Moore 348 FIELDPAC FIELD MOUNTED CONTROLLERAdd to my manuals
220.127.116.11 ACK/STEP UP
With FIELDPAC in normal operating mode, pressing this button will open the status window to view any active status conditions or it will acknowledge any flashing status conditions.
With the FIELDPAC in configuration mode, each push of this button will step the configuration menu up one level.
18.104.22.168 ALARM/STEP DOWN
With FIELDPAC in normal operating mode, pressing this button permits the operator to quickly access the alarm limits, deadband, and enable parameters associated with the alarm function blocks. After pressing the
ALARM/STEP DOWN button, LOOP 1 is displayed in the digital display. The user can toggle between LOOP 1
(FB12 alarm parameters) and LOOP 2 (FB73 alarm parameters) by pressing the TUNE/---> button. Once the appropriated LOOP is selected, press the ALARM/STEP DOWN button to access the alarm parameters.
With the FIELDPAC in configuration mode, each push of this button will step the configuration menu down one level.
3.2 OPERATING MODES
The operating modes required for any FIELDPAC operation are dependent upon the user configuration of the station type and the control strategy. All typical operating modes for standard industrial controller types can be configured for use by the FIELDPAC.
Refer to sections 7 and 8 for more detailed information on all the FIELDPAC functions and its configuration procedure.
The AUTO/MAN (Automatic/Manual), PB1 and PB2 pushbutton mode switches are used to establish the operating modes locally. Any combination of these switches can be configured for use. Each mode switch has a corresponding function block from which the switch function or functions are selected.
3.3 DISPLAY TEST
Pushing the ENTER/EXIT CONF button followed by a push of the D button will activate all display segments of the Liquid Crystal Display. A three-step test is automatically performed on the alphanumeric display to activate all its segments. The two-button push sequence must be initiated when the Station is in the operating mode. If the
Station is in the configuration mode when the ENTER/EXIT CONF and the D pushbuttons are pressed, the Station will exit configuration without performing a display test.
* Your assessment is very important for improving the workof artificial intelligence, which forms the content of this project