Samsung SAMMWRSH10N Touch Wired Remote for NS0714DXEA Air Conditioner Installation Manual
Wired remote controller MWR-SH10N Air Conditioner installation manual This manual is made with 100% recycled paper. imagine the possibilities Thank you for purchasing this Samsung product. EN ES FR IT PT DE EL RU AR DB68-05567A-00 Contents Preparation Safety precautions . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .3 Before installation. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .5 Installation Wired remote controller installation . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . .6 Others Wired remote controller installation/service mode. . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 15 ENGLISH-2 Safety precautions This installation manual explains how to install a wired remote controller connected to the indoor unit of your Samsung system air conditioner. Please read this manual thoroughly before installing the product. (Please refer to appropriate installation for any optional product installation.) CAUTION Hazards or unsafe practices that may result in minor personal injury or property damage. WARNING Contact a service center for installation. fPotential risk of malfunction, water leak, electric shock and fire. Install the product with proper power supply. fPotential risk of fire or product damage. Consult the place of purchase or a contact center to disassemble or repair the product. fPotential risk of malfunction, electric shock, or fire. The electric work must be done by qualified person according to national wiring regulations and installation guide. fIf an unauthorized person performs the installation, any resulting defects can cause malfunctions, electrical shocks, or fire accidents. Install the product on a hard and even place that can support its weight. fIf the place cannot support its weight, the product may fall down and it may cause product damage. Do not move or reinstall the product on your discretion. fPotential risk of electric shock or fire. Check if the installation work is done correctly according to the installation manual. fIncorrect installation may cause electric shock or fire. When you want to dispose your wired remote controller, ask the service center. ENGLISH-3 PREPARATION Hazards or unsafe practices that may result in severe personal injury or death. 01 WARNING Safety precautions CAUTION Do not install the product where there’s combustible gas. fPotential risk of fire and explosion. Ensure no water gets into the wired remote controller. fPotential risk of electric shock or fire. Install the air conditioner away from direct exposure to sunlight, in room temperature range of 0 °C(32 °F) ~ 39 °C(102 °F). fPotential risk of electric shock or malfunction. Do not handle the product with sharp objects. fPotential risk of electric shock or product damage. Do not install the product in areas exposed to oil or vapor. fPotential risk of product damage or malfunction. Do not put undue stress on the power cable. fPotential risk of broken cable and fire. Do not install the product in areas with frequent use of acid or alkali spray. fPotential risk of electric shock or product malfunction Do not connect power cable to a communication terminal. fPotential risk of fire. Be cautious not to interfere any other electrical devices if the product is installed in a place such as hospital. fPotential risk of product malfunction. Please take the product gently after unpacking the package. fDrop or throwing can lead to the potential risk of product damage. ENGLISH-4 Before installation Optional accessories M4X16 screw (4) User manual (1) Installation manual (1) 01 Wired remote controller (1) PREPARATION CAUTION t The wired remote controller should be installed by an installation expert. t Check and confirm the power is off before installing your wired remote controller. t Install the wired remote controller cables in accordance with the electrical wiring rules, and allow it to pass through the inner area of the wall so that other people can’t reach it. External dimensions 122.0 (4.804) [Unit : mm(inch)] 94.2 (3.710) ENGLISH-5 19.5 (0.768) Wired remote controller installation Wired remote controller installation 1. Insert a small flat head screwdriver into the square groove in the bottom of your wired remote controller, and then pull up the front cover to separate it from the rear cover. 2. Arrange the communication cable so that they fit in the housing along the edges of the rear cover. Remove it 5 cm (2 inch) < When the cable is not concealed > 5 cm (2 inch) < When the cable is concealed > ENGLISH-6 3. Using more than two screws, firmly affix the rear cover of the remote controller to the wall, and then connect the communication and power cable [(F3,F4) or (3, 4)], making sure these cables have reasonable length, to the terminal at the back of the cover. F1 F2 V1 V2 F3 F4 NNJODI PSNPSF *OEPPSVOJU 8JSFOPUTVQQMJFE 4DSFXIPMF 8JSFESFNPUF DPOUSPMMFS NNJODI PSNPSF F3 F4 3FBSDPWFS K#FGPSFGJYJOHUIFSFBSDPWFSTFDVSFBUMFBTU NNJODI TQBDFPGVQQFSTJEFMFGU TJEFSJHIUTJEFBOECPUUPNTJEF 1$#UFSNJOBM K:PVNVTUGJUUIFTDSFXTJOUP UIFTDSFXIPMFT 'SPOUDPWFS K%POPUUJHIUFOUIFTDSFXTPOUIF 1$#UFSNJOBMXJUIFYDFTTJWFGPSDF 4. Reassemble your wired remote controller. tAlign the controller with the upper groove first, and insert it by turning it downward as shown in the figure. After assembly, check and confirm that no wires are stuck in the gap between the rear and front cover. CAUTION t When installing a wired remote controller by using a cable longer than 10 m(32.80 ft), you must install the communication cable and the power cable separately. (Electrical interference can cause your wired remote controller to malfunction.) t 8IFOJOTUBMMJOHZPVSXJSFESFNPUFDPOUSPMMFSPOUIFXBMMDPOTJEFSUIFTJ[FPGUIFXJSFIPMFBOETFMFDUBXJSFXJUIBQSPQFS thickness. t * GZPVJOTUBMMUIFXJSFESFNPUFDPOUSPMMFSCZVTJOHUXPQJFDFTPG17$XJSFSFNPWFUIFDNJODI PGUIF sheath of the cable and install it only with the two pieces of wires. (Recommended specification: AWG22) t .BYJNVNEJTUBODFGPSDPOOFDUJOHDPNNVOJDBUJPOBOEQPXFSDBCMFNGU t 4 DSFXTPOUIF1$#UFSNJOBMNVTUCFUJHIUFOFEXJUIMFTTUIBO/DNUJHIUFOJOHUPSRVF*GUIFUJHIUFOJOHUPSRVFJT HSFBUFSJUNBZEBNBHFUIFTDSFXUISFBE ENGLISH-7 INSTALLATION NNJODI PSNPSF 02 NNJODI PSNPSF Wired remote controller installation Tracking your indoor unit from the wired remote controller Indicates tracking in progress Displays the total number of indoor units searched 1. Tracking of your wired remote controller will automatically start when you turn on the power after installation. 2. If you want to perform tracking again after installation, then press the top right corner (hidden button) of the display for more than 7 seconds. - The system will reset, and tracking will start again. 3. During tracking, the total number of currently searched indoor units will be displayed. 4. It may take about 3 minutes at initial installation or when you re-set the power master setting. CAUTION t If you want to reset the system of your wired remote controller, then press the top right corner (hidden button) of the display for more than 7 seconds. ENGLISH-8 Individual control with your wired remote controller Individual control means that you are using one remote controller to control one indoor unit. 02 Outdoor unit $0.'' Indoor unit $0.'' Wired remote controller CAUTION INSTALLATION $0.'' Indoor unit $0.'' Wired remote controller Indoor unit $0.'' Wired remote controller t 3FHBSEMFTTPGUIFJOEPPSHSPVQBEESFTT3.$BEESFTT POMZUIFJOEPPSVOJUDPOOFDUFEUP$0.JTJOEJWJEVBMMZ controlled. ENGLISH-9 Wired remote controller installation Group control with your wired remote controller Group control means that you are using one wired remote controller to control two or more indoor units at the same time. 1. Using one wired remote controller to control three indoor Units Outdoor unit $0.'' $0.'' $0.'' Indoor unit Indoor unit $0.'' Indoor unit $0.'' Wired remote controller 2. Using one wired remote controller to control indoor units connected to different outdoor unit Outdoor unit $0.'' Indoor unit Outdoor unit $0.'' Wired remote controller $0.'' Indoor unit $0.'' CAUTION t 3FHBSEMFTTPGUIFJOEPPSVOJUTHSPVQBEESFTT3.$BEESFTT POMZUIFJOEPPSVOJUTDPOOFDUFEUP$0.BSF controlled in group. t Regardless of your outdoor units, you can control a maximum of 16 indoor units as a group. t When controlling group of indoor units connected to different outdoor unit, address of the each outdoor unit must be set differently. ENGLISH-10 Controlling 2-Remote controller 2-Remote controller is controlling one indoor unit or a group of indoor units with two remote controllers. 02 Outdoor unit INSTALLATION $0.'' Indoor unit $0.'' Wired remote DPOUSPMMFS.BTUFS CAUTION Wired remote controller (Slave) t For the slave wired remote controller settings, please refer to the sections about the additional functions of the wired remote controller. (Refer to 'Additional Functions of your wired remote controller' main menu 1 ¤ sub menu 1, master/slave setting) t You can only use several functions on the master setting. - On-off timer - Outing - Easy tuning - Displays the total number of indoor units - Adjust temperature and select mode when relative temperature is displayed t8JSFESFNPUFDPOUSPMMFSXJUIPVUBNBTUFSTMBWFTFUUJOHJTQSPQFSMZDPOOFDUFECVU*GZPVOFFEUPTFUBTQFDJöD wired remote controller as a master, you have to set master/slave in the service mode 1-1. ENGLISH-11 Wired remote controller installation Initializing your wired remote controller communication If the number of indoor unit is decreased while you are using your remote control to control one indoor unit or a group of indoor units, then you need to initialize your remote controller communication. Press the top right corner (hidden button) of the display for more than 7 seconds. - Your wired remote controller will be initialized, and the device will search for the indoor units connected to your wired remote controller again. ENGLISH-12 Errors displayed on your wired remote controller Error codes for the wired remote controller and the indoor units connected to your wired remote controller will be displayed in the LCD display. 02 INSTALLATION LCD Display When an error occurs in your indoor/outdoor units (product group display : A) - The product address for the error will be displayed, followed by the error code. Example : Error 101 occurs for Indoor Unit no. 10 (decimal digits) Indoor unit Outdoor unit address (hexadecimal digits) Indoor unit main address (hexadecimal digits) When an error occurs in your wired remote controller - Only an error code will be displayed. (No address will be displayed.) Example : Error 601 has occurred at your wired remote controller. ENGLISH-13 Error code Wired remote controller installation Wired remote controller error codes Display Description Communication error between wired remote controller and indoor units (When communication is lost for over 3 minutes after detecting the indoor unit and the wired remote controller) /PDPNNVOJDBUJPOCFUXFFO.BTUFS.BJO BOE4MBWF4VC XJSFESFNPUFDPOUSPMMFST No communication between wired remote controller and indoor units (Including communication error between indoor units and outdoor units) - Exceeded maximum number of indoor unit connection (16 indoor units) - Reset is required after checking the number of indoor units Two or more wired remote controllers set as slave(sub) Temperature sensor open/short error &&130.FSSPS t For the error codes for your indoor/outdoor units, refer to the installation manual of each device. CAUTION ENGLISH-14 Wired remote controller installation/service mode Additional functions of your wired remote controller ʒʓ Page OTHERS .PWFNFOV Setting value .PWFQBHF 1. If you want to use the various additional functions for your wired remote controller, press the top right corner (hidden button) of the display for more than 3 seconds and drop it. Then you can press [ + ]/[ - ] buttons and select No.3 and press [ OK ] button. - You will enter the additional function settings, and the main menu will be displayed. - If you select the other number and press [ OK ] button, then you can go back to the normal display. 2. Refer to the list of additional functions for your wired remote controller on the next page, and select the desired menu. - Using the [ + ]/[ - ] buttons, select a main menu number and press the [ Mode ] button to enter the sub-menu setting screen. - Using the [ + ]/[ - ] buttons, select a sub menu number and press the [ Mode ] button to enter data setting screen. - Using the [ + ]/[ - ] buttons, select the settings. - Press the [ Fan ] button to select page. - Press the [ OK ] button to save the current settings. the [ OK ] button is invalid on the main menu or sub menu setting screen. - Press the [ Cancel ] button for more than 3 seconds to exit to normal mode without saving settings. ENGLISH-15 03 Sub menu .BJONFOV Wired remote controller installation/service mode Additional functions of your wired remote controller NOTE Main menu t If communication initialization is needed after the setting, the system will reset automatically and communication will be initialized. Sub menu Function description Cooling/Heating selection 1 2 1 5 6 7 0 2 1 2 1 2 4 3 4 Setting value Page Save location Value Factory default 0 - Cooling/Heating, 0 01 Wired remote controller 1 - Cooling only Use of wireless remote controller 0 - No use, 1 - Use for indoor unit .BTUFS4MBWFXJSFESFNPUF .BTUFS4MBWF controller 0 - Celsius(°C), Temperature unit 1 - Fahrenheit(°F) 0 - Indoor unit, Temperature sensor selection 1-Wired remote controller 0 - No use, 1 - Use Wired remote Use of average temperature controller Use of Auto mode 0 - No use, 1 - Use setting/ 0 - Set temperature checking (2) 1 - Room Temperature display temperature 2 - Relative temperature 1)* Room -9 ~ 40 °C temperature Temperature control reference compensation Temperature compensation value -9.9 ~ 9.9 °C 2)* Number of connected Number of indoor units 0 ~ 16 units Temperature increment/decrement unit 0 - 1 °C, 1 - 0.5 °C, 2 0.1 °C (°C only) 0 - Unchanged, Factory option setting 1 - Factory setting Software code Software code Software version Software version Target address of Target address setting indoor unit (Example : 20 02 1F) 0~4F (in hexadecimal .BJOBEESFTTTFUUJOHDIFDLJOH digits) Indoor unit 3.$BEESFTTTFUUJOHDIFDLJOH 0x00~0xFE 4)* address/ option setting/ checking 3)* Basic option setting/checking Option code Wired remote controller setting/ checking (1) 5 Install option setting/checking Option code 6 Install(2) option setting/checking Option code ENGLISH-16 1 02 Wired remote controller 0 03 Wired remote controller 0 04 Wired remote controller 0 01 Wired remote controller 0 1 02 03 Wired remote controller Wired remote controller 0 04 Wired remote controller Current sensor temperature 01 Wired remote controller 0 02,03 Wired remote controller 0 01 None 0 01 Wired remote controller 0 01 None None None 01~03 01~03 None None 7JFXNBTUFS 01~03 None 01 None 01 None .BJOBEESFTTPG target 3.$BEESFTTPG target Basic option of target Install option of target Install(2) option of target 01~20 5)* 01~20 5)* 01~20 5)* None None None Main menu Sub menu 2 4 1 7 2 3 8 0 1 2 3 1 2 3 Use of discharge temperature control Cooling discharge temperature 0 - No use, 1 - Use 0 01 Indoor unit 8~18 °C 15 02 Indoor unit Heating discharge temperature 30~43 °C 38 03 Indoor unit Cooling discharge temperature 13~25 °C 18 01 Fresh duct indoor unit Heating discharge temperature 18~30 °C 25 02 Fresh duct indoor unit 0 - No use, 1 - Use 0 01 AHU Indoor unit 8~25 °C 15 02 AHU Indoor unit 18~43 °C 38 03 AHU Indoor unit Use of discharge temperature control Cooling discharge temperature Heating discharge temperature Indoor unit view Indoor unit view master setting/ Indoor unit view 01~03 master address checking master (Example : 20 02 1F) Indoor unit master .PEFNBTUFS .PEFNBTUFSJOEPPSVOJU address (Example : none 01~03 checking indoor unit 20 02 1F) setting/ .PEFNBTUFSJOEPPSVOJUTFUUJOH 0-No use, 1-Use, checking none 01 6)* 2-Release 7)* Status of automatic air volume setting 1 0 01 Automatic air volume operation 1 0 01 Automatic air volume voltage setting 1 2 01 1 0 Factory setting Reset Power master reset 8)* 1 0 Outdoor units reset 1 0 None None None Indoor unit Indoor unit Indoor unit None None None 1)* Relative temperature means that the wired remote controller only displays the temperature increase or decrease (± 3) compared to the reference temperature. Reference temperature is determined by other controller's desired temperature setting. &YBNQMF%.4TFU¡$¡' ¤ 24 °C (75 °F) is reference temperature. Wired remote controller displays it as '0' ) 2)* Only the celsius temperature unit is allowed when this function setting and checking in the service mode. For the fahrenheit temperature, you need temperature conversion before this function setting and checking by the celsius temperature unit. 3)* When setting the address/option, you can set the target indoor unit by selecting sub menu 1. ENGLISH-17 OTHERS 3 Indoor unit discharge temperature setting/ checking 2)* Fresh duct indoor unit discharge temperature setting/ checking 2)* AHU Indoor unit discharge temperature setting/ checking 2)* 7JFXNBTUFS setting/ checking Save location 03 5 Setting value Page Value Factory default Function description Wired remote controller installation/service mode 3.$ _'3.$ _'IFYBEFDJNBMEJHJUT 8IFO3.$ JTTFUBT'3.$ TFUUJOHJTPOMZBWBJMBCMFVQUP&3.$ (SPVQDIBOOFM3.$ (SPVQBEESFTT t .BJOBEESFTTPGUIFJOEPPSVOJUJTEJTQMBZFEBOEFOUFSFEJOIFYBEFDJNBMEJHJUT1MFBTFSFGFSUPUIFGPMMPXJOHUBCMF NOTE Hexadecimal Decimal 00 0 01 1 02 2 03 3 04 4 05 5 06 6 07 7 08 8 09 9 0A 10 0B 11 0C 12 0D 13 0E 14 0F 15 Hexadecimal Decimal 10 16 11 17 12 18 13 19 14 20 15 21 16 22 17 23 18 24 19 25 1A 26 1B 27 1C 28 1D 29 1E 30 1F 31 Hexadecimal Decimal 20 32 21 33 22 34 23 35 24 36 25 37 26 38 27 39 28 40 29 41 2A 42 2B 43 2C 44 2D 45 2E 46 2F 47 Hexadecimal Decimal 30 48 31 49 32 50 33 51 34 52 35 53 36 54 37 55 38 56 39 57 3A 58 3B 59 3C 60 3D 61 3E 62 3F 63 Hexadecimal Decimal 40 64 41 65 42 66 43 67 44 68 45 69 46 70 47 71 48 72 49 73 4A 74 4B 75 4C 76 4D 77 4E 78 4F 79 5)* The total option codes are 24 digits. You can set six digits at a time and it is distinguished by number. - Press the [ Fan ] button to go to the next page. CAUTION t Indoor unit's option setting is from SEG1 to SEG24. - SEG1, SEG7, SEG13, SEG19 cannot be set and will not be displayed. - SEG2 is a type of option and it cannot be set. - Each SEG is displayed in the corresponding page below: . SEG2 ~ SEG6 : Page1 ~ Page5 . SEG8 ~ SEG12 : Page6 ~Page10 . SEG14 ~ SEG18 : Page11 ~ Page15 . SEG20 ~ SEG24 : Page16 ~ Page20 - Press the [ Fan ] button to go to the next page. Page1 Page2 Page3 Page4 SEG2 SEG3 SEG4 SEG5 X X X X Page11 Page12 Page13 Page14 SEG13 SEG14 SEG15 SEG16 SEG17 2 X X X X SEG1 0 Page5 Page6 Page7 SEG6 SEG7 SEG8 SEG9 X 1 X X Page15 Page16 Page17 SEG18 SEG19 SEG20 SEG21 X 3 X X Page8 SEG10 X Page18 SEG22 X Page9 SEG11 X Page19 SEG23 X PAGE 1 PAGE 2 PAGE 3 <SEG 2> <SEG 3> <SEG 4> ENGLISH-18 Page10 SEG12 X Page20 SEG24 X 1. Press the top right corner (hidden button) of the display for more than 3 seconds and drop it. Then you can press [ + ]/[ - ] buttons and select No.3 and press [ OK ] button. - .BJONFOVXJMMCFEJTQMBZFE1SFTT [ + ]/[ - ] buttons and select No.1. 2. Press [ Mode ] button to select the number you will set. - Press [ + ]/[ - ] buttons and select No.1. 3. Press [ Mode ] button to enter the data setting stage. - When you enter the setting stage, the current setting value will be displayed. 4. Press [ + ]/[ - ] buttons to select No.1 - The wired remote controller option is set from both cooling and heating to cooling only. 5. Press the [ Fan ] button to select page No.2, then Press [ + ]/[ - ] buttons to select No.0 - The wired remote controller option is set to no use of wireless remote controller. 6. Press the [ OK ] button to save the current settings. - Press the [ Cancel ] button for more than three seconds to exit to normal mode without saving settings. ENGLISH-19 OTHERS The example of installation/service mode setting 03 6)* Setting is available when there is only 1 indoor unit connection and while the indoor unit operation is not operating. 7)* You can see no.0(no use) and no.1(use) while mode master indoor unit setting. For the mode master indoor unit setting, select the no.1(use). And you can release the mode master unit setting by selecting the no.2(release). 8)* Power master reset is a setting needed to supply optimized power to wired remote controller when multiple indoor units are connected to wired remote controller in a group.
* Your assessment is very important for improving the workof artificial intelligence, which forms the content of this project
Samsung AR09KSWSJWKXCV Smart Whisper 9 MBH Wall Mount Outdoor 1 Tons Mini-Split Single-Zone Installation manual