3 CONTENTS INDOOR UNIT PAGE IMPORTANT SAFETY INFORMATION........................................................1 TEMPORARY OPERATIONS.....................................................................2 AIR CONDITIONER OPERATIONS AND PERFORMANCE............................3 1 HINTS FOR ECONOMICAL OPERATION.....................................................4 ADJUSTING AIR FLOW DIRECTION..........................................................4 SOPHIA MULTI-ZONE AU CO DR HE FAN 4 TO OL FOLLOWING SYMPTOMS ARE NOT AIR CONDITIONER TROUBLES..........5 TROUBLESHOOTING.................................................................................6 6 TEM SE P T Y AT CLOC SET FAN MO M MAINTENANCE.........................................................................................4 2 K HOU SPEE R D DE FAN SPE ED SW SW AIR ING RESE T LOCK ING C/H DIRE CTIO N CLO OK TIM ECO TIM CK 8 7 1. To prevent injury to the user or other people and property damage, the following instructions must be followed. Incorrect operation due to ignoring of instructions may cause harm or damage. 9 The safety precautions listed are divided into two categories. In either case, important safety information is listed which must be read. WARNING USER'S MANUAL OR Failure to observe a warning may result in death. The appliance shall be installed in accordance with national wiring regulations. 9 7 CAUTION 7 8 8 Failure to observe a caution may result in injury or damage to the equipment. 9 WARNING Ask your dealer for installation of the air conditioner. Incomplete installation performed by yourself may result in a water leakage, electric shock, and fire. Models: CH-18MSPHFC-230VI CH-24MSPHFC-230VI 8 IMPORTANT NOTE: • Read this manual carefully before installing or operating your new air conditioning unit. Make sure to save this manual for future reference. • This manual only describes the installation of outdoor unit. When installing the indoor unit, refer to the installation manual of indoor unit. 8 8 INDOOR UNIT 1 2 3 4 5 6 Never use a flammable spray such as hair spray, lacquer or paint near the unit. It may cause a fire. Do not place items which might be damaged by moisture under the indoor unit. Condensation may form if the humidity is above 80%, the drain outlet is blocked or the filter is polluted. Never touch the air outlet or the horizontal blades while the swing flap is in operation. Fingers may become caught or the unit may break down. After a long use, check the unit stand and fitting for damage. If damaged, the unit may fall and result in injury. Never put any objects into the air inlet or outlet. Objects touching the fan at high speed can be dangerous. To avoid oxygen deficiency, ventilate the room sufficiently if equipment with burner is used together with the air conditioner. Ask your dealer for improvement, repair, and maintenance. Incomplete improvement, repair, and maintenance may result in a water leakage, electric shock, and fire. Fig.1 OUTDOOR UNIT 7 8 9 Air flow louver (at air outlet) Air inlet (with air filter in it) Installation part Connecting pipe In order to avoid electric shock, fire or injury, or if you detect any abnormality such as smell of fire, turn off the power supply and call your dealer for instructions. Air inlet Air outlet Never let the indoor unit or the remote controller get wet. It may cause an electric shock or a fire. Display panel Remote controller Never press the button of the remote controller with a hard, pointed object. The remote controller may be damaged. Drain pipe Never replace a fuse with that of wrong rated current or other wires when a fuse blows out. Use of wire or copper wire may cause the unit to break down or cause a fire. NOTE All the pictures in this manual are for explanation purpose only. They may be slightly different from the air conditioner you purchased(depend on model). The actual shape shall prevail. Turn off any combustible heating devices, ventilate the room, and contact the dealer where you purchased the unit. Do not use the air conditioner until a service person confirms that the portion where the refrigerant leaks is repaired. CAUTION Symptom 2: Change into the fan mode during cooling mode Never use a damp cloth on the remote controller. In order to prevent the indoor evaporator frosting, the system will change into fan mode automatically, restore to the cooling mode after soon. The air-in side should face up when using vacuum cleaner. Do not use a chemically-treted duster for wiping or leave such material on the unit for long. it may damage or fade the surface of the unit. The air-in side should face down when using water. Do not dry out the air filter under direct sunshine or with fire. Maintenance after a long stop period Before cleaning, be sure to stop the operation, turn the breaker off or pull out the supply cord. Otherwise, an electric shock and injury may result. Open the air intake with the screwdriver or something like that .(Refer to Fig.6-1) Take out the air filter.(Refer to Fig.6-2) Clean the air cleaning filter with water or vacuum cleaer,then dry it in cool place. Re-install the air filter in the reverse order of Fig.6-2. 2 14-16KW Directly pull out the air filter from air inlet as indicated in Fig.6-3. Clean the air cleaning filter with water or vacuum cleaner, then dry it in cool place. Re-install the air filter in the reverse order of Fig.6-3. 2 Communication malfunction between indoor and outdoor units E1 OFF 2 3 Indoor fan speed malfunction E3 OFF 4 OFF 6 A "pishi-pishi" squeaking sound is heard when the system stops after heating operation. Expansion and contraction of plastic parts caused by temperature change make this noise. Symptom 4.2: Indoor unit, outdoor unit A continuous low hissing sound is heard when the system is in operation. This is the sound of refrigerant gas flowing through both indoor and outdoor units. A hissing sound which is heard at the start or immediately after stopping operation or defrost operation. This is the noise of refrigerant caused by flow stop or flow change. Fig.6-3 If the air conditioner is installed in a dust place, clean the the air filter frequent. 3.2-10.5KW 1 E5 Clean air filters and casings of indoor units. Refer to " Cleaning the air filter" for details on how to proceed and make sure to install cleaned air filters back in the same position. 1 OFF Evaporator coil temperature sensor open circuit or short circuit A continuous low "shah" sound is heard when the system is in cooling operation or at a stop. When the drain pump (optional accessories) is in operation,this noise is heard. Symptom 4.3: Outdoor unit When the tone of operating noise changes. This noise is caused by the change of frequency. FOLLOWING SYMPTOMS ARE NOT AIR CONDITIONER TROUBLES E0 5 Fig.6-2 7. Indoor EEPROM error A safety device such as a fuse, a breaker frequently actuates. (eg. at the end of the season) The filter cleaning should be performed by a suitable service provider. 1 Obstacles and water enter the unit. Water leaks from indoor unit. Other malfunctions. If the system does not properly operate except the above mentioned cases or the above mentioned malfunctions is evident, investigate the system according to the following procedures. (See in Table 8-2) 8.2 Troubles and causes of remote controller Before asking for serving or repairing, check the following points.(See in Table 8-3) 6 Refrigerant leakage detection malfunction EC OFF 7 7 Water-level alarm malfunction EE OFF 8 8 Communication malfunction between two indoor units (for twins model) E8 OFF 9 9 Other malfunction of twins model E9 OFF 10 10 Current overload protection F0 ON 1 11 Outdoor room temperature sensor open circuit or short circuit F1 ON 2 12 Outdoor condenser pipe temperature sensor error F2 ON 3 13 Discharging air temperature sensor error F3 ON 14 Outdoor EEPROM error F4 ON 5 15 Outdoor fan speed malfunction (Only for DC fan motor) F5 ON 6 16 T2b sensor error F6 ON 7 17 Inverter module IPM protection P0 Flash 1 18 High/Low voltage protection P1 Flash 2 19 High temperature protection of compressor top P2 Flash 3 20 Outdoor low temp. protection P3 Flash 4 21 Compressor drive error P4 Flash 5 22 Mode conflict P5 Flash 6 Unit does not start Air flowing normally but completely can't cooling Units start or stop frequently Low cooling effect 4 Low heating effect Be sure the air conditioner is grounded. In order to avoid electric shock, make sure that the unit is grounded and that the earth wire is not connected to gas or water pipe, lightning conductor or telephone earth wire. If the operation lamp and the "PRE-DEF indicator(cooling and heating type) or fan only indicator(cooling only type)" light, it means you choose the heating model, When just starting, if the compressor has not started, the indoor unit appears "anti cold wind" protection because of its overlow outlet temperature. owner’s manual 5 The unit can absorb the smell of rooms, furniture, cigarettes, etc., and then emit it again. Symptom 7: The outdoor unit fan does not spin. During operation. The speed of the fan is controlled in order to optimize product operation. 6 DEF./FAN Fig. 2-5 NOTE:DEF indicator(cooling and heating type) or FAN indicator(cooling only type) owner’s manual 7 owner’s manual 8 Lighting or a car wireless telephone operating nearby may cause the unit to malfunction. Disconnect the unit with the power and then connect the unit with the power again. Push the ON/OFF button on the remote controller to restart operation. ALARM , Infrared signal receiver NOTE:DEF indicator(cooling and heating type) or FAN indicator(cooling only type) Display panel Fig. 2-1 DEF./FAN Display panel For some models, the machine is special designed with louver angle memory function.Power failure during operation or pressing the ON/OFF button on the remote controller will stop the unit completely.When the power restores or pressing the ON/OFF button on the remote controller again,the unit restarts automatically with the previous open angle of the horizontal louver by the memory function.So we strongly recommend that the open angle of the horizontal louver should not be set too small,in case the condensed water forms and drops from the horizontal louver. Press the Manual control button and the open angle of the horizontal louver will be restored to the standard angle. Fig. 2-6 Operation lamp Infrared signal receiver Timer indicator ALARM PRE-DEF indicator(cooling and heating type) or fan only indicator(cooling only type) Infrared signal receiver Temporary button PRE-DEF indicator(cooling and heating type) or fan only indicator(cooling only type) MANUAL Operation lamp Alarm indicator Temporary button Temperature indecator Display panel Timer indicator Display panel Fig. 2-2 Operation lamp AIR CONDITIONER OPERATIONS AND PERFORMANCE 4. Outdoor temperature Mode Temporary button Cooling operation 0°C ~ 50°C / 32 °F~122°F -15°C ~ 50°C / 5 °F~122°F (for the models with low temperature cooling system) Heating operation (cooling only type without) -15°C ~ 24°C / 5 °F~76°F Drying operation 0°C ~ 50°C / 32 °F~122°F Room temperature Timer indicator Alarm indicator Display panel Infrared signal receiver Fig. 2-3 Timer indicator Temperature indecator Alarm indicator Display panel Fig. 2-8 For inverter type,this switch is used for after-sales service purpose only,the user should not push it. 2 3 5.2 Auto-swing Press SWING H button, the louver will swing left and right automatically. In cooling, close the curtains to avoid direct sunlight. 17°C ~ 32°C ( 62 °F ~ 90°F) 0°C ~ 30°C / 32 °F~86°F Set the timer for the desired operating time. 17°C ~ 32°C ( 62 °F ~ 90°F) Never put obstructions near the air outlet or the air inlet. Or it will cause lower efficiency, even a sudden stop. owner’s manual 3 2 Fig. 5-4 To keep cool or warm air in the room, never open doors or windows more often than necessary. If you don't plan to use the unit for a long time, please disconnect power and remove the batteries from the remote controller. When the power switch is connected, some energy will be consumed, even if the air conditioner isn't in operation. So please disconnect the power to save energy. And please switch the power on 12 hours before you restart the unit to ensure a smooth operation. If air conditioner is used outside the above conditions, it may cause the unit to function abnormally. The phenomenon is normal that the surface of air conditioning may condense water when the relative larger humidity in room, please close the door and window. Optimum performance will be achieved within these operating temperature range. owner’s manual Adjust the Vertical louver Adjust the room temperature properly to get a comfortable situation and to avoid supercooling and superheat. NOTE 1 HINTS FOR ECONOMICAL OPERATION Adjust the air flow direction properly to avoid winding toward your body. Temperature Fig. 2-7 Operation lamp When heating Adjust the louver downwards. (vertically) The following should be noticed to ensure an economical operation. (Refer to corresponding chapterfor details) Table 3-1 PRE-DEF indicator(cooling and heating type) or fan only indicator(cooling only type) Infrared signal receiver PRE-DEF indicator(cooling and heating type) or fan only indicator(cooling only type) 3. Temperature indecator Alarm indicator Fig. 5-2 Fig. 5-3 Use the system in the following temperature for safe and effective operation. The Max operation temperature for the air conditioner.(Cooling/Heating) MANUAL When cooling Adjust the louver horizontally. , Louver Angle Memory Function(optional): MANUAL OPERATION TIMER Fig. 5-1 Refrigerant Leakage Detection(optional): This manual does not include Remote Controller Operations, see the<<Remote Controller Owner's manual>> packed with the unit for details. Infrared signal receiver Adjust the horizontal louver Manual Swing Adjust the louver to achieve better cooling/heating effects when cooling /heating. With this new technology, the dipsplay area will appear EC (if applicable) and the LED indication lamps continue flashing when the outdoor unit detects refrigerant leakage. Causes Solution Power failure. Power switch is off. Fuse of power switch may have burned. Batteries of remote controller exhausted or other problem of controller. Wait for the comeback of power. Switch on the power. Replace the fuse. Replace the batterises or check the controller. Temperature is not set correctly. Be in 3 minutes protection compressor. Set the temperature properly. Wait. of Refrigerant is too little or too much. Air or no concretingc gas in the refrigerating circuit. Compressor is malfunction. Voltage is too high or too low. System circuit is blocked. Check leakage, and rightly recharge refrigerant. Vacuum and recharge refrigerant. Maintenance or change compressor. Install manostat. Find reasons and solution. Outdoor unit and indoor unit heat exchanger is dirty. The air filter is dirty. Inlet/outlet of indoor/outdoor units is blocked. Doors and windows are open Sunlight directly shine. Too much heat resource. Outdoor temp. is too high. Leakage of refrigerant or lack of refrigerant. Clean the heat exchanger. Clean the air filter. Eliminate all dirties and make air smooth. Close doors and windows. Make curtains in order to shelter from sunshine. Reduce heat source. AC cooling capacity reduces (normal). Check leakage and rightly recharge refrigerant. Outdoor temperature is lower than 7 C Doors and windows not completely closed. Leakage of refrigerant or lack of refrigerant. Use heating device. Close doors and windows. Check leakage and rightly recharge refrigerant. Symptoms The fan speed can not be changed. Causes A clogged air filter will reduce cooling or heating efficiency, please clean it once two weeks. 6. MAINTENANCE CAUTION Before you clean the air conditioner, be sure the power supply is off. Check if the wiring is not broken off or disconnected. Use a dry cloth to wipe the indoor unit and remote controller. owner’s manual 4 Check whether the MODE indicated on the display is "AUTO" When the automatic mode is selected, the air conditioner will automatically change the fan speed. Check whether the MODE indicated on the display is "DRY" When dry operation is selected, the air conditioner automatically change the fan speed. The fan speed can be selected during "COOL" , "FAN ONLY", and "HEAT". Check whether the batteries in the remote controller are exhausted. The TEMP. indicator does not come on. Check whether the MODE indicated on the display is FAN ONLY The temperature cannot be set during FAN mode. Check whether the timer operation has come to an end when the TIMER OFF is indicated on the display. The air conditioner operation will stop up to the set time. Check whether the timer operation is started when the TIMER ON is indicated on the display. Up to the set time, the air conditioner will automatically start and the appropriate indicator will go off. The TIMER ON indicator goes off after a lapse of certain time. www.cooperandhunter.us THIS WARRANTY DOES NOT COVER: LIMITED WARRANTY STATEMENT MULTI ZONE INVERTER AIR CONDITIONING SYSTEM WITH HEAT PUMP The remote controller signal is not transmitted even when the ON/OFF button is pushed. The indication on the display disappears after a lapse of time. LIMITATIONS OF WARRANTIES: ALL IMPLIED WARRANTIES AND/OR CONDITIONS (INCLUDING IMPLIED WARRANTIES OR CONDITIONS OF MERCHANTABILITY AND FITNESS FOR A PARTICULAR USE OR PURPOSE) ARE LIMITED TO THE DURATION OF THIS LIMITED WARRANTY. SOME STATES OR PROVINCES DO NOT ALLOW LIMITATIONS ON HOW LONG AN IMPLIED WARRANTY OR CONDITION LASTS, SO THE ABOVE MAY NOT APPLY TO YOU. THE EXPRESS WARRANTIES MADE IN THIS WARRANTY ARE EXCLUSIVE AND MAY NOT BE ALTERED, ENLARGED, OR CHANGED BY ANY DISTRIBUTOR, DEALER, OR OTHER PERSON, WHATSOEVER. Solution The power supply is off. This warranty should be registered on our web-site www.cooperandhunter.us The warranty is only valid when installed by a Licensed HVAC Technician FOR WARRANTY SERVICE OR REPAIR: Contact your installing contractor. You may find the installer’s name on the equipment or in your Owner’s packet. Complete product registration below and send back by e-mail at email@example.com PRODUCT REGISTRATION: Model No.: ______________________________________________________________________________________________ Serial No.: _______________________________________________________ Date of Installation: ______________________ Owner Name: ____________________________________________________________________________________________ No receiving tone sounds from the indoor unit even when the ON/OFF button is pressed. Check whether the signal transmitter of the remote controller is properly directed to the infrared signal receiver of the indoor unit when the ON/OFF button is pressed. Directly transmit the signal transmitter of the remote controller to the infrared signal receiver of the indoor unit, and then repeatly push the ON/OFF button twice. Address of Installation:_____________________________________________________________________________________ Installing Contractor: ______________________________________________________________________________________ Address: ________________________________________________________________________________________ Phone No. / E-mail: _______________________________________________________________________________ C&H distributor (hereinafter “Company”) warrants this product against failure due to defect in materials or workmanship under normal use and maintenance as follows. All warranty periods begin on the date of original installation. If the date cannot be verified, the warranty period begins one hundred twenty (120) days from date of manufacture. Damage resulting from failure to use, install or maintain the product in a manner consistent with our/manufacturer’s recommendations shall render the warranty void. Cooper&Hunter, at its option, may request a report from a qualified technician prior to honoring a warranty claim. If a part fails due to defect during the applicable warranty period Company will provide a new or remanufactured part, at Company’s option, to replace the failed defective part at no charge for the part. This limited warranty is subject to all provisions, conditions, limitations and exclusions listed below. ● A warranty period of Seven (7) years on compressor to the original registered end-user. ● A warranty period of Five (5) years on all parts to the original registered end user. ● A warranty period of One (1) year on the remote control provided with the original unit. ● Limited warranty applies only to systems that are properly installed by a state certified or licensed HVAC contractor, under applicable local and state law in accordance with all applicable building codes and permits; C&H installation and operation instructions and good trade practices. ● Warranty applies only to products remaining in their original installation location. ● Defective parts must be returned to the distributor through a registered servicing dealer for credit. Symptom 6: The units can give off odours owner’s manual Display panel TIMER OPERATION ADJUSTING AIR FLOW DIRECTION Auto-swing Press SWING V button, the louver will swing up and down automatically. To restart operation, push the ON/OFF button on the remote controller. ALARM Date of Purchase: _______________________________________________________________________________ When the unit is used for the first time in a long time. This is because dust has gotten into the unit. The air conditioner does not start immediately after the ON/OFF button on the romote controller is pressed. If the operation lamp lights, the system is in normal condition.To prevent overloading of the compressor motor, the air conditioner starts 3 minutes after it is turned ON. DEF./FAN 5.1 The OPERATION lamp on the indoor unit will start flashing when power is restored. OFF The OPERATION lamp goes off. The air conditioner is OFF while the remote controller operation is enabled. MANUAL 5. Power failure during operation will stop the unit completely. NOTE MANUAL Children should be supervised to ensure that they do not play with the appliance. In order to avoid injury, do not remove the fan guard of the outdoor unit. 3 OPERATION TIMER Power failure FORCED COOL The OPERATION lamp flashes, the air conditioner will turn to FORCED AUTO after it is enforced to cool with a wind speed of HIGH for 30 minutes. The remote controller operation is disabled. Place Of Purchase: ________________________________________________________________________________________ Symptom 5: Dust comes out of the unit Symptom 1: The system does not operate Function indicators on indoor unit display panel 2 Infrared signal receiver The air conditioner consists of the indoor unit, the outdoor unit, the connecting pipe and the remote controller. (See Fig.1) A protection feature prevents the air conditioner from being activated for approximately 3 minutes when it restarts immediately after operation. 1 FORCED AUTO The OPERATION lamp is lit, and the air conditioner will run under FORCED AUTO mode. The remote controller operation is enabled to operate according to the received signal. Fig. 2-4 NOTE:DEF indicator(cooling and heating type) or FAN indicator(cooling only type) Three-minute protection feature For fixed-frequency type,this function is used to operate the unit temporarily in case you misplace the remote controller or its batteries are exhausted. Two modes including FORCED AUTO and FORCED COOL can be selected through the TEMPORARY BUTTON on the air-in grill control box of the indoor unit. Once you push this button, the air conditioner will run in such order: FORCED AUTO, FORCED COOL, OFF, and back to FORCED AUTO. Table 8-3 Symptoms running lamp (flashes per second) Symptom 3.1: Indoor unit Symptom 4.1: Indoor unit If the accumulated dust is too heavy to be cleaned, please replace the filter with a new one(replaceable air filter is an optional fitting). timer lamp 5 Sptom 4: Noise of air conditionerscooling Cleaning the air filter display (nixie tube) OFF Symptom 3.2: Indoor unit, outdoor unit Maintenance before a long stop period Malfunction E4 When humidity is high during cooling operation If the interior of an indoor unit is extremely contaminated, the temperature distribution inside a room becomes uneven. It is necessary to clean the interior of the indoor unit. Ask your dealer for details on cleaning the unit. This operation requires a qualified service erson Air filter The air filter can prevent the dust or other particulate from going inside. In case of blockage of the filter, the working efficiency of the air conditioner may greatly decrease. Therefore, the filter must be cleaned once two weeks during long time usage. The operation lamp is flashing rapidly (5Hz) This lamp is still flashing rapidly after turn off the power and turn on again. (See in Table 8-1) NO. Indoor room temperature sensor open circuit or short circuit When the system is changed over to heating operation after defrost operation Moisture generated by defrost becomes steam and is exhausted. Let the indoor units run in fan only operation for about half a day in order to dry the interior of the units. If one of the following malfunctions occur, stop operation, shut off the power, and contact with your dealer. TEMPORARY OPERATIONS This appliance is not intended for use by persons (including children) with reduced physical, sensory or mental capabilities,or lack of experience and knowledge, unless they have been given supervision or instruction concerning use of the appliance by a person responsible for their safety. In order to avoid electric shock or fire, make sure that an earth leak detector is installed. Table 8-2 4 Check and remove everything that might be blocking inlet and outlet vents of indoor units and outdoor units. Turn on the power at least 12 hours before operating the unit in order to ensure smoother operation. As soon as he power is turned on, the remote controller displays appear. Troubles and causes of air conditioner Table 8-1 Remote controller receives malfunction or the button does not work well. Air Inlet Fig.6-1 TROUBLESHOOTING Symptom 3: White mist comes out of a unit (eg. at the beginning of the season) Clean air filters and casings of indoor units. Refer to "Cleaning the air filter" for details on how to proceed and make sure to install cleaned air filters back in the same position. 8.1 When the room temperature drops to the set temperature, the compressor goes off and the indoor unit changes to fan mode; when the temperature rises up, the compressor starts again. It is same in the heating mode. CAUTION Do not use benzine, thinner, polishing powder, or similar solvents for cleaning. These may cause the plastic surface to crack or deform. 8. 2. This appliance can be used by children aged from 8 years and above and persons with reduced physical, sensory or mental capabilities or lack of experience and knowledge if they have been given supervision or instruction concerning use of the appliance in a safe way and understand the hazards involved. Children shall not play with the appliance.Cleaning and user maintenance shall not be made by children without supervision. Do not use the air conditioner for other purposes. In order to avoid any quality deterioration, do not use the unit for cooling precision instruments, food, plants, animals or works of art. ALARM Display panel Do not install the air conditioner at any place where flammable gas may leak out. If the gas leaks out and stays around the air conditioner, a fire may break out. The appliance is not intended for use by young children or infirm persons without supervision. 1 NOTE Do not place appliances which produce open fire in places exposed to the air flow from the unit or under the indoor unit. It may cause incomplete combustion or deformation of the unit due to the heat. DEF./FAN NOTE:DEF indicator(cooling and heating type) or FAN indicator(cooling only type) Do not operate the air conditioner when using a room fumigation - type insecticide. Failure to observe could cause the chemicals to become deposited in the unit, which could endanger the health of those who are hypersensitive to chemicals. The refrigerant in the air conditioner is safe and normally does not leak. If the refrigerant leaks in the room, contact with a fire of a burner, a heater or a cooker may result in a harmful gas. TIMER Infrared signal receiver Do not allow a child to mount on the outdoor unit or avoid placing any object on it. Falling or tumbling may result in injury. To prevent refrigerant leak, contact your dealer. When the system is installed and runs in a small room, it is required to keep the concentration of the refrigerant, if by any chance coming out, below the limit. Otherwise, oxygen in the room may be affected, resulting in a serious accident. OPERATION Temperature indecator Never expose little children, plants or animals directly to the air flow. Adverse influence to little children, animals and plants may result. If electrical appliances are disposed of in landfills or dumps, hazardous substances can leak into the groundeater and get into the food chain, damaging your health and well-being. MANUAL Do not operate your air conditioner in a wet room such as a bathroom or laundry room. Never touch the internal parts of the controller. Do not remove the front panel. Some parts inside are dangerous to touch, and a machine trouble may happen. Do not dispose of electrical appliances as unsorted municipal waste, use separate collection facilities. Contact you local government for information regarding the connection systems available. owner’s manual A wet cloth may be used to clean the indoor unit if it is very dirty. Arrange the drain hose to ensure smooth drainage. Incomplete drainage may cause wetting of the building, furniture etc. Do not dispose this product as unsorted municipal waste. Collection of such waste separately for special treatment is necessary. IMPORTANT SAFETY INFORMATION If the supply cord is damaged, it must be replaced by the manufacturer, its service agent or similarly qualified persons in order to avoid a hazard. Do not touch the heat exchanger fins. These fins are sharp and could result in cutting injuries. Never inspect or service the unit by yourself. Ask a qualified service person to perform this work. DUCTLESS INVERTER INDOOR UNIT Do not insert fingers, rods or other objects into the air inlet or outlet. When the fan is rotating at high speed, it will cause injury. E ON 8 OUTDOOR UNIT Do not operate the air conditioner with a wet hand. An electric shock may happen. E OFF 5 SPLIT AIR CONDITIONER WITH HEAT PUMP UNIVERSAL FLOOR/CEILING It is not good for your health to expose your body to the air flow for a long time. 1. Labor or other costs incurred for diagnosing, repairing, removing, installing, shipping, servicing, or handling of defective parts, replacement parts, or new units. 2. 3. Product cleaning required prior to warranty service and repair. Normal maintenance as outlined in the installation and servicing instructions or user's manual, including filter cleaning and/or replacement and lubrication. Failure, damage, or repairs due to faulty installation, misapplication, abuse, improper servicing, unauthorized alteration, or improper operation. Failure to start due to voltage conditions, blown fuses, open circuit breakers, or damages due to the inadequacy or interruption of electrical service. Failure or damage due to floods, winds, fires, lightning, accidents, corrosive environments (rust, etc.), or other conditions beyond the control of Company. Failure or damage of coils or piping due to corrosion on installations within one (1) mile of a sea coast or a corrosive body. Parts not supplied or designated by Company, or damages resulting from their use. Products installed outside the continental USA and Canada. Electricity or fuel costs, or increases in electricity or fuel costs for any reason whatsoever, including additional or unusual use of supplemental electric heat. Any cost to replace, refill, or dispose of refrigerant, including the cost of refrigerant. Shipping damage or damage as a result of transporting the unit. Accessories such as condensate pumps, line sets, and so forth. Any special, indirect, or consequential property or commercial damage of any nature whatsoever. Some states or provinces do not allow the exclusion of incidental or consequential damages, so the above limitation may not apply to you. 4. 5. 6. 7. 8. 9. 10. 11. 12. 13. 14. This warranty gives you specific legal rights, and you may also have other rights which vary from state to state or province to province.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project