Crestron CLS-EXP-DIMFLV Installation guide
CLS-EXP-DIMFLV 0-10 V Fluorescent Dimmer Expansion Module Installation Guide Description Additional Resources The Crestron® CLS-EXP-DIMFLV enables the expansion of iLux® Integrated Lighting System (CLS-C6 Series) and other Crestron lighting dimmers to allow control of 0-10 volt fluorescent dimming ballasts. It can also be used to switch nondimmable loads including LED, incandescent, MLV, ELV, HID, fluorescent ballasts, and motors. The CLS-EXP-DIMFLV supports 120, 230, or 277 volt loads up to 16 amps. Any output channel of the iLux system can be used to control the CLS-EXP-DIMFLV to dim a fully loaded circuit. It is also compatible with CLW-series in-wall dimmers and select CLX-series lighting control modules. The metal enclosure is designed for mounting to a vertical surface and can be installed in an environmental air-handling space above a suspended ceiling. Conduit knockouts are provided on the bottom and lower sides. All connections are made via screw terminals behind the front cover. NOTE: CLX-series lighting control modules are compatible only with forward-phase dimming modules. CLS-EXP-DIMFLV Specifications Specification Visit the product page on the Crestron website (www.crestron.com) for additional information and the latest firmware updates. Use a QR reader application on your mobile device to scan the QR image. 1 Lamp Load Rating Motor Load Rating 16 Amps @ 120 to 277 Volts; 0.5 HP @ 120 Volts, 1 HP @ 230/277 Volts Minimum Load at 120 volts at 230 volts at 277 volts 15 watts 25 watts 30 watts Load Types Dimmable Load 0-10 Volt fluorescent ballast or LED driver (4-wire) Switch Load LED, incandescent, fluorescent, magnetic low voltage, electronic low voltage, neon/cold cathode, high-intensity discharge (HID), motors 4.99 in (127 mm) Ø 0.19 in (5 mm) 120–277 Vac, 50/60 Hz Control Input 120–230 Vac, 50/60 Hz, phase independent of line power and load; Presents a 25 watt load to the controlling device Electrical Terminals Enclosure Captive screw type; Accommodates two 22–12 AWG (0.34–4.0 mm2) wires Surface mount module with (2) integral mounting flanges, galvanized steel with gray matte powder coat front panel, extruded aluminum heat sink, (4) 1/2 in (13 mm) and 3/4 in (20 mm) conduit knockouts provided on bottom and lower left and right sides Module Installation 1.64 in (42 mm) 1.64 in (42 mm) Mounting surface CLS-EXP-DIMFLV Hardware Connections INPUT CTRL: Control input from CLS(I)-C6 Series, CLW-DIM Series, CLX(I)-DIM Series, GLX-DIM6, GLXX-2DIM8, DIN-1DIM4, or DIN1-DIMU4 dimmers NEUT: Neutral connection for control input CLS-EXP-DIMFLV 8.31 in (212 mm) 8.82 in (224 mm) 7.31 in (186 mm) Input Voltages Line Power NOTE: Install in accordance with all local and national electrical codes. NOTE: To prevent potential heat damage to the drywall, do not mount the CLS-EXP-DIMFLV directly onto drywall. Mount a piece of 1/2 in (13 mm) minimum thick plywood between the CLS-EXP-DIMFLV and the drywall. Physical Description Load Ratings Installation Refer to the following diagram when installing a CLS-EXP-DIMFLV module. NOTE: To ensure proper ventilation, the device must be installed vertically on a vertical surface. Install the device with 6 inches (153 mm) of clearance from the top and bottom of the device. This section provides information on the connections and indicators available on the CLS-EXP-DIMFLV. CLS-EXP-DIMFLV Overall Dimensions - Front View 5.79 in (148 mm) Details Dimmer Channels CLS-EXP-DIMFLV Overall Dimensions - Rear View 6.39 in (163 mm) Ø 0.25 in (7 mm) 0.50 in (13 mm) CLS-EXP-DIMFLV Overall Dimensions - Side View 3.18 in (81 mm) 3.07 in (78 mm) OUTPUT SW OUT: Switched load output HOT: Line power input NEUT: Neutral connection for line power input and load 0-10V +/-: (2) Captive screw terminals,1 dimming control output; Class 1 or Class 2 wiring allowed; Control voltage: 0-10 Vdc, 70 mA Environmental Temperature Humidity Heat Dissipation Dimensions Height Width Depth #8 mounting screw (not included) 32° to 104 °F (0° to 40 °C) 10% to 90% RH (noncondensing) 70 Btu/h at maximum load, 16 amps 8.82 in (224 mm) 6.39 in (163 mm) 3.18 in (81 mm) Weight 3.3 lbs (1.5 kg) Maximum Expansion Modules per Controller Output 5 1.56 in (40 mm) 2.02 in (53 mm) Ground (1) 3-terminal chassis ground bus bar Wiring To wire the CLS-EXP-DIMFLV, remove the cover and make the connections. WARNING: RISK OF SERIOUS PERSONAL INJURY. Turn off power at the circuit breaker(s) prior to installation. Installing with the power on can result in serious personal injury and damage to the device. Remove the Cover Use a #2 Phillips screwdriver to remove the cover screws and then the cover. Remove Cover Screws Make the Connections There are seven captive screw terminals on the CLS-EXP-DIMFLV that allow power input, power output, and load control. NOTE: Observe the following points: • Strip wires to 7/16 in (12 mm). • Tighten terminal screws to 7 in-lbs (0.79 Nm). • Captive screw terminals accept up to two 22 to 12 AWG (0.34 to 4 mm2) wires per terminal. Problem Solving The following table provides corrective action for possible trouble situations. If further assistance is required, please contact a Crestron customer service representative. CLS-EXP-DIMFLV Troubleshooting Trouble Possible Cause(s) Corrective Action The load does not turn on. The controlling dimmer or switch is not working. Make sure that the controller is powered on. Make sure that a compatible dimmer is being used. No power is applied to the HOT terminal. Check the circuit breaker. Check that the green power LED inside the unit is lit. The controlling unit is either not a dimmer or has been set to non-dim. Verify that dimmer is compatible with the CLS-EXP-DIMFLV. Refer to "CLS-EXP-DIMFLV Specifications" on page 1. • Dimmer channels controlling one or more CLS-EXP-DIMFLV modules must not be wired to control any other type of load. • While these diagrams show a CLS-C6 as the controlling source, other Crestron products such as CLW-series wall dimmers (Cresnet® and infiNET™ dimmers) and CLX-series dimming modules can be used as well. Refer to “CLS-EXP-DIMFLV Specifications” on page 1 for details. Cover screws • Use a neutral wire for a CLW-Series wall dimmer. The load turns on and off but does not dim. • Use 75°C copper wire only. • The CLS-EXP-DIMFLV presents a 25 W load to the controlling dimmer. A maximum of five CLS-EXP-DIMFLV modules may be connected to the controlling dimmer, which cannot be wired to control any other loads besides the CLS-EXP-DIMFLV modules. • Separate Class 1 and Class 2 wires. When wiring a 0-10 V fluorescent dimmer, the + and – make connections using Class 1 or Class 2 wiring. If Class 1 wiring is used, the barrier between the NEUT and + terminals can be removed. Wire the CLS-EXP-DIMFLV for a 0-10 V dimming or a switching application. CLS-EXP-DIMFLV Wiring for 0-10 V Dimming Hot (120 to 277 Vac) Verify that the controlling channel has not been programmed as non-dim. The lights do not dim properly. An incompatible dimmer is being used. Make sure that the dimmer is one of those listed in "CLS-EXP-DIMFLV Specifications" on page 1. Neutral LOAD 3 LOAD 1 CLS(I)-C6 HOT NEUTRAL Neutral Violet Gray LOAD 2 Black White Hot (120 to 230 Vac) 0-10 V fluorescent dimming ballast CLS-EXP-DIMFLV Wiring for Switching Application Hot (120 to 277 Vac) Neutral LOAD 3 LOAD 2 LOAD 1 CLS(I)-C6 HOT NEUTRAL Neutral Black White Hot (120 to 230 Vac) Switched load After wiring is complete, replace the cover and the cover screws. Apply power to the line or load and turn on the controlling device. The power indicator LED lights indicating that power is supplied to the module. This product is Listed to applicable UL® Standards and requirements tested by Underwriters Laboratories Inc. CAUTION: Changes or modifications not expressly approved by the manufacturer responsible for compliance could void the user’s authority to operate the equipment. Ce produit est homologué selon les normes et les exigences UL applicables par Underwriters Laboratories Inc. NOTE: This equipment has been tested and found to comply with the limits for a Class B digital device, pursuant to part 15 of the FCC Rules. These limits are designed to provide reasonable protection against harmful interference in a residential installation. This equipment generates, uses and can radiate radio frequency energy and, if not installed and used in accordance with the instructions, may cause harmful interference to radio communications. However, there is no guarantee that interference will not occur in a particular installation. If this equipment does cause harmful interference to radio or television reception, which can be determined by turning the equipment off and on, the user is encouraged to try to correct the interference by one or more of the following measures: Federal Communications Commission (FCC) Compliance Statement This device complies with part 15 of the FCC Rules. Operation is subject to the following conditions: (1) This device may not cause harmful interference and (2) this device must accept any interference received, including interference that may cause undesired operation. • Reorient or relocate the receiving antenna. • Increase the separation between the equipment and receiver. • Connect the equipment into an outlet on a circuit different from that to which the receiver is connected. • Consult the dealer or an experienced radio/TV technician for help. The product warranty can be found at www.crestron.com/warranty. The specific patents that cover Crestron products are listed at patents.crestron.com. Certain Crestron products contain open source software. For specific information, please visit www.crestron.com/opensource. Crestron, the Crestron logo, Cresnet, iLux, and infiNET are either trademarks or registered trademarks of Crestron Electronics, Inc. in the United States and/or other countries. Crestron and the Crestron logo are either trademarks or registered trademarks of Crestron Electronics, Inc. in the United States and/ or other countries. UL and the UL logo are either trademarks or registered trademarks of Underwriters Laboratories, Inc. in the United States and/or other countries. Other trademarks, registered trademarks, and trade names may be used in this document to refer to either the entities claiming the marks and names or their products. Crestron disclaims any proprietary interest in the marks and names of others. Crestron is not responsible for errors in typography or photography. This document was written by the Technical Publications department at Crestron. ©2017 Crestron Electronics, Inc. Crestron Electronics, Inc. 15 Volvo Drive Rockleigh, NJ 07647 Tel: 888.CRESTRON Fax: 201.767.7576 www.crestron.com Installation Guide - DOC. 6680C (2020652) 07.17 Specifications subject to change without notice.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project