GB.ELQZ455.050101 Installation Instructions for the ELQZ-2-455-1-0/1 Push Button, GOLD 1. General The push button kit consists of a non-locking push button and a surface-mounting frame. 2. Field of application The push button is used for prolonging the operation of the GOLD air handling unit’s fans at the high-speed or low-speed setting, outside the ordinary operating periods set in the GOLD unit’s internal time switch. The push button can also be used for controlling the GOLD unit when the internal time switch is not used. 3. Operation The GOLD air handling unit is controlled to the appropriate operating conditions by means of an impulse transmitted from the push button. The time delay can be preset in the GOLD unit’s hand-held micro terminal. See the Section 6.2.7 of the Operating and Maintenance Instructions. Important! The push button cannot be used for controlling the GOLD air handling unit to operate at low speed when it is running at high speed. Push button with indicating lamp, ELQZ-2-455-1-1 4. Installation For recessed installation in equipment cubicles, dimension c-c is 60 mm. For surface mounting, use the surface-mounting frame supplied. 5. Technical data Enclosure Class: Colour: Materials: IP 20 E white, NCS 1005Y20R Sheet steel, thermoplastic. Does not contain halogen ated PVC or lead. Red, 24V~ Indicating lamp Dimensions: Push button: 82x82 mm Surface-mounting frame (WxHxD) 82x82x18 mm Speciﬁcations are subject to alteration without notice. Push button without indicating lamp, ELQZ-2-455-1-0 www.swegon.se 1 GB.ELQZ455.050101 6. Electrical Wiring The electrical wiring should be carried out by a qualiﬁed electrician in accordance with local regulations. Low speed GOLD version B High speed GOLD version B Terminals on controller card Terminals on controller card 29 30 31 32 1 2 1 2 1 2 1 2 L X L X X ELQZ-2-455-1-0 ELQZ-2-455-1-0 Low speed with indicating lamp GOLD version B High speed with indicating lamp GOLD version B 103 104 19 20 29 30 2 3 4 1 1 2 H1 3 103 104 1 L X ELQZ-2-455-1-1 Indicating lamp lit while the GOLD air handling unit is in operation. 2 www.swegon.se 2 1 4 H2 X 16 17 X 31 32 3 4 2 H1 3 4 H2 X L X ELQZ-2-455-1-1 Indicating lamp lit while the GOLD air handling unit’s fans operate at high speed. Speciﬁcations are subject to alteration without notice.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project