Conventional Audible Visual Devices Sounders with supplementary light indicator > Product Overview KAC’s conventional Sounder Beacon is ideal for applications where a sounder is required as the primary method of alarm, but a supplementary light indicator would also be of benefit. The product features a new folded horn design, LED technology and advanced optics, providing outstanding sound output and supplementary light indication at very low current draw. The ENscape sounder beacon delivers outstanding quality, reliability and extended operational life, making it the ideal choice for a wide range of applications. ENscape Sounder Beacon Benefits > Simple, Fast, Flexible Installation Outstanding Performance • • • • • • • Modern design and aesthetics eliminates the need for device orientation. • First fix capability allows electrical continuity testing prior to device fitting. • Deep base option with multiple cable entries for flixible installations. • Designed with full range of common fixing centres. • Positive fit engagement & feedback of base with device for easy installation. Quality & Reliability Universal Device • • • Approved to EN54-3 for sound. Global tone set: 32 approved tones including bell tone. LED technology & advanced optics provides light indication at very low current draw. Synchronisation of flash and sound. Red or Amber light flash Operates on 12V and 24V systems, making the range suitable for use in security applications. • Suitable for wall and ceiling mount applications. Available in red or white body colours with red or amber lens. Range of installation and base options, for indoor and applications up to IP65. Independently approved to all relevant standards: - Manufacturing: Constructive Products Regulation (CPR) - Product performance: EN54-3 for sound - Environmental : RoHS, WEEE > Introducing the Range Approvals Body Colour Flash Colour Installation Options Lens Colour Environmental Compliance Device ENscape Sounder/Indicator EN54-23 EN54-3 Red White Red White Standard Device First Fix Red or Amber RoHS/ WEEE > This product is not approved to EN54-23 (Visual Alarm Device) and must not be used as a visual alarm device to provide a primary warning notification of fire. CAV-SIND Rev. No.2 Sounder Beacons – Technical Specification Electrical Specification Operating Voltage: Current consumption, average: Environmental Specification Operating Temperature: Relative Humidity: Ingress Protection: For RoHS & WEEE 12 to 29 VDC 22mA @ 29VDC (Tone 7) Mechanical Specification Body colour: Sound Output, maximum: Number of Tones: Red / White 107dB(A) @1m (Tone 23) 32 and includes a bell tone. -25°C to 70°C 93% ±3%, non condensing IP21C - low profile base IP65 – deep base Please visit www.kac.co.uk Dimensions Full tone table available on website & installation manual Volume setting: Synchronisation: Cable Terminal Size: Material Lens/Body: Gross Weight: Standard device: First Fix option: High or medium Automatically at power on 0.5 - 2.5mm² Flame retardant PC/ABS 236g (low profile), 242g (deep / IP65) Wiring Options 246g (low profile), 252g (deep / IP65) First Fix Device Standard Device Connections Out of Box Contents: Standard Device First Fix Option Deep / IP 65 Option Deep / IP 65 & First Fix Option Sounder beacon including selected base ü ü ü ü P pack (includes terminal block & continuity link) û ü û ü O Ring for IP65 Sealing û û ü ü Installation data sheet ü ü ü ü ENscape Sounder Beacon INSTALLATION INSTRUCTIONS FOR CONVENTIONAL WALL & CEILING MOUNT SOUNDER BEACON DIMENSIONS Shallow and Deep Base INSTALLATION 122mm 100mm STEP 1 98mm MODELS CWSS-xx-S3 = Sounder Beacon, Shallow Base, O Class CWSS-xx-S4 = Sounder Beacon, Shallow Base, O Class, First Fix CWSS-xx-S5 = Sounder Beacon, Shallow Base, W Class, C Class CWSS-xx-S6 = Sounder Beacon, Shallow Base, W Class, First Fix, C Class CWSS-xx-W3 = Sounder Beacon, Deep Base, O Class CWSS-xx-W4 = Sounder Beacon, Deep Base, O Class, First Fix CWSS-xx-W5 = Sounder Beacon, Deep Base, W Class, C Class CWSS-xx-W6 = Sounder Beacon, Deep Base, W Class, First Fix, C Class xx Denotes Body & Lens Colour TECHNICAL INFORMATION STEP 2 VOLTAGE RANGE (OPERATING) C/W Class 12-29 V VOLTAGE RANGE (EN54- 23) C/W Class approved at 1 - First stage wiring 2 - Second stage wiring INSTALLATION TIPS These products are universal devices suitable for wall & ceiling mount installations. 12-29 V MAX CURRENT CONSUMPTION C/W Class 101mA MAX POWER CONSUMPTION C/W Class These products are not designed for use with pulsed panel outputs. If more than 1 mode is required use the second stage tone. 2.9 W VOLTAGE RANGE (OPERATING) O Class 12-29 V VOLTAGE RANGE (EN54-23) O Class approved at VOLTAGE RANGE (EN54-3) 24-29 V 9-14V 18-29V MAX CURRENT CONSUMPTION O Class 51mA MAX POWER CONSUMPTION O Class 1.5 W No. OF STAGES + _ _ _ STEP 3 + _ Continuity link board. Drill out the required mounting and wiring holes in the rear of the base. Do not attempt to “knock-out” the holes with a screwdriver. First-fix option. Factory setting is Tone 1 at medium volume. 2 BEACON FLASH RATE 0.5Hz MONITORING Installation tools required: Pliers, Screwdriver, Drill. Reverse polarity RELATIVE HUMIDITY Accessories: SC076 = 5x Earth Strap, SC077 = 5x Terminal Block, SC078 = 5x Installer Link, P310 = 5x Deep Base O-Ring, P311 = 5x Deep Base Gasket, CSR = 5x Shallow BaseRed, CSW = 5x Shallow Base-White, CWW=5x IP65 Deep Base-White, CWR = 5x IP65 Deep Base-Red. Up to 93% (± 3%) - non condensing WIRE GAUGE FOR TERMINAL OPERATING TEMPERATURE 0.5mm2 - 2.5mm2 (max) -25 to +70oC VOLUME SETTINGS Volume setting is adjusted by switch 6 on the 6-way DIP switch on the bottom of the product. (See switch diagram overleaf). TONE SETTINGS See Tone Table on reverse. STEP 4 “click” The tone setting is selected by switches 1 to 5 on the 6-way DIP switch. The switch diagram and tone table are overleaf. The second stage tone is related to the first stage tone selection made via the DIP switch. The second stage is controlled by the fire panel and becomes active through the wiring configuration. BASES/IP RATING Shallow Base (IP21C) The sounder minimum voltage is limited to 12V to maintain beacon performance. WALL & CEILING MOUNT SOUNDER BEACON MODELS: CWSS-xx-S3, CWSS-xx-S4 CWSS-xx-S5, CWSS-xx-S6 CWSS-xx-W3 CWSS-xx-W4 CWSS-xx-W5 CWSS-xx-W6 1 STEP 5 If the Deep Base IP65 option is used, the o-ring seal must be fitted to the base as shown. If required, the deep base gasket accessory can be installed between the base and the mounting surface. WARNING: Use extreme caution when adjusting the switches on the 6-way DIP switch. The switch contacts and exposed PCB can be affected by electro-static discharge. WARNING: Care must be taken when installing first-fix model types with the KAC continuity link board. DO NOT touch the exposed link board contacts as this may result in an electrical shock. 2 Deep Base (IP65) See installation step 3 for anti-tamper screw location. D 1101 Issue C Accessories: Low Profile Bases Deep Bases IP and Earthing Kits Electrical Items CSR – Red low profile base, pack of 5 CWR – Red deep / IP 65, pack of 5 PS 189 – Deep base gasket, pack of 5 SCO77- Terminal block, pack of 5 CSW – White low profile base, pack of 5 CWW – White deep / IP 65 base, pack of 5 PS 188 - Deep base O Ring, pack of 5 SCO78- Installer link, pack of 5 SC076 - Earth strap, pack of 5 Order Information: Code CWSS Body Colour R=Red W=White Flash Colour R=Red Base Option Install Option Lens Colour Example Part No. S=Low Profile 7=Standard Fix R=Red CWSS-RB-S7 W=IP65/Deep 8=First Fix A=Amber CWSS-WA-W8 > KAC Alarm Company Ltd KAC House, Thornhill Road, North Moons Moat, Redditch, B98 9ND, United Kingdom Tel: +44 (0) 1527 406655 Fax: +44 (0) 1527 406677 e-mail: email@example.com We reserve the right to amend the content of this document without prior notice.