Valve Body Installation FV217.BASE 3/4” rough mixer unit for thermostatic set (COLD) Mark indicates COLD side Remove these parts after installation Plastic cover Template (HOT) Mark indicates HOT side Plug to close off either top or bottom outlet IMPORTANT NOTE: Make sure to mount this valve adapter to the stem of the valve body. (This is packaged separately in valve box) Rough Valve Installation Guide *Align the valve so the HOT side is facing you on the left, COLD on the right. Hot and Cold sides are marked on the valve body. *You may use the top or bottom outlet when connecting your volume control, but not both. Use the plug provided to close off the outlet not used. If you are using multiple volume control valves, they all must branch off the main line. *Mount valve to cross support using shims and screws (not included) between wall studs. Use the valves protective cover to determine the placement of the cross support. *Use the provided plastic valve cover as your rough-in guide. This guide will show you the distance necessary for proper placement of the valve in relation to the finish wall. This step will insure that trim cover and handle will fit at the end of your installation. Measurement Shim NPT 3/4” Max (2 Min 1/8”) (1 5/8”) Plastic cover/ finished wall indicator DO NOT TURN Cartridge stem (It has been calibrated at our factory to the proper position) Plug NPT 3/4” Finished wall Replacement parts This cartridge is designed for a minimun of maintenance in normal domestic use. If malfunctioning occurs, a complete cartridge replacement is necessary. The cartridge has not internally serviceable parts. If replacement parts are required, contact your installer or dealer. Connecting Water Supply 1_Thoroughly flush supply lines to remove any debris, metallic shavings, flux, etc. 2_Shut off water supply to valve. 3_Hot and Cold water supplies MUST be connected to designated sides for proper operation of valve. 4_If solder/brazing connections, pre-assemble hot & cold adapters (not provided) to copper piping. Use Teflon tape or equivalent to connect adapters inlet port. IMPORTANT: All excessive heat shall be a minimun of 4” from valve. 5_Connect outlet pipe to stop valve/volume control (not included). 6_Connect stop valve pipe to various end devices. 7_Turn on water supply to valve and check for leaks. Outlet pipe for shower connection Cold water supply Hot water supply DO NOT TURN Cartridge stem (It has been calibrated at our factory to the proper position) FV S.A. & FVA reserve the right to make revisions without notice in the design of faucets and bathroom accessories or in packaging. FV S.A. se reserva el derecho de introducir mejoras y/o modificaciones de diseño según convenga, sin previo aviso. FOLFV217.BASE / Edition No 1 _ June, 2010.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project