Technical Data Industrial Tower Uninterruptible Power Supply Specifications Bulletin Numbers 1609-P Topic Page 1609-P Specifications 2 1609-P Approximate Dimensions and Shipping Weights 3 Additional Resources These documents contain additional information concerning related products from Rockwell Automation. Resource Description Industrial Automation Wiring and Grounding Guidelines, publication 1770-4.1 Provides general guidelines for installing a Rockwell Automation industrial system. Product Certifications website, http://www.ab.com Provides declarations of conformity, certificates, and other certification details. You can view or download publications at http://www.rockwellautomation.com/literature/. To order paper copies of technical documentation, contact your local Allen-Bradley distributor or Rockwell Automation sales representative. 1609-P Tower Uninterruptible Power Supply Specifications Specifications Electrical Ratings Input 1609-P3000N 1609-P3000A 1609-P5000E 1609-P8000E 1609-P10000E V nom. (V AC) 120 230 208/230 208/230 208/230 Voltage Range, default (V AC) 90…150V Current (A) 20 nom., 28 max. Capacity 160…280V 11 nom., 14 max. 3000VA (2100 W) Frequency 19 nom., 24 max. 30 nom., 40 max. 39 nom., 48 max. 5000VA (3500 W) 8000VA (6400 W) 10 000VA (8000 W) 45…65 Hz (self sensing) PFC Output > 0.95 Protection N/A V nom. 120V Capacity N/A N/A 3000VA (2100 W) Protection 5000VA (3500 W) Reg. Protection +/- 2% static +/- 5% dynamic <5% at full load Crest Factor 3:01 On Battery 86% On Line 88% Surge IEC 1000-4-4 Overload 125% : 1 minute, 150% : 30 seconds Output Short Input circuit breakers and/or premises branch protection Yes Bypass N/A Safety EN 61000-3-2 UL 1778, cULus, IEC 60950 EMC FCC (Class A) EN50091-2 FCC (Class A), EN50091-2 Markings cULus, CSA CE Indicators and Controls Sealed Lead Acid, valve regulated, hot swappable, user replaceable 192V Charger Temperature compensated current limited, float charger Less than 3 hours to 90% capacity Less than 3 hours to 85% capacity Lifetime 2…4 years @ 25 °C ambient Temperature 0…40 °C (operating), -20…60 °C (short term storage) Altitude 10 000 ft (operating) Humidity 0…95% non-condensing (operating) Heat Output (Full Load) 655 BTU/hour Audible Noise <50 dB @ 1 meter (full load) AC Outlets (6) NEMA 5…15 (2) NEMA 5…20 AC Inlets NEMA L5…30 DB9 Communication 5…7 minutes @ full load, 13…18 minutes @ half load Voltage Recharge Time Rear Panel cULus, CSA, CE 14 minutes @ full load, 34 minutes @ half load Type Environment 70 A input circuit breaker UL 1778, cULus, IEC 60950 Run Time Battery Pack N/A +/- 1% static, +/- 5% dynamic Thermal Protection Regulatory 10 000VA (8000 W) N/A Nominal +/- 3 Hz THD Efficiency 8000VA (6400 W) 3…15 A circuit breaker Frequency On Battery 70 A input circuit breaker 208V 1040 BTU/hour 1536 BTU/hour 2216 BTU/hour <55 dB @ 1 meter (full load) (8) IEC C13 (2) IEC C19 IEC C14 (12) IEC C13 (2) IEC C19 IEC C20 3 position terminal blocks Serial and Contact Closures EPO Via Contact Closure Network Via Network Management Card (1609-NMC, provided as standard with units >3 KVA) LED Status On-line, In Bypass Mode, On Battery, Overload and Replace Battery, Fault, Bar graph for Load, Bar graph for Battery Fuel Gauge, Bar graph for Measured Input Voltage when recessed switch is held Control (Front panel) On/self-test/alarm silence/cold start/load off Audible On Battery: 4 short beeps repeats about 20 seconds (mutable), Low Battery: persistent 0.5 second beep every 1 second (mutable), In Bypass: continuous beeping, Failure: continuous tone, Replace Battery: occasional on/off change - single beep Wiring of the UPS should be performed by a qualified electrician. Use appropriate size wires. In 230V AC applications, the UPS must be protected with a circuit breaker that complies with European standards for branch rated protection per the country of installation. In 208V AC applications, the UPS must be protected by a dual-pole, 10 A branch rated, UL 489 circuit breaker. The 120V AC 1609-P3000N has supplementary circuit breaker protection. The unit should be protected by a singlepole, 15 A branch rated, UL 489 circuit breaker. Allen-Bradley part number 1492-MCAA115 is suggested. The branch circuit breaker must be off prior to wiring the unit. 2 Rockwell Automation Publication -1609-TD001A-EN-P 1609-P Tower Uninterruptible Power Supply Approximate Dimensions Notes 208V AC applications: The 1609-P5000E, 1609-P8000E, and 1609-P10000E, ship ready for 230V AC sources. When operating one of these in 208V AC applications, the UPS low transfer voltage settings are adjusted through the PowerChute® software or the Network Management Card. Refer to the PowerChute® User Guide or the Network Management Card instructions for details. Approximate Dimensions and Shipping Weights Approximate dimensions are shown in millimeters (in.) unless otherwise indicated. Dimensions are not to be used for manufacturing purposes. (5.1) (25.3) (17.4) (10.3) (25.3) (17.4) Approximate Shipping Weights Output Power Input Voltage Cat. No. Approx. Shipping Weight [kg (lb)] 63.5 (140) 3000VA (2100 W) 120V AC 1609-P3000N 3000VA (2100 W) 230V AC 1609-P3000A 63.5 (140) 5000VA (3500 W) 208/230V AC 1609-P5000E 63.5 (140) 8000VA (6400 W) 208/230V AC 1609-P8000E 128.8 (284) 10000VA (8000 W) 208/230V AC 1609-P10000E 128.8 (284) Approximate dimensions are shown in millimeters (in.) unless otherwise indicated. Dimensions are not to be used for manufacturing purposes. Rockwell Automation Publication -1609-TD001A-EN-P 3 1609-P Tower Uninterruptible Power Supply Approximate Dimensions (3.7) (22.8) (4.8) (25.3) (5.1) (17.4) (25.3) (5.1) (17.4) Approximate Shipping Weights Description Cat. No. Approx. Shipping Weight [kg (lb)] Replacement battery 1609-PBAT 37.2 (82) External battery pack 1609-PXBP 101.2 (223) 1609-5000CCT 63.5 (140) 1609-PRK1 3.6 (8) 5000VA CCT (120V step down transformer) Rail kit 4 Rockwell Automation Publication -1609-TD001A-EN-P Important User Information Read this document and the documents listed in the additional resources section about installation, configuration, and operation of this equipment before you install, configure, operate, or maintain this product. Users are required to familiarize themselves with installation and wiring instructions in addition to requirements of all applicable codes, laws, and standards. Activities including installation, adjustments, putting into service, use, assembly, disassembly, and maintenance are required to be carried out by suitably trained personnel in accordance with applicable code of practice. If this equipment is used in a manner not specified by the manufacturer, the protection provided by the equipment may be impaired. In no event will Rockwell Automation, Inc. be responsible or liable for indirect or consequential damages resulting from the use or application of this equipment. The examples and diagrams in this manual are included solely for illustrative purposes. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. cannot assume responsibility or liability for actual use based on the examples and diagrams. No patent liability is assumed by Rockwell Automation, Inc. with respect to use of information, circuits, equipment, or software described in this manual. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc., is prohibited. Documentation Feedback Your comments will help us serve your documentation needs better. If you have any suggestions on how to improve this document, complete this form, publication RA-DU002, available at http://www.rockwellautomation.com/literature/. Allen-Bradley, Rockwell Software, Rockwell Automation, and LISTEN. THINK. SOLVE are trademarks of Rockwell Automation, Inc. Trademarks not belonging to Rockwell Automation are property of their respective companies. Rockwell Otomasyon Ticaret A.Ş., Kar Plaza İş Merkezi E Blok Kat:6 34752 İçerenköy, İstanbul, Tel: +90 (216) 5698400 Publication 1609-TD001A-EN-P - August 2014 Copyright © 2014 Rockwell Automation, Inc. All rights reserved. Printed in the U.S.A.