Mastech MS8360G User manual
5.3 Replacing Test Leads ..........................28 Note-Important safety information, refer to the instruction manual. Caution, possibility of electric shock Equipment protected throughout by double insulation or reinforced insulation. Conforms to UL STD. 61010-1, 61010-2-032, 61010-2-033; Certified to CSA STD C22.2 NO. 61010-1, 61010-2-032,61010-2-033 Complies with European (EU) safety standards Earth (ground) TERMINAL Direct current Alternating current CAT III: MEASUREMENT CATEGORY III is applicable to test and measuring circuits connected to the distribution part of the building's low-voltage MAINS installation. 50±20Ω 188x92x50mm. 3.0V 50±20Ω 3 / -4°F~32°F 2 15 0.1°C/F 33°F~752°F 753°F~1832°F ±(5.0% of rdg +7 digit) ±(1.0% of rdg +3 digit) / ±(2.0% of rdg +4 digit) /1°F / ±(2.0% of rdg +4 digit) 5.3 Replacing Test Leads Replace test leads if leads become damaged or worn. WARNING Use meet EN 61010-031 standard, rated CAT III 600V, or better test leads.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project