NS-Series Programmable Terminals HOST CONNECTION MANUAL | Section 1
This section explains in general how to connect hosts other than NS-V1/V2 Series Omron PLC and which models to connect.
1-1List of combinations
1-2CX-Designer and System Program version
1-1 List of combinations
This explains the configuration when host is other than Omron PLCs.
1-1-1 Connection of temperature controller
Communicates with Omron temperature controller via RS-485.
Connect RS-422 converter CJ1W-CIF11 to serial port A or B and set communication mode to RS-485.
For details, refer to ‘Chapter 2: connection of temperature controller’.
1-1-2 Connection with memory link
When host other than PLC such as board-controller and personal computer is used, connection via memory link is possible. Use serial port A or B to connect host equipment. For details, refer to ‘chapter 3: connection via memory
1-2 CX-Designer and System Program versions
1-2-1 CX-Designer versions
With CX-Designer Ver.1.0 or later version, you can create and edit projects for Temperature Controller connections and Memory Link connections.
1-2-2 System Program versions
System program Ver.5.0 or later.
A copy of this version is included CX-Designer.
NS Series V1/V2 models (NS15 –V2, NS12/10/8/5 –V1/V2), and NSJ Series (NSJ12/10/8/5) are supported for those connections.
NS without –V1/V2 suffix models are not supported.
When system program version is earlier than Ver.5.0, you need to upgrade. For details on how to upgrade, refer to the manual (PDF)(How To RecoverUpdate the system) in CX-Designer.
* Your assessment is very important for improving the work of artificial intelligence, which forms the content of this project