HydroBoost In-Wall Bottle Filler with HRF-ER ® FILTERED MODEL HTHBWF-HRFER These water coolers are certiﬁed to NSF/ANSI 61 and 372. GENERAL In-wall, recessed bottle filling station paired with the single Contour™ refrigerated fountain Includes 3000 gallon capacity WaterSentry® Plus filtration system. HYDROBOOST ® BOTTLE FILLER In-wall, recessed design with solid lower panel. Quick ﬁll rate is 1.1 gallons per minute. Includes laminar ﬂow to provide a clean fill with minimal splash and easy maintenance. Equipped with automatic 20-second shut-off timer. User interface design makes touchless operation intuitive. Key plastic components are integrated with silver ion anti-microbial protection to inhibit growth of mold and mildew. Designed with hinged top and bottom stainless steel panels for easy access and service. GREEN COUNTER™ Visually displays count of plastic bottles saved from waste. (Based on 16 oz. bottles) WATERSENTRY ® PLUS FILTRATION Equipped with the HWF3000 WaterSentry ® Plus Filter which is designed to reduce lead particles and chlorine. Also reduces discoloration and odors from incoming water. Features include the Quick-Disconnect,1/4 turn installation and auto inlet shut-off valve that closes when the filter is removed. Green, yellow, and red LEDs visually indicate when ﬁlter maintenance is required. For service replacement, order as: 55898C - Single replacement filter 55898C_3PK - Filter three pack. 55898C_12PK - Filter twelve pack. 55898C_24PK - Filter twenty-four pack. 55898C_48PK - Filter forty-eight pack. SUGGESTED SPECIFICATION Model HTHBWF-HRFER provides 8.0 gph of 50ºF drinking water at 90ºF ambient and 80ºF inlet water. Bottle filler shall be recessed design and include electronic sensor activation with 20second automatic water shut-off. Shall provide 1.1 gpm flow rate with laminar flor to prevent splashing. Shall include anti-microbial protected plastic components to prevent mold and mildew. Shall include WaterSentry® Plus filter, certified to NSF/ANSI 61 and 372 for lead reduction, with visual monitor to indicate when replacement is necessary. Shall include visual display of plastic bottles saved from waste. Fountain shall be oval design with self-closing pushbars and contoured basin. Shall include water conservation bubbler with auto stream height regulator. Shall include SJ8 water chiller. Shall meet ADA guidelines for reach ranges, when properly installed. Shall be lead-free design which meets the Safe Drinking Water Act and is certified to NSF/ANSI 61 & 372. Shall be certified to UL399 and CAN/CSA 22.2 No. 120 electrial requirements. FOUNTAIN Features contoured basin and softly rounded corners and edges. HALSEY TAYLOR DOUBLE BUBBLER ™ Exclusive one-piece, chrome-plated two-stream moundbuilding bubbler with non-removable anti-squirt feature and integral hood insures a satisfying drink of water. Each HTHBWF-HRFER is shipped in 6 cartons including: HYDROBOOST Station with Solid Lower Panel HRF-ER Fountain Mounting Frames (2) HWF3000 WaterSentry® Plus Filter Cooling unit - SJ8 NOTE: Continued product improvement makes speciﬁcations subject to change without notice. See Halsey Taylor website for most current spec sheet. JOB NAME: AUTOMATIC STREAM HEIGHT REGULATOR Self-closing assembly is located inside unit to prevent tampering. A constant stream height is automatically maintained under line pressure that varies from 20 to 105 psi. PUSHBUTTON ACTIVATION Self-closing, vandal-resistant pushbutton does not require grasping or twisting. MOUNTING FRAMES Manufactured from corrosion resistant, galvanized steel. Open construction design for ease of installation. Mounting frames can be shipped in advance for roughin installation. ENGINEER/CONTRACTOR NAME: APPROVAL: DATE: halseytaylor.com HALSEY TAYLOR, 2222 CAMDEN COURT, OAK BROOK, ILLINOIS 60523 THIRD-PARTY CERTIFIED TO: * UL399 & CAN/CSA 22.2 NO. 120 * NSF/ANSI 61 and 372 MODEL HTHBWF-HRFER HydroBoost ® In-Wall Bottle Filler OPERATING PRESSURES: Supply water - 105 psi maximum * Rated for Indoor Use Only ELECTRICAL Hydroboost station equipped with electric cord and three-prong molded rubber plug for use with 15-amp minimum receptacle. For the cooling unit, a junction box for a (3) wire , 10 amp branch circuit is provided. Rated at 115 volt, 60 Hz, single phase. Minimum 40 psi supply line pressure required in special circumstances when both sides of bilevel are in use simultaneously to ensure adequate stream height. Does not apply to non-refrigerated units. MFWS100 DOUBLE STUD OR 3 INCHES (76 mm) BETWEEN MOUNTING FRAMES IF PLACED NEXT TO ANOTHER FOUNTAIN OR WALL WOOD OR STEEL FRAME SHOWN (NOT PROVIDED) FRAME 40" 1016mm 1" 25mm SIDE VIEW ELECTRICAL INLET LOCATION ON CHILLER 5/16" SCREWS OR BOLTS (10 REQ'D-NOT PROVIDED) 8" 1 1/8" 203mm ( 29mm TO FLOOR LINE HOOK RODS (2) P/N 101567443730 4 1/2 114mm STANDARD HEIGHT 18 3/4" 476mm INSTALL (2) SCREWS (P/N 111008343890) IN FRAME BEFORE INSTALLING IN OPENING ) 3/8" O.D. TUBE CONNECT (CHILLER WATER INLET) SHUT OFF VALVE BY OTHERS SCREWS OR BOLTS (NOT PROVIDED) ANDARD HEIGHT 3" ( 79mm ) CHILLER SHELF P/N 27638C DOUBLE STUD OR 3" (76mm) BETWEEN MOUNTING FRAMES BACK OF WALL TO 5 1/8" IF PLACED NEXT TO ANOTHER BE 12" (305mm) 130mm OR WALL FOUNTAIN MIN DEPTH 1 1/8" ( 29mm ) 1/4" O.D. TUBE CONNECT (CHILLER WATER OUTLET) 3/8" O.D. TUBE CONNECT (CHILLER WATER INLET) SHUT OFF VALVE BY OTHERS 1 3/16" ( 30mm ) 1/4" O.D. TUBE CONNECT (CHILLER WATER OUTLET) 9 3/8" 8 1/8" ( 206mm ) ( 238mm ) DOUBLE STUD OR 3" (76mm) 18 3/4" BETWEEN MOUNTING FRAMES ( 476mm ) IF PLACED NEXT TO ANOTHER FOUNTAIN OR WALL FILTER LOCATION (OPTIONAL) 1 3/16"1 3/16" ( 30mm( 30mm ) ) 19 3/4" ( 502mm ) 17 3/8" ( 441mm ) FRONT VIEW / WALL 12" *LAYOUT 1 3/16" ( 30mm ) ( 305mm ) MINIMUM DEPTH 12" * * 7" minimum depth ( 305mm ) for non-refrigerated models MINIMUM 38 7/8" ( 987mm ) 20 7/16" ( 519mm ) 27" ( 681mm ) ELECTRICAL 20 7/16" ( 519mm ) 25 1/4" INLET ( 641mm ) * 7" minimum depth for non-refrigerated models BACK WALL LINE 1-1/4" (32MM) WASTE TUBE FURNISHED 27" ( 681mm ) ELECTRICAL 25 1/4" INLET 25 7/8" ( 641mm3 )1/2" ( 657mm ) ( 89mm ) FINISHED FLOOR FINISHED FLOOR 1 1/8" ( 29mm ) FILTER LOCATION (OPTIONAL) DEPTH 2 7/8" ( 73mm ) 1-1/4" (32MM) WASTE TUBE FURNISHED 2 7/8"20 3/8" ( 73mm ) ( 518mm ) 20 3/8" ( 518mm ) FINISHED FLOOR 9 3/8" ( 238mm ) 18 3/4" ( 476mm ) 4" ( 102mm ) BACK WALL LINE 38 7/8" ( 987mm ) 8 1/8" ( 206mm ) FLOOR LINE 4" ( 102mm ) 19 3/4" ( 502mm ) 17 3/8" ( 441mm ) 3" ( 79mm ) 25 7/8" 3 1/2" ( 657mm ) ( 89mm ) FINISHED FLOOR 11" ( 279mm ) 1 1/8" 4 1/2"( 29mm ) ( 116mm) 11" ( 279mm ) 4 1/2" ( 116mm) Speciﬁcations and measurements are subject to change without notiﬁcation. Please visit halseytaylor.com for most current version. Printed in the U.S.A. MODEL HTHBWF-HRFER HRF-ER (CONTINUED) TOP & SIDE VIEWS WALL OPENING IMPORTANT: It is necessary to create a wall opening 18 3/4 " W x 37 3/4 " H and 4 1/ 2" above the ﬂoor line. MOUNTING INSTRUCTIONS Refer to rough-in for location of plumbing and electrical sources. The support frame is to be installed ﬁrst. The shelf for the water chiller should be assembled to the wall frame, and then place chiller into position. Hang upper fountain panel to hanger on frame. Fountain is to be attached to panel and wall frame. Water service line, waste line and electrical is assembled as required. The bottom panel is attached last, after a ﬁnal check for leaks and correct functions of fountains and chiller. (For details see the installation instructions.) B OPERATING PRESSURES: Supply water - 105 psi maximum ELECTRICAL DATA Junction box for a (3) wire 10 AMP branch circuit. Standard 120 volt, 60 HZ, single phase. FRONT VIEW C D A = 3/8” O.D. TUBE CONNECT (CHILLER WATER INLET) SHUT OFF VALVE BY OTHERS B = 1/4” O.D. TUBE CONNECT (WATER OUTLET) C = 1-1/4” TRAP D = ELECTRICAL INLET Printed in the U.S.A. MODEL HTHBWF-HRFER HRF-ER MOUNTING FRAME (CONTINUED) 1. Cut a rectangular wall opening 18-3/4” (475 mm) W x 37-3/4” (959 mm) H and 4-1/2” (114 mm) above the floor line (see Figure 9). The dimensions are required to obtain proper rim and bubbler heights for compliance with ANSI standard A117.1. 2. Reinforce the wall opening on all sides to adequately support the water fountain. This reinforcement must support up to 150 lbs. static load and provide a means for securing the frame assembly in place. NOTE: 3. Building construction must allow for adequate air flow on both sides, top and back of chiller. A minimum of 4” (102 mm) on both sides and top is required. See chiller installation for additional instructions. Install plumbing and electrical rough-ins. A junction box for a (3) wire, 10 amp branch circuit is provided on the inside of the chiller. (Standard 120 Volts, 60 Hz, and single phase.) 4. Remove frame and related hardware from packaging. Release the two shelf rods by cutting cable ties. 5. Install the frame squarely in wall opening with frame upright edges flush with the finished wall surface. Place shelf inside frame and line up the (2) holes on each. Insert loose ends of rods into holes on sides of shelf panel. Using appropriately sized screws or bolts (not provided), fasten the shelf and frame to the bottom of wall opening. Secure the frame sides and top to the wall using (10) 5/16” bolts or screws (not provided). NOTE: Be sure that frame is squared in location. Do not use less than the required screw quantity and size. Printed in the U.S.A.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project