INSTALLATION AND SAFETY INSTRUCTIONS FIGURE 1 *NOT SUPPLIED BACKPLATE (A) GLASS SUPPORT BRACE (D) *OUTLET BOX GLASS (E) FIGURE 2 *WIRE CONNECTOR GROUND WIRE CAP NUTS (R) *OUTLET BOX SCREWS GLASS SUPPORT BRACE (D) FOR YOUR SAFETY WARNING: BE SURE THE ELECTRICITY TO THE WIRES YOU ARE WORKING ON IS SHUT OFF. EITHER THE FUSE REMOVED OR THE CIRCUIT BREAKER OFF . GENERAL You don’t need special tools to install this fixture. Be sure to follow the steps in the order given. Read instructions carefully. If you are unclear as to how to proceed, consult a qualified electrician. NOTE: Proper wiring is essential for the safe operation of this fixture. GLASS (E) FIGURE 3 ASSEMBLY Carefully remove the fixture from the carton and check that all parts are included, as shown in Figure 1, 2 & 3. Be careful not to misplace any of the screws or parts which are needed to install this fixture. STEP 1 Remove glass support brace (D) from backplate (A). STEP 2 Install glass through support brace (D). NOTE: FOR FIXTURES PROVIDED WITH 75˚C OR 90˚C SUPPLY WIRE WARNING ONLY-(THESE WARNINGS ARE PROVIDED ON THE U.L. LABEL AND ON THE FIXTURE CARTON): RISK OF FIRE. MOST DWELLINGS BUILT BEFORE 1985 HAVE SUPPLY WIRE RATED 60˚C. CONSULT A QUALIFIED ELECTRICIAN BEFORE INSTALLING. Installation And Safety Instruction HC-844 022205 Fill In Item Number On Carton And File This Sheet For Fixture Reference. ITEM#_______________ INSTALLATION HC-844 STEP 1: Punch out appropriate holes in backplate [A], if applicable, to correspond with holes in outlet box. STEP 2: Push socket wires thru plastic bushing (If applicable). STEP 3: A. Take note of the color of the wire(s) on your fixture. Identify which group your fixture wire(s) falls into and connect the wires according to the directions below: STEP 4: GROUNDING INSTRUCTIONS: Wrap the ground wire from the fixture (if supplied) and the ground wire from the outlet box (bare metal or green insulated wire) around the green grounding screw on the back plate (A); (Or if applicable).The green grounding screw is to be inserted into the hole with two raised dimples provided on the back plate (A). NOTE: Underwriters Laboratories (U.L.) does not require all fixtures to have ground wires. These fixtures still meet all U.L. specifications. The listing mark of Underwriters on the product identifies products manufactured under its listing and Follow-Up Service Programs. NEVER CONNECT GROUND WIRE TO BLACK OR WHITE POWER SUPPLY WIRES. FINAL ASSEMBLY Make sure no bare wires can be seen outside wire connectors. STEP 1: Tuck wires into outlet box. Attach backplate (A) to outlet box by placing outlet box screws (not supplied) through punched out holes in backplate (A). STEP 2: Install lamp. GROUP A: CONNECT TO BLACK HOUSE WIRE BLACK GROUP B: CONNECT TO WHITE HOUSE WIRE WHITE STEP 3: Secure support brace (D) and glass (E) to backplate with cap nuts (R). CLEANING B. Take your fixture wire(s) from group A and place evenly against the black wire from the outlet box. Do Not twist wires together before using wire connectors. C. Fit a wire connector (not supplied) over the wires and screw the connector clockwise until you feel a firmness. D. Try gently to pull the connector off the wires. If you can pull the connector off, carefully re-do steps B and C, as above, and check again for a firm connection. E. Connect the fixture wire from group B to the white wire from the outlet box in the same manner. To clean, wipe fixture with a soft cloth. Clean glass with a mild soap. Do not use abrasive materials such as scouring pads or powders, steel wool or abrasive paper. ORDERING PARTS Keep this sheet for future reference, and in case you need to order replacement parts. All parts for this fixture can be ordered from place of purchase. Be sure to use exact wording from illustration when ordering parts.