Installing Multiple Management Cards Overview When installing more than one APC management card, you must install the cards in the order described in this document because they share a serial link with the connected UPS. Installing the cards in any other order may result in failure for them to operate properly. Before you start The following table identifies the priority of the management cards you will be installing. Management cards that have more control over the UPS have higher priority. • Level 6: Exerts total control • Level 5: Exerts wide, but not total, control • Level 4: Exerts limited control • Level 3: Passes commands to the UPS • Level 2: Exerts no control • Level 1: Exerts no control and must be installed closest to the UPS Management Card Priority Network Management Card1 (AP9617, AP9618, AP9619, AP9630, AP9631) Level 6 Out-of-Band Management Card (AP9608) Level 5 Relay I/O Module (AP9610) Level 4 Interface Expander Card (AP9607) Level 3 Building Management Integration Card2 (AP9622) Level 2 Environmental Monitoring Card (AP9612TH) Level 1 1. Attach no more than two Network Management Cards to a UPS. 2. Attach only one Building Management Integration Card to a UPS. Two models of expansion chassis If you need management card slots in addition to those in your UPS, use one or more expansion chassis available from APC. Chassis Compatible UPSs Expansion Chassis (AP9600), one slot APC UPSs that are not installed in a rack or enclosure. Triple Expansion Chassis (AP9604BLK), three slots All APC UPSs Installing cards in an expansion chassis Install the lowest-priority cards in any available card slots in the UPS, and then use an expansion chassis for remaining higher-priority cards. In a Triple Expansion Chassis: • Install each card, starting with the lowest priority (see “Before you start” on page 1) in the lowest-numbered slot. • If you are installing a Network Management Card, install it in slot 3, even if you are leaving another slot empty. 2 1 GND Sensor Zones 1 2 3 2 Probes 4 1 3 2 Monitoring Port 3 USB Management Port U niv ers al I /O U niv ers al I /O 24 VDC To UPS Config AP9612TH Environmental Monitoring Card AP9608 Out-of-Band Management Card Power Network Status – – + Reset Smart Slot 10/100 A P963 1 Network Management Card 2 Status mph0461 1 Installing cards in expansion chassis set up serially If you have increased your management card capacity by connecting multiple expansion chassis serially (in a cascading setup), install the Network Management Card in the highest-numbered slot, and the Out-of-Band Management Card in the second-highest-numbered slot of the chassis installed farthest from the UPS. Warning: Do not attach more than two Network Management Cards or one Building Management Integration Card to a UPS. If the Network Management Card is pre-installed in the UPS, refer instead to “When a management card has been pre-installed” on page 4. 2 Installing Multiple Management Cards Installing cards in a Symmetra UPS If you are installing a Network Management Card without an attached expansion chassis, install that card in the highest numbered slot, even if you are leaving other slots empty. If you are using an expansion chassis, see “Installing cards in an expansion chassis” on page 2. For Symmetra models with 4, 3, or 2 slots, install each card, starting with the lowest priority (as listed in the table on page 1) in the lowest numbered slot. Use the following illustrations to determine model-specific slot numbering. AP9612TH Environmental Monitoring Card 4 1 Probe s 2 AP9607 UPS Interfac e Expander 3 2 mph0462 C onfig GND 1 Se nsor Zones TM Config 0 1q 1234 2 USB 1 Basic Monitoring Ports Status AP9608 Out-of-Band Management Card Sma rt Slot Management Port R es et A P 9631 Network Management Card 2 Network 10/100 Universal I/O Universal I/O Interface Comm. Display q Computer Comm. 1 Comm. 2 Battery Communications • When 4 slots are available, arranged in a horizontal row, the lowest-numbered slot is at the right. • When slots are arranged in a vertical column: – If 3 slots are available, the lowest-numbered slot is at the top (as shown in the following illustration). – If 2 slots are available, the lowest-numbered slot is at the bottom (as shown in the following illustration). Probe s Sensor Zone s GND 1 2 3 4 1 2 AP9612TH Environmental Monitoring Card Management Port USB Universal I/O Universal I/O Network Status C onfig Universal I/O Universal I/O Smart Slot Network A P 963 1 N etw ork M anagement Card 2 Management Port Status C onfig R eset 10/100 Smart Slot A P 963 1 N etw ork M anagement Card 2 AP9608 Out-of-Band Management Card Installing Multiple Management Cards mph0463a USB R eset 10/100 AP9608 Out-of-Band Management Card 3 When a management card has been pre-installed For Symmetra UPS models that are shipped with a Network Management Card already installed (such as Symmetra RM models), the UPS itself may have only one remaining card slot available. Referring to the table on page 1, install the lowest priority card in the UPS and use one or more expansion chassis for any other cards, as described beginning on page 2. To use an Out-of-Band Management Card, install it in the highest-numbered slot of the expansion chassis farthest from the UPS. Customer support and warranty information is available at the APC Web site, www.apc.com. © 2010 APC by Schneider Electric. All trademarks are owned by Schneider 990-0231G-001 Electric Industries S.A.S., American Power Conversion Corporation, or 5/10 their affiliated companies.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project