Addressable Peripherals UL, ULC, CSFM Listed; FM Approved; MEA (NYC) Acceptance* 4090-9117 Addressable Power Isolator for 4100ES, 4100U and 4010ES Series Fire Alarm Controls Features 24VB- 24VA- ADDRESSABLE PWR ISOLATOR IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 34 5 6 78 ADDRESS CODE 4090-9117 Addressable Power Isolator for 4100ES/4100U/4010ES IDNet Communications (shown approximately 1/2 size) Product Selection Model 4090-9117 4090-9801 4090-9802 Description Addressable Power Isolator For semi-flush mounted box For surface mounted box Optional trim plate with LED viewing window, includes mounting screws; galvanized steel Specifications Electrical Current Rating 2 A maximum @ 32 VDC maximum Input Power 10 mA maximum @ 24 VDC, system power Communications Description Short Circuit Isolation. Under normal conditions, the 4090-9117 Addressable Power Isolator provides continuity between ports. In the event of a short circuit, or if requested from the control panel, the isolator opens a two-pole electronic switch, isolating both power circuit conductors. Operation. Isolators power-up in isolation mode and are directed to connect by the control panel. If the output wiring is acceptable, the isolator will connect to the rest of the circuit. If the output wiring is shorted, the isolator remains isolated. Status Tracking. The isolator reports to the panel when it is in isolation mode and the extent of shorted wiring is available at the panel by identifying non-communicating device addresses. [Isolators are assigned sequentially to low number addresses to expedite Signaling Line Circuit (SLC) power-up. Refer to Installation Instructions 574-873 for additional information.] Earth Faults. During system installation, earth faults frequently occur. Finding these faults normally requires extensive wiring disconnection. With the Addressable Power Isolator, earth faults on fire alarm system power wiring can be more quickly located to expedite repair. 24VB+ 24VA+ Dual port, bi-directional power isolator for use with ® Simplex 4100ES, 4100U and 4010ES Series fire alarm control panels: Either port can serve as an input or output, ports are automatically separated when a power wiring short circuit occurs Isolation can also be activated from the 4100ES, 4100U, or 4010ES control panel for system diagnostics For use with fire alarm control panel system power, rated for up to 2 A @ 32 VDC Isolators communicate their location specific address and status, and accept control via 4100ES, 4100U, or 4010ES IDNet™ communications Small size fits into 4” square electrical box and allows convenient mounting where protection is required Visible LED flashes to indicate communications; optional covers are available to view LED after installation Earth fault isolation reduces time to fix wiring problems: Built-in control panel diagnostics can activate the addressable power isolator, assisting in locating earth fault conditions – the most common installation wiring problem For Class B or Class A power wiring: Power is monitored from either port Two Isolators can be connected to produce Class A power wiring that can optimize operation by maintaining connection with devices outside of the isolated wiring section UL listed to Standard 864 Wire Connections 4100ES/4100U/4010ES IDNet, 1 address, one unit load Screw terminals for input and output wiring, 18 to 14 AWG (0.82 mm2 to 2.08 mm2), two wires/terminal; up to 12 AWG (3.31 mm2), one wire/terminal Wiring Reference Power Wiring IDNet Communications Wiring Reference Refer to individual devices for wiring distances Compatible with 2081-9028 Circuit Protector Up to 2500 ft ( 762 m) from fire alarm control Up to 10,000 ft ( 3048 m) total wiring distance (including T-Taps) Compatible with Simplex 2081-9044 Overvoltage Protectors Mechanical Dimensions 4-1/8” H x 4-1/8” W x 1-3/8” D (105 mm x 105 mm x 35 mm) Temperature Humidity Range 32° to 120° F (0° to 49° C) indoor operation only 10 to 90% RH at 90° F (32° C) * This product has been approved by the California State Fire Marshal (CSFM) pursuant to Section 13144.1 of the California Health and Safety Code. See CSFM Listing 7300-0026:252 for allowable values and/or conditions concerning material presented in this document. It is subject to re-examination, revision, and possible cancellation. Additional listings may be applicable; contact your local Simplex product supplier for the latest status. S4090-0006-6 Power Isolator Multi-Floor Example 1 Earth Fault Isolation. In the event of an earth wiring fault, each floor’s power wiring can be individually isolated using 4100ES/4100U/4010ES control panel diagnostics. This narrows the search area by disconnecting the isolated wiring section and can result in decreasing the time required to locate and correct the earth fault. Short Circuit Isolation. The one-line diagram on this page shows a multiple floor example with Class B IDNet communications and conventional Class B power wiring. Each floor’s wiring starts at an isolator. If any floor wiring beyond the isolator experiences a short circuit, each floor will be individually separated from the next, preventing the short circuit from disabling the entire wiring run. Duct sensor housing with relay output I air handling syste m in which it is installed, smoke variab dilution lesaatification such over aswhich which this device is attached as a secondary detection device. DO NOT REMO VE THI S NOTICE! 24VA+ 24VB+ 24VA- 24VB- ADDRESSABLE PWR ISOLAT OR IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE Third floor I 1 +0V 24V ZONE PWR 5 + 2 ZONE PWR 6 3 IDC + 4+IDNET - IDNET IDC - 7 8 To local zone 1 5 2 6 3 Zone Adapter Module 7 CO. SIMPLEX TI ME R ECORDER 4090-9101 MONITOR Z AM, CLASS B INSTAL. INSTR. 574-183 8 DATE COD E: 1 4 24VA+ 24VB+ 24VA- 24VB- ADDRESSABLE PWR ISOLAT OR IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE Second floor I 24VA+ 24VB+ 24VA- 24VB- System power , 24 VDC nominal ADDRESSABLE PWR ISOLAT OR First floor IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE In-duct sensor with relay output 4100ES/4100U/4010ESIDNet communications , 2 wire (see wiring notes ) Class B risers 24VA+ 24VB+ 24VA- 24VB- 4090 -9117 IDNet Addressable Power Isolator ADDRESSABLE PWR ISOLAT OR IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE TrueAlarm sensor with relay base I IDNet Addressable Isolator 4090 -9116 (see note 3) Wiring Notes : 1. This is a one -line drawing showing only IDNet communications and power wiring . 2. Operation of the 4090 -9117 Addressable IDNet Power Isolator requires connection to a 4100ES, 4100U or 4010ES IDNet communications channel . Simplex 4100 ES Series Fire Control Panel (shown for reference) 3. IDNet isolators are shown for typical reference but are not required . 2 S4090-0006-6 Power Isolator Multi-Floor Example 2 Class A Wiring. The illustration below is a modification of Example 1. Each floor wiring loop connects to the next floor in a Class A connection. From the last device, the wiring returns to the panel providing a secondary path that is monitored for loop integrity. Class A power wiring is available from a 4100ES/4100U/4010ES Fire Control Panel programmed for this application using two 40909117 Power Isolators mounted close-nippled at the panel. Diagnostic Assistance. It is recommended that for Class A wiring, isolators be located as the first and last devices in the loop (as shown below). With the resulting wiring isolation flexibility, locating earth wiring faults can be made easier Last Remote Powered Device 24VA+ Last IDNet Device (see note 3) 24VB+ 24VA- Alternate Wiring Example Class A riser with Class B taps using Isolators 24VB- IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE I Duct sensor housing with relay output I air handling syste m in which it is installed, variab les such over as which which this device is attached as a secondary detection device. DO NOT REMO VE THI S NOTICE! 24VA+ 24VB+ 24VA- 24VB- IDNet+ IDNetON 1 2 3 4 5 1 2 3 4 5 6 78 6 7 8 ADDRESS C ODE Third floor I 1 +0V 24V ZONE PWR 5 + 2 ZONE PWR 6 3 IDC + 4+IDNET - IDNET IDC - 7 8 To local zone 1 5 2 6 3 4 24VA+ 7 CO. SIMPLEX TI ME R ECORDER 4090-9101 MONITOR Z AM, CLASS B INSTAL. INSTR. 574-183 8 DATE COD E: 1 24VA+ 24VB+ 24VA- 24VB- 24VA- 24VB+ 24VA+ 24VB- 24VA- IDNet+ IDNet- 24VB+ 24VB- IDNet+ ON 1 2 3 4 5 6 78 ADDRESS C ODE IDNet- ON 1 2 3 4 5 6 78 ADDRESS C ODE IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE Zone Adapter Module Second floor I 24VA+ 24VB+ 24VA- 24VB- IDNet+ IDNetON 1 2 First floor 3 4 5 6 7 8 1 2 3 4 5 6 78 ADDRESS C ODE First Remote Powered Device First IDNet device (see note 3) In-duct sensor with relay output Class A system power 24 VDC nominal 4100ES/4100U/4010ES IDNet communications , 2 wire (see wiring notes ) Primary Return 24VA+ 24VB+ 24VA- 24VB- 4090-9117 IDNet Addressable Power Isolator Two, 4090-9117 IDNet Addressable Power Isolators, close-nippled in conduit ADDRESSABLE PWR ISOLAT OR IDNet+ IDNetON 1 2 3 4 5 6 7 8 1 2 3 4 5 6 78 24VA+ 24VB+ 24VA+ 24VB+ 24VA- 24VB- 24VA- 24VB- ADDRESS C ODE ADDRESSABLE PWR ISOLAT OR IDNet+ IDNet+ IDNet- IDNetON 1 2 3 4 5 1 2 3 4 5 6 78 ADDRESS C ODE 6 7 8 ON 1 2 3 4 5 1 2 3 4 5 6 78 6 7 8 ADDRESS C ODE TrueAlarm sensor with relay base I Class B System power, 24 VDC nominal IDNet Addressable Isolator 4090-9116 (see note 3) Wiring Notes: 1. This is a one-line drawing showing power wiring and IDNet communications only . Class A power requires using two 4090-9117 Power Isolators located close-nippled at the panel with Class A operation performed by panel control of the Isolators. 2. Operation of the 4090-9117 Addressable IDNet Power Isolator requires connection to a 4100ES, 4100U or 4010ES IDNet Communications . Channel 3. IDNet isolators are shown for typical reference but are not required. For Class A IDNet SLCs, locate isolators as first and last device on the SLC for service convenience. Simplex 4100ES Control Panel (shown for reference) 3 S4090-0006-6 Mounting Information Status indicating LED 4" (102 mm) square box, 2-1/8" (54 mm) minimum depth, RACO 232 or equal (supplied by others) 4090-9117 Addressable Power Isolator Double gang blank cover plate and mounting screws, for use when LED is not required to be externally viewed (supplied by others) Mounting Reference, Double Gang Blank Cover Plate Light pipe for LED viewing 4-5/16" (109 mm) 4-9/16" (116 mm) 4-9/16" (116 mm) 4-5/16" (109 mm) 4090-9801, Trim plate for semi-flush mounted box 4090-9802, Trim plate for surface mounted box Optional Trim Plates for Visible LED Tyco is a registered trademark of Tyco International Services GmbH and is used under license. Simplex, the Simplex logo, TrueAlarm, and IDNet are trademarks of Tyco International Ltd. and its affiliates and are used under license. SimplexGrinnell LP Westminster • Westminster, MA • 01441-0001 • USA www.simplexgrinnell.com S4090-0006-6 © 2011 Tyco. All rights reserved. All specifications and other information shown were current as of document revision date and are subject to change without notice.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project