Mr Slim New PEAD-RP100EA2 Product Information PEAD-RP100EA2 Power Inverter Heat Pump R410A Ceiling Concealed Ducted System Advanced inverter technology makes the Mr Slim Power Inverter the number one choice for improving comfort. They provide energy savings of up to 70% annually when compared to a previous non-inverter model. Operating noise has also been reduced thanks to improvements in fan design, while existing pipe work is reusable for easier maintenance and installation. Pictures not to scale Product Details Dimensions PEAD-RP100EA2 Indoor Unit Capacity (kW): PEAD-RP100EA2 Heating (Nominal) (Low - High) 11.20 (4.50 - 14.00) Cooling (Nominal) (Low - High) 10.00 (4.90 - 11.40) Heating (UK) (Low - High) 9.50 (3.85 - 11.90) Cooling (UK) (Low - High) 9.00 (4.40 - 10.25) SHF R410A (Nominal) 0.86 COP / EER (Nominal) 3.51 / 3.27 Energy Label Heating / Cooling B/A Width - mm 1415 Depth - mm 740 Height - mm 325 Weight - kg 65 Airflow (m3/min) - Lo-Hi 33.5-42 External Static Pressure Pa - Lo-Hi 70-130 Noise (dBA) - Lo-Hi Pipe Size Gas mm (in) Pipe Size Liquid mm (in) Electrical Supply Phase Fuse Rating (BS88) - HRC (A) Interconnecting Cable No. Cores Remote Controller Ref 44-50 15.88 (5/8) 9.52 (3/8) Fed by Outdoor Unit Single 6 4 PAR-21MAA PUHZ-RP100VHA2 PUHZ-RP100VHA2 Outdoor Unit Width - mm 950 Depth - mm 330 + 30 Height - mm 1350 Weight - kg Noise (dBA) (Heating / Cooling) Electrical Supply Phase Fuse Rating (BS88) - HRC (A) 121 51 / 49 220-240v, 50Hz Single 32 System Power Input (kW) - Heating (Nominal) 3.19 System Power Input (kW) - Cooling (Nominal) 3.06 System Power Input (kW) - Heating (UK) 2.84 System Power Input (kW) - Cooling (UK) 2.6 Starting Current (A) System Running Current (A) - Heating / Cooling Mains Cable No. Cores 5 15.01 / 15.15 3 Max Pipe Length (m) 75 Max Height Difference (m) 30 Charge (kg) - 30m 5 Telephone: 01707 282880 Email: firstname.lastname@example.org Website: http://www.mitsubishielectric.co.uk/aircon Tel: Fax: Mitsubishi Electric reserves the right to make any variation in technical specification to the equipment described, or to withdraw or replace products without prior notification or public announcement.