SPEC SHEET Easily add annunciator output relays to panels Model 860 Relay Output Module includes one relay and provides three additional sockets allowing expansion of up to four relays. These relays can be used for: • Electrical isolation between the alarm panel and other systems • Switching voltage to control various functions The 860 is compatible with all DMP Command Processor™ Panels. 860 RELAY OUTPUT MODULE SYSTEM FEATURES • Mounts in panel enclosure • Simple 4-wire harness connection to panel • Module operates from panel keypad bus power • Provides one Form C (SPDT) relay (expandable to four) • Relay contact wiring connects to high quality terminal blocks for secure, long-lasting connections • Designed, engineered, and assembled in the USA 860 MODULE INSTALLATION The 860 mounts inside a Command Processor™ panel enclosure using the standard 3-hole pattern. Plastic standoffs are provided with the module for easy installation. A 4-wire harness is also provided that connects the Model 860 to the DMP panel. SYSTEM SPECIFICATIONS Primary Power 12 VDC Current Draw for 1 Relay 34mA for 2 Relays 69mA for 3 Relays 104mA for 4 Relays 138mA Contact Rating 2 Amps @ 30 VDC Wire Gauge 12 to 22 AWG ACCESSORIES Model 305 Form C Relay COMPATIBILITY XR5FC/SL, XRSuper6, XR20, XR40, XR500 Series, and XR2500F Command Processor™ Panels 800 - 641 - 4282 ORDER INFORMATION The 860 comes from the factory with one installed relay, three plastic mounting standoffs, one 4-wire harness assembly, and one Installation Sheet (LT-0484). Three additional Model 305 Form C (SPDT) relays can be purchased separately. LISTINGS AND APPROVALS Underwriters Laboratories (UL) Listed UL 294 Access Control System Units UL 365 Police Station Alarm Units UL 609 Local Burglary Alarm Units and Systems UL 864 Control Units for Fire-Protective Signaling Systems UL 985 Household Fire Warning System Unit UL 1076 Proprietary Burglary Alarm Units and Systems UL 1076 Proprietary Alarm Units UL 1610 Central Station Burglary Alarm Units UL 1635 Digital Alarm Communicator System Units California State Fire Marshal (CSFM) INTRUSION • FIRE • ACCESS • NETWORKS www.dmp.com 2500 North Partnership Boulevard Made in the USA S p r i n g fi e l d , M i s s o u r i 6 5 8 0 3 - 8 8 7 7 LT-0485 (9/06) © 2006 Digital Monitoring Products, Inc. OPERATION Each relay on the 860 Module is controlled by the panel’s open collector annunciator outputs that switch the relay coil voltage to ground. Power is supplied to the relay coils from the panel’s keypad bus. The annunciator outputs can be programmed to respond to various system conditions such as communication failures, entry and exit timers, alarms, armed area annunciation, and more.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project