For Germany, Austria and Switzerland October 2013 – Version 2 User Manual T8 LED Lamp Always have a qualified electrician to do your electrical work! Switch off power before starting the installation! Instructions for mounting: Schematic steps for removing a fluorescent lamp and inserting a double-capped LED lamp p.f.correction capacitor S 1 3 2 4 5 7 6 8 •Installation instructions (1) Switch off electricity. (2) and (3) Remove the conventional lamp. (4) and (5) Replace the old starter with the LED tube starter. (6) Insert the LED lamp into the lamp holder. (7) Secure it in position by turning the lamp 90˚. (8) Switch on electricity. ※ The overall energy efficiency and light distribution of installed lamps are determined by the design of the installation. ※ Existing power factor compensation capacitors worsen the power factor, but can remain within the light fitting. Environment: 0°C to +30°C ,<95% humidity ,no guarantee for water proof 600mm L-Tube suitable for G13 Base Socket Replacement: 600mm 10.0W to replace fluorescent lamp 18.0W Packing details: LED tube, LED starter, User manual Notice: This lamp is designed for general lighting service (excluding eg.explosive atmospheres) This LED tube is compatible with Magnetic ballast only. This lamp is not suitable for use in emergency light fittings designed for double-capped fluorescent lamps. Do not use this product in outdoor areas. For dry locations only - not for use where exposed to the weather. 50/60 Hz EL Warning: Any modification of the light fitting when installing the LED lamps is not permitted. Please do not install this Magnetic ballast compatible LED tube using a glow starter. Please do not install this Magnetic ballast compatible LED tube using a direct connection to an AC source. Please do not install this Magnetic ballast compatible LED tube using another independent LED driver. Please do not replace with a different type of LED tube! Risk of electrical shock! Please use only for a single lamp (do not install over a double lamp and above). Series connection is not permitted when installing this product. Do not use this product in outdoor areas. For dry locations only - not for use where exposed to the weather. Turn off power before installing or replacing lamp. Do not touch this product with wet hands. Do not look directly at the lamp when being used. Do not use in totally enclosed fixtures. Do not disassemble, repair or alter in any way. Model Name Power consumption Size SI-L8R10206Cxy SI-L8T10206Cxy SI-L8V10206Cxy 10.0W 10.0W 10.0W D28 x L604.0mm max D28 x L604.0mm max D28 x L604.0mm max CCT 5000K 4000K 3000K xy denotation : xy can be A-Z, standing for national/regional abbreviations eg. EU, CN, etc. EU – European Union Ballast Information:(One lamp) Warranty: Maker Helvar Helvar Vossloh & Schwabe Vossloh & Schwabe Vossloh & Schwabe Vossloh & Schwabe TRIDONIC ABB ABB Model Name L18A-K L18TL4 LN18.127 LN18.220 LN18.510 LN18.507 EC 18 LC111K VVG 18-059 CF28 18-059 CF55 The installation date must be documented to make a warranty claim. The Samsung Electronics guarantees a product life-time of 3 years after the purchase date. If you do not have a receipt (or invoice) the warranty starts from the production date. The Samsung Electronics guarantee does not apply to failures caused by abnormal use. In such circumstances all service and repair costs must be paid for by the customer. The LED tube starter is a consumable, which can be purchased from your dealer.