Safety Stations with Eyewash F G1902P Safety Station with Eyewash, Plastic Bowl Application: Combination eyewash and shower safety station. Two GS-Plus™ spray-type outlet heads deliver a flood of water for rinsing eyes. Shower Head: 10" diameter orange ABS plastic. Shower Valve: 1" IPS chrome plated brass stay-open ball valve. Valve is US-made with chrome plated brass ball and Teflon® seals. Furnished with stainless steel actuating arm and 29" stainless steel pull rod. Spray Head Assembly: Two GS-Plus™ spray heads. Each head has a “flip top” dust cover, internal flow control and filter to remove impurities from water. Eyewash Bowl: 11-1/2" ABS plastic. Eyewash Valve: 1/2" IPS chrome plated brass stay-open ball valve. Valve is US-made with chrome plated brass ball and Teflon® seals. Pipe and Fittings: Schedule 40 galvanized steel. Furnished with orange polyethylene covers for vertical piping for high visibility and corrosion resistance. Supply: 1-1/4" NPT female top or side inlet. Waste: 1-1/4" NPT female outlet. Outlet can be positioned at either 9-1/4" or 19-5/8" above finished floor by reversing lower pipe nipples. Sign: Furnished with ANSI-compliant identification sign. Quality Assurance: Valve and spray head assemblies are factory assembled and water tested prior to shipment. Available Options F GC Powder coated finish on galvanized Pipe and Fittings:. Available colors include orange, yellow, red and green. F FC20 Regulates shower flow rate to 20 GPM. F GRN Green ABS plastic shower head and bowl. F YEL Yellow ABS plastic shower head and bowl. F SSH Stainless steel shower head. F AP275-100 Electric Light and Alarm Horn Light and alarm horn summon assistance when eyewash or shower is activated. F AP250-015 Modesty Curtain Modesty curtain for mounting on safety station. F TMV G3800LF thermostatic mixing valve precisely blends hot and cold water to deliver warm (tepid) water as required by ANSI Z358.1-2014. Guardian Equipment 1140 N North Branch St Chicago, IL 60642 312 447 8100 telephone 312 447 8101 facsimile gesafety.com UPC listed 8116. ETL listed 101496. Units have been tested to and comply with ANSI Z358.1-2014. Safety Stations with Eyewash F G1902P Safety Station with Eyewash, Plastic Bowl 5 3/4" (146mm) 1" IPS CHROME PLATED BRASS STAY-OPEN BALL VALVE 24" (610mm) STAINLESS STEEL ACTUATING ARM 1-1/4" NPT FEMALE INLET ABS PLASTIC SHOWER HEAD AND ELBOW 29" (737mm) Ø10" (254mm) 23 1/2" (597mm) NOTES: 1. EACH GS-PLUS SPRAY HEAD HAS A "FLIP-TOP" DUST COVER, INTERNAL FLOW CONTROL AND FILTER TO REMOVE IMPURITIES FROM THE WATER FLOW. 2. REVERSING THE TWO LOWEST PIPE NIPPLES RAISES THE DRAIN OUTLET TO 19-5/8" A.F.F. 89" (2261mm) STAINLESS STEEL PULL ROD 84" (2134mm) GALVANIZED STEEL PIPE AND FITTINGS 64 3/4" (2) GS-PLUS SPRAY HEADS 11 3/4" (299mm) ABS PLASTIC BOWL 6 1/2" (165mm) 1-1/4" NPT FEMALE INLET (PLUGGED) (1645mm) 1/2" IPS CHROME PLATED BRASS STAYOPEN BALL VALVE POWDER-COATED CAST ALUMINUM FLAG HANDLE 5" (127mm) 6" (152mm) DETAIL "A" UNIVERSAL FLOOR FLANGE 9 1/4" POWDER COATED CAST ALUMINUM FLOOR FLANGE (SEE DETAIL "A") 37 1/2" (953mm) (235mm) Ø7/16" MOUNTING SLOTS ON 7-5/8" BOLT CIRCLE 9 1/4" (235mm) Ø9" (229mm) this space for architect/engineer approval 1-1/4" NPT FEMALE OUTLET Sign Included Due to continuing product improvement, the information contained in this document is subject to change without notice. All dimensions are ± 1/4" (6mm). rev. 0615 Guardian Equipment 1140 N North Branch St Chicago, IL 60642 312 447 8100 telephone 312 447 8101 facsimile gesafety.com UPC listed 8116. ETL listed 101496. Units have been tested to and comply with ANSI Z358.1-2014.