of burning. Smoke detectors cannot sense In addition to the items which void the Warranty, the following items shall not be covered by Warranty: (i) freight cost to the repair centre; (ii) products which are not identified with DSC's product label and lot number all types of fires equally well. Smoke detectors may not provide timely warning of fires caused by careor serial number; (iii) products disassembled or repaired in such a manner as to adversely affect performance lessness or safety hazards such as smoking in bed, violent explosions, escaping gas, improper storage of flammable materials, overloaded electrical circuits, children playing with matches or arson. or prevent adequate inspection or testing to verify any warranty claim. Access cards or tags returned for Even if the smoke detector operates as intended, there may be circumstances when there is insufficient warnreplacement under warranty will be credited or replaced at DSC's option. Products not covered by this waring to allow all occupants to escape in time to avoid injury or death. ranty, or otherwise out of warranty due to age, misuse, or damage shall be evaluated, and a repair estimate Motion Detectors shall be provided. No repair work will be performed until a valid purchase order is received from the CusMotion detectors can only detect motion within the designated areas as shown in their respective installation tomer and a Return Merchandise Authorization number (RMA) is issued by DSC's Customer Service. Digital Security Controls Ltd.’s liability for failure to repair the product under this warranty after a reasonable instructions. They cannot discriminate between intruders and intended occupants. Motion detectors do not number of attempts will be limited to a replacement of the product, as the exclusive remedy for breach of war- provide volumetric area protection. They have multiple beams of detection and motion can only be detected in unobstructed areas covered by these beams. They cannot detect motion which occurs behind walls, ceilings, ranty. Under no circumstances shall Digital Security Controls be liable for any special, incidental, or consequential damages based upon breach of warranty, breach of contract, negligence, strict liability, or any other floor, closed doors, glass partitions, glass doors or windows. Any type of tampering whether intentional or uninlegal theory. Such damages include, but are not limited to, loss of profits, loss of the product or any associated tentional such as masking, painting, or spraying of any material on the lenses, mirrors, windows or any other equipment, cost of capital, cost of substitute or replacement equipment, facilities or services, down time, pur- part of the detection system will impair its proper operation. Passive infrared motion detectors operate by sensing changes in temperature. However their effectiveness can chaser’s time, the claims of third parties, including customers, and injury to property. The laws of some jurisdictions limit or do not allow the disclaimer of consequential damages. If the laws of such a jurisdiction apply be reduced when the ambient temperature rises near or above body temperature or if there are intentional or unintentional sources of heat in or near the detection area. Some of these heat sources could be heaters, radito any claim by or against DSC, the limitations and disclaimers contained here shall be to the greatest extent permitted by law. Some states do not allow the exclusion or limitation of incidental or consequential damages, ators, stoves, barbeques, fireplaces, sunlight, steam vents, lighting and so on. Warning Devices so that the above may not apply to you. Warning devices such as sirens, bells, horns, or strobes may not warn people or waken someone sleeping if Disclaimer of Warranties there is an intervening wall or door. If warning devices are located on a different level of the residence or This warranty contains the entire warranty and shall be in lieu of any and all other warranties, whether premise, then it is less likely that the occupants will be alerted or awakened. Audible warning devices may be expressed or implied (including all implied warranties of merchantability or fitness for a particular purpose) interfered with by other noise sources such as stereos, radios, televisions, air conditioners or other appliances, and of all other obligations or liabilities on the part of Digital Security Controls. Digital Security Controls neither assumes responsibility for, nor authorizes any other person purporting to act on its behalf to modify or or passing traffic. Audible warning devices, however loud, may not be heard by a hearing-impaired person. Telephone Lines to change this warranty, nor to assume for it any other warranty or liability concerning this product. This disclaimer of warranties and limited warranty are governed by the laws of the province of Ontario, Canada. If telephone lines are used to transmit alarms, they may be out of service or busy for certain periods of time. WARNING: Digital Security Controls recommends that the entire system be completely tested on a regular Also an intruder may cut the telephone line or defeat its operation by more sophisticated means which may be basis. However, despite frequent testing, and due to, but not limited to, criminal tampering or electrical disdifficult to detect. ruption, it is possible for this product to fail to perform as expected. Insufficient Time Out of Warranty Repairs There may be circumstances when the system will operate as intended, yet the occupants will not be protected Digital Security Controls will at its option repair or replace out-of-warranty products which are returned to its from the emergency due to their inability to respond to the warnings in a timely manner. If the system is monfactory according to the following conditions. Anyone returning goods to Digital Security Controls must first itored, the response may not occur in time to protect the occupants or their belongings. obtain an authorization number. Digital Security Controls will not accept any shipment whatsoever for which Component Failure prior authorization has not been obtained. Although every effort has been made to make this system as reliable as possible, the system may fail to funcProducts which Digital Security Controls determines to be repairable will be repaired and returned. A set fee tion as intended due to the failure of a component. which Digital Security Controls has predetermined and which may be revised from time to time, will be Inadequate Testing charged for each unit repaired. Products which Digital Security Controls determines not to be repairable will be replaced by the nearest equi- Most problems that would prevent an alarm system from operating as intended can be found by regular testing valent product available at that time. The current market price of the replacement product will be charged for and maintenance. The complete system should be tested weekly and immediately after a break-in, an attempted break-in, a fire, a storm, an earthquake, an accident, or any kind of construction activity inside or outside each replacement unit. the premises. The testing should include all sensing devices, keypads, consoles, alarm indicating devices and WARNING – READ CAREFULLY any other operational devices that are part of the system. Note to Installers This warning contains vital information. As the only individual in contact with system users, it is your responsibility to bring each item in this warning to the attention of the users of this system. System Failures Security and Insurance Regardless of its capabilities, an alarm system is not a substitute for property or life insurance. An alarm system also is not a substitute for property owners, renters, or other occupants to act prudently to prevent or minimize the harmful effects of an emergency situation. This system has been carefully designed to be as effective as possible. There are circumstances, however, IMPORTANT - READ CAREFULLY: DSC Software purchased with or without involving fire, burglary, or other types of emergencies where it may not provide protection. Any alarm system Products and Components is copyrighted and is purchased under the following of any type may be compromised deliberately or may fail to operate as expected for a variety of reasons. license terms: Some but not all of these reasons may be: l ThisEnd-User License Agreement(“EULA”) isa legalagreementbetweenYou(the company,individualor Inadequate Installation A security system must be installed properly in order to provide adequate protection. Every installation should entitywhoacquiredthe Software andanyrelatedHardware) andDigitalSecurityControls,a divisionof Tyco be evaluated by a security professional to ensure that all access points and areas are covered. Locks and SafetyProductsCanada Ltd.(“DSC”),the manufacturer of the integratedsecuritysystemsandthe developer latches on windows and doors must be secure and operate as intended. Windows, doors, walls, ceilings and of the software andanyrelatedproductsor components(“HARDWARE”) whichYouacquired. other building materials must be of sufficient strength and construction to provide the level of protection expec- l If the DSC software product(“SOFTWAREPRODUCT” or “SOFTWARE”) isintendedtobe accompanied byHARDWARE,andisNOTaccompaniedbynewHARDWARE,Youmaynotuse,copyor installthe ted. A reevaluation must be done during and after any construction activity. An evaluation by the fire and/or SOFTWAREPRODUCT.The SOFTWAREPRODUCTincludescomputer software,andmayinclude assopolice department is highly recommended if this service is available. ciatedmedia,printedmaterials,and“online” or electronic documentation. Criminal Knowledge l Anysoftware providedalongwiththe SOFTWAREPRODUCTthatisassociatedwitha separate end-user This system contains security features which were known to be effective at the time of manufacture. It is poslicense agreementislicensedtoYouunder the termsof thatlicense agreement. sible for persons with criminal intent to develop techniques which reduce the effectiveness of these features. It l Byinstalling,copying,downloading,storing,accessingor otherwise usingthe SOFTWAREPRODUCT,You agree unconditionallytobe boundbythe termsof thisEULA,evenif thisEULAisdeemedtobe a modification of anypreviousarrangementor contract.If Youdonotagree tothe termsof thisEULA,DSC isunwillingto license the SOFTWAREPRODUCTtoYou,andYouhave norighttouse it. SOFTWARE PRODUCT LICENSE The SOFTWARE PRODUCT is protected by copyright laws and international copyright treaties, as well as other intellectual property laws and treaties. The SOFTWARE PRODUCT is licensed, not sold. 1. GRANT OF LICENSE This EULA grants You the following rights: (a) Software Installation and Use - For each license You acquire, You may have only one copy of the SOFTWARE PRODUCT installed. (b) Storage/Network Use - The SOFTWARE PRODUCT may not be installed, accessed, displayed, run, shared or used concurrently on or from different computers, including a workstation, terminal or other digital electronic device (“Device”). In other words, if You have several workstations, You will have to acquire a license for each workstation where the SOFTWARE will be used. (c) Backup Copy - You may make back-up copies of the SOFTWARE PRODUCT, but You may only have one copy per license installed at any given time. You may use the back-up copy solely for archival purposes. Except as expressly provided in this EULA, You may not otherwise make copies of the SOFTWARE PRODUCT, including the printed materials accompanying the SOFTWARE. 2. DESCRIPTION OF OTHER RIGHTS AND LIMITATIONS (a) Limitations on Reverse Engineering, Decompilation and Disassembly - You may not reverse engineer, decompile, or disassemble the SOFTWARE PRODUCT, except and only to the extent that such activity is expressly permitted by applicable law notwithstanding this limitation. You may not make any changes or modifications to the Software, without the written permission of an officer of DSC. You may not remove any proprietary notices, marks or labels from the Software Product. You shall institute reasonable measures to ensure compliance with the terms and conditions of this EULA. (b) Separation of Components - The SOFTWARE PRODUCT is licensed as a single product. Its component parts may not be separated for use on more than one HARDWARE unit. (c) Single INTEGRATED PRODUCT - If You acquired this SOFTWARE with HARDWARE, then the SOFTWARE PRODUCT is licensed with the HARDWARE as a single integrated product. In this case, the SOFTWARE PRODUCT may only be used with the HARDWARE as set forth in this EULA. (d) Rental - You may not rent, lease or lend the SOFTWARE PRODUCT. You may not make it available to others or post it on a server or web site. (e) Software Product Transfer - You may transfer all of Your rights under this EULA only as part of a permanent sale or transfer of the HARDWARE, provided You retain no copies, You transfer all of the SOFTWARE PRODUCT (including all component parts, the media and printed materials, any upgrades and this EULA), and provided the recipient agrees to the terms of this EULA. If the SOFTWARE PRODUCT is an upgrade, any transfer must also include all prior versions of the SOFTWARE PRODUCT. f) Termination - Without prejudice to any other rights, DSC may terminate this EULA if You fail to comply with the terms and conditions of this EULA. In such event, You must destroy all copies of the SOFTWARE PRODUCT and all of its component parts. (g) Trademarks - This EULA does not grant You any rights in connection with any trademarks or service marks of DSC or its suppliers. 3. COPYRIGHT - All title and intellectual property rights in and to the SOFTWARE PRODUCT (including but not limited to any images, photographs, and text incorporated into the SOFTWARE PRODUCT), the accompanying printed materials, and any copies of the SOFTWARE PRODUCT, are owned by DSC or its suppliers. You may not copy the printed materials accompanying the SOFTWARE PRODUCT. All title and intellectual property rights in and to the content which may be accessed through use of the SOFTWARE PRODUCT are the property of the respective content owner and may be protected by applicable copyright or other intellectual property laws and treaties. This EULA grants You no rights to use such content. All rights not expressly granted under this EULA are reserved by DSC and its suppliers. 4. EXPORT RESTRICTIONS - You agree that You will not export or re-export the SOFTWARE PRODUCT to any country, person, or entity subject to Canadian export restrictions. 5. CHOICE OF LAW - This Software License Agreement is governed by the laws of the Province of Ontario, Canada. 6. ARBITRATION - All disputes arising in connection with this Agreement shall be determined by final and binding arbitration in accordance with the Arbitration Act, and the parties agree to be bound by the arbitrator’s decision. The place of arbitration shall be Toronto, Canada, and the language of the arbitration shall be English. 7. LIMITED WARRANTY (a) NO WARRANTY - DSC PROVIDES THE SOFTWARE “AS IS” WITHOUT WARRANTY. DSC DOES NOT WARRANT THAT THE SOFTWARE WILL MEET YOUR REQUIREMENTS OR THAT OPERATION OF THE SOFTWARE WILL BE UNINTERRUPTED OR ERROR-FREE. (b) CHANGES IN OPERATING ENVIRONMENT - DSC shall not be responsible for problems caused by changes in the operating characteristics of the HARDWARE, or for problems in the interaction of the SOFTWARE PRODUCT with non-DSC-SOFTWARE or HARDWARE PRODUCTS. (c) LIMITATION OF LIABILITY; WARRANTY REFLECTS ALLOCATION OF RISK - IN ANY EVENT, IF ANY STATUTE IMPLIES WARRANTIES OR CONDITIONS NOT STATED IN THIS LICENSE AGREEMENT, DSC’S ENTIRE LIABILITY UNDER ANY PROVISION OF THIS LICENSE AGREEMENT SHALL BE LIMITED TO THE GREATER OF THE AMOUNT ACTUALLY PAID BY YOU TO LICENSE THE SOFTWARE PRODUCT AND FIVE CANADIAN DOLLARS (CAD$5.00). BECAUSE SOME JURISDICTIONS DO NOT ALLOW THE EXCLUSION OR LIMITATION OF LIABILITY FOR CONSEQUENTIAL OR INCIDENTAL DAMAGES, THE ABOVE LIMITATION MAY NOT APPLY TO YOU. (d) DISCLAIMER OF WARRANTIES - THIS WARRANTY CONTAINS THE ENTIRE WARRANTY AND SHALL BE IN LIEU OF ANY AND ALL OTHER WARRANTIES, WHETHER EXPRESSED OR IMPLIED (INCLUDING ALL IMPLIED WARRANTIES OF MERCHANTABILITY OR FITNESS FOR A PARTICULAR PURPOSE) AND OF ALL OTHER OBLIGATIONS OR LIABILITIES ON THE PART OF DSC. DSC MAKES NO OTHER WARRANTIES. DSC NEITHER ASSUMES NOR AUTHORIZES ANY OTHER PERSON PURPORTING TO ACT ON ITS BEHALF TO MODIFY OR TO CHANGE THIS WARRANTY, NOR TO ASSUME FOR IT ANY OTHER WARRANTY OR LIABILITY CONCERNING THIS SOFTWARE PRODUCT. (e) EXCLUSIVE REMEDY AND LIMITATION OF WARRANTY - UNDER NO CIRCUMSTANCES SHALL DSC BE LIABLE FOR ANY SPECIAL, INCIDENTAL, CONSEQUENTIAL OR INDIRECT DAMAGES BASED UPON BREACH OF WARRANTY, BREACH OF CONTRACT, NEGLIGENCE, STRICT LIABILITY, OR ANY OTHER LEGAL THEORY. SUCH DAMAGES INCLUDE, BUT ARE NOT LIMITED TO, LOSS OF PROFITS, LOSS OF THE SOFTWARE PRODUCT OR ANY ASSOCIATED EQUIPMENT, COST OF CAPITAL, COST OF SUBSTITUTE OR REPLACEMENT EQUIPMENT, FACILITIES OR SERVICES, DOWN TIME, PURCHASERS TIME, THE CLAIMS OF THIRD PARTIES, INCLUDING CUSTOMERS, AND INJURY TO PROPERTY. WARNING: DSC recommends that the entire system be completely tested on a regular basis. However, despite frequent testing, and due to, but not limited to, criminal tampering or electrical disruption, it is possible for this SOFTWARE PRODUCT to fail to perform as expected. FCC Compliance Statement This equipment generates and uses radio frequency energy and if not installed and used properly, in strict accordance with the manufacturer’s instructions, may cause interference to radio and television reception. It has been type tested and found to comply with the limits for Class B device in accordance with the specifications in Subpart “B” of Part 15 of FCC Rules, which are designed to provide reasonable protection against such interference in any residential installation. However, there is no guarantee that interference will not occur in a particular installation. If this equipment does cause interference to television or radio reception, which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one or more of the following measures: - Re-orient the receiving antenna - Relocate the alarm control with respect to the receiver - Move the alarm control away from the receiver - Connect the alarm control into a different outlet so the alarm control & receiver are on different circuits. If necessary, the user should consult the dealer or an experienced radio/television technician for additional suggestions. The user may find the following booklet prepared by the FCC helpful: “How to Identify and Resolve Radio/Television Interference Problems”. This booklet is available from the U.S. Government Printing Office, Washington, D.C. 20402, Stock # 004-000-00345-4. IC Statement This device complies with Industry Canada license-exempt RSS standard(s). Operation is subject to the following two conditions: (1) this device may not cause interference, and (2) this device must accept any interference, including interference that may cause undesired operation of the device. Le présent appareil est conforme aux CNR d'Industrie Canada applicables +HUHE\ '6& GHFODUHV WKDW WKLV GHYLFH LV LQ FRPSOLDQFH ZLWK WKH HVVHQWLDO aux appareils radio exempts de licence. L'exploitation est autorisée aux UHTXLUHPHQWVDQGRWKHUUHOHYDQWSURYLVLRQVRI'LUHFWLYH(& 7KH FRPSOHWH 577( 'HFODUDWLRQ RI &RQIRUPLW\ FDQ EH IRXQG DW deux conditions suivantes : (1) l'appareil ne doit pas produire de brouilKWWSZZZGVFFRPOLVWLQJVBLQGH[DVS[ &=( '6& MDNR Y¿UREFH SURKODģXMH ŀH WHQWR Y¿UREHN MH Y VRXODGX VH YģHPL lage, et (2) l'utilisateur de l'appareil doit accepter tout brouillage radiUHOHYDQWQ¯PLSRŀDGDYN\VPÝUQLFH(& '$1'6&HUNO¨UHUKHUYHGDWGHQQHNRPSRQHQWHQRYHUKROGHUDOOHYLNWLJHNUDYVDPW oélectrique subi, même si le brouillage est susceptible d'en compromettre DQGUHEHVWHPPHOVHUJLWWLGLUHNWLY(& '87 +LHUELM YHUNODDUW '6& GDW GLW WRHVWHO LQ RYHUHHQVWHPPLQJ LV PHW GH HLVHQ HQ le fonctionnement. EHSDOLQJHQYDQULFKWOLMQ(& ),1'6&YDNXXWWDDODLWWHHQW¦\WW¦Y¦QGLUHNWLLYLQ(&ROHQQDLVHWYDDWLPXNVHW This Class B digital apparatus meets all requirements of the Canadian )5( 3DU OD SU«VHQWH '6& G«FODUH TXH FH GLVSRVLWLI HVW FRQIRUPH DX[ H[LJHQFHV HVVHQWLHOOHVHWDXWUHVVWLSXODWLRQVSHUWLQHQWHVGHOD'LUHFWLYH(& interference-causing equipment regulations. *(5+LHUGXUFKHUNO¦UW'6&GD¡GLHVHV*HU¦WGHQHUIRUGHUOLFKHQ%HGLQJXQJHQXQG Cet appareil numérique de la Classe B respecte toutes les exigences de 9RUUDXVHW]XQJHQGHU5LFKWOLQLH(&HQWVSULFKW *5(˂˜˞˱ˬ˲˭˞ˮ˹˪˱ˬ˯ˤ'6&ˡˤ˨˻˪ˢ˦˹˱˦˞˲˱˛ˤ˰˲˰˧ˢ˲˛ˢ˜˪˞˦˰˺˩˳˶˪ˤ˩ˢ˱˦˯ règlement sur le matériel brouilleur du Canada. ˬ˲˰˦˻ˡˤ˯˞˭˞˦˱˛˰ˢ˦˯˧˞˦˩ˢ˹˨ˢ˯˱˦˯˙˨˨ˢ˯˰˴ˢ˱˦˧˚˯˞˪˞˳ˬˮ˚˯˱ˤ˯ˍˡˤˠ˜˞˯(& ,7$ &RQ OD SUHVHQWH OD 'LJLWDO 6HFXULW\ &RQWUROV GLFKLDUD FKH TXHVWR SURGRWWR ª IC:160A-HS2HOST9. FRQIRUPH DL UHTXLVLWL HVVHQ]LDOL HG DOWUH GLVSRVL]LRQL ULOHYDQWL UHODWLYH DOOD 'LUHWWLYD &( The term ‘IC:’ before the radio certification number only signifies that 125'6&HUNO¨UHUDWGHQQHHQKHWHQHULVDPVYDUPHGGHJUXQQOHJJHQGHNUDYRJ ºYULJHUHOHYDQWHNUDYLGLUHNWLY() Industry Canada technical specifications were met. 32/'6&RĝZLDGF]DľHXU]ÇG]HQLHMHVWZ]JRGQRĝFL]]DVDGQLF]\PLZ\PDJDQLDPL RUD]SR]RVWDĄ\PLVWRVRZQ\PLSRVWDQRZLHQLDPL'\UHNW\Z\:( 3253RUHVWHPHLRD'6&GHFODUDTXHHVWHHTXLSDPHQWRHVW£HPFRQIRUPLGDGH FRP RV UHTXLVLWRV HVVHQFLDLV H RXWUDV GHWHUPLQD©·HV UHOHYDQWHV GD 'LUHFWLYD (& 63$3RUODSUHVHQWH'6&GHFODUDTXHHVWHHTXLSRHVW£HQFRQIRUPLGDGFRQORV UHTXLVLWRVHVHQFLDOHV\RWURVUHTXLVLWRVUHOHYDQWHVGHOD'LUHFWLYD(& 6:('6&EHNU¦IWDUK¦UPHGDWWGHQQDDSSDUDWXSSI\OOHUGHY¦VHQWOLJDNUDYHQRFK DQGUDUHOHYDQWDEHVW¦PPHOVHUL'LUHNWLYHW(& EU Compliance Statement The Model HSM2HOST8 Wireless Transceiver has been certified by Telefication according to EN50131-1:2006 + A1:2009 and EN50131-3:2009, for Grade 2, Class II. Note: For EN50131 compliant installations only, the intrusion portion of the alarm system has been investigated. Fire Alarm and Auxiliary (Medical) Alarm functions were not included in the evaluation of this product under the requirements of the above mentioned standards. © 2015 Tyco Security Products. All Rights Reserved. www.dsc.com The trademarks, logos, and service marks displayed on this document are registered in the United States [or other countries]. Any misuse of the trademarks is strictly prohibited and Tyco will aggressively enforce its intellectual property rights to the fullest extent of the law, including pursuit of criminal prosecution wherever necessary. All trademarks not owned by Tyco are the property of their respective owners, and are used with permission or allowed under applicable laws. Product offerings and specifications are subject to change without notice. Actual products may vary from photos. Not all products include all features. Availability varies by region; contact your sales representative.