Local Display Software Manual www.homesystems-legrandgroup.com Local Display Software Manual Local Display Software Manual Contents Start 4 Interaction with the device 4 Device configuration 5 Configuration Parameters 7 Home page 8 Project items 9 Sub-pages 10 Display 10 Property/Project 11 Functions 12 Load control 12 Temperature control 13 Sound system 15 Scenarios 17 Programmed scenarios 18 Energy Data 19 Other settings 20 Economic evaluation setup 3 20 Local Display Software Manual Start Interaction with the device To Send or Receive the Configuration, Update the Firmware and Request Device Info, it is first of all necessary to connect the device to a PC, and make sure that the right port has been selected. Connect Local Display to the PC using a USB-miniUSB cable. For communication to take place, the device must be connected to the BUS. USB connection 4 Local Display Software Manual Device configuration The device can be configured by creating a new project, or by opening and existing one, which can then be changed and resent to the device. These operation can be performed inside the global area of the software, using some dedicated device management pushbuttons: File Menu 1 2 1. Import project 2. Export project To import or export the configuration project created in the specific area, select the device, and click the corresponding key. 5 Local Display Software Manual Device Menu 1 2 3 4 5 6 7 1. Open the specific device configuration area 2. Request Device Info 3. Receive the configuration from the connected device 4. Send the configuration to the connected device 5. Select a firmware for the device 6. Update the device firmware 7. Open the Help file for the device selected To interact with the device, first select it, and then click the desired function keys. 6 Local Display Software Manual Configuration Parameters • Identification name Enter the project name • Local address Enter the address of the device within the system • Standby Timeout(s) Select the time after which the device enters stand-by 7 Local Display Software Manual Home page The page is divided into three sections: On the left section ( ) is the “Project items” area. The centre section ( ), is the “Display” area. This is used to configure what will then be displayed as the Home Page of the device, and its subpages. On the right side of the screen ( ) is the “Property/Project area”, which can be used to configure the object selected in the Display area. 1 2 3 4 5 6 C A B 7 7 1. Options. Disable automatic save 2. View. Show/hide the info and error area Reset the default settings 3. Language. Select the software interface language 4. Display the device Help icons and some software information . 5. Save the project. 6. Return to the global area. 7. Pushbutton used to navigate through the pages. Navigate through sections Navigate through the configuration pages Navigate within a section Go to the start page 8 Local Display Software Manual 11 10 9 8 8. Delete an object. 9. Editing bar: Copy an object Cut an object Paste an object Align to the grid Select the skin 10. Open the section showing any information, or error messages. 11. File save display. Project items This area shows all the objects that can be used to build the pages. To do this simply drag the objects. You can include up to a maximum of 4 functions. 9 Local Display Software Manual Sub-pages Some objects are used for connection to other pages, where correlated objects can be grouped together. The configuration of the sub-pages is performed following the order the objects have been included in the Home Page. Display The “Display” area shows the future setup of the Home Page and the sub-pages of the device. 10 Local Display Software Manual Property/Project This area is split into two sections, which can be selected by clicking the labels at the bottom; the “Property” section shows the configuration fields for the object currently selected in the Display area. The “Project” section displays the objects by page in a tree menu format. In addition to selecting the objects, the user can also navigate through the project, selecting any available sub-pages. 6 1 2 3 4 5 1. Selected object page parameters. 2. Indications for the configuration of the selected parameters. 3. Selected object parameters. 4. Addition/Removal/Moving of objects. 5. Property/Project selection label. 6. Home page. 7. Sub-page. 11 7 Local Display Software Manual Functions LOAD CONTROL TEMPERATURE CONTROL SOUND SYSTEM SCENARIOS PROGRAMMED SCENARIOS ENERGY DATA Load control By including the “Load Control” function, Local Display will enable the user to check the status of the individual loads controlled by the central unit and, in case of disconnection, force them back on. 1 2 3 1. Configure the object (page): • Beep: enable/disable the notification sound emitted when the load is disabled by the central unit. • Alarm: enable/disable the display of an alarm screen when the load is disabled by the central unit. • Address: enter the central unit address. 2. Configure the object (element): • Description: customise the load description. • Switch-off priority: select the priority assigned to the load (from 1 to 255). • Interface: select the interface type, either Basic or Advanced interface. Add a load Remove the selected Load Remove all the loads Move the selected load up Move the selected load down 3. Once the page configuration/customisation operation has been completed, click the next page. 12 to go to Local Display Software Manual Temperature control By including the “Temperature control” function, Local Display will operate as a temperature probe, enabling the user to display the temperature measured, and change the parameters set by the central unit. 1 2 1. Configure the object: • Address: set the zone address of Local Display. • Local Probe: set if a local probe is present. • Probes Number: set the number of Slave probes. • Central unit: set if a central unit is present, and its type (99 zones o 4 zones). If no central unit is present, Local Display will operate as a room thermostat. • Address (4 zone central unit): if a 4 zone Central unit has been set, select the address of the central unit within the system. Operation of Local Display as a thermostat • Zone Actuators: click to set the actuators used to control the zone valves. 1 2 – – – – Heating Type: select the type of installation for the heating system (On/Off, Open/ Close, Fancoil, Gateway). Cooling Type: select the type of installation for the cooling system (On/Off, Open/ Close, Fancoil, Gateway). Address: enter the address of the zone actuator. Type: select if the actuator will operate for the heating system, the cooling system, or both. 1. Add an actuator. 2. Remove the selected actuator. 13 Local Display Software Manual • Pump Actuators: click the to set which actuators will control the pumps of the system. 1 2 – – – – Heating Delay: select the switch on delay in minutes for the heating system pumps. Cooling Delay: select the switch on delay in minutes for the cooling system pumps. Address: Enter the address of the pump actuator. Type: select if the pump actuator will operate for the cooling system, the heating system, or both. 1. Add a pump. 2. Remove the selected pump. • Thermal SetPoint: thermal protection temperature. • Anti-Freeze SetPoint: anti-freeze temperature. • Manual SetPoint: preset temperature for manual operation. • Season Mode: set the seasonal operating mode, selecting between summer and winter. 2. Once the page configuration/customisation operation has been completed, click the next page. 14 to go to Local Display Software Manual Sound system By including the “Sound system” function (single channel or multichannel, depending on the installed type) Local Display will enable the user to control the amplifier of the zone of reference, and select the sound source. 1 2 1. Configure the object: • Multimedia sources: click to configure the list of multimedia sources. 1 2 – – – Address: select an address for the sound source selected. Description: enter a customised description for sound source selected. Type: select the source type (Radio Source / AUX Source / Multimedia Source). The Radio Source refers to the Radio Tuner, the AUX source to an external source (e.g. CD player) connected to the Stereo Control, or to an RCA input, while the Multimedia source refers to any MyHOME_Screens that operate as system sources. 1. Add sources. 2. Remove the selected source. 15 Local Display Software Manual • Address: click – • to configure the address of the amplifier to control. A, PF: configure in the same way as the device to control Default Source Address: sound source that comes on when the amplifier is switched on. 2. Once the page configuration/customisation operation has been completed, click the next page. 16 to go to Local Display Software Manual Scenarios By including the “Scenarios” function, Local Display will enable the user to recall and change the scenarios saved in the scenario module. 2 1 3 1. Select a function from the “Display” area. 2. Configure the object: • Description: customise the description of the scenario module. • Address: click • Scenario: identification number of the scenario within the scenario module. • Icon: select an icon (among the 18 available) to associate to the scenario. to configure the address of the scenario module. 3. Once the page configuration/customisation operation has been completed, click the next page. 17 to go to Local Display Software Manual Programmed scenarios By including the “Programmed Scenarios” function Local Display will enable the user can recall and change the programmed scenarios saved in the scenario programmer. 2 1 3 1. Select a function from the “Display” area. 2. Configure the object: • Type of command: select the type of command (CEN/CEN Plus). • Pushbutton: select the scenario pushbutton. • Address: click • Icon: select an icon (among the 18 available) to associate to the scenario. to configure the CEN/CEN PLUS command address. 3. Once the page configuration/customisation operation has been completed, click the next page. 18 to go to Local Display Software Manual Energy Data By including the “Energy Data” function, Local Display will enable the user to display the consumption data for the configured lines. 1 2 1. Configure the object: • Type: select the type of meter. • Description: customise the description of the selected function. • Address: select the meter address (from 1 to 255). • Economic Evaluation: enable or disable the economic evaluation of the measurement. • Type: select the type of measurement between Consumption and Production. • Thresholds: enable the setting on Local Display of two alarm thresholds. • Beep: enable/disable the notification sound emitted when the thresholds have been reached. • Auto on: enable/disable the display of an alarm screen when the thresholds have been reached. • DataLogger: select “Present” when the Energy IP Data Logger is installed on the system. Add a consumption/production item Remove the selected consumption/production item Remove all the consumption/production items Move the selected consumption/production item up Move the selected consumption/production item down 2. Once the page configuration/customisation operation has been completed, click the next page. 19 to go to Local Display Software Manual Other settings Economic evaluation setup This section can be used to set tariffs that will be applied to the consumptions set in the “Energy data“ section. 1 2 3 1. Select the currency. 2. Enter the tariff. 3. Enter the number of decimals to display on Local Display for the evaluation. At the end of the configuration click to save the project, and and export the project, or send it to the device. 20 to return to the Global Area Local Display Software Manual 21 Legrand SNC 128, av. du Maréchal-de-Lattre-de-Tassigny 87045 Limoges Cedex - France www.legrand.com BTicino SpA Viale Borri, 231 21100 Varese www.bticino.com Legrand SNC reserves at any time the right to modify the contents of this booklet and to communicate, in any form and modality, the changes brought to the same.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project