5 Battery and Surge Protected Outlets The unit has four battery powered/surge suppression outlets for connected equipment to ensure temporary uninterrupted operation of your equipment during a power failure. (DO NOT plug a laser printer, paper shredder, copier, space heater, vacuum cleaner, sump pump or other large electrical devices into the “Battery and Surge Protected Outlets”. The power demands of these devices may CST1400G User’s Manual overload and damage the unit.) 6 K01-0000294-01 7 8 This manual contains important safety instructions. Please read and follow all instructions carefully during installation and operation of the unit. Read this manual thoroughly before attempting to unpack, install, or operate your UPS. CAUTION! To prevent the risk of fire or electric shock, install in a temperature and humidity controlled indoor area free of conductive (Please see specifications for acceptable temperature and humidity range). servicing the batteries. There are no user serviceable parts inside except for the battery. 9 Do not plug into an outlet that is not If you need to de-energize this equipment, turn off and unplug the unit. 10 component. ANSI/NFPA 75. CAUTION! To reduce the risk of fire, connect only to a circuit provided with 20 amperes maximum branch circuit over current protection in accordance with the National Electric Code, ANSI/NFPA 70. DO NOT USE FOR MEDICAL OR LIFE SUPPORT EQUIPMENT! CyberPower Systems does not sell products for life support or medical applications. DO NOT use in any circumstance that would affect the operation and safety of life support equipment, medical applications, or patient care. DO NOT USE WITH OR NEAR AQUARIUMS! To reduce the risk of fire or electric shock, do not use with or near an aquarium. Condensation from the aquarium can cause the unit to short out. DO NOT USE THE UPS ON ANY TRANSPORTATION! To reduce the risk of fire or electric shock, do not use the unit on any transportation such as airplanes or ships. The effect of shock or vibration caused during transit and the damp environment can cause the unit to short out. INSTALLING YOUR UPS SYSTEM Serial/USB Ports to PC The ports allow connection and communication between the USB/DB-9 port on the computer and the UPS unit. Note: Only one of these two ports can be used to communicate with your computer at one time. Coax/Cable/DSS Surge Protection The Coax/Cable/DSS protection ports will protect any cable modem, CATV converter, or DSS receiver. 12 Outlet Designed for AC Adapters The unit has one outlet spaced to allow AC power adapter blocks to be plugged into the UPS without overlapping or blocking adjacent CAUTION! To avoid electric shock, turn off the unit and unplug it from the AC power source before servicing the battery or installing a computer CAUTION! Not for use in a computer room as defined in the Standard for the Protection of Electronic Computer/Data Processing Equipment, Circuit Breaker Located on the back of the UPS, the circuit breaker serves to provide overload and fault protection. 11 CAUTION! Hazardous live parts inside can be energized by the battery even when the AC input power is disconnected. Communication Protection Ports Communication protection ports will protect any standard modem, fax, telephone line, network or Ethernet connection (RJ11/RJ45). CAUTION! To reduce the risk of electric shock, do not remove the cover except to service the battery. Turn off and unplug the unit before grounded. If not provide surge protection without being plugged into a grounded and properly wired wall outlet. (SAVE THESE INSTRUCTIONS) CAUTION! The UPS must be connected to an AC power outlet with fuse or circuit breaker protection. Wiring Fault Indicator This LED indicator will illuminate to warn the user that a wiring problem exists, such as bad ground, missing ground or reversed wiring. this is illuminated, disconnect all electrical equipment from the outlet and have an electrician verify the outlet is properly wired. The unit will IMPORTANT SAFETY WARNINGS contaminants. Full-Time Surge Protection Outlets The unit has four surge suppression outlets. outlets. REPLACING THE BATTERY CAUTION! Read and follow the IMPORTANT SAFETY INSTRUCTIONS before servicing the battery. Service the battery under the supervision of personnel knowledgeable of batteries and their precautions. CAUTION! Use only the specified type of battery. See your dealer for replacement batteries. CAUTION! The battery may present a risk of electrical shock. Do not dispose of battery in a fire as it may explode. Follow all local ordinances regarding proper disposal of batteries. Almost any retailer that sells lead-acid batteries collects used batteries for recycling, as required by most state laws. CAUTION! Do not open or mutilate the batteries. Released electrolyte is harmful to skin and eyes and may be toxic. CAUTION! A battery can present a high risk of short circuit current and electrical shock. Take the following precautions before replacing the battery: 1. Remove all watches, rings or other metal objects. 2. Only use tools with insulated handles. 3. Do not lay tools or metal parts on top of battery or any terminals. 4. Wear rubber gloves and boots. UNPACKING 5. (a) UPS unit (b) User’s manual (c) USB A+B type cable *PowerPanel® Personal Edition software is available on our website. Please visit www.cpsww.com and go to the Software Section for free download. 1. Determine if the battery is inadvertently grounded. If grounded, remove the source of ground. CONTACT WITH GROUNDED BATTERY CAN RESULT IN ELECTRICAL SHOCK! Inspect the UPS upon receipt. The box should contain the following: OVERVIEW The CST1400G provides complete power protection from utility power that is not always consistent. The CST1400G features 1500 Joules of surge prot ection. Both units provide long lasting battery backup during power outages with maintenance free batteries. The CST1400G ensures consistent power to your electronic equipment and includes software that will automatically save your open files and shutdown your electronic equipment during a utility power loss. AUTOMATIC VOLTAGE REGULATOR The CST1400G stabilizes inconsistent utility power voltage to nominal levels that are safe for equipment. Inconsistent incoming utility BATTERY REPLACEMENT PROCEDURE: Turn off and unplug all connected equipment. 2. Turn the UPS off and unplug it from the AC power source. 3. Turn the UPS upside down. 4. Remove the retaining screw. 5. Slide the battery compartment cover (front panel) completely off of the unit. 6. Remove the batteries from the compartment. 7. Disconnect the battery wires from the batteries. 8. Install the replacement batteries by connecting the red wire (+) and black wire (-) to the same color connectors from the battery pack. 9. Put the batteries back into the compartment. 10. Slide back the battery compartment cover and tighten the retaining screws. 11. Recharge the UPS for 8-16 hours to fully charge the battery. power may be damaging to important data files and hardware, but with Automatic Voltage Regulation (AVR), damaging voltage levels are corrected to safe levels. AVR automatically increases low utility power and decreases high utility power to a consistent and safe 110/120 volts. HOW TO DETERMINE THE POWER REQUIREMENTS OF YOUR EQUIPMENT 1. Ensure that the equipment plugged into the UPS does not exceed the UPS unit’s rated capacity (1400VA/840W for CST1400G). If the rated capacities of the unit are exceeded, an overload condition may occur and cause the UPS unit to shut down or the circuit breaker to trip. 2. There are many factors that can affect the amount of power that your electronic equipment will require. It is suggested that the load placed on the battery outlets not exceed 80% of the unit’s capacity. REMINDER: Batteries are considered HAZARDOUS WASTE and must be disposed of properly. Most retailers that sell lead-acid batteries collect used batteries for recycling, as required by local regulations. DEFINITIONS FOR ILLUMINATED LED INDICATORS HARDWARE INSTALLATION GUIDE 1. Your new UPS may be used immediately upon receipt. However, after receiving a new UPS, to ensure the battery’s maximum charge capacity, it is recommended that you charge the battery for at least 8 hours. Your UPS is equipped with an auto-charge feature. When the UPS is CONDITION plugged into an AC outlet, the battery will automatically charge whether the UPS is turned on or off. 2. With the UPS unit turned off and unplugged, connect your computer, monitor, and any other peripherals requiring battery backup into the battery power supplied outlets. DO NOT plug a laser printer, paper shredder, copier, space heater, vacuum cleaner, sump pump or other large electrical devices into the “Battery and Surge Protected Outlets”. The power demands of these devices may overload and damage the unit. 3. To protect a fax, phone or modem line, connect a telephone cable or network cable from the wall jack outlet to the IN Power ON Wiring Fault Alarm On Off Off On Off On Off jack of the UPS. Connect a telephone cable or network cable from the OUT jack of the UPS to a fax machine, telephone, modem, or network devices. 4. Plug the UPS into a 2 pole, 3 wire grounded receptacle (wall outlet). Make sure the wall branch outlet is Beep twice every 30 seconds Rapid Beeping every 1/2 second protected by a fuse or circuit breaker and does not service equipment with large electrical demands (e.g. air Off in conjunction with the UPS unit. Off Constant tone The Power On indicator light will illuminate and the unit will “beep”. Rapid beeping listed capacity of the UPS. Turn the UPS off, unplug at least one piece of equipment from battery outlets, wait 10 seconds, reset the Electrical Wiring Fault - This indicates a wiring problem with the Make sure the circuit breaker is depressed and then turn the UPS on. 7. To maintain optimal battery charge, leave the UPS plugged into an AC outlet at all times. On/Off 8. To store the UPS for an extended period of time, cover it and store with the battery fully charged. While in storage, recharge the battery On None AC outlet such as bad ground, missing ground, or reversed wiring. Disconnect all electrical equipment from the outlet and have an electrician check the outlet to insure proper wiring. every three months to ensure battery life. 9. Ensure the wall outlet and UPS are located near the equipment being attached for proper accessibility. DESCRIPTION Utility Failure- The UPS is providing battery power. indicates the unit will run out of power shortly. circuit breaker and turn the unit on. 6. If an overload is detected, an audible alarm will sound and the unit will emit one long beep. To correct this, turn the UPS off and unplug at least one piece of equipment from the battery power supplied outlets. Utility Failure- The UPS is providing power to battery power-supplied outlets from its battery. Battery Overload - Occurs when connected equipment exceeds the conditioner, copier, etc…). The warranty prohibits the use of extension cords, outlet strips, and surge strips 5. Press the power switch to turn the unit on. Normal DEFINITIONS FOR ILLUMINATED LCD INDICATORS BASIC OPERATION 1. INPUT voltage meter: This meter measures the AC voltage that the UPS system is receiving from the utility wall outlet. The UPS is designed to continuously supply connected equipment with stable output voltage In the event of a complete power loss, severe brownout, or over-voltage, the UPS relies on its internal battery to supply consistent 110/120 output voltage. The INPUT voltage meter can be used as a diagnostic tool to 1 identify poor-quality input power. Power Switch 2. Used as the master ON/OFF switch for equipment connected to the battery power supplied outlets. 2 This meter measures, in real time, the AC voltage that the UPS system is providing to the computer, such as normal line mode, AVR mode, Power On Indicator This LED is illuminated when the utility power is normal and the UPS outlets are providing power, free of surges and spikes. 3 LCD module display High resolution and intelligent LCD display shows all the UPS information using icons and messages. For more information please review the “Definitions for Illuminated LCD Indicators” section below. 4 OUTPUT voltage meter: LCD Display Toggle/Selected Switch The switch can be used to select the LCD display contents including Input Voltage, Output Voltage, and Estimated Run Time. The toggle frequency is set to one time per second. Holding the switch for more than two seconds while running on battery will silence the buzzer. and battery backup mode. (Note: The OUTPUT voltage meter shows the status of the battery backup outlets.) 3. ESTIMATED RUN TIME: 4. NORMAL icon: 5. BATTERY icon: This displays the run time estimate of the UPS with current battery capacity and load. This icon appears when the UPS is working under normal conditions. During a severe brownout or blackout, this icon appears and an alarm sounds (two short beeps followed by a pause) to indicate the UPS is operating from its internal batteries. The alarm will continue to sound during a prolonged brownout or blackout. Limited Warranty and Connected Equipment Guarantee The BATT.CAPACITY meter will show one 20% capacity segment remaining to indicate the UPS's batteries are nearly out of power. You should save files and turn off your equipment immediately. 6. AVR (Automatic Voltage Regulation) icon: This icon appears whenever your UPS is automatically correcting low AC line voltage without using battery power. This is a normal, automatic operation of your UPS, and no action is required on your part. 7. This icon appears whenever the UPS is in silent mode. The buzzer does not beep during silent mode until the battery reaches low capacity. This icon appears and an alarm sounds to indicate the battery-supplied outlets are overloaded. To clear the overload, unplug some of your equipment from the battery-supplied outlets until the icon turns off and the alarm stops. This icon appears if there is a problem with the UPS, Contact CyberPower Systems at firstname.lastname@example.org for further help and support. BATT. CAPACITY meter: This meter displays the approximate charge level (in 20% increments) of the UPS’s internal battery. During a blackout or severe brownout, the UPS switches to battery power, the BATTERY icon appears, and the charge level decreases. 11. This meter displays the approximate output load level (in 20% increments) of the UPS battery outlets. Possible Cause The UPS does not perform expected runtime. The UPS will not turn on. ® PowerPanel Personal Edition is inactive (all icons are gray). It also covers What is the Period of Coverage? Who Is Covered? This warranty only covers the original purchaser. Coverage ends if you sell or otherwise transfer the Product. TROUBLESHOOTING Circuit breaker button is projecting from the back of the unit. This warranty covers defects in materials and workmanship in the Product under normal use and conditions. equipment that was connected to the Product and damaged because of the failure of the Product. This warranty covers the Product for three years. Connected equipment is covered for as long as you own the Product. LOAD CAPACITY meter: Problem CyberPower Systems (USA), Inc. (“CyberPower”) provides this Limited Warranty. What Does This Warranty Cover? FAULT icon: 10. should return the Product for a full refund prior to using it. Who is Providing this Warranty? OVER LOAD icon: 9. Product you consent to be bound by and become a party to the terms and conditions of this Limited Warranty and Connected Equipment Guarantee (together referred to as this “Warranty”). If you do not agree to the terms and conditions of this Warranty, you SILENT MODE icon: 8. Read the following terms and conditions carefully before using the CyberPower CST1400G (the “Product”). By using the Solution How Do You Get Warranty Service? 1. Before contacting CyberPower, identify Your Product model number, the Purchase Date, and each item of Connected 2. Visit our web site at http://www.cpsww.com/support or Call us at (877) 297-6937. Circuit breaker has been tripped due to an overload. Turn the UPS off and unplug at least one piece of equipment. Wait 10 seconds, reset the circuit breaker by pressing the button, and then turn the UPS on. Battery not fully charged. Recharge the battery by leaving the UPS plugged in. Battery is worn out. Contact CyberPower Systems about replacement batteries at email@example.com The on/off switch is designed to prevent damage from rapidly turning it off and on. Turn the UPS off. Wait 10 seconds and then turn the UPS on. 3. The unit is not connected to an AC outlet. The unit must be connected to a 110/120V 60Hz outlet. 4. The battery is worn out. Contact CyberPower Systems about replacement batteries at firstname.lastname@example.org Mechanical problem. Contact CyberPower Systems at email@example.com The USB / serial cable is not connected. Connect the USB / serial cable to the UPS unit and an open USB / serial port on the back of the computer. You must use the cable that came with the unit. The USB / serial cable is connected to a bad USB port. Check for a different USB port and plug the cable in. The unit is not providing battery power. Shutdown your computer and turn the UPS off. Wait 10 seconds and turn the UPS back on. This should reset the unit. 3. Equipment (E.G. Computer tower, Computer Monitor, Ink Jet Printer, Cable Modem, etc). If your product requires warranty service you must provide a copy of your dated purchase receipt or invoice. How Do You Open A Connected Equipment Claim? 1. 2. Call us at (877) 297-6937 or write to us at Cyber Power Systems (USA), Inc., 4241 12th Ave. E., STE 400, Shakopee, MN 55379, or send us an e-mail message at firstname.lastname@example.org for instructions, within 10 days of the occurrence. When you contact CyberPower, identify the Product, the Purchase Date, and the item(s) of Connected Equipment. Have information on all applicable insurance or other resources of recovery/payment that are available to the Initial Customer and Request a Claim Number. You must provide a dated purchase receipt (or other proof of the original purchase) and provide a description of the damage to your connected equipment. Pack and ship the product to CyberPower and, if requested, the item(s) of Connected Equipment, a repair cost estimate for the damage to the Connected Equipment, and all claim forms that CyberPower provides to you. Show the Claim Number on the shipping label or include it with the product. You must prepay all shipping costs, you are responsible for packaging and shipment, and you must pay the cost of the repair estimate. How Long Do I Have To Make A Claim? All claims must be made within ten days of the occurrence. What Will We Do To Correct Problems? CyberPower will inspect and examine the Product. If the Product is defective in material or workmanship, CyberPower will repair or replace it at CyberPower's expense, or, if CyberPower is unable to or decides not to repair or replace the Product (if defective) within a reasonable time, CyberPower will refund to you the full purchase price you paid for the Product (purchase receipt showing price paid is required). If it appears that our Product failed to protect any equipment plugged into it, we will also send you forms for making your claim for the Additional troubleshooting information can be found under “Support” at www.CPSww.com connected equipment. We will repair or replace the equipment that was damaged because of the failure of our Product or pay you TECHNICAL SPECIFICATIONS another a third-party valuation guide, or eBay, craigslist, or other source to establish that amount. Our maximum liability is limited to the fair market value (NOT REPLACEMENT COST) of the equipment at of the time of the damage. We will use Orion Blue Book, or $500,000 for CST1400G . Who Pays For Shipping? Model CST1400G Capacity 1400VA / 840W We pay when we send items to you; you pay when you send items to us. What isn’t covered by the warranty? 1. This Warranty does not cover any software that was damaged or needs to be replaced due to the failure of the Product or any data that is lost as a result of the failure or the restoration of data or records, or the reinstallation of software. Nominal Input Voltage 125Vac Input Frequency 60 Hz ± 3 Hz On-Battery Output Voltage 120Vac ± 5% Transfer Time 4ms Typical What are the Limitations? 1400VA / 840W 1. Max. Load for UPS Outlets (4 Outlets) Max. Load for Full-Time Surge 2. maintenance, or use with items not designed or intended for use with the Product, such as laser printers, appliances, aquariums, medical or life support devices, etc. The sole and exclusive remedies of the Initial Customer are those provided by this Warranty. 12 Amp Protection outlets (8 Outlets) On-Battery Output Wave Form 2. Simulated Sine Wave Operating Temperature 32°F to 100.4° F / 0° C to 38° C Operating Relative Humidity 0 to 90% non-condensing Size (W x H x D) 13.3" x 3.9" x 9.8" (338 x 100 x 249 mm) Net W eight 3 to 6 years, depending on number of discharge/recharge cycles Recommended Battery Sealed Maintenance Free Lead Acid Battery Safety Approvals UL1778, cUL107, FCC/DoC Class B The Product and equipment connected to it must have been used properly in a suitable and proper environment and in 4. The Product must have been used at all times within the limitations on the Product’s VA/Watt capacity. conformance with any license, instruction manual, or warnings provided with the Product and the equipment connected to it. 1. 2. code-compliant 120 volt power lines in the United States and Canada; transients, surges or spikes on standard telephone land lines, PBX telephone equipment lines or Base 10T Ethernet lines, when properly installed and connected. (This exclusion 3. 4. AVR Loss of or damage to data, records, or software or the restoration of data or records, or the reinstallation of software. Damage from causes other than AC Power Line Transients, spikes, or surges on properly installed, grounded and applies, for example, to fluctuations in data transmission or reception, by CATV or RF transmission or fluctuations, or by SYSTEM FUNCTIONAL BLOCK DIAGRAM Output 5. transients in such transmission.) Damage from any circumstance described as excluded above with respect to the Product. Damages from fire, flood, wind, rain, rising water, leakage or breakage of plumbing, abuse, misuse or alteration of either the product or the Connected Equipment. CyberPower excludes any liability for personal injury under the Limited Warranty and Connected Equipment Guarantee. CyberPower excludes any liability for direct, indirect, special, incidental or consequential damages, whether for damage to or loss of property [EXCEPT FOR (AND ONLY FOR) the specific limited agreement of CyberPower to provide certain warranty Inverter benefits regarding "Connected Equipment" under this Warranty], loss of profits, business interruption, or loss of information or Normal Mode Battery Mode or device similar to the Product, surge suppressor, or power tap. Any such installation voids the Limited Warranty. 3. will be deemed outside the rated capabilities of the Product and the Limited Warranty is void. CyberPower Does Not Cover or Typical Battery Life Charger AC/DC directly connected to the Product and not “daisy-chained” together in serial fashion with any extension cords, another Product Undertake Any Liability in Any Event for Any of the Following: 8 hours from total discharge Surge Suppressor of any adapters or other connectors. The Product must have been plugged directly into the power source and the equipment connected to the Product must be The Product was designed to eliminate disrupting and damaging effects of momentary (less than 1ms) voltage spikes or impulses Typical Battery Recharge Time EMI Filter This Warranty does not apply unless the Product and the equipment that was connected to it were connected to properly wired and grounded outlets (including compliance with electrical and safety codes of the most current electrical code), without the use from lightning or other power transients. If it can be shown that a voltage spike lasting longer than 1ms has occurred, the occurrence 24.4lbs Input This Warranty does not cover or apply to: misuse, modification, operation or storage outside environmental limits of the Product or the equipment connected to it, nor for damage while in transit or in storage, nor if there has been improper operation or data. NOTE: Some States or Provinces do not allow the exclusion or limitation of incidental or consequential damages, so the Battery CYBERPOWER GREENPOWER UPS™ TECHNOLOGY Advanced Energy-Saving Patented Bypass Technology CyberPower’s patented GreenPower UPS™ with Bypass Technology reduces UPS energy costs by up to 75% compared to conventional UPS models. Even when utility power is normal, conventional UPS models 6. above limitation may not apply to you. The Product is not for use in high-risk activities or with aquariums. The Product is not designed or intended for use in hazardous environments requiring fail-safe performance, or for use in any circumstance in which the failure of the Product could lead directly to death, personal injury, or severe physical or property damage, or that would affect operation or safety of any medical or life support device (collectively, "High Risk Activities"). CyberPower expressly disclaims any express or implied warranty of fitness for High Risk Activities or with aquariums. CyberPower does not authorize use of any Product in any High Risk Activities or with Aquariums. ANY SUCH USE IS IMPROPER AND IS A MISUSE OF THE PRODUCT. constantly pass power through a transformer. By contrast, under normal conditions the advanced circuitry Where Can I Get More Information? increased while decreasing waste heat, using less energy, and reducing energy costs. CyberPower is the warrantor under this Limited Warranty. of a GreenPower UPS™ bypasses the transformer. As a result, the power efficiency is significantly When an abnormal power condition occurs, the GreenPower UPS™ automatically runs power through its transformer to regulate voltage and provide “safe” power. Since utility power is normal over 88% of the time, the GreenPower UPS™ operates primarily in its efficient bypass mode. The GreenPower UPS™ is also manufactured in accordance with the Restriction on Hazardous Substances (RoHS) directive making it one of the most environmentally-friendly on the market today. The application of the United Nations Convention of Contracts for the International Sale of Goods is expressly excluded. For further information please feel free to contact CyberPower at CyberPower Systems (USA), Inc. 4241 12th Ave E., STE 400, Shakopee, MN 55379; call us at (877) 297-6937; or send us an e-mail message at email@example.com. CyberPower Systems encourages environmentally sound methods for disposal and recycling of its UPS products. Please dispose and/or recycle your UPS and batteries in accordance to the local regulations of your state. All rights reserved. Reproduction without permission is prohibited.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project