Project/Location: Contractor: Date: Genesis LER800 Series ™ Prepared by: Die-Cast Aluminum Exit Sign FEATURES TYPICAL SPECIFICATIONS •Durable, powder-coated Die-Cast construction •Slim contoured body design with brushed aluminum faceplate (single or double face option) •Diagnostic/self-test feature comes standard on all Self-Powered units •Universal mounting – wall, end or ceiling mounting •100% bright, even illumination in both normal and emergency operation •Long-life, energy-efficient, ALINGAP technology LED light source reduces maintenance and energy costs •Energy efficient – consumes less than 3W •Maintenance-free, long-life sealed Nickel-Cadmium battery •Normal AC and emergency DC operation – 120 to 347V universal AC input; 6 to 48V universal DC input •NEXUS® compatible (for more information on NEXUS®, please consult your sales representative) •CSA certified, meets or exceeds C860 requirements DIMENSIONS Supply and install the Lumacell® LER800 Series LED Exit Signs. The equipment shall operate with universal two-wire AC input voltage from 120VAC to 347VAC at less than 3W and universal two-wire DC input voltage from 6VDC to 48VDC at less than 1.5W for single and double face signs. The faceplate(s) and the back plate shall snap together and shall be made of die cast aluminum. The light source shall be light emitting diodes (LED). The LED lamps shall provide illumination in normal and emergency operation and shall be mounted inside the exit on a plastic frame/reflector. Red LED technology shall be ALINGAP. An LED-sensitive diffuser shall be mounted behind the legend to provide the 6” high by 3/4” stroke letters with even illumination. The Self-Powered model shall stay illuminated during emergency operation for at least 90 minutes (red) and at least 60 minutes (green) upon AC failure. The selfpowered model shall include self-testing and self-diagnostic functions: the equipment shall automatically test itself for 5 minutes every 30 days, 30 minutes every 60 days and 90 minutes annually. A “Service Required” lamp shall be located near the test switch and flash in the case of a fault detection. A two-LED diagnostic display shall be located inside the equipment and shall be capable of identifying the source of failure that may occur (battery, charger circuitry, or LED lamp failure). The Exit Sign shall be CSA-C860 approved. The equipment shall be Lumacell® Model: . WIRE GUARDS Dimensions are approximate and subject to change. 460.0079-L 87/8” [23 cm] 93/4” [24.8 cm] 45/8” [11.8 cm] 61/4” [16 cm] Lumacell Model: 131/8” [33 cm] 13/4” [4.3 cm] 14” [35 cm] Wall Mount 460.0027-L End Mount 460.0028-L Ceiling Mount POWER CONSUMPTION MODEL AC SPECS AC/DC red 120/347VAC Less than 3W DC SPECS 6 to 48VDC Less than 1.5W AC/DC green 120/347VAC Less than 3W 6 to 48VDC Less than 1.5W Self-Powered red 120/347VAC Less than 3W Ni-Cd Battery Min. 90 minutes Self-Powered green 120/347VAC Less than 3W Ni-Cd Battery Min. 60 minutes ORDERING INFORMATION SERIES LER= EXIT FACEPLATES 850U= single face, universal mount 860U= double face, universal mount EXAMPLE: LER850WH 26 www.lumacell.com HOUSING FACEPLATES COLOURS VOLTAGE OPTIONS WH= factory white B= black BA= brushed aluminum CH= all chrome PB= all polished brass BZ= bronze BBA= black/brushed aluminum WBA= white/brushed aluminum Blank= 120VAC to 347VAC, 6VDC to 48VDC SPD= 120VAC to 347VAC, Self-Powered c/w auto diagnostics NEX= NEXUS® system interface* TP= tamper proof screws VRTP= polycarbonate shield with tamper-proof screws* GN= green legend 990.0119-L= tamper proof bit** Other colours available. Consult your sales representative. *Consult your sales representative for options available with NEXUS® System. *Indicate single or double face. **One bit needed per order.