Delta UPS – Agilon Family VX Series, Line-interactive No. Item 1 LED Indicator (Only For 600VA Model) LCD Touch Panel (Only For 1000VA/ 1500VA Model) 600-1500 VA 2 Installation & Operation Quick Guide 3 ENGLISH 1 Package Inspection No. ON/ OFF Button Output Socket 4 AC Input 5 Fuse 6 USB Port 7 Cooling Fan (Only For 1500VA Model) yyConnect to Utility Power Q'ty 1 UPS 1 PC 2 Quick Guide 1 PC 3 USB Cable 1 PC Connect the AC power cord to the utility power. Then, the UPS will start to charge its inside battery (batteries). For best result, charge the battery (batteries) for 6 hours prior to initial use. It is not recommended to connect the UPS’s AC power cord to any generator. Remove the UPS from its package and inspect it for damage that may have occurred during shipping. If any damage is discovered, re-pack the unit and return it to the place of purchase. yyPlug in Equipment Plug your equipment to the Output Socket on the rear panel of the UPS. WARNING: 1. Make sure that the UPS is powered on to protect all important devices from data loss during power failure. 2. NEVER connect a laser printer or scanner to the Output Socket of the UPS. The equipment may draw significant power to overload the UPS. 2 Front Panel & Rear Panel 600VA (Front Panel) (Rear Panel) 2 4 LED Indicator (Only For 600VA Model) Item 3 Operation Item 1 No. yyConnect to USB Port and Install Software 6 5 4 3 Connect one end of the supplied USB cable to your PC and the other to the USB port located at the rear of the UPS. Download the latest version of ViewPower software (http://www.deltapowersolutions.com/en/mcis/600va1500va-single-phase-ups-vx-series-software-download.php) to your hard drive. Follow on-screen instructions to complete the software installation. yyTurn On/ Off the UPS 1000VA (Front Panel) When the UPS is OFF, press the ON/ OFF Button to turn on the UPS and the LED/ LCD will be on. When the UPS is ON, press the ON/ OFF Button to turn off the UPS and the LED/ LCD will shut off. (Rear Panel) 1 6 2 4 Alarm ON OFF ON Sounds all the time Flashing Sounds every 10 seconds Flashing Sounds every second OFF OFF (Front Panel) When the UPS always runs in battery mode, it might be because the fuse is damaged. If yes, please follow the following procedures to replace the fuse. 3 Remove the fuse cover from the rear panel. 2 7 UPS Mode 2 Replace the original fuse 1 with the provided backup fuse 3 2 . (Install) 2 (Take Out) 3 www.deltapowersolutions.com Low battery. The UPS is off. LCD Touch Panel LCD information will be displayed in the following order when the LCD is touched. AC Mode When AVR is functioning, icon will flash every second. Overload In AC Mode Put the fuse cover back to the rear panel. Description When the UPS is powered on, it will enter this mode for 4 seconds. UPS Power On icon will flash. Battery Mode Overload In Battery Mode (Fuse Cover) 1 5 Power failure occurs and the UPS runs in battery mode. When battery level is low, icon will flash. 6 4 UPS fault. yyOperation Display: (1500VA) (Rear Panel) 1 The main AC power is normal and the UPS runs normally. 5 LCD Display (Only For 1000VA/ 1500VA Model) (Pull) 1500VA UPS Status yyFuse Replacement 1 5 LED icon will flash. 1. Output voltage 2. Input voltage 3. Load level 4. Battery capacity When overload occurs, alarm will beep every 0.5 second. Alarm will beep every 10 seconds and LCD information will be displayed in the following order when the LCD is touched. 1. Output voltage 2. Input voltage 3. Load level 4. Battery capacity When overload occurs, alarm will beep every 0.5 second. NOTE: If backlight shuts off, you can activate it by touching the screen. Continue to the Next Page yyFault Code Table: Fault Condition yyA battery can present a risk of electrical shock and high short circuit curLCD Touch Panel Solutions Output Short Circuited Disconnect short-circuited loads and restart the UPS again. Overload Fault Disconnect all output loads and restart the UPS again. Over Charge Fault Call for service immediately. Battery Too Low Fault Please replace the battery (batteries). Battery Mode Output High Fault Call for service immediately. Over Temperature 1. Turn off the UPS and wait for cooling. 2. Or remove excessive loads and wait for cooling. If any fault alarm occurs, please call for service immediately. 6 Safety Caution SAVE THESE INSTRUCTIONS-This quick guide contains important instructions that should be followed during installation and maintenance of the UPS and battery (batteries). yyThe UPS utilizes voltage that may be hazardous. Do not attempt to disassemble the unit. The unit contains no user replaceable parts. Only factory service personnel may perform repairs. yyThis pluggable type A equipment with battery (batteries) already installed by the supplier is operator installable and may be operated by laymen. yyThe mains socket outlet that supplies the UPS shall be installed near the UPS and shall be easily accessible. yyDuring the installation of this equipment it should be assured that the sum of the leakage current of the UPS and the connected loads does not exceed 3.5mA. yyConnection to any other type of receptacle other than a two-pole, three- wire grounded receptacle may result in shock hazard as well as violate local electrical codes. yyIn the event of an emergency, press the ON/ OFF Button and disconnect the power cord from the AC power supply to properly disable the UPS. yyDo not allow any liquid or any foreign object to enter the UPS. Do not place beverages or any other liquid-containing vessels on or near the unit. yyThe unit is intended for installation in a controlled environment (tempera- ture controlled, indoor area free of conductive contaminants). Avoid installing the UPS in any location where there is standing or running water, or excessive humidity. yyDo not plug the UPS input into its own output. yyDo not attach a power strip or surge suppressor to the UPS. yyDo not attach non-computer-related items, such as medical equipment, life-support equipment, microwave ovens, or vacuum cleaners to the UPS. yyDo not dispose of battery (batteries) in a fire as they may explode. yyDo not open or mutilate the battery or batteries. Release electrolyte is harmful to the skin and eyes. It may be toxic. www.deltapowersolutions.com rent. The following precautions should be observed when working on batteries: 1. Remove watches, rings, or other metal objects from the hands. 2. Use tools with insulated handles. 3. Wear rubber gloves and boots. 4. Do not lay tools or metal parts on top of battery (batteries). 5. Disconnect charging source prior to connecting or disconnecting the terminals of battery (batteries). 6. Remove battery grounds during installation and maintenance to reduce likelihood of shock. Remove the connection from ground if any part of the battery is determined to be grounded. yyInternal battery voltage is 12Vdc. Battery type is sealed, lead-acid, 6-cell battery. yyServicing of batteries should be performed or supervised by personnel knowledgeable of batteries and the required precautions. Keep unauthorized personnel away from batteries. 8 Technical Specifications Model Capacity yyUnplug the UPS prior to cleaning and do not use liquid or spray detergent. 7 Troubleshooting Problem LED doesn’t illuminate or nothing is displayed on the LCD panel. The UPS always runs in battery mode. The UPS continuously beeps. Backup time is too short. Possible Cause Solutions The UPS is not on. Press the ON/ OFF Button again to turn on the UPS. Battery voltage is too low. Charge the battery (batteries) at least 6 hours. Battery fault. Replace the battery (batteries). The power cord becomes loose. Re-plug the power cord. Replace the fuse. For how to The fuse is damaged. replace the fuse, please refer to 3 Operation . 1kVA/600W 1.5kVA/900W 230 Vac 170 ~ 280 Vac 230 Vac ± 10% (Bat. mode) Transfer Time Typical 2 ~ 6 ms Waveform Battery Type & No. Simulated Sine Wave 12V/7Ah x 1 Charging Time Net Weight (kgs) vents and avoid exposing the unit to direct sunlight or installing the unit near heat emitting appliances such as heaters or furnaces. 600VA/360W Output Voltage yyAttention! Hazardous through electric shock. Even disconnection of this yyTo reduce the risk of overheating the UPS, do not cover the UPS’s cooling 1500VA Input Voltage Range Dimensions (D x W x H) unit from the mains, hazardous voltage still may be accessible through supply from the battery (batteries). The battery supply should be therefore disconnected in the plus and minus pole at the connectors of the battery (batteries) when maintenance or service work inside the UPS is necessary. 1000VA Nominal Input Voltage yyWhen replacing battery (batteries), replace with the same number and type of sealed lead-acid battery (batteries). 600VA 12V/7Ah x 2 12V/7Ah x 2 Typical 6 ~ 8 hours 279 x 101 x 142 mm Humidity Noise Level 4.2 320 x 130 x 182 mm 8.2 10.4 0 - 90% RH @ 0 - 40°C (non-condensing) Less than 40dB Less than 45dB * Specifications are subject to change without notice. 9 Warranty Seller warrants this product, if used in accordance with all applicable instructions, to be free from original defects in material and workmanship within the warranty period. If the product has any failure problem within the warranty period, Seller will repair or replace the product at its sole discretion according to the failure situation. This warranty does not apply to normal wear or to damage resulting from improper installation, operation, usage, maintenance or irresistible force (i.e. war, fire, natural disaster, etc.), and this warranty also expressly excludes all incidental and consequential damages. Maintenance service for a fee is provided for any damage out of the warranty period. If any maintenance is required, please directly contact the supplier or Seller. WARNING: The individual user should take care to determine prior to use whether the environment and the load characteristic are suitable, adequate or safe for the installation and the usage of this product. The Quick Guide must be carefully followed. Seller makes no representation or warranty as to the suitability or fitness of this product for any specific application. Please check the Fault Code Table for the details. Please check the Fault Code Table for the details. Battery voltage is too low. Charge the battery (batteries) at least 6 hours. Overload. Remove some unnecessary loads. Before reconnecting equipment, please verify that the load matches the UPS capability specified in the specs. Copyright © 2017 by Delta Electronics Inc. All Rights Reserved. This Quick Guide is subject to change without prior notice. Battery defect. Replace the battery (batteries). Version Date : 2017_08_16 If any abnormal situations occur that are not listed above, please call for service immediately. WARNING: This is a category C2 UPS product. In a residential environment, this product may cause radio interference, in which case the user many be required to take additional measures.