Illustration 7 Control Board Diagram (Wiring) CIRCUIT BOARD FUNCTIONS COMPONENT Exhaust Blower (Combustion) OPERATION START Starts Immediately. Stirrer Three minutes after starting, the Stirrer will begin to turn. When starting, the auger will begin to turn. Auger Room Fan (Convection) Begins when 110 degrees is reached. Automatic Shutdown If, after 15 minutes, the unit has not reached the preset operating temp., the unit will begin to automatically shut down. This will be evidenced by the red light on the Control Board. If, after 15 minutes, the preset operating temperature of 110 degrees is achieved, normal operation will continue. Normal Operation OPERATION END Will continue until shutdown. Shutdown will occur when the operating temperature is below 90 degrees. Will continue intermittently, as determined by the Heat Setting, until Shutdown The auger will continue at the feed rate determined by the Heat Setting. NOTE: Safety switch, Hi Limit and Vacuum Sensor must be activated to continue proper operation. Will continue to operate until the unit cools down to below 90 degrees. This may take from several minutes up to an hour. If the timer should expire before the preset operating temperature is achieved, resetting the timer is possible by switching the Control Board “OFF” and then back “ON.” Operation will continue until either the Control Board is turned “OFF,” or the operating temperature falls to below 90 degrees. At this time, the unit will default to “Automatic Shutdown.” 25 IMPORTANT! READ AND FOLLOW ALL INSTALLATION AND MAINTENANCE INSTRUCTIONS, INCLUDING CLEANING THE UNIT AS SPECIFIED, AND REPLACING GASKETS ANNUALLY, AND PARTS AS NEEDED. ENGLAND’S STOVE WORKS IS NOT RESPONSIBLE FOR ANY DAMAGE OR INJURY INCURRED DUE TO NEGLECT, OR DUE TO UNSAFE INSTALLATION OR USAGE OF THIS PRODUCT. CALL TECHNICAL SUPPORT WITH QUESTIONS.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project